<table style="width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;">
<tbody>
<tr style="background: #30358C; color: white;"><th style="padding: 20px; text-align: left; font-weight: 600;">Parameter</th><th style="padding: 20px; text-align: left; font-weight: 600;">Value</th></tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px; font-size: 17px; font-weight: bold;">Three-Phase Hybrid Inverter SUN-50K-SG01HP3-EU-BM4</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px;">Battery Input Data</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Battery Type</td>
<td style="padding: 14px 20px;">Li-ion</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Battery Voltage Range (V)</td>
<td style="padding: 14px 20px;">160-800</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. Charging Current (A)</td>
<td style="padding: 14px 20px;">50+50</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. Discharging Current (A)</td>
<td style="padding: 14px 20px;">50+50</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Charging Strategy for Li-Ion Battery</td>
<td style="padding: 14px 20px;">Self-adaptation to BMS</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Number of Battery Inputs</td>
<td style="padding: 14px 20px;">2</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px;">PV String Input Data</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. PV Access Power (W)</td>
<td style="padding: 14px 20px;">100000</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. DC Input Power (W)</td>
<td style="padding: 14px 20px;">80000</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. DC Input Voltage (V)</td>
<td style="padding: 14px 20px;">1000</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Start Voltage (V)</td>
<td style="padding: 14px 20px;">180</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">MPPT Voltage Range (V)</td>
<td style="padding: 14px 20px;">150-800</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Rated DC Input Voltage (V)</td>
<td style="padding: 14px 20px;">600</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. Operating PV Input Current (A)</td>
<td style="padding: 14px 20px;">36+36+36+36</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. Input Short-Circuit Current (A)</td>
<td style="padding: 14px 20px;">55+55+55+55</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Number of MPP Trackers / Number of Strings per MPP Tracker</td>
<td style="padding: 14px 20px;">4/2+2+2+2</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px;">AC Input/Output Side</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Rated AC Input/Output Active Power</td>
<td style="padding: 14px 20px;">50000</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. AC Input/Output Apparent Power</td>
<td style="padding: 14px 20px;">55000</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">AC Input/Output Rated Current (A)</td>
<td style="padding: 14px 20px;">75.8/72.5</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. AC Input/Output Current (A)</td>
<td style="padding: 14px 20px;">83.4/79.8</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. Continuous AC Passthrough (Grid for Charging)</td>
<td style="padding: 14px 20px;">200</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Peak Power (off-grid)</td>
<td style="padding: 14px 20px;">1.5 times rated output power, 10 s</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Power Factor Adjustment Range</td>
<td style="padding: 14px 20px;">0.8 leading to 0.8 lagging</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Rated Input/Output Voltage/Range (V)</td>
<td style="padding: 14px 20px;">220/380V, 230/400V 0.85Un-1.1Un</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Rated Input/Output Grid Frequency/Range (Hz)</td>
<td style="padding: 14px 20px;">50/45-55, 60/55-65</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Grid Connection Type</td>
<td style="padding: 14px 20px;">3L+N+PE</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Total Harmonic Current Distortion (THDi)</td>
<td style="padding: 14px 20px;">&lt;3% (Rated Power)</td>
</tr>
<tr>
<td style="padding: 14px 20px;">DC Current Injection</td>
<td style="padding: 14px 20px;">&lt;0.5% In</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px;">Efficiency</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. Efficiency</td>
<td style="padding: 14px 20px;">97.6%</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Euro Efficiency</td>
<td style="padding: 14px 20px;">97.0%</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">MPPT Efficiency</td>
<td style="padding: 14px 20px;">&gt;99%</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px;">Device Protection</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Integrated</td>
<td style="padding: 14px 20px;">DC Polarity Reverse Connection Protection, AC Output Overcurrent Protection, Thermal Protection, AC Output Overvoltage Protection, AC Output Short-Circuit Protection, DC Component Monitoring, Overvoltage Load Drop Protection, Ground Fault Current Monitoring, Arc Fault Current Interrupter (optional), Grid Monitoring, Anti-Island Protection Monitoring, Ground Fault Detection, DC Input Switch, DC Insulation Impedance Monitoring, Backfeed Detection (RCD), Overvoltage Protection Level</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Overvoltage Protection Level</td>
<td style="padding: 14px 20px;">TYPE II (DC), TYPE II (AC)</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px;">Interface</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">LCD/LED Display</td>
<td style="padding: 14px 20px;">LCD</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Communication Interface</td>
<td style="padding: 14px 20px;">WIFI, RS485, CAN</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Monitoring Mode</td>
<td style="padding: 14px 20px;">GPRS/WIFI/Bluetooth/4G/LAN (optional)</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px;">General Data</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Operating Temperature Range (&#176;C)</td>
<td style="padding: 14px 20px;">-40 to +60&#176;C, &gt;45&#176;C Power Derating</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Permissible Ambient Humidity</td>
<td style="padding: 14px 20px;">0-100%</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Permissible Altitude</td>
<td style="padding: 14px 20px;">2000m</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Noise (dB)</td>
<td style="padding: 14px 20px;">&lt;65 db="" a="" td=""&gt; <!--65--><!--65--></td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Protection Rating</td>
<td style="padding: 14px 20px;">IP 65</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Inverter Topology</td>
<td style="padding: 14px 20px;">Non-isolated</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Overvoltage Category</td>
<td style="padding: 14px 20px;">OVC II (DC), OVC III (AC)</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Dimensions (WxHxD mm)</td>
<td style="padding: 14px 20px;">527&#215;894&#215;294 (Without connectors and brackets)</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Weight (kg)</td>
<td style="padding: 14px 20px;">80</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Cooling Mode</td>
<td style="padding: 14px 20px;">Intelligent Cooling</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Warranty</td>
<td style="padding: 14px 20px;">5-year/10-year warranty period depends on installation conditions of the inverter. For details, see the general warranty conditions.</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Grid Regulation</td>
<td style="padding: 14px 20px;">IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002, OVE Guideline R25, G99, VDE-AR-N 4105</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Safety EMC / Standard</td>
<td style="padding: 14px 20px;">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</td>
</tr>
</tbody>
</table>