INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(555, '<table selecttype=\"all\">\n<tbody>\n<tr height=\"36\">\n<td colspan=\"2\" width=\"1178\"><strong>PV String Input Data</strong></td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Max. PV Input Power (kW)</td>\n<td width=\"90\">15</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Max. PV Input Voltage (V)&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;</td>\n<td width=\"900\">1100</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Start-up Voltage (V)</td>\n<td width=\"900\">140</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">MPPT Voltage Range (V)</td>\n<td width=\"900\">120-1000</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Rated PV Input Voltage (V)&#160;</td>\n<td width=\"900\">600</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Max. Operating PV Input Current (A)</td>\n<td width=\"810\">20+20</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Max. Input Short Circuit Current (A)</td>\n<td width=\"810\">30+30</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">No. of MPP Trackers/<br />No. of StringsperMPP Tracker</td>\n<td width=\"810\">2/1+1</td>\n</tr>\n<tr height=\"36\">\n<td colspan=\"2\" width=\"1178\">\n<p></p>\n<p><strong>AC Output Side</strong></p>\n</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Rated AC Output Active Power (kW)</td>\n<td width=\"90\">10</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Max.AC Output Apparent Power (kVA)</td>\n<td width=\"90\">11</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Rated AC Output Current (A)</td>\n<td width=\"90\">15.2/14.5</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Max. AC Output Current (A)</td>\n<td width=\"90\">16.7/16</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Rated Output Voltage/Range (V)&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;</td>\n<td width=\"900\">220/380V, 230/400V 0.85Un-1.1Un</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Grid Connection Form</td>\n<td width=\"900\">3L/N/PE</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Rated Output Grid Frequency/Range(Hz)</td>\n<td width=\"900\">50/45-55, 60/55-65</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Power Factor Adjustment Range</td>\n<td width=\"900\">0.8 leading to 0.8 lagging</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Total Current Harmonic Distortion THDi</td>\n<td width=\"900\">&lt;3%</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">DC Injection Current</td>\n<td width=\"900\">&lt;0.5%ln</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">\n<p></p>\n<p><strong>E&#64259;ciency</strong></p>\n</td>\n<td width=\"900\"></td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Max. Ef&#64257;ciency</td>\n<td width=\"450\">98.3%</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Euro Ef&#64257;ciency</td>\n<td width=\"450\">97.8%</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">MPPTEf&#64257;ciency</td>\n<td width=\"900\">&gt;99%</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">\n<p></p>\n<p><strong>Equipment Protection</strong></p>\n</td>\n<td width=\"900\"></td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">DC Polarity Reverse Connection Protection</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">AC Output Overcurrent Protection</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">AC Output Overvoltage Protection</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">AC Output Short Circuit Protection</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Thermal Protection</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">DC Terminal Insulation Impedance Monitoring</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">DC Component Monitoring</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr>\n<td>\n<div><span>Arc Fault Circuit Interrupter (AFCI)</span></div>\n</td>\n<td>\n<div><span>Optional</span></div>\n</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Ground Fault Current Monitoring</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Power Network Monitoring</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Island Protection Monitoring</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Earth Fault Detection</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Overvoltage Load Drop Protection</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Residual Current (RCD) Detection</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Surge Protection Level</td>\n<td width=\"900\">TYPE II(DC),TYPE II(AC)</td>\n</tr>\n<tr height=\"36\">\n<td colspan=\"2\" width=\"1178\">\n<p></p>\n<p><strong>Interface</strong></p>\n</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Communication Interface</td>\n<td width=\"900\">RS485/RS232</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Monitor Mode</td>\n<td width=\"900\">GPRS/WIFI/Bluetooth/4G/LAN(optional)</td>\n</tr>\n<tr height=\"36\">\n<td colspan=\"2\" width=\"1178\">\n<p></p>\n<p><strong>General Data</strong></p>\n</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Operating Temperature Range (&#176;C)</td>\n<td width=\"900\"><span>-25 to +60</span><span>&#8451;</span><span>, &gt;45</span><span>&#8451;&#160;</span><span>Derating</span></td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Permissible Ambient Humidity</td>\n<td width=\"900\">0-100%</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Permissible Altitude (m)</td>\n<td width=\"900\">4000m</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Noise (dB)</td>\n<td width=\"900\">&lt;45</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Ingress Protection(IP) Rating</td>\n<td width=\"900\">IP 65</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Inverter Topology</td>\n<td width=\"900\">Non-Isolated</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Over Voltage Category</td>\n<td width=\"900\">OVC II(DC), OVC III(AC)</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Cabinet Size (WxHxD mm)</td>\n<td width=\"900\">283&#215;463&#215;178 (Excluding Connectors and Brackets)</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Weight (kg)</td>\n<td width=\"900\">11</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Warranty</td>\n<td width=\"900\">5 Years</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Type of Cooling</td>\n<td width=\"900\">Natural Cooling</td>\n</tr>\n<tr height=\"42\">\n<td width=\"278\">Grid Regulation</td>\n<td width=\"900\">IEC 61727, IEC 62116,CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,<br />OVE-Richtlinie R25,G98, G99,VDE-AR-N 4105</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Safety EMC/Standard</td>\n<td width=\"900\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</td>\n</tr>\n</tbody>\n</table>', 2, 'SUN-10K-G06P3-EU-AM2-P1 | Three Phase String Inverter | 2 MPPT', '<p>Thi Deye&#160;SUN-10K-G06P3-EU-AM2-P1 inverter series offers outstanding performance with a maximum efficiency of up to 98.5%, and a European efficiency rating between 97.5% and 98%, ensuring optimal energy conversion under various conditions. It supports zero export functionality to prevent feeding excess energy into the grid&#8212;ideal for regions with export restrictions. The integrated Virtual Synchronous Generator (VSG) feature enhances grid stability, while optional string intelligent monitoring enables real-time performance tracking of individual panel strings. With a wide output voltage range for flexible system design and an optional anti-PID function to protect panels from voltage-induced degradation, this series delivers reliable, efficient, and adaptable solar energy solutions.</p>\n<h3>Key Features</h3>\n<ul>\n<li><strong>High Efficiency:</strong>&#160;The inverters in this series boast a maximum efficiency of up to 98.5%, ensuring that the majority of the solar energy is converted into usable electricity. The European efficiency rating varies between 97.5% and 98%, highlighting the inverter&#8217;s effectiveness in various conditions.</li>\n<li><strong>Zero Export Application:</strong>&#160;This feature prevents excess energy from being fed back into the electrical grid. It is particularly useful in areas with restrictions on energy export or where compensation for exported energy is not available.</li>\n<li><strong>VSG Application:</strong>&#160;The Virtual Synchronous Generator (VSG) feature allows the inverter to simulate the behavior of a synchronous generator, which aids in maintaining grid stability and reliability.</li>\n<li><strong>String Intelligent Monitoring:</strong>&#160;Available as an optional feature, this allows real-time monitoring of the performance of each string of solar panels, helping to identify issues quickly and maintain optimal performance.</li>\n<li><strong>Wide Output Voltage Range:</strong>&#160;The inverters support a broad range of output voltages, facilitating adaptability to different system designs and requirements.</li>\n<li><strong>Anti-PID Function:</strong>&#160;The optional Anti-potential Induced Degradation (PID) function helps to extend the lifespan of the solar panels by preventing the degradation caused by high system voltages.<br /><br /></li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-008.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<p></p>\n<h3 id=\"protection-and-monitoring\">Protection and Monitoring</h3>\n<ul>\n<li>DC Injection Current: Less than 0.5% of the nominal current, maintaining grid compliance.</li>\n<li>MPPT Efficiency: Greater than 99%, ensuring optimal energy harvest from the solar panels.</li>\n<li>Protection Mechanisms: Includes DC polarity reverse connection protection, AC output overcurrent and overvoltage protection, thermal protection, insulation impedance monitoring, and ground fault current monitoring.</li>\n<li>Surge Protection: Type II DC and Type II AC surge protection is included to safeguard against voltage spikes.</li>\n<li>Communication Interface: Supports RS485 and RS232 interfaces for easy integration with monitoring systems. Optional communication modes include GPRS, WIFI, Bluetooth, 4G, and LAN for flexible connectivity.</li>\n</ul>\n<h3 id=\"physical-and-environmental-specifications\">Physical and Environmental Specifications</h3>\n<ul>\n<li>Operating Temperature Range: -25 to +60 &#176;C, with derating above 45&#176;C to protect the inverter under high-temperature conditions.</li>\n<li>Permissible Ambient Humidity: 0-100% relative humidity, making it suitable for various climates.</li>\n<li>Permissible Altitude: Up to 4000 meters, accommodating installations at high altitudes.</li>\n<li>Noise Level: Less than 45 dB, ensuring quiet operation.</li>\n<li>Cooling: Employs natural cooling or intelligent air cooling, depending on the model.</li>\n<li>Ingress Protection (IP) Rating: IP 65, making it dust-tight and protected against water jets, suitable for outdoor installations.</li>\n<li>Weight and Dimensions: Each unit weighs 11 kg, with dimensions of 283&#215;463&#215;178 mm (excluding connectors and brackets).</li>\n<li>Warranty: A standard 5-year warranty is provided for peace of mind.</li>\n</ul>\n<h3 id=\"certifications-and-compliance\">Certifications and Compliance</h3>\n<ul>\n<li>Regulatory Standards: Compliant with IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002, OVE-Richtlinie R25, G99, and VDE-AR-N 4105.</li>\n<li>Safety Standards: Meets the requirements of IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, and IEC/EN 62109-2.</li>\n</ul>', '<span>The Deye SUN-10K-G06P3-EU-AM2-P1 series is designed to cater to the needs of modern solar energy systems with its cutting-edge technology and advanced features. These three-phase string inverters are capable of delivering high efficiency, flexibility, and reliability, making them suitable for a wide range of applications, including residential, commercial, and industrial settings. The series offers a maximum efficiency of up to 98.5%, ensuring optimal energy conversion from solar panels to the electrical grid.</span>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(556, '<table selecttype=\"all\">\n<tbody>\n<tr height=\"36\">\n<td colspan=\"2\" width=\"1178\"><strong>PV String Input Data</strong></td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Max. PV Input Power (kW)</td>\n<td width=\"90\">18</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Max. PV Input Voltage (V)&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;</td>\n<td width=\"900\">1100</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Start-up Voltage (V)</td>\n<td width=\"900\">140</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">MPPT Voltage Range (V)</td>\n<td width=\"900\">120-1000</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Rated PV Input Voltage (V)&#160;</td>\n<td width=\"900\">600</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Max. Operating PV Input Current (A)</td>\n<td width=\"810\">20+20</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Max. Input Short Circuit Current (A)</td>\n<td width=\"810\">30+30</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">No. of MPP Trackers/<br />No. of StringsperMPP Tracker</td>\n<td width=\"810\">2/1+1</td>\n</tr>\n<tr height=\"36\">\n<td colspan=\"2\" width=\"1178\">\n<p></p>\n<p><strong>AC Output Side</strong></p>\n</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Rated AC Output Active Power (kW)</td>\n<td width=\"90\">12</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Max.AC Output Apparent Power (kVA)</td>\n<td width=\"90\">13.2</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Rated AC Output Current (A)</td>\n<td width=\"90\">18.2/17.4</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Max. AC Output Current (A)</td>\n<td width=\"90\">20/19.2</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Rated Output Voltage/Range (V)&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;</td>\n<td width=\"900\">220/380V, 230/400V 0.85Un-1.1Un</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Grid Connection Form</td>\n<td width=\"900\">3L/N/PE</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Rated Output Grid Frequency/Range(Hz)</td>\n<td width=\"900\">50/45-55, 60/55-65</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Power Factor Adjustment Range</td>\n<td width=\"900\">0.8 leading to 0.8 lagging</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Total Current Harmonic Distortion THDi</td>\n<td width=\"900\">&lt;3%</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">DC Injection Current</td>\n<td width=\"900\">&lt;0.5%ln</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">\n<p></p>\n<p><strong>E&#64259;ciency</strong></p>\n</td>\n<td width=\"900\"></td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Max. Ef&#64257;ciency</td>\n<td width=\"450\">98.3%</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Euro Ef&#64257;ciency</td>\n<td width=\"450\">97.8%</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">MPPTEf&#64257;ciency</td>\n<td width=\"900\">&gt;99%</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">\n<p></p>\n<p><strong>Equipment Protection</strong></p>\n</td>\n<td width=\"900\"></td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">DC Polarity Reverse Connection Protection</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">AC Output Overcurrent Protection</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">AC Output Overvoltage Protection</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">AC Output Short Circuit Protection</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Thermal Protection</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">DC Terminal Insulation Impedance Monitoring</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">DC Component Monitoring</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr>\n<td>\n<div><span>Arc Fault Circuit Interrupter (AFCI)</span></div>\n</td>\n<td>\n<div><span>Optional</span></div>\n</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Ground Fault Current Monitoring</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Power Network Monitoring</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Island Protection Monitoring</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Earth Fault Detection</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Overvoltage Load Drop Protection</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Residual Current (RCD) Detection</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Surge Protection Level</td>\n<td width=\"900\">TYPE II(DC),TYPE II(AC)</td>\n</tr>\n<tr height=\"36\">\n<td colspan=\"2\" width=\"1178\">\n<p></p>\n<p><strong>Interface</strong></p>\n</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Communication Interface</td>\n<td width=\"900\">RS485/RS232</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Monitor Mode</td>\n<td width=\"900\">GPRS/WIFI/Bluetooth/4G/LAN(optional)</td>\n</tr>\n<tr height=\"36\">\n<td colspan=\"2\" width=\"1178\">\n<p></p>\n<p><strong>General Data</strong></p>\n</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Operating Temperature Range (&#176;C)</td>\n<td width=\"900\"><span>-25 to +60</span><span>&#8451;</span><span>, &gt;45</span><span>&#8451;&#160;</span><span>Derating</span></td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Permissible Ambient Humidity</td>\n<td width=\"900\">0-100%</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Permissible Altitude (m)</td>\n<td width=\"900\">4000m</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Noise (dB)</td>\n<td width=\"900\">&lt;45</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Ingress Protection(IP) Rating</td>\n<td width=\"900\">IP 65</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Inverter Topology</td>\n<td width=\"900\">Non-Isolated</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Over Voltage Category</td>\n<td width=\"900\">OVC II(DC), OVC III(AC)</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Cabinet Size (WxHxD mm)</td>\n<td width=\"900\">283&#215;463&#215;178 (Excluding Connectors and Brackets)</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Weight (kg)</td>\n<td width=\"900\">11</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Warranty</td>\n<td width=\"900\">5 Years</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Type of Cooling</td>\n<td width=\"900\">Natural Cooling</td>\n</tr>\n<tr height=\"42\">\n<td width=\"278\">Grid Regulation</td>\n<td width=\"900\">IEC 61727, IEC 62116,CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,<br />OVE-Richtlinie R25,G98, G99,VDE-AR-N 4105</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Safety EMC/Standard</td>\n<td width=\"900\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</td>\n</tr>\n</tbody>\n</table>', 2, 'SUN-12K-G06P3-EU-AM2-P1 | Three Phase String Inverter | 2 MPPT', '<p>Thi Deye&#160;SUN-12K-G06P3-EU-AM2-P1 inverter series offers outstanding performance with a maximum efficiency of up to 98.5%, and a European efficiency rating between 97.5% and 98%, ensuring optimal energy conversion under various conditions. It supports zero export functionality to prevent feeding excess energy into the grid&#8212;ideal for regions with export restrictions. The integrated Virtual Synchronous Generator (VSG) feature enhances grid stability, while optional string intelligent monitoring enables real-time performance tracking of individual panel strings. With a wide output voltage range for flexible system design and an optional anti-PID function to protect panels from voltage-induced degradation, this series delivers reliable, efficient, and adaptable solar energy solutions.</p>\n<h3>Key Features</h3>\n<ul>\n<li><strong>High Efficiency:</strong>&#160;The inverters in this series boast a maximum efficiency of up to 98.5%, ensuring that the majority of the solar energy is converted into usable electricity. The European efficiency rating varies between 97.5% and 98%, highlighting the inverter&#8217;s effectiveness in various conditions.</li>\n<li><strong>Zero Export Application:</strong>&#160;This feature prevents excess energy from being fed back into the electrical grid. It is particularly useful in areas with restrictions on energy export or where compensation for exported energy is not available.</li>\n<li><strong>VSG Application:</strong>&#160;The Virtual Synchronous Generator (VSG) feature allows the inverter to simulate the behavior of a synchronous generator, which aids in maintaining grid stability and reliability.</li>\n<li><strong>String Intelligent Monitoring:</strong>&#160;Available as an optional feature, this allows real-time monitoring of the performance of each string of solar panels, helping to identify issues quickly and maintain optimal performance.</li>\n<li><strong>Wide Output Voltage Range:</strong>&#160;The inverters support a broad range of output voltages, facilitating adaptability to different system designs and requirements.</li>\n<li><strong>Anti-PID Function:</strong>&#160;The optional Anti-potential Induced Degradation (PID) function helps to extend the lifespan of the solar panels by preventing the degradation caused by high system voltages.<br /><br /></li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-008.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<p></p>\n<h3 id=\"protection-and-monitoring\">Protection and Monitoring</h3>\n<ul>\n<li>DC Injection Current: Less than 0.5% of the nominal current, maintaining grid compliance.</li>\n<li>MPPT Efficiency: Greater than 99%, ensuring optimal energy harvest from the solar panels.</li>\n<li>Protection Mechanisms: Includes DC polarity reverse connection protection, AC output overcurrent and overvoltage protection, thermal protection, insulation impedance monitoring, and ground fault current monitoring.</li>\n<li>Surge Protection: Type II DC and Type II AC surge protection is included to safeguard against voltage spikes.</li>\n<li>Communication Interface: Supports RS485 and RS232 interfaces for easy integration with monitoring systems. Optional communication modes include GPRS, WIFI, Bluetooth, 4G, and LAN for flexible connectivity.</li>\n</ul>\n<h3 id=\"physical-and-environmental-specifications\">Physical and Environmental Specifications</h3>\n<ul>\n<li>Operating Temperature Range: -25 to +60 &#176;C, with derating above 45&#176;C to protect the inverter under high-temperature conditions.</li>\n<li>Permissible Ambient Humidity: 0-100% relative humidity, making it suitable for various climates.</li>\n<li>Permissible Altitude: Up to 4000 meters, accommodating installations at high altitudes.</li>\n<li>Noise Level: Less than 45 dB, ensuring quiet operation.</li>\n<li>Cooling: Employs natural cooling or intelligent air cooling, depending on the model.</li>\n<li>Ingress Protection (IP) Rating: IP 65, making it dust-tight and protected against water jets, suitable for outdoor installations.</li>\n<li>Weight and Dimensions: Each unit weighs 11 kg, with dimensions of 283&#215;463&#215;178 mm (excluding connectors and brackets).</li>\n<li>Warranty: A standard 5-year warranty is provided for peace of mind.</li>\n</ul>\n<h3 id=\"certifications-and-compliance\">Certifications and Compliance</h3>\n<ul>\n<li>Regulatory Standards: Compliant with IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002, OVE-Richtlinie R25, G99, and VDE-AR-N 4105.</li>\n<li>Safety Standards: Meets the requirements of IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, and IEC/EN 62109-2.</li>\n</ul>', '<span>The Deye SUN-12K-G06P3-EU-AM2-P1 series is designed to cater to the needs of modern solar energy systems with its cutting-edge technology and advanced features. These three-phase string inverters are capable of delivering high efficiency, flexibility, and reliability, making them suitable for a wide range of applications, including residential, commercial, and industrial settings. The series offers a maximum efficiency of up to 98.5%, ensuring optimal energy conversion from solar panels to the electrical grid.</span>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(557, '<table selecttype=\"all\">\n<tbody>\n<tr height=\"36\">\n<td colspan=\"2\" width=\"1178\"><strong>PV String Input Data</strong></td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Max. PV Input Power (kW)</td>\n<td width=\"90\">22.5</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Max. PV Input Voltage (V)&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;</td>\n<td width=\"900\">1100</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Start-up Voltage (V)</td>\n<td width=\"900\">140</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">MPPT Voltage Range (V)</td>\n<td width=\"900\">120-1000</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Rated PV Input Voltage (V)&#160;</td>\n<td width=\"900\">600</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Max. Operating PV Input Current (A)</td>\n<td width=\"90\">20+26</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Max. Input Short Circuit Current (A)</td>\n<td width=\"90\">30+39</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">No. of MPP Trackers/<br />No. of StringsperMPP Tracker</td>\n<td width=\"90\">2/1+2</td>\n</tr>\n<tr height=\"36\">\n<td colspan=\"2\" width=\"1178\">\n<p></p>\n<p><strong>AC Output Side</strong></p>\n</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Rated AC Output Active Power (kW)</td>\n<td width=\"90\">15</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Max.AC Output Apparent Power (kVA)</td>\n<td width=\"90\">16.5</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Rated AC Output Current (A)</td>\n<td width=\"90\">22.8/21.8</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Max. AC Output Current (A)</td>\n<td width=\"90\">25/24</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Rated Output Voltage/Range (V)&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;&#160;</td>\n<td width=\"900\">220/380V, 230/400V 0.85Un-1.1Un</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Grid Connection Form</td>\n<td width=\"900\">3L/N/PE</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Rated Output Grid Frequency/Range(Hz)</td>\n<td width=\"900\">50/45-55, 60/55-65</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Power Factor Adjustment Range</td>\n<td width=\"900\">0.8 leading to 0.8 lagging</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Total Current Harmonic Distortion THDi</td>\n<td width=\"900\">&lt;3%</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">DC Injection Current</td>\n<td width=\"900\">&lt;0.5%ln</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">\n<p></p>\n<p><strong>E&#64259;ciency</strong></p>\n</td>\n<td width=\"900\"></td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Max. Ef&#64257;ciency</td>\n<td width=\"90\">98.5%</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Euro Ef&#64257;ciency</td>\n<td width=\"90\">98%</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">MPPTEf&#64257;ciency</td>\n<td width=\"900\">&gt;99%</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">\n<p></p>\n<p><strong>Equipment Protection</strong></p>\n</td>\n<td width=\"900\"></td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">DC Polarity Reverse Connection Protection</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">AC Output Overcurrent Protection</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">AC Output Overvoltage Protection</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">AC Output Short Circuit Protection</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Thermal Protection</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">DC Terminal Insulation Impedance Monitoring</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">DC Component Monitoring</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr>\n<td>\n<div><span>Arc Fault Circuit Interrupter (AFCI)</span></div>\n</td>\n<td>\n<div><span>Optional</span></div>\n</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Ground Fault Current Monitoring</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Power Network Monitoring</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Island Protection Monitoring</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Earth Fault Detection</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Overvoltage Load Drop Protection</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Residual Current (RCD) Detection</td>\n<td width=\"900\">Yes</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Surge Protection Level</td>\n<td width=\"900\">TYPE II(DC),TYPE II(AC)</td>\n</tr>\n<tr height=\"36\">\n<td colspan=\"2\" width=\"1178\">\n<p></p>\n<p><strong>Interface</strong></p>\n</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Communication Interface</td>\n<td width=\"900\">RS485/RS232</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Monitor Mode</td>\n<td width=\"900\">GPRS/WIFI/Bluetooth/4G/LAN(optional)</td>\n</tr>\n<tr height=\"36\">\n<td colspan=\"2\" width=\"1178\">\n<p></p>\n<p><strong>General Data</strong></p>\n</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Operating Temperature Range (&#176;C)</td>\n<td width=\"900\"><span>-25 to +60</span><span>&#8451;</span><span>, &gt;45</span><span>&#8451;&#160;</span><span>Derating</span></td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Permissible Ambient Humidity</td>\n<td width=\"900\">0-100%</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Permissible Altitude (m)</td>\n<td width=\"900\">4000m</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Noise (dB)</td>\n<td width=\"900\">&lt;45</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Ingress Protection(IP) Rating</td>\n<td width=\"900\">IP 65</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Inverter Topology</td>\n<td width=\"900\">Non-Isolated</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Over Voltage Category</td>\n<td width=\"900\">OVC II(DC), OVC III(AC)</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Cabinet Size (WxHxD mm)</td>\n<td width=\"900\">283&#215;463&#215;178 (Excluding Connectors and Brackets)</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Weight (kg)</td>\n<td width=\"900\">11</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Warranty</td>\n<td width=\"900\">5 Years</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Type of Cooling</td>\n<td>\n<div><span>Intelligent</span></div>\n<div><span>air cooling</span></div>\n</td>\n</tr>\n<tr height=\"42\">\n<td width=\"278\">Grid Regulation</td>\n<td width=\"900\">IEC 61727, IEC 62116,CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,<br />OVE-Richtlinie R25,G98, G99,VDE-AR-N 4105</td>\n</tr>\n<tr height=\"36\">\n<td width=\"278\">Safety EMC/Standard</td>\n<td width=\"900\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</td>\n</tr>\n</tbody>\n</table>', 2, 'SUN-15K-G06P3-EU-AM2-P1 | Three Phase String Inverter | 2 MPPT', '<p>Thi Deye&#160;SUN-15K-G06P3-EU-AM2-P1 inverter series offers outstanding performance with a maximum efficiency of up to 98.5%, and a European efficiency rating between 97.5% and 98%, ensuring optimal energy conversion under various conditions. It supports zero export functionality to prevent feeding excess energy into the grid&#8212;ideal for regions with export restrictions. The integrated Virtual Synchronous Generator (VSG) feature enhances grid stability, while optional string intelligent monitoring enables real-time performance tracking of individual panel strings. With a wide output voltage range for flexible system design and an optional anti-PID function to protect panels from voltage-induced degradation, this series delivers reliable, efficient, and adaptable solar energy solutions.</p>\n<h3>Key Features</h3>\n<ul>\n<li><strong>High Efficiency:</strong>&#160;The inverters in this series boast a maximum efficiency of up to 98.5%, ensuring that the majority of the solar energy is converted into usable electricity. The European efficiency rating varies between 97.5% and 98%, highlighting the inverter&#8217;s effectiveness in various conditions.</li>\n<li><strong>Zero Export Application:</strong>&#160;This feature prevents excess energy from being fed back into the electrical grid. It is particularly useful in areas with restrictions on energy export or where compensation for exported energy is not available.</li>\n<li><strong>VSG Application:</strong>&#160;The Virtual Synchronous Generator (VSG) feature allows the inverter to simulate the behavior of a synchronous generator, which aids in maintaining grid stability and reliability.</li>\n<li><strong>String Intelligent Monitoring:</strong>&#160;Available as an optional feature, this allows real-time monitoring of the performance of each string of solar panels, helping to identify issues quickly and maintain optimal performance.</li>\n<li><strong>Wide Output Voltage Range:</strong>&#160;The inverters support a broad range of output voltages, facilitating adaptability to different system designs and requirements.</li>\n<li><strong>Anti-PID Function:</strong>&#160;The optional Anti-potential Induced Degradation (PID) function helps to extend the lifespan of the solar panels by preventing the degradation caused by high system voltages.<br /><br /></li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-008.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<p></p>\n<h3 id=\"protection-and-monitoring\">Protection and Monitoring</h3>\n<ul>\n<li>DC Injection Current: Less than 0.5% of the nominal current, maintaining grid compliance.</li>\n<li>MPPT Efficiency: Greater than 99%, ensuring optimal energy harvest from the solar panels.</li>\n<li>Protection Mechanisms: Includes DC polarity reverse connection protection, AC output overcurrent and overvoltage protection, thermal protection, insulation impedance monitoring, and ground fault current monitoring.</li>\n<li>Surge Protection: Type II DC and Type II AC surge protection is included to safeguard against voltage spikes.</li>\n<li>Communication Interface: Supports RS485 and RS232 interfaces for easy integration with monitoring systems. Optional communication modes include GPRS, WIFI, Bluetooth, 4G, and LAN for flexible connectivity.</li>\n</ul>\n<h3 id=\"physical-and-environmental-specifications\">Physical and Environmental Specifications</h3>\n<ul>\n<li>Operating Temperature Range: -25 to +60 &#176;C, with derating above 45&#176;C to protect the inverter under high-temperature conditions.</li>\n<li>Permissible Ambient Humidity: 0-100% relative humidity, making it suitable for various climates.</li>\n<li>Permissible Altitude: Up to 4000 meters, accommodating installations at high altitudes.</li>\n<li>Noise Level: Less than 45 dB, ensuring quiet operation.</li>\n<li>Cooling: Employs natural cooling or intelligent air cooling, depending on the model.</li>\n<li>Ingress Protection (IP) Rating: IP 65, making it dust-tight and protected against water jets, suitable for outdoor installations.</li>\n<li>Weight and Dimensions: Each unit weighs 11 kg, with dimensions of 283&#215;463&#215;178 mm (excluding connectors and brackets).</li>\n<li>Warranty: A standard 5-year warranty is provided for peace of mind.</li>\n</ul>\n<h3 id=\"certifications-and-compliance\">Certifications and Compliance</h3>\n<ul>\n<li>Regulatory Standards: Compliant with IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002, OVE-Richtlinie R25, G99, and VDE-AR-N 4105.</li>\n<li>Safety Standards: Meets the requirements of IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, and IEC/EN 62109-2.</li>\n</ul>', '<span>The Deye SUN-15K-G06P3-EU-AM2-P1 series is designed to cater to the needs of modern solar energy systems with its cutting-edge technology and advanced features. These three-phase string inverters are capable of delivering high efficiency, flexibility, and reliability, making them suitable for a wide range of applications, including residential, commercial, and industrial settings. The series offers a maximum efficiency of up to 98.5%, ensuring optimal energy conversion from solar panels to the electrical grid.</span>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', '');
INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(558, '<table selecttype=\"cells\">\n<tbody>\n<tr height=\"24\">\n<td width=\"240\"><strong>PV String Input Data</strong></td>\n<td width=\"873\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Max. PV Input Power(kW)</span></td>\n<td width=\"200\"><span>26</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Max. PV Input Voltage(V)</span></td>\n<td width=\"873\"><span>1100</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Start-up Voltage(V)</span></td>\n<td width=\"873\"><span>250</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>MPPT voltage range(V)</span></td>\n<td width=\"873\"><span>200-1000</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Rated PV Input voltage(V)</span></td>\n<td width=\"873\"><span>600</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Max. Input Short Circuit Current (A)</span></td>\n<td width=\"873\"><span>39+39</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Max. Operating PV Input Current(A)</span></td>\n<td width=\"873\"><span>26+26</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<p><span>No. of MPP Trackers/No. of Strings per MPP Tracker</span></p>\n<p></p>\n</td>\n<td width=\"873\"><span>2/2+2</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<div><strong>AC Output Side</strong></div>\n<div></div>\n</td>\n<td width=\"873\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Rated AC Output Active Power(kW)</span></td>\n<td width=\"200\"><span>20</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Max. AC Output Apparent Power(kVA)</span></td>\n<td width=\"200\"><span>22</span></td>\n</tr>\n<tr height=\"31\">\n<td width=\"240\"><span>Rated AC output current (A)</span></td>\n<td width=\"200\"><span>30.3/29</span></td>\n</tr>\n<tr height=\"29\">\n<td width=\"240\"><span>Max. AC Output Current(A)</span></td>\n<td width=\"200\"><span>33.3/31.9</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Rated output voltage/range (V)</span></td>\n<td width=\"873\"><span>220/380V, 230/400V 0.85Un-1.1Un</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Grid Connection Form</span></td>\n<td width=\"873\"><span>3L/N/PE</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Rated Output Grid Frequency/range(Hz)</span></td>\n<td width=\"873\"><span>50/45-55, 60/55-65</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Power Factor Adjustment Range</span></td>\n<td width=\"873\"><span>0.8 leading to 0.8 lagging</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Total Current Harmonic Distortion THDi</span></td>\n<td width=\"873\"><span>&lt;3%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">DC Injection Current</td>\n<td width=\"873\"><span>&lt;0.5%ln</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<p></p>\n<p><strong>Efficiency</strong></p>\n</td>\n<td width=\"873\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Max. Efficiency</span></td>\n<td width=\"873\"><span>98.5%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Euro Efficiency</span></td>\n<td width=\"873\"><span>98%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>MPPT Efficiency</span></td>\n<td width=\"873\"><span>&#65310;99%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<p></p>\n<p><strong>Equipment Protection</strong></p>\n</td>\n<td width=\"873\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">DC Reverse Polarity Protection</td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>AC Output Overcurrent Protection</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>AC Output Overvoltage Protection</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>AC Output Short Circuit Protection</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Thermal Protection</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Insulation Impedance Detection</td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>DC Component Monitoring</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td>\n<div><span>Arc Fault Circuit Interrupter (AFCI)</span></div>\n</td>\n<td>\n<div><span>Optional</span></div>\n</td>\n</tr>\n<tr>\n<td width=\"240\">\n<p>Anti-islanding Protection</p>\n</td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Residual Current Detection</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Surge Protection Level</span></td>\n<td width=\"900\"><span>TYPE II(DC),TYPE II(AC)</span></td>\n</tr>\n<tr height=\"24\">\n<td>\n<div><span>DC Switch</span></div>\n</td>\n<td><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<p></p>\n<p><strong>Interface</strong></p>\n</td>\n<td width=\"873\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Communication Interface</span></td>\n<td width=\"873\"><span>RS485/RS232</span></td>\n</tr>\n<tr>\n<td>\n<div><span>Monitor Mode</span></div>\n</td>\n<td>GPRS/WIFI/Bluetooth/4G/LAN(optional)</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<p></p>\n<p><strong>General Data</strong></p>\n</td>\n<td width=\"873\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Operating Temperature Range (&#176;C)</span></td>\n<td width=\"873\"><span>-25 to +60&#8451;, &gt;45&#8451; Derating</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Permissible Ambient Humidity</span></td>\n<td width=\"873\"><span>0&#126;100%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Permissible Altitude (m)</span></td>\n<td width=\"873\"><span>4000m</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Noise (dB)</span></td>\n<td width=\"873\"><span>&#8804; 50dB(A)</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Ingress Protection(IP) Rating</span></td>\n<td width=\"873\"><span>IP 65</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Inverter Topology</span></td>\n<td width=\"873\"><span>Non-Isolated</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Over Voltage Category</span></td>\n<td width=\"873\"><span>OVC II(DC),OVC III(AC)</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Cabinet Size (WxHxD mm)</span></td>\n<td width=\"873\"><span>362mm*527mm*220mm&#65288;Excluding connectors and brackets&#65289;</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Weight [kg]</span></td>\n<td width=\"873\"><span>20</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Warranty [year]</span></td>\n<td width=\"873\"><span>5 years</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Type Of Cooling</span></td>\n<td width=\"873\"><span>Intelligent air cooling</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Grid Regulation</span></td>\n<td width=\"873\"><span>IEC 61727,IEC 62116,CEI 0-21,EN 50549&#65292;NRS 097,RD 140,UNE 217002,OVE-Richtlinie R25,G99,VDE-AR-N 4105</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Safety EMC/Standard</span></td>\n<td width=\"873\"><span>IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</span></td>\n</tr>\n</tbody>\n</table>', 2, 'SUN-20K-G05 | Three Phase String Inverter | 2 MPPT', '<p data-start=\"0\" data-end=\"519\">The Deye SUN-20K-G05 series inverters are engineered for high performance and reliability, boasting a maximum efficiency of up to 98.6% and a European efficiency rating of 98%, ensuring minimal energy loss and optimal power conversion. With MPPT efficiency greater than 99% and a wide MPPT voltage range of 200&#8211;1000V, the system guarantees maximum energy yield and flexible panel configurations. The inverters support a rated PV input voltage of 600V and a start-up voltage of 250V, accommodating diverse solar setups.</p>\n<p data-start=\"521\" data-end=\"1024\">Designed for substantial power output, models like the SUN-20K-G05 offer <span>20</span>kW rated AC output and up to <span>22</span>kVA apparent power, with compatibility across grid standards such as 220/380V and 230/400V in 3L/N/PE form, allowing integration into various grid systems. The inverters are protected by a comprehensive safety suite, including DC polarity reversal protection, AC overcurrent and overvoltage protection, thermal regulation, earth fault detection, and DC injection current limitation under 0.5%ln.</p>\n<p data-start=\"1026\" data-end=\"1626\" data-is-last-node=\"\" data-is-only-node=\"\">Built for diverse environmental conditions, they operate between -25&#176;C and +60&#176;C with noise levels below 50 dB and an IP65 rating for water and dust resistance. The compact and lightweight design (362&#215;527&#215;220 mm, 20 kg) allows for easy installation and maintenance. Connectivity options are extensive, featuring GPRS, WIFI, Bluetooth, 4G, LAN, and RS485/RS232 interfaces for advanced monitoring and management. With TYPE II surge protection on both AC and DC sides and a standard 5-year warranty, the SUN-20K-G05 series offers a robust, efficient, and user-friendly solution for solar energy systems.</p>\n<h3>Key Features</h3>\n<ul>\n<li><strong>Maximized Efficiency:</strong>&#160;The Deye SUN-20K-G05 series boasts a maximum efficiency of up to 98.6% with a European efficiency rating of 98%. This high efficiency ensures maximum energy conversion from the solar panels, minimizing losses and ensuring optimal performance.</li>\n<li><strong>MPPT Efficiency:&#160;</strong>With an MPPT efficiency greater than 99%, these inverters ensure that the solar panels operate at their optimal power point, leading to higher energy yields. The MPPT voltage range of 200-1000V provides flexibility in selecting panels and configurations.</li>\n<li><strong>PV Input Specifications:&#160;</strong>The inverters support a maximum PV input power accommodated comfortably within various models&#8217; specific ranges. They come with a start-up voltage of 250V and can handle a rated PV input voltage of 600V, ensuring compatibility with a broad array of solar panel setups.</li>\n<li><strong>AC Output Capacities:&#160;</strong>Equipped to handle significant power outputs, the SUN-20K-G05 model, for instance, offers a rated AC output active power of 20kW with a maximum AC output apparent power of up to 22kVA. They provide robust AC output options suitable for different grid standards, including 220/380V and 230/400V.</li>\n<li><strong>Grid Compatibility:</strong>&#160;The inverters support a grid connection form of 3L/N/PE with rated output voltages of 220/380V and 230/400V, and a permissible range of 0.85Un-1.1Un. This adaptability ensures seamless integration into various grid configurations.</li>\n<li><strong>Comprehensive Protection:</strong>&#160;The series incorporates extensive protection features, including DC polarity reverse connection protection, AC output overcurrent and overvoltage protection, and DC injection current regulation to less than 0.5%ln. Additionally, it has thermal protection, earth fault detection, and ground fault current monitoring, ensuring safe and reliable operation.</li>\n<li><strong>Environmental Robustness and Noise Management:&#160;</strong>Designed to operate in temperatures from -25 to +60&#176;C with derating above 45&#176;C, these inverters can function effectively in diverse climates. They maintain noise levels below 50 dB and are rated IP65 for dust and water resistance, ensuring durability and reliability.</li>\n<li><strong>Advanced Monitoring and Connectivity:&#160;</strong>These inverters offer various monitoring modes including GPRS, WIFI, Bluetooth, 4G, and LAN, along with RS485/RS232 communication interfaces, facilitating easy and efficient system management and monitoring.</li>\n<li><strong>Surge Protection:&#160;</strong>The inverters are equipped with TYPE II surge protection for both DC and AC sides, enhancing their longevity and reliability by protecting against electrical surges.</li>\n<li><strong>Easy Installation and Maintenance:</strong>&#160;With a compact design (362&#215;527&#215;220 mm) and a weight of 20 kg, excluding connectors and brackets, these inverters are easy to handle and install.</li>\n<li><strong>Warranty:&#160;</strong>A standard 5-year warranty underscores the reliability and durability of these inverters, offering peace of mind to investors and users.<br /><br /></li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-009.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<p></p>\n<h3 id=\"protection-and-monitoring\">Protection and Monitoring</h3>\n<ul>\n<li>DC Injection Current: Less than 0.5% of the nominal current, maintaining grid compliance.</li>\n<li>MPPT Efficiency: Greater than 99%, ensuring optimal energy harvest from the solar panels.</li>\n<li>Protection Mechanisms: Includes DC polarity reverse connection protection, AC output overcurrent and overvoltage protection, thermal protection, insulation impedance monitoring, and ground fault current monitoring.</li>\n<li>Surge Protection: Type II DC and Type II AC surge protection is included to safeguard against voltage spikes.</li>\n<li>Communication Interface: Supports RS485 and RS232 interfaces for easy integration with monitoring systems. Optional communication modes include GPRS, WIFI, Bluetooth, 4G, and LAN for flexible connectivity.</li>\n</ul>\n<h3 id=\"physical-and-environmental-specifications\">Physical and Environmental Specifications</h3>\n<ul>\n<li>Operating Temperature Range: -25 to +60 &#176;C, with derating above 45&#176;C to protect the inverter under high-temperature conditions.</li>\n<li>Permissible Ambient Humidity: 0-100% relative humidity, making it suitable for various climates.</li>\n<li>Permissible Altitude: Up to 4000 meters, accommodating installations at high altitudes.</li>\n<li>Noise Level: Less than 45 dB, ensuring quiet operation.</li>\n<li>Cooling: Employs natural cooling or intelligent air cooling, depending on the model.</li>\n<li>Ingress Protection (IP) Rating: IP 65, making it dust-tight and protected against water jets, suitable for outdoor installations.</li>\n<li>Weight and Dimensions: Each unit weighs 20 kg, with dimensions of&#160;<span>362 x 527 x 220</span>&#160;mm (excluding connectors and brackets).</li>\n<li>Warranty: A standard 5-year warranty is provided for peace of mind.</li>\n</ul>\n<h3 id=\"certifications-and-compliance\">Certifications and Compliance</h3>\n<ul>\n<li>Regulatory Standards: Compliant with IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002, OVE-Richtlinie R25, G99, and VDE-AR-N 4105.</li>\n<li>Safety Standards: Meets the requirements of IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, and IEC/EN 62109-2.</li>\n</ul>', '<span>The Deye Three-Phase String Inverter SUN-20K-G05 delivers cutting-edge solar energy solutions with maximal efficiency reaching up to 98.6%. Featuring dual MPP (Maximum Power Point) trackers, this range is designed to optimize energy harvesting from solar panels, making them ideal for zero export and VSG (Virtual Synchronous Generator) applications. Their robust build and advanced functionality make these inverters a top choice for both residential and commercial solar installations.</span>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(559, '<table selecttype=\"cells\">\n<tbody>\n<tr height=\"24\">\n<td width=\"240\"><strong>PV String Input Data</strong></td>\n<td width=\"873\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Max. PV Input Power(kW)</span></td>\n<td width=\"120\"><span>32.5</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Max. PV Input Voltage(V)</span></td>\n<td width=\"873\"><span>1100</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Start-up Voltage(V)</span></td>\n<td width=\"873\"><span>250</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>MPPT voltage range(V)</span></td>\n<td width=\"873\"><span>200-1000</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Rated PV Input voltage(V)</span></td>\n<td width=\"873\"><span>600</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Max. Input Short Circuit Current (A)</span></td>\n<td width=\"873\"><span>39+39</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Max. Operating PV Input Current(A)</span></td>\n<td width=\"873\"><span>26+26</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<p><span>No. of MPP Trackers/No. of Strings per MPP Tracker</span></p>\n<p></p>\n</td>\n<td width=\"873\"><span>2/2+2</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<div><strong>AC Output Side</strong></div>\n<div></div>\n</td>\n<td width=\"873\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Rated AC Output Active Power(kW)</span></td>\n<td width=\"120\"><span>25</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Max. AC Output Apparent Power(kVA)</span></td>\n<td width=\"120\"><span>27.5</span></td>\n</tr>\n<tr height=\"31\">\n<td width=\"240\"><span>Rated AC output current (A)</span></td>\n<td width=\"120\"><span>37.9/36.2</span></td>\n</tr>\n<tr height=\"29\">\n<td width=\"240\"><span>Max. AC Output Current(A)</span></td>\n<td width=\"120\"><span>41.7/39.8</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Rated output voltage/range (V)</span></td>\n<td width=\"873\"><span>220/380V, 230/400V 0.85Un-1.1Un</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Grid Connection Form</span></td>\n<td width=\"873\"><span>3L/N/PE</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Rated Output Grid Frequency/range(Hz)</span></td>\n<td width=\"873\"><span>50/45-55, 60/55-65</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Power Factor Adjustment Range</span></td>\n<td width=\"873\"><span>0.8 leading to 0.8 lagging</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Total Current Harmonic Distortion THDi</span></td>\n<td width=\"873\"><span>&lt;3%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">DC Injection Current</td>\n<td width=\"873\"><span>&lt;0.5%ln</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<p></p>\n<p><strong>Efficiency</strong></p>\n</td>\n<td width=\"873\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Max. Efficiency</span></td>\n<td width=\"873\"><span>98.5%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Euro Efficiency</span></td>\n<td width=\"873\"><span>98%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>MPPT Efficiency</span></td>\n<td width=\"873\"><span>&#65310;99%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<p></p>\n<p><strong>Equipment Protection</strong></p>\n</td>\n<td width=\"873\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">DC Reverse Polarity Protection</td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>AC Output Overcurrent Protection</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>AC Output Overvoltage Protection</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>AC Output Short Circuit Protection</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Thermal Protection</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Insulation Impedance Detection</td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>DC Component Monitoring</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td>\n<div><span>Arc Fault Circuit Interrupter (AFCI)</span></div>\n</td>\n<td>\n<div><span>Optional</span></div>\n</td>\n</tr>\n<tr>\n<td width=\"240\">\n<p>Anti-islanding Protection</p>\n</td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Residual Current Detection</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Surge Protection Level</span></td>\n<td width=\"900\"><span>TYPE II(DC),TYPE II(AC)</span></td>\n</tr>\n<tr height=\"24\">\n<td>\n<div><span>DC Switch</span></div>\n</td>\n<td><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<p></p>\n<p><strong>Interface</strong></p>\n</td>\n<td width=\"873\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Communication Interface</span></td>\n<td width=\"873\"><span>RS485/RS232</span></td>\n</tr>\n<tr>\n<td>\n<div><span>Monitor Mode</span></div>\n</td>\n<td>GPRS/WIFI/Bluetooth/4G/LAN(optional)</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<p></p>\n<p><strong>General Data</strong></p>\n</td>\n<td width=\"873\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Operating Temperature Range (&#176;C)</span></td>\n<td width=\"873\"><span>-25 to +60&#8451;, &gt;45&#8451; Derating</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Permissible Ambient Humidity</span></td>\n<td width=\"873\"><span>0&#126;100%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Permissible Altitude (m)</span></td>\n<td width=\"873\"><span>4000m</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Noise (dB)</span></td>\n<td width=\"873\"><span>&#8804; 50dB(A)</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Ingress Protection(IP) Rating</span></td>\n<td width=\"873\"><span>IP 65</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Inverter Topology</span></td>\n<td width=\"873\"><span>Non-Isolated</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Over Voltage Category</span></td>\n<td width=\"873\"><span>OVC II(DC),OVC III(AC)</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Cabinet Size (WxHxD mm)</span></td>\n<td width=\"873\"><span>362mm*527mm*220mm&#65288;Excluding connectors and brackets&#65289;</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Weight [kg]</span></td>\n<td width=\"873\"><span>20</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Warranty [year]</span></td>\n<td width=\"873\"><span>5 years</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Type Of Cooling</span></td>\n<td width=\"873\"><span>Intelligent air cooling</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Grid Regulation</span></td>\n<td width=\"873\"><span>IEC 61727,IEC 62116,CEI 0-21,EN 50549&#65292;NRS 097,RD 140,UNE 217002,OVE-Richtlinie R25,G99,VDE-AR-N 4105</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Safety EMC/Standard</span></td>\n<td width=\"873\"><span>IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</span></td>\n</tr>\n</tbody>\n</table>', 2, 'SUN-25K-G05 | Three Phase String Inverter | 2 MPPT', '<p data-start=\"0\" data-end=\"519\">The Deye SUN-25K-G05 series inverters are engineered for high performance and reliability, boasting a maximum efficiency of up to 98.6% and a European efficiency rating of 98%, ensuring minimal energy loss and optimal power conversion. With MPPT efficiency greater than 99% and a wide MPPT voltage range of 200&#8211;1000V, the system guarantees maximum energy yield and flexible panel configurations. The inverters support a rated PV input voltage of 600V and a start-up voltage of 250V, accommodating diverse solar setups.</p>\n<p data-start=\"521\" data-end=\"1024\">Designed for substantial power output, models like the SUN-25K-G05 offer <span>25</span>kW rated AC output and up to <span>27.5</span>kVA apparent power, with compatibility across grid standards such as 220/380V and 230/400V in 3L/N/PE form, allowing integration into various grid systems. The inverters are protected by a comprehensive safety suite, including DC polarity reversal protection, AC overcurrent and overvoltage protection, thermal regulation, earth fault detection, and DC injection current limitation under 0.5%ln.</p>\n<p data-start=\"1026\" data-end=\"1626\" data-is-last-node=\"\" data-is-only-node=\"\">Built for diverse environmental conditions, they operate between -25&#176;C and +60&#176;C with noise levels below 50 dB and an IP65 rating for water and dust resistance. The compact and lightweight design (362&#215;527&#215;220 mm, 20 kg) allows for easy installation and maintenance. Connectivity options are extensive, featuring GPRS, WIFI, Bluetooth, 4G, LAN, and RS485/RS232 interfaces for advanced monitoring and management. With TYPE II surge protection on both AC and DC sides and a standard 5-year warranty, the SUN-25K-G05 series offers a robust, efficient, and user-friendly solution for solar energy systems.</p>\n<h3>Key Features</h3>\n<ul>\n<li><strong>Maximized Efficiency:</strong>&#160;The Deye SUN-20K-G05 series boasts a maximum efficiency of up to 98.6% with a European efficiency rating of 98%. This high efficiency ensures maximum energy conversion from the solar panels, minimizing losses and ensuring optimal performance.</li>\n<li><strong>MPPT Efficiency:&#160;</strong>With an MPPT efficiency greater than 99%, these inverters ensure that the solar panels operate at their optimal power point, leading to higher energy yields. The MPPT voltage range of 200-1000V provides flexibility in selecting panels and configurations.</li>\n<li><strong>PV Input Specifications:&#160;</strong>The inverters support a maximum PV input power accommodated comfortably within various models&#8217; specific ranges. They come with a start-up voltage of 250V and can handle a rated PV input voltage of 600V, ensuring compatibility with a broad array of solar panel setups.</li>\n<li><strong>AC Output Capacities:&#160;</strong>Equipped to handle significant power outputs, the SUN-25K-G05 model, for instance, offers a rated AC output active power of 25kW with a maximum AC output apparent power of up to 27.5kVA. They provide robust AC output options suitable for different grid standards, including 220/380V and 230/400V.</li>\n<li><strong>Grid Compatibility:</strong>&#160;The inverters support a grid connection form of 3L/N/PE with rated output voltages of 220/380V and 230/400V, and a permissible range of 0.85Un-1.1Un. This adaptability ensures seamless integration into various grid configurations.</li>\n<li><strong>Comprehensive Protection:</strong>&#160;The series incorporates extensive protection features, including DC polarity reverse connection protection, AC output overcurrent and overvoltage protection, and DC injection current regulation to less than 0.5%ln. Additionally, it has thermal protection, earth fault detection, and ground fault current monitoring, ensuring safe and reliable operation.</li>\n<li><strong>Environmental Robustness and Noise Management:&#160;</strong>Designed to operate in temperatures from -25 to +60&#176;C with derating above 45&#176;C, these inverters can function effectively in diverse climates. They maintain noise levels below 50 dB and are rated IP65 for dust and water resistance, ensuring durability and reliability.</li>\n<li><strong>Advanced Monitoring and Connectivity:&#160;</strong>These inverters offer various monitoring modes including GPRS, WIFI, Bluetooth, 4G, and LAN, along with RS485/RS232 communication interfaces, facilitating easy and efficient system management and monitoring.</li>\n<li><strong>Surge Protection:&#160;</strong>The inverters are equipped with TYPE II surge protection for both DC and AC sides, enhancing their longevity and reliability by protecting against electrical surges.</li>\n<li><strong>Easy Installation and Maintenance:</strong>&#160;With a compact design (362&#215;527&#215;220 mm) and a weight of 20 kg, excluding connectors and brackets, these inverters are easy to handle and install.</li>\n<li><strong>Warranty:&#160;</strong>A standard 5-year warranty underscores the reliability and durability of these inverters, offering peace of mind to investors and users.<br /><br /></li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-009.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<p></p>\n<h3 id=\"protection-and-monitoring\">Protection and Monitoring</h3>\n<ul>\n<li>DC Injection Current: Less than 0.5% of the nominal current, maintaining grid compliance.</li>\n<li>MPPT Efficiency: Greater than 99%, ensuring optimal energy harvest from the solar panels.</li>\n<li>Protection Mechanisms: Includes DC polarity reverse connection protection, AC output overcurrent and overvoltage protection, thermal protection, insulation impedance monitoring, and ground fault current monitoring.</li>\n<li>Surge Protection: Type II DC and Type II AC surge protection is included to safeguard against voltage spikes.</li>\n<li>Communication Interface: Supports RS485 and RS232 interfaces for easy integration with monitoring systems. Optional communication modes include GPRS, WIFI, Bluetooth, 4G, and LAN for flexible connectivity.</li>\n</ul>\n<h3 id=\"physical-and-environmental-specifications\">Physical and Environmental Specifications</h3>\n<ul>\n<li>Operating Temperature Range: -25 to +60 &#176;C, with derating above 45&#176;C to protect the inverter under high-temperature conditions.</li>\n<li>Permissible Ambient Humidity: 0-100% relative humidity, making it suitable for various climates.</li>\n<li>Permissible Altitude: Up to 4000 meters, accommodating installations at high altitudes.</li>\n<li>Noise Level: Less than 45 dB, ensuring quiet operation.</li>\n<li>Cooling: Employs natural cooling or intelligent air cooling, depending on the model.</li>\n<li>Ingress Protection (IP) Rating: IP 65, making it dust-tight and protected against water jets, suitable for outdoor installations.</li>\n<li>Weight and Dimensions: Each unit weighs 20 kg, with dimensions of&#160;<span>362 x 527 x 220</span>&#160;mm (excluding connectors and brackets).</li>\n<li>Warranty: A standard 5-year warranty is provided for peace of mind.</li>\n</ul>\n<h3 id=\"certifications-and-compliance\">Certifications and Compliance</h3>\n<ul>\n<li>Regulatory Standards: Compliant with IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002, OVE-Richtlinie R25, G99, and VDE-AR-N 4105.</li>\n<li>Safety Standards: Meets the requirements of IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, and IEC/EN 62109-2.</li>\n</ul>', '<span>The Deye Three-Phase String Inverter SUN-25K-G05 delivers cutting-edge solar energy solutions with maximal efficiency reaching up to 98.6%. Featuring dual MPP (Maximum Power Point) trackers, this range is designed to optimize energy harvesting from solar panels, making them ideal for zero export and VSG (Virtual Synchronous Generator) applications. Their robust build and advanced functionality make these inverters a top choice for both residential and commercial solar installations.</span>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', '');
INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(560, '<table selecttype=\"cells\">\n<tbody>\n<tr height=\"24\">\n<td width=\"240\"><strong>PV String Input Date</strong></td>\n<td width=\"753\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Max. PV Input Power(kW)</td>\n<td width=\"200\">39</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Max. PV Input Voltage(V)</td>\n<td width=\"753\">1100</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Start-up Voltage(V)</td>\n<td width=\"753\">250</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">MPPT voltage range(V)</td>\n<td width=\"753\">200-1000</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Rated PV Input voltage(V)</td>\n<td width=\"753\">600</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Max. Input Short Circuit Current (A)</td>\n<td width=\"753\">60+60</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Max. Operating PV Input Current(A)</td>\n<td width=\"753\">40+40</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<p>No. of MPP Trackers/No. of Strings per MPP Tracker</p>\n<p></p>\n</td>\n<td width=\"753\">2/3+3</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<div></div>\n<div><strong>AC Output Side</strong></div>\n</td>\n<td width=\"753\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Rated AC Output Active Power(kW)</td>\n<td width=\"200\">30</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Max. AC Output Apparent Power(kVA)</td>\n<td width=\"200\">33</td>\n</tr>\n<tr height=\"31\">\n<td width=\"240\">Rated AC output current (A)</td>\n<td width=\"200\">45.5/43.5</td>\n</tr>\n<tr height=\"29\">\n<td width=\"240\">Max. AC Output Current(A)</td>\n<td width=\"200\">50/47.9</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Rated output voltage/range (V)</td>\n<td width=\"753\">220/380V, 230/400V 0.85Un-1.1Un</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Grid Connection Form</td>\n<td width=\"753\">3L/N/PE</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Rated Output Grid Frequency/range(Hz)</td>\n<td width=\"753\">50/45-55, 60/55-65</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Power Factor Adjustment Range</td>\n<td width=\"753\">0.8 leading to 0.8lagging</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Total Current Harmonic Distortion THDi</td>\n<td width=\"753\">&lt;3%</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">DC Injection Current</td>\n<td width=\"753\">&lt;0.5%ln</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<p></p>\n<p><strong>Efficiency</strong></p>\n</td>\n<td width=\"753\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Max. Efficiency</td>\n<td width=\"753\">98.6%</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Euro Efficiency</td>\n<td width=\"753\">98.1%</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">MPPT Efficiency</td>\n<td width=\"753\">&#65310;99%</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Equipment Protection</td>\n<td width=\"753\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">DC Reverse Polarity Protection</td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>AC Output Overcurrent Protection</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>AC Output Overvoltage Protection</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>AC Output Short Circuit Protection</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Thermal Protection</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Insulation Impedance Detection</td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>DC Component Monitoring</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td>\n<div><span>Arc Fault Circuit Interrupter (AFCI)</span></div>\n</td>\n<td>\n<div><span>Optional</span></div>\n</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<p>Anti-islanding Protection</p>\n</td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr>\n<td width=\"240\"><span>Residual Current Detection</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Surge Protection Level</span></td>\n<td width=\"900\"><span>TYPE II(DC),TYPE II(AC)</span></td>\n</tr>\n<tr height=\"24\">\n<td>\n<div><span>DC Switch</span></div>\n</td>\n<td><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<p></p>\n<p><strong>Interface</strong></p>\n</td>\n<td width=\"753\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Communication Interface</td>\n<td width=\"753\">RS485/RS232</td>\n</tr>\n<tr>\n<td>\n<div><span>Monitor Mode</span></div>\n</td>\n<td>&#160;GPRS/WIFI/Bluetooth/4G/LAN(optional)</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<p></p>\n<p><strong>General Data</strong></p>\n</td>\n<td width=\"753\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Operating Temperature Range (&#176;C)</td>\n<td width=\"753\">-25 to +60&#8451;, &gt;45&#8451; Derating</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Permissible Ambient Humidity</td>\n<td width=\"753\">0&#126;100%</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Permissible Altitude (m)</td>\n<td width=\"753\">4000m</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Noise (dB)</td>\n<td width=\"753\">&#8804; 60</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Ingress Protection(IP) Rating</td>\n<td width=\"753\">IP 65</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Inverter Topology</td>\n<td width=\"753\">Non-Isolated</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Over Voltage Category</td>\n<td width=\"753\">OVC II(DC),OVC III(AC)</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Cabinet Size (WxHxD mm)</td>\n<td width=\"753\">330*572*206&#65288;Excluding connectors and brackets&#65289;</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Weight [kg]</td>\n<td width=\"753\">28.7</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Warranty [year]</td>\n<td width=\"753\">5 years</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Type Of Cooling</td>\n<td width=\"753\">Intelligent air cooling</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Grid Regulation</td>\n<td width=\"753\">IEC 61727,IEC 62116,CEI 0-21,EN 50549&#65292;NRS 097,RD 140,UNE 217002,OVE-Richtlinie R25,G99,VDE-AR-N 4105</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Safety EMC/Standard</td>\n<td width=\"753\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</td>\n</tr>\n</tbody>\n</table>', 2, 'SUN-30K-G04 | Three Phase String Inverter | 2 MPPT', '<p data-start=\"0\" data-end=\"519\">The Deye SUN-30K-G04 series inverters are engineered for high performance and reliability, boasting a maximum efficiency of up to 98.6% and a European efficiency rating of 98%, ensuring minimal energy loss and optimal power conversion. With MPPT efficiency greater than 99% and a wide MPPT voltage range of 200&#8211;1000V, the system guarantees maximum energy yield and flexible panel configurations. The inverters support a rated PV input voltage of 600V and a start-up voltage of 250V, accommodating diverse solar setups.</p>\n<p data-start=\"521\" data-end=\"1024\">Designed for substantial power output, models like the SUN-30K-G04 offer <span>30</span>kW rated AC output and up to <span>27.5</span>kVA apparent power, with compatibility across grid standards such as 220/380V and 230/400V in 3L/N/PE form, allowing integration into various grid systems. The inverters are protected by a comprehensive safety suite, including DC polarity reversal protection, AC overcurrent and overvoltage protection, thermal regulation, earth fault detection, and DC injection current limitation under 0.5%ln.</p>\n<p data-start=\"1026\" data-end=\"1626\" data-is-last-node=\"\" data-is-only-node=\"\">Built for diverse environmental conditions, they operate between -25&#176;C and +60&#176;C with noise levels below 50 dB and an IP65 rating for water and dust resistance. The compact and lightweight design (362&#215;527&#215;220 mm, 20 kg) allows for easy installation and maintenance. Connectivity options are extensive, featuring GPRS, WIFI, Bluetooth, 4G, LAN, and RS485/RS232 interfaces for advanced monitoring and management. With TYPE II surge protection on both AC and DC sides and a standard 5-year warranty, the SUN-30K-G04 series offers a robust, efficient, and user-friendly solution for solar energy systems.</p>\n<h3>Key Features</h3>\n<ul>\n<li><strong>High Efficiency:</strong>&#160;The SUN-30K-G04 series boasts a maximum efficiency of up to 98.6%, ensuring that more of the harvested solar energy is converted into usable power. Additionally, it features a European efficiency of 98.1%, making it one of the most efficient inverters available on the market.</li>\n<li><strong>Versatile Input Capabilities:&#160;</strong>With a maximum PV input power of 39 kW, these inverters can handle significant power inputs. The wide MPPT (Maximum Power Point Tracking) voltage range of 200V to 850V allows for flexible design options and compatibility with various types of solar panels. Furthermore, the inverters can start operating at a low voltage of 250V, enhancing their operational flexibility.</li>\n<li><strong>Advanced Protection Mechanisms:&#160;</strong>The Deye SUN-30K-G04 series is equipped with comprehensive protection features to ensure system safety and longevity. These include DC reverse polarity protection, AC overcurrent and overvoltage protection, surge protection (Type II), and short circuit protection. Additionally, the inverters come with advanced monitoring capabilities such as ground fault current monitoring, island protection, and earth fault detection.</li>\n<li><strong>Robust and Reliable Design:&#160;</strong>Built for durability, these inverters can operate in harsh environmental conditions with a wide temperature range from -25&#176;C to 60&#176;C, with derating above 45&#176;C. The inverters are also designed to withstand dust and water ingress with an IP65 rating, ensuring reliable performance in various outdoor settings. The permissible altitude is up to 4000 meters, making it suitable for installations in high-altitude areas.</li>\n<li><strong>Efficient Cooling System:</strong>&#160;The intelligent air cooling system ensures optimal thermal management, preventing overheating and maintaining efficiency under high-load conditions. This feature significantly extends the lifespan of the inverter and ensures stable performance over time.</li>\n<li><strong>Advanced Communication Options:</strong>&#160;The SUN-30K-G04 series supports multiple communication interfaces including RS485 and RS232, and offers optional communication modules such as GPRS, WiFi, Bluetooth, 4G, and LAN. These options provide seamless integration with monitoring systems and facilitate remote management and diagnostics.</li>\n<li><strong>Standards and Compliance:&#160;</strong>The inverters comply with numerous international and regional standards including IEC 61727, IEC 62116, CEI 0-21, EN 50549, and various others, which guarantees their reliability and integration with different grid requirements around the world.</li>\n</ul>\n<br /><br />\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-010.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<p></p>\n<h3>Technical Specifications</h3>\n<ul>\n<li><span>Max PV Input Power:</span>&#160;39kW</li>\n<li><span>Rated AC Output Power:</span>&#160;30kW</li>\n<li><span>Max Operating PV Input Current:</span>&#160;40+40A</li>\n<li><span>Rated Output Voltage:</span>&#160;220/380V, 230/400V</li>\n<li><span>Total Harmonic Distortion (THD):</span>&#160;&lt;3%</li>\n<li><span>Overall Dimensions:</span>&#160;362x577x215 mm</li>\n<li><span>Weight:</span>&#160;23 kg</li>\n</ul>\n<p>The Deye SUN-30K-G04 series is ideally suited for applications requiring robust, efficient, and reliable inverters. Whether for large-scale commercial installations or industrial solar power systems, these inverters deliver unparalleled performance and versatility.</p>', '<span>One of the standout features of the SUN-30K-G04 series is its exceptional efficiency. With a maximum efficiency of 98.6% and a European efficiency of 98.1%, these inverters ensure optimal energy conversion, minimizing losses and maximizing the return on investment. The inverters support a maximum PV input power up to 39 kW. They also boast a wide MPPT (Maximum Power Point Tracking) voltage range of 200V to 850V, allowing for flexibility in system design and ensuring compatibility with a wide variety of solar panels.</span>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(561, '<table selecttype=\"cells\">\n<tbody>\n<tr height=\"24\">\n<td width=\"240\"><strong>PV String Input Date</strong></td>\n<td width=\"600\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Max. PV Input Power(kW)</span></td>\n<td width=\"200\"><span>52</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Max. PV Input Voltage(V)</span></td>\n<td width=\"600\"><span>1100</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Start-up Voltage(V)</span></td>\n<td width=\"600\"><span>250</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>MPPT voltage range(V)</span></td>\n<td width=\"600\"><span>200-1000</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Rated PV Input voltage(V)</span></td>\n<td width=\"600\"><span>600</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Max. Input Short Circuit Current (A)</span></td>\n<td width=\"400\"><span>60+60+60</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Max. Operating PV Input Current(A)</span></td>\n<td width=\"400\"><span>40+40+40</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<p><span>No. of MPPT Trackers/No. of Strings per MPPT Trackers</span></p>\n<p></p>\n</td>\n<td width=\"400\"><span>3/3+3+3</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<div><strong>AC Output Side</strong></div>\n</td>\n<td width=\"600\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Rated AC Output Active Power(kW)</span></td>\n<td width=\"200\"><span>40</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Max. AC Output Apparent Power(kVA)</span></td>\n<td width=\"200\"><span>44</span></td>\n</tr>\n<tr height=\"31\">\n<td width=\"240\"><span>Rated AC output current (A)</span></td>\n<td width=\"200\"><span>60.6/58</span></td>\n</tr>\n<tr height=\"29\">\n<td width=\"240\"><span>Max. AC IOutput Current(A)</span></td>\n<td width=\"200\"><span>66.7/63.8</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Rated output voltage/range (V)</span></td>\n<td width=\"600\"><span>220/380V, 230/400V 0.85Un-1.1Un</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Grid Connection Form</span></td>\n<td width=\"600\"><span>3L/N/PE</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Rated Output Grid Frequency/range(Hz)</span></td>\n<td width=\"600\"><span>50/45-55, 60/55-65</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Power Factor Adjustment Range</span></td>\n<td width=\"600\"><span>0.8 leading to 0.8 lagging</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Total Current Harmonic Distortion THDi</span></td>\n<td width=\"600\"><span>&lt;3%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<p>DC Injection Current</p>\n<p></p>\n</td>\n<td width=\"600\"><span>&lt;0.5%ln</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><strong>Efficiency</strong></td>\n<td width=\"600\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Max. Efficiency</span></td>\n<td width=\"600\"><span>98.7%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Euro Efficiency</span></td>\n<td width=\"200\"><span>98.1%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<p><span>MPPT Efficiency</span></p>\n<p></p>\n</td>\n<td width=\"600\"><span>&#65310;99%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><strong>Equipment Protection</strong></td>\n<td width=\"600\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">DC Reverse Polarity Protection</td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>AC Output Overcurrent Protection</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>AC Output Overvoltage Protection</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>AC Output Short Circuit Protection</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Thermal Protection</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Insulation Impedance Detection</td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>DC Component Monitoring</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td>\n<div><span>Arc Fault Circuit Interrupter (AFCI)</span></div>\n</td>\n<td>\n<div><span>Optional</span></div>\n</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<p>Anti-islanding Protection</p>\n</td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr>\n<td width=\"240\"><span>Residual Current Detection</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Surge Protection Level</span></td>\n<td width=\"900\"><span>TYPE II(DC),TYPE II(AC)</span></td>\n</tr>\n<tr height=\"24\">\n<td>\n<div><span>DC Switch</span></div>\n<div></div>\n</td>\n<td><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><strong>Interface</strong></td>\n<td width=\"600\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Communication Interface</span></td>\n<td width=\"600\"><span>RS485/RS232</span></td>\n</tr>\n<tr>\n<td>\n<div><span>Monitor Mode</span></div>\n<div></div>\n</td>\n<td>GPRS/WIFI/Bluetooth/4G/LAN(optional)</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><strong>General Data</strong></td>\n<td width=\"600\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Operating Temperature Range (&#176;C)</span></td>\n<td width=\"600\"><span>-25 to +60&#8451;, &gt;45&#8451; Derating</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Permissible Ambient Humidity</span></td>\n<td width=\"600\"><span>0&#126;100%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Permissible Altitude (m)</span></td>\n<td width=\"600\"><span>4000m</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Noise (dB)</span></td>\n<td width=\"600\"><span>&lt;65</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Ingress Protection(IP) Rating</span></td>\n<td width=\"600\"><span>IP 65</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Inverter Topology</span></td>\n<td width=\"600\"><span>Non-Isolated</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Over Voltage Category</span></td>\n<td width=\"600\"><span>OVC II(DC),OVC III(AC)</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Cabinet Size (WxHxD mm)</span></td>\n<td width=\"600\"><span>434&#215;570&#215;243 (Excluding Connectors and Brackets)</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Weight [kg]</span></td>\n<td width=\"600\"><span>39</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Warranty [year]</span></td>\n<td width=\"600\"><span>5 Years</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Type Of Cooling</span></td>\n<td width=\"600\"><span>Intelligent Air Cooling</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Grid Regulation</span></td>\n<td width=\"600\"><span>IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,</span><br /><span>OVE-Richtlinie R25, G99, VDE-AR-N 4105</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Safety EMC/Standard</span></td>\n<td width=\"600\"><span>IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</span></td>\n</tr>\n</tbody>\n</table>', 2, 'SUN-40K-G04 | Three Phase String Inverter | 3 MPPT', '<p data-start=\"0\" data-end=\"519\">The Deye SUN-40K-G04 inverter offers exceptional efficiency with a peak of 98.7% and 98.1% European efficiency, ensuring reliable performance across varying conditions. It supports zero export and VSG applications, features a wide MPPT voltage range (200&#8211;1000V) for flexible system design, and includes optional intelligent string monitoring for detailed diagnostics. A robust protection suite, optional anti-PID function, and intelligent air cooling enhance safety and durability. With IP65 protection, broad temperature tolerance (-25&#176;C to +60&#176;C), and extensive communication interfaces (WIFI, GPRS, LAN, etc.), it is suited for diverse environments. The inverter complies with major international standards, ensuring safe and efficient integration into global solar systems.</p>\n<h3>Key Features</h3>\n<ul>\n<li><span><strong>High Efficiency</strong>:</span>&#160;The Deye SUN-40K-G04 series boasts an impressive maximum efficiency of 98.7%, ensuring minimal energy loss during the conversion process. Coupled with a European efficiency rate of 98.1%, this inverter stands out for its consistent and optimal performance under diverse conditions.</li>\n<li><strong>Versatile Applications:&#160;</strong>Designed to support zero export applications and Virtual Synchronous Generator (VSG) applications, this inverter is adaptable to a range of grid requirements and regulations. This makes the SUN-40K-G04 a versatile choice for different types of solar installations.</li>\n<li><strong>String Intelligent Monitoring:&#160;</strong>Optional intelligent string monitoring provides granular insights into the performance of each solar string, aiding in precise diagnostics and system maintenance for enhanced longevity and efficiency.</li>\n<li><strong>Wide Voltage Range:&#160;</strong>Operating within a wide MPPT voltage range of 200 to 1000V, the inverter allows for flexible system design and maximizes energy yield. This versatility is crucial for optimizing power conversion from varying sunlight conditions.</li>\n<li><strong>Comprehensive Protection Suite:</strong>&#160;The SUN-40K-G04 series comes equipped with extensive protective features, including DC polarity reverse connection protection, AC overcurrent protection, AC overvoltage protection, and AC output short circuit protection. Enhanced safety measures such as thermal protection, DC terminal insulation impedance monitoring, ground fault current monitoring, power network monitoring, island protection, and earth fault detection ensure the inverter operates reliably under all conditions.</li>\n<li><strong>Anti-PID Function (Optional):</strong>&#160;The anti-PID (Potential Induced Degradation) function is available to prevent long-term performance degradation of solar panels, ensuring the system maintains high efficiency over its lifespan.</li>\n<li><strong>Robust and Durable Design:&#160;</strong>With an IP65 rating, this inverter is protected against dust and water ingress, making it ideal for outdoor installations. It can operate efficiently in a broad temperature range from -25&#176;C to +60&#176;C, with derating applied above 45&#176;C to safeguard the system.</li>\n<li><strong>Intelligent Air Cooling:&#160;</strong>Advanced air cooling technology ensures efficient thermal management, contributing to the inverter&#8217;s durability and operational stability even in high-temperature environments.</li>\n<li><strong>Comprehensive Communication and Monitoring:&#160;</strong>Supports various communication interfaces including GPRS, WIFI, Bluetooth, 4G, and LAN on an optional basis. Standard interfaces include RS485/RS232, facilitating seamless integration with different monitoring systems and enhancing ease of maintenance and operational tracking.</li>\n<li><strong>Compliance with International Standards:&#160;</strong>The inverter meets numerous international and regional standards, including IEC 61727, EN 50549, VDE-AR-N 4105, and more, ensuring it adheres to the highest safety and performance criteria required for widespread deployment.</li>\n</ul>\n<br /><br />\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-011.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<p></p>\n<h3>Technical Specifications</h3>\n<ul>\n<li><span>Max. PV Input Power:</span>&#160;Up to 52kW</li>\n<li><span>Max. PV Input Voltage:</span>&#160;1100V</li>\n<li><span>Rated AC Output Power:</span>&#160;40kW</li>\n<li><span>Max. AC Output Apparent Power:</span>&#160;Up to 44kVA</li>\n<li><span>MPPT Efficiency:</span>&#160;&gt;99%</li>\n<li><span>Total Current Harmonic Distortion (THDi):</span>&#160;&lt;3%</li>\n<li><span>Operating Temperature Range:</span>&#160;-25 to +60&#176;C, with derating above 45&#176;C</li>\n<li><span>Noise Level:</span>&#160;&lt;50 db=\"\" li=\"\"&gt;<!--50--><!--50--><!--50--><!--50--><!--50--><!--50--><!--50--><!--50--><!--50--><!--50--><!--50--></li>\n<li><span>Dimensions:</span>&#160;434 x 570 x 243 mm</li>\n<li><span>Weight:</span>&#160;37.1 kg</li>\n<!--50--></ul>\n<p>The Deye SUN-40K-G04 series is ideally suited for applications requiring robust, efficient, and reliable inverters. Whether for large-scale commercial installations or industrial solar power systems, these inverters deliver unparalleled performance and versatility.</p>', '<span>Experience the pinnacle of solar energy conversion with the Deye SUN-40K-G04 series, a line of advanced three-phase string inverters tailored for demanding commercial installations. Crafted for maximum efficiency and reliability, the SUN-40K-G04 series is built to cater to various solar power needs with an emphasis on performance, flexibility, and comprehensive protection features.</span>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(562, '<table selecttype=\"cells\">\n<tbody>\n<tr height=\"24\">\n<td width=\"240\"><strong>PV String Input Date</strong></td>\n<td width=\"600\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Max. PV Input Power(kW)</span></td>\n<td width=\"200\"><span>65</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Max. PV Input Voltage(V)</span></td>\n<td width=\"600\"><span>1100</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Start-up Voltage(V)</span></td>\n<td width=\"600\"><span>250</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>MPPT voltage range(V)</span></td>\n<td width=\"600\"><span>200-1000</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Rated PV Input voltage(V)</span></td>\n<td width=\"600\"><span>600</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Max. Input Short Circuit Current (A)</span></td>\n<td width=\"200\"><span>60+60+60+60</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Max. Operating PV Input Current(A)</span></td>\n<td width=\"200\"><span>40+40+40+40</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<p><span>No. of MPPT Trackers/No. of Strings per MPPT Trackers</span></p>\n<p></p>\n</td>\n<td width=\"200\"><span>4/3+3+3+3</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<div><strong>AC Output Side</strong></div>\n</td>\n<td width=\"600\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Rated AC Output Active Power(kW)</span></td>\n<td width=\"200\"><span>50</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Max. AC Output Apparent Power(kVA)</span></td>\n<td width=\"200\"><span>55</span></td>\n</tr>\n<tr height=\"31\">\n<td width=\"240\"><span>Rated AC output current (A)</span></td>\n<td width=\"200\"><span>75.8/72.5</span></td>\n</tr>\n<tr height=\"29\">\n<td width=\"240\"><span>Max. AC IOutput Current(A)</span></td>\n<td width=\"200\"><span>83.3/79.7</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Rated output voltage/range (V)</span></td>\n<td width=\"600\"><span>220/380V, 230/400V 0.85Un-1.1Un</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Grid Connection Form</span></td>\n<td width=\"600\"><span>3L/N/PE</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Rated Output Grid Frequency/range(Hz)</span></td>\n<td width=\"600\"><span>50/45-55, 60/55-65</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Power Factor Adjustment Range</span></td>\n<td width=\"600\"><span>0.8 leading to 0.8 lagging</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Total Current Harmonic Distortion THDi</span></td>\n<td width=\"600\"><span>&lt;3%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<p>DC Injection Current</p>\n<p></p>\n</td>\n<td width=\"600\"><span>&lt;0.5%ln</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><strong>Efficiency</strong></td>\n<td width=\"600\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Max. Efficiency</span></td>\n<td width=\"600\"><span>98.7%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Euro Efficiency</span></td>\n<td width=\"200\"><span>98.1%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<p><span>MPPT Efficiency</span></p>\n<p></p>\n</td>\n<td width=\"600\"><span>&#65310;99%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><strong>Equipment Protection</strong></td>\n<td width=\"600\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">DC Reverse Polarity Protection</td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>AC Output Overcurrent Protection</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>AC Output Overvoltage Protection</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>AC Output Short Circuit Protection</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Thermal Protection</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">Insulation Impedance Detection</td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>DC Component Monitoring</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td>\n<div><span>Arc Fault Circuit Interrupter (AFCI)</span></div>\n</td>\n<td>\n<div><span>Optional</span></div>\n</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<p>Anti-islanding Protection</p>\n</td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr>\n<td width=\"240\"><span>Residual Current Detection</span></td>\n<td width=\"900\"><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Surge Protection Level</span></td>\n<td width=\"900\"><span>TYPE II(DC),TYPE II(AC)</span></td>\n</tr>\n<tr height=\"24\">\n<td>\n<div><span>DC Switch</span></div>\n<div></div>\n</td>\n<td><span>Yes</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\">\n<p></p>\n<p><strong>Interface</strong></p>\n</td>\n<td width=\"600\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Communication Interface</span></td>\n<td width=\"600\"><span>RS485/RS232</span></td>\n</tr>\n<tr>\n<td>\n<div><span>Monitor Mode</span></div>\n</td>\n<td>GPRS/WIFI/Bluetooth/4G/LAN(optional)</td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>General Data</span></td>\n<td width=\"600\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Operating Temperature Range (&#176;C)</span></td>\n<td width=\"600\"><span>-25 to +60&#8451;, &gt;45&#8451; Derating</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Permissible Ambient Humidity</span></td>\n<td width=\"600\"><span>0&#126;100%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Permissible Altitude (m)</span></td>\n<td width=\"600\"><span>4000m</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Noise (dB)</span></td>\n<td width=\"600\"><span>&lt;65</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Ingress Protection(IP) Rating</span></td>\n<td width=\"600\"><span>IP 65</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Inverter Topology</span></td>\n<td width=\"600\"><span>Non-Isolated</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Over Voltage Category</span></td>\n<td width=\"600\"><span>OVC II(DC),OVC III(AC)</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Cabinet Size (WxHxD mm)</span></td>\n<td width=\"600\"><span>434&#215;570&#215;243 (Excluding Connectors and Brackets)</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Weight [kg]</span></td>\n<td width=\"600\"><span>39</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Warranty [year]</span></td>\n<td width=\"600\"><span>5 Years</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Type Of Cooling</span></td>\n<td width=\"600\"><span>Intelligent Air Cooling</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Grid Regulation</span></td>\n<td width=\"600\"><span>IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,</span><br /><span>OVE-Richtlinie R25, G99, VDE-AR-N 4105</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"240\"><span>Safety EMC/Standard</span></td>\n<td width=\"600\"><span>IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</span></td>\n</tr>\n</tbody>\n</table>', 2, 'SUN-50K-G04 | Three Phase String Inverter | 4 MPPT', '<p data-start=\"0\" data-end=\"519\">The Deye SUN-50K-G04 inverter offers exceptional efficiency with a peak of 98.7% and 98.1% European efficiency, ensuring reliable performance across varying conditions. It supports zero export and VSG applications, features a wide MPPT voltage range (200&#8211;1000V) for flexible system design, and includes optional intelligent string monitoring for detailed diagnostics. A robust protection suite, optional anti-PID function, and intelligent air cooling enhance safety and durability. With IP65 protection, broad temperature tolerance (-25&#176;C to +60&#176;C), and extensive communication interfaces (WIFI, GPRS, LAN, etc.), it is suited for diverse environments. The inverter complies with major international standards, ensuring safe and efficient integration into global solar systems.</p>\n<h3>Key Features</h3>\n<ul>\n<li><span><strong>High Efficiency</strong>:</span>&#160;The Deye SUN-50K-G04 series boasts an impressive maximum efficiency of 98.7%, ensuring minimal energy loss during the conversion process. Coupled with a European efficiency rate of 98.1%, this inverter stands out for its consistent and optimal performance under diverse conditions.</li>\n<li><strong>Versatile Applications:&#160;</strong>Designed to support zero export applications and Virtual Synchronous Generator (VSG) applications, this inverter is adaptable to a range of grid requirements and regulations. This makes the SUN-50K-G04 a versatile choice for different types of solar installations.</li>\n<li><strong>String Intelligent Monitoring:&#160;</strong>Optional intelligent string monitoring provides granular insights into the performance of each solar string, aiding in precise diagnostics and system maintenance for enhanced longevity and efficiency.</li>\n<li><strong>Wide Voltage Range:&#160;</strong>Operating within a wide MPPT voltage range of 200 to 1000V, the inverter allows for flexible system design and maximizes energy yield. This versatility is crucial for optimizing power conversion from varying sunlight conditions.</li>\n<li><strong>Comprehensive Protection Suite:</strong>&#160;The SUN-50K-G04 series comes equipped with extensive protective features, including DC polarity reverse connection protection, AC overcurrent protection, AC overvoltage protection, and AC output short circuit protection. Enhanced safety measures such as thermal protection, DC terminal insulation impedance monitoring, ground fault current monitoring, power network monitoring, island protection, and earth fault detection ensure the inverter operates reliably under all conditions.</li>\n<li><strong>Anti-PID Function (Optional):</strong>&#160;The anti-PID (Potential Induced Degradation) function is available to prevent long-term performance degradation of solar panels, ensuring the system maintains high efficiency over its lifespan.</li>\n<li><strong>Robust and Durable Design:&#160;</strong>With an IP65 rating, this inverter is protected against dust and water ingress, making it ideal for outdoor installations. It can operate efficiently in a broad temperature range from -25&#176;C to +60&#176;C, with derating applied above 45&#176;C to safeguard the system.</li>\n<li><strong>Intelligent Air Cooling:&#160;</strong>Advanced air cooling technology ensures efficient thermal management, contributing to the inverter&#8217;s durability and operational stability even in high-temperature environments.</li>\n<li><strong>Comprehensive Communication and Monitoring:&#160;</strong>Supports various communication interfaces including GPRS, WIFI, Bluetooth, 4G, and LAN on an optional basis. Standard interfaces include RS485/RS232, facilitating seamless integration with different monitoring systems and enhancing ease of maintenance and operational tracking.</li>\n<li><strong>Compliance with International Standards:&#160;</strong>The inverter meets numerous international and regional standards, including IEC 61727, EN 50549, VDE-AR-N 4105, and more, ensuring it adheres to the highest safety and performance criteria required for widespread deployment.</li>\n</ul>\n<br /><br />\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-011.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<p></p>\n<h3>Technical Specifications</h3>\n<ul>\n<li><span>Max. PV Input Power:</span>&#160;Up to 65kW</li>\n<li><span>Max. PV Input Voltage:</span>&#160;1100V</li>\n<li><span>Rated AC Output Power:</span>&#160;50kW</li>\n<li><span>Max. AC Output Apparent Power:</span>&#160;Up to 55kVA</li>\n<li><span>MPPT Efficiency:</span>&#160;&gt;99%</li>\n<li><span>Total Current Harmonic Distortion (THDi):</span>&#160;&lt;3%</li>\n<li><span>Operating Temperature Range:</span>&#160;-25 to +60&#176;C, with derating above 45&#176;C</li>\n<li><span>Noise Level:</span>&#160;&lt;50 db=\"\" li=\"\"&gt;<!--50--><!--50--><!--50--><!--50--><!--50--><!--50--><!--50--><!--50--><!--50--><!--50--></li>\n<li><span>Dimensions:</span>&#160;434 x 570 x 243 mm</li>\n<li><span>Weight:</span>&#160;37.1 kg</li>\n<!--50--></ul>\n<p>The Deye SUN-50K-G04 series is ideally suited for applications requiring robust, efficient, and reliable inverters. Whether for large-scale commercial installations or industrial solar power systems, these inverters deliver unparalleled performance and versatility.</p>', '<span>Experience the pinnacle of solar energy conversion with the Deye SUN-50K-G04 series, a line of advanced three-phase string inverters tailored for demanding commercial installations. Crafted for maximum efficiency and reliability, the SUN-40K-G04 series is built to cater to various solar power needs with an emphasis on performance, flexibility, and comprehensive protection features.</span>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', '');
INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(563, '<table selecttype=\"cells\">\n<tbody>\n<tr height=\"24\">\n<td width=\"322\"><strong>PV String Input Data</strong></td>\n<td width=\"600\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Max. PV Input Power(W)</span></td>\n<td width=\"200\"><span>210-560 (2 Pieces)</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Max. PV Input Voltage(V)</span></td>\n<td width=\"600\"><span>60</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Start-up Voltage(V)</span></td>\n<td width=\"600\"><span>20</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>MPPT voltage range(V)</span></td>\n<td width=\"600\"><span>25-55</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Rated PV Input voltage(V)</span></td>\n<td width=\"600\"><span>42.5</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Max. Input Short-Circuit Current (A)</span></td>\n<td width=\"600\"><span>19.5+19.5</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Max. Operating PV Input Current(A)</span></td>\n<td width=\"600\"><span>13+13</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\">\n<p><span>No. of MPP Trackers/No. of String per MPP Tracker</span></p>\n<p></p>\n</td>\n<td width=\"600\"><span>2/1</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\">\n<div></div>\n<div><strong>AC Output Side</strong></div>\n</td>\n<td width=\"600\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Rated AC Output Active Power(W)</span></td>\n<td width=\"200\"><span>800</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Max.AC Output Apparent Power(VA)</span></td>\n<td width=\"200\"><span>800</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Rated AC output current (A)</span></td>\n<td width=\"200\"><span>3.7/3.5</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Max.AC Output Current(A)</span></td>\n<td width=\"200\"><span>3.7/3.5</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Rated output voltage/range (V)</span></td>\n<td width=\"600\"><span>220/230 0.85Un-1.1Un</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Grid Connection Form</span></td>\n<td width=\"600\"><span>L/N/PE</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Rated Output Grid Frequency/range(Hz)</span></td>\n<td width=\"600\"><span>50/45-55, 60/55-65</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Max. unit per branch</span></td>\n<td width=\"200\"><span>6</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Power Factor Adjustment Range</span></td>\n<td width=\"600\"><span>0.9 leading to 0.9lagging</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Total Current Harmonic Distortion THDi</span></td>\n<td width=\"600\"><span>&lt;3%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\">\n<p>DC Injection Current</p>\n<p></p>\n</td>\n<td width=\"600\"><span>&lt;0.5%ln</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\">\n<p></p>\n<p><strong>Efficiency</strong></p>\n</td>\n<td width=\"600\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Max. Efficiency</span></td>\n<td width=\"600\"><span>96.5%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Euro Efficiency</span></td>\n<td width=\"200\"><span>96.0%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\">\n<p><span>MPPT Efficiency</span></p>\n<p></p>\n</td>\n<td width=\"600\"><span>&gt;99%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\">\n<p></p>\n<p><strong>Equipment Protection</strong></p>\n</td>\n<td width=\"600\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>DC Reverse Polarity Protection</span></td>\n<td width=\"600\"><span>YES</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>AC Output Overcurrent Protection</span></td>\n<td width=\"600\"><span>YES</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>AC Output Overvoltage Protection</span></td>\n<td width=\"600\"><span>YES</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>AC Output Short Circuit Protection</span></td>\n<td width=\"600\"><span>YES</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Thermal Protection</span></td>\n<td width=\"600\"><span>YES</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Insulation Impedance Detection</span></td>\n<td width=\"600\"><span>YES</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Anti-islanding Protection</span></td>\n<td width=\"600\"><span>YES</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\">\n<p><span>Surge Protection Level</span></p>\n<p></p>\n</td>\n<td width=\"600\"><span>TYPE II(AC)</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\">\n<p></p>\n<p><strong>Interface</strong></p>\n</td>\n<td width=\"600\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\">\n<p><span>Communication Interface</span></p>\n<p></p>\n</td>\n<td width=\"600\"><span>WiFi</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\">\n<p></p>\n<p><strong>General Data</strong></p>\n</td>\n<td width=\"600\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Operating Temperature Range (&#176;C)</span></td>\n<td width=\"600\"><span>-40 to +65&#8451;, &gt;45&#8451; Derating</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Permissible Ambient Humidity</span></td>\n<td width=\"600\"><span>0&#126;100%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Permissible Altitude (m)</span></td>\n<td width=\"600\"><span>2000m</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Noise (dB)</span></td>\n<td width=\"600\"><span>&#8804; 25</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Ingress Protection(IP) Rating</span></td>\n<td width=\"600\"><span>IP 67</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Inverter Topology</span></td>\n<td width=\"600\"><span>Isolated</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Over Voltage Category</span></td>\n<td width=\"600\"><span>OVC II(DC),OVC III(AC)</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Cabinet Size&#65288;W*H*D&#65289;[mm]</span></td>\n<td width=\"600\"><span>280.5*190*40&#65288;Excluding connectors and brackets&#65289;</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Weight [kg]</span></td>\n<td width=\"600\"><span>3</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Warranty [year]</span></td>\n<td width=\"600\"><span>15 Years</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Type Of Cooling</span></td>\n<td width=\"600\"><span>natural cooling</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Grid Regulation</span></td>\n<td width=\"600\"><span>IEC 61727,IEC 62116,CEI 0-21,EN 50549&#65292;NRS 097,RD 140,UNE 217002, ,G98,VDE-AR-N 4105</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Safety EMC/Standard</span></td>\n<td width=\"600\"><span>IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</span></td>\n</tr>\n</tbody>\n</table>', 2, 'SUN-M80G4-EU-Q0 | Micro Inverter | 2 MPPT', '<p data-start=\"0\" data-end=\"519\">The Deye SUN-M80G4-EU-Q0 inverter features dual MPPT for optimized energy harvest, an IP67-rated enclosure for dust and water protection, and built-in WiFi for real-time monitoring. It includes a rapid shutdown function compliant with safety standards, supports easy plug-and-play installation for balcony PV systems, and offers extended relay life for durability. Designed for long-term reliability, it comes with a 25-year design life and a 15-year warranty.</p>\n<h3>Key Features</h3>\n<ul>\n<li><strong>Dual MPPT:</strong> Equipped with two MPP trackers per module, maximizing energy harvest by optimizing power conversion from each PV module.</li>\n<li><strong>Robust Protection:</strong> The IP67 rating ensures resistance to dust and water, enhancing the inverter&#8217;s longevity and reliability in various environments.</li>\n<li><strong>WiFi Integration:</strong> Built-in WiFi facilitates real-time system monitoring and management through an intuitive interface.</li>\n<li><strong>Rapid Shutdown Function:</strong> Enhances safety by complying with the DIN VDE V 0126-95 standard, ensuring AC discharge within &lt;100ms for=\"\" rapid=\"\" shutdown=\"\" li=\"\"&gt;<!--100ms--><!--100ms--><!--100ms--><!--100ms--><!--100ms--><!--100ms--><!--100ms--><!--100ms--><!--100ms--></li>\n<li><strong>Ease of Installation:</strong> Designed for quick-plug balcony PV systems, simplifying the installation process and minimizing setup time.</li>\n<li><strong>Extended Relay Life:</strong> External relay designed for low-temperature operation, offering long life and easier maintenance.</li>\n<li><strong>Long-Term Reliability:</strong> With a 25-year design lifetime and a 15-year warranty, providing assurance of long-term operation and support.</li>\n<!--100ms--></ul>\n<br /><br />\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-012.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<p></p>\n<h3 id=\"technical-specifications\">Technical Specifications</h3>\n<ul>\n<li><span>PV Input</span>:\n<ul>\n<li>Max. Input Power:&#160;<span>210-560 (2 Pieces)</span></li>\n<li>Max. Input Voltage: 60V</li>\n<li>Start-up Voltage: 20V</li>\n<li>MPPT Voltage Range: 25-55V</li>\n<li>Max. Operating PV Input Current: 13 + 13A</li>\n<li>Max. Input Short Circuit Current: 19.5 + 19.5A<br /><br /></li>\n</ul>\n</li>\n<li><span>AC Output</span>:\n<ul>\n<li>Rated Active Power: 600-1000W</li>\n<li>Max. Apparent Power: 600-1000VA</li>\n<li>Grid Connection: L/N/PE</li>\n<li>Rated Output Voltage: 220/230V (Range: 0.85Un-1.1Un)</li>\n<li>Rated Output Frequency: 50/60Hz</li>\n<li>Power Factor: 0.9 leading to 0.9 lagging</li>\n<li>Total Harmonic Distortion (THDi): &lt;3%</li>\n<li>Max. Efficiency: 96.5%</li>\n<li>Euro Efficiency: 96.0%</li>\n<li>MPPT Efficiency: &gt;99%</li>\n<li>Max. Units per Branch: Up to 8 units<br /><br /></li>\n</ul>\n</li>\n<li><span>Protection Features</span>:\n<ul>\n<li>DC Polarity Reverse Connection Protection</li>\n<li>AC Output Overcurrent Protection</li>\n<li>AC Output Overvoltage Protection</li>\n<li>AC Output Short Circuit Protection</li>\n<li>Thermal Protection</li>\n<li>DC Terminal Insulation Monitoring</li>\n<li>Power Network Monitoring</li>\n<li>Island Protection</li>\n<li>Earth Fault Detection</li>\n<li>Overvoltage Load Drop Protection<br /><br /></li>\n</ul>\n</li>\n<li><span>Environmental Specifications</span>:\n<ul>\n<li>Operating Temperature: -40 to +65&#176;C (Derating above 45&#176;C)</li>\n<li>Permissible Ambient Humidity: 0-100%</li>\n<li>Permissible Altitude: 2000m</li>\n<li>Noise Level: &#8804;25dB<br /><br /></li>\n</ul>\n</li>\n<li><span>Physical Characteristics</span>:\n<ul>\n<li>Ingress Protection Rating: IP67</li>\n<li>Cooling Method: Natural Cooling</li>\n<li>Dimensions: 280.5&#215;190&#215;40 mm (excluding connectors and brackets)</li>\n<li>Weight: 3 kg<br /><br /></li>\n</ul>\n</li>\n<li><span>Certifications and Standards</span>:\n<ul>\n<li>Grid Regulations: IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002, OVE-Richtlinie R25, G99, VDE-AR-N 4105</li>\n<li>Safety and EMC Standards: IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</li>\n</ul>\n</li>\n</ul>', 'The SUN-80G4-EU-Q0 series microinverter is a cutting-edge solution designed for efficient and reliable performance in photovoltaic (PV) systems. Featuring dual Maximum Power Point (MPP) trackers, module-level monitoring, and an IP67 protection rating, this microinverter series ensures superior power conversion and durability for a range of solar energy applications.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(564, '<table selecttype=\"cells\">\n<tbody>\n<tr height=\"24\">\n<td width=\"322\"><strong>PV String Input Data</strong></td>\n<td width=\"600\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Max. PV Input Power(W)</span></td>\n<td width=\"200\"><span>210-700 (2 Pieces)</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Max. PV Input Voltage(V)</span></td>\n<td width=\"600\"><span>60</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Start-up Voltage(V)</span></td>\n<td width=\"600\"><span>20</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>MPPT voltage range(V)</span></td>\n<td width=\"600\"><span>25-55</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Rated PV Input voltage(V)</span></td>\n<td width=\"600\"><span>42.5</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Max. Input Short-Circuit Current (A)</span></td>\n<td width=\"600\"><span>19.5+19.5</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Max. Operating PV Input Current(A)</span></td>\n<td width=\"600\"><span>13+13</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\">\n<p><span>No. of MPP Trackers/No. of String per MPP Tracker</span></p>\n<p></p>\n</td>\n<td width=\"600\"><span>2/1</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\">\n<div></div>\n<div><strong>AC Output Side</strong></div>\n</td>\n<td width=\"600\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Rated AC Output Active Power(W)</span></td>\n<td width=\"200\"><span>1000</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Max.AC Output Apparent Power(VA)</span></td>\n<td width=\"200\"><span>1000</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Rated AC output current (A)</span></td>\n<td width=\"200\"><span>4.6/4.4</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Max.AC Output Current(A)</span></td>\n<td width=\"200\"><span>4.6/4.4</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Rated output voltage/range (V)</span></td>\n<td width=\"600\"><span>220/230 0.85Un-1.1Un</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Grid Connection Form</span></td>\n<td width=\"600\"><span>L/N/PE</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Rated Output Grid Frequency/range(Hz)</span></td>\n<td width=\"600\"><span>50/45-55, 60/55-65</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Max. unit per branch</span></td>\n<td width=\"200\"><span>5</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Power Factor Adjustment Range</span></td>\n<td width=\"600\"><span>0.9 leading to 0.9lagging</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Total Current Harmonic Distortion THDi</span></td>\n<td width=\"600\"><span>&lt;3%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\">\n<p>DC Injection Current</p>\n<p></p>\n</td>\n<td width=\"600\"><span>&lt;0.5%ln</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\">\n<p></p>\n<p><strong>Efficiency</strong></p>\n</td>\n<td width=\"600\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Max. Efficiency</span></td>\n<td width=\"600\"><span>96.5%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Euro Efficiency</span></td>\n<td width=\"200\"><span>96.0%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>MPPT Efficiency</span></td>\n<td width=\"600\"><span>&gt;99%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Equipment Protection</span></td>\n<td width=\"600\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>DC Reverse Polarity Protection</span></td>\n<td width=\"600\"><span>YES</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>AC Output Overcurrent Protection</span></td>\n<td width=\"600\"><span>YES</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>AC Output Overvoltage Protection</span></td>\n<td width=\"600\"><span>YES</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>AC Output Short Circuit Protection</span></td>\n<td width=\"600\"><span>YES</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Thermal Protection</span></td>\n<td width=\"600\"><span>YES</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Insulation Impedance Detection</span></td>\n<td width=\"600\"><span>YES</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Anti-islanding Protection</span></td>\n<td width=\"600\"><span>YES</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\">\n<p><span>Surge Protection Level</span></p>\n<p></p>\n</td>\n<td width=\"600\"><span>TYPE II(AC)</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\">\n<p></p>\n<p><strong>Interface</strong></p>\n</td>\n<td width=\"600\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\">\n<p><span>Communication Interface</span></p>\n<p></p>\n</td>\n<td width=\"600\"><span>WiFi</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\">\n<p></p>\n<p><strong>General Data</strong></p>\n</td>\n<td width=\"600\"></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Operating Temperature Range (&#176;C)</span></td>\n<td width=\"600\"><span>-40 to +65&#8451;, &gt;45&#8451; Derating</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Permissible Ambient Humidity</span></td>\n<td width=\"600\"><span>0&#126;100%</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Permissible Altitude (m)</span></td>\n<td width=\"600\"><span>2000m</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Noise (dB)</span></td>\n<td width=\"600\"><span>&#8804; 25</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Ingress Protection(IP) Rating</span></td>\n<td width=\"600\"><span>IP 67</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Inverter Topology</span></td>\n<td width=\"600\"><span>Isolated</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Over Voltage Category</span></td>\n<td width=\"600\"><span>OVC II(DC),OVC III(AC)</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Cabinet Size&#65288;W*H*D&#65289;[mm]</span></td>\n<td width=\"600\"><span>280.5*190*40&#65288;Excluding connectors and brackets&#65289;</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Weight [kg]</span></td>\n<td width=\"600\"><span>3</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Warranty [year]</span></td>\n<td width=\"600\"><span>15 Years</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Type Of Cooling</span></td>\n<td width=\"600\"><span>natural cooling</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Grid Regulation</span></td>\n<td width=\"600\"><span>IEC 61727,IEC 62116,CEI 0-21,EN 50549&#65292;NRS 097,RD 140,UNE 217002, ,G98,VDE-AR-N 4105</span></td>\n</tr>\n<tr height=\"24\">\n<td width=\"322\"><span>Safety EMC/Standard</span></td>\n<td width=\"600\"><span>IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</span></td>\n</tr>\n</tbody>\n</table>', 2, 'SUN-M100G4-EU-Q0 | Micro Inverter | 2 MPPT', '<p data-start=\"0\" data-end=\"519\">The Deye SUN-M100G4-EU-Q0 inverter features dual MPPT for optimized energy harvest, an IP67-rated enclosure for dust and water protection, and built-in WiFi for real-time monitoring. It includes a rapid shutdown function compliant with safety standards, supports easy plug-and-play installation for balcony PV systems, and offers extended relay life for durability. Designed for long-term reliability, it comes with a 25-year design life and a 15-year warranty.</p>\n<h3>Key Features</h3>\n<ul>\n<li><strong>Dual MPPT:</strong> Equipped with two MPP trackers per module, maximizing energy harvest by optimizing power conversion from each PV module.</li>\n<li><strong>Robust Protection:</strong> The IP67 rating ensures resistance to dust and water, enhancing the inverter&#8217;s longevity and reliability in various environments.</li>\n<li><strong>WiFi Integration:</strong> Built-in WiFi facilitates real-time system monitoring and management through an intuitive interface.</li>\n<li><strong>Rapid Shutdown Function:</strong> Enhances safety by complying with the DIN VDE V 0126-95 standard, ensuring AC discharge within &lt;100ms for=\"\" rapid=\"\" shutdown=\"\" li=\"\"&gt;<!--100ms--><!--100ms--><!--100ms--><!--100ms--><!--100ms--><!--100ms--><!--100ms--><!--100ms--><!--100ms--><!--100ms--></li>\n<li><strong>Ease of Installation:</strong> Designed for quick-plug balcony PV systems, simplifying the installation process and minimizing setup time.</li>\n<li><strong>Extended Relay Life:</strong> External relay designed for low-temperature operation, offering long life and easier maintenance.</li>\n<li><strong>Long-Term Reliability:</strong> With a 25-year design lifetime and a 15-year warranty, providing assurance of long-term operation and support.</li>\n<!--100ms--></ul>\n<br /><br />\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-012.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<p></p>\n<h3 id=\"technical-specifications\">Technical Specifications</h3>\n<ul>\n<li><span>PV Input</span>:\n<ul>\n<li>Max. Input Power:&#160;<span>210-700 (2 Pieces)</span></li>\n<li>Max. Input Voltage: 60V</li>\n<li>Start-up Voltage: 20V</li>\n<li>MPPT Voltage Range: 25-55V</li>\n<li>Max. Operating PV Input Current: 13 + 13A</li>\n<li>Max. Input Short Circuit Current: 19.5 + 19.5A<br /><br /></li>\n</ul>\n</li>\n<li><span>AC Output</span>:\n<ul>\n<li>Rated Active Power: 600-1000W</li>\n<li>Max. Apparent Power: 600-1000VA</li>\n<li>Grid Connection: L/N/PE</li>\n<li>Rated Output Voltage: 220/230V (Range: 0.85Un-1.1Un)</li>\n<li>Rated Output Frequency: 50/60Hz</li>\n<li>Power Factor: 0.9 leading to 0.9 lagging</li>\n<li>Total Harmonic Distortion (THDi): &lt;3%</li>\n<li>Max. Efficiency: 96.5%</li>\n<li>Euro Efficiency: 96.0%</li>\n<li>MPPT Efficiency: &gt;99%</li>\n<li>Max. Units per Branch: Up to 8 units<br /><br /></li>\n</ul>\n</li>\n<li><span>Protection Features</span>:\n<ul>\n<li>DC Polarity Reverse Connection Protection</li>\n<li>AC Output Overcurrent Protection</li>\n<li>AC Output Overvoltage Protection</li>\n<li>AC Output Short Circuit Protection</li>\n<li>Thermal Protection</li>\n<li>DC Terminal Insulation Monitoring</li>\n<li>Power Network Monitoring</li>\n<li>Island Protection</li>\n<li>Earth Fault Detection</li>\n<li>Overvoltage Load Drop Protection<br /><br /></li>\n</ul>\n</li>\n<li><span>Environmental Specifications</span>:\n<ul>\n<li>Operating Temperature: -40 to +65&#176;C (Derating above 45&#176;C)</li>\n<li>Permissible Ambient Humidity: 0-100%</li>\n<li>Permissible Altitude: 2000m</li>\n<li>Noise Level: &#8804;25dB<br /><br /></li>\n</ul>\n</li>\n<li><span>Physical Characteristics</span>:\n<ul>\n<li>Ingress Protection Rating: IP67</li>\n<li>Cooling Method: Natural Cooling</li>\n<li>Dimensions: 280.5&#215;190&#215;40 mm (excluding connectors and brackets)</li>\n<li>Weight: 3 kg<br /><br /></li>\n</ul>\n</li>\n<li><span>Certifications and Standards</span>:\n<ul>\n<li>Grid Regulations: IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002, OVE-Richtlinie R25, G99, VDE-AR-N 4105</li>\n<li>Safety and EMC Standards: IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</li>\n</ul>\n</li>\n</ul>', 'The SUN-100G4-EU-Q0 series microinverter is a cutting-edge solution designed for efficient and reliable performance in photovoltaic (PV) systems. Featuring dual Maximum Power Point (MPP) trackers, module-level monitoring, and an IP67 protection rating, this microinverter series ensures superior power conversion and durability for a range of solar energy applications.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(565, '<table border=\"0\" width=\"1529\" height=\"1242\" style=\"width: 1529px; height: 1242px;\">\n<tbody>\n<tr>\n<td colspan=\"2\"><strong>PV String Input Data</strong></td>\n</tr>\n<tr>\n<td width=\"294\">Max. PV Input Power(W)</td>\n<td width=\"166\">210-560(4 Pieces)</td>\n</tr>\n<tr>\n<td width=\"294\">Max. PV Input Voltage(V)</td>\n<td width=\"872\">60</td>\n</tr>\n<tr>\n<td width=\"294\">Start-up Voltage(V)</td>\n<td width=\"872\">20</td>\n</tr>\n<tr>\n<td width=\"294\">MPPT voltage range(V)</td>\n<td width=\"872\">25-55</td>\n</tr>\n<tr>\n<td width=\"294\">Rated PV Input voltage(V)</td>\n<td width=\"872\">42.5</td>\n</tr>\n<tr>\n<td width=\"294\">Max. Operating PV Input Current (A)</td>\n<td width=\"720\">15+15+15+15</td>\n</tr>\n<tr>\n<td width=\"294\">Max. Input Short Circuit Current (A)</td>\n<td width=\"720\">22.5+22.5+22.5+22.5</td>\n</tr>\n<tr>\n<td width=\"294\">No. of MPP Trackers/No. of String per MPP Tracker</td>\n<td width=\"872\" data-online-value=\"45748\">4/1</td>\n</tr>\n<tr>\n<td colspan=\"2\">\n<p></p>\n<p><strong>AC Output Side</strong></p>\n</td>\n</tr>\n<tr>\n<td width=\"294\">Rated AC Output Active Power(W)</td>\n<td width=\"166\">1600</td>\n</tr>\n<tr>\n<td width=\"294\">Max.AC Output Apparent Power(VA)</td>\n<td width=\"166\">1600</td>\n</tr>\n<tr>\n<td width=\"294\">Rated AC output current (A)</td>\n<td width=\"166\">7.3/7</td>\n</tr>\n<tr>\n<td width=\"294\">Max.AC Output Current(A)</td>\n<td width=\"166\">7.3/7</td>\n</tr>\n<tr>\n<td width=\"294\">Rated output voltage/range (V)</td>\n<td width=\"872\">220/230 0.85Un-1.1Un</td>\n</tr>\n<tr>\n<td width=\"294\">Grid Connection Form</td>\n<td width=\"872\">L/N/PE</td>\n</tr>\n<tr>\n<td width=\"294\">Rated Output Grid Frequency/range(Hz)</td>\n<td width=\"872\">50/45-55, 60/55-65</td>\n</tr>\n<tr>\n<td width=\"294\">Max. unit per branch</td>\n<td width=\"166\">4</td>\n</tr>\n<tr>\n<td width=\"294\">Power Factor Adjustment Range</td>\n<td width=\"872\">0.9 leading to 0.9 lagging</td>\n</tr>\n<tr>\n<td width=\"294\">Total Current Harmonic Distortion THDi</td>\n<td width=\"872\">&lt;3%</td>\n</tr>\n<tr>\n<td width=\"294\">DC Injection Current</td>\n<td width=\"872\">&lt;0.5%ln</td>\n</tr>\n<tr>\n<td colspan=\"2\">\n<p></p>\n<p><strong>Efficiency</strong></p>\n</td>\n</tr>\n<tr>\n<td width=\"294\">Max. Efficiency</td>\n<td width=\"872\" data-online-value=\"0.965\">96.50%</td>\n</tr>\n<tr>\n<td width=\"294\">Euro Efficiency</td>\n<td width=\"872\">96</td>\n</tr>\n<tr>\n<td width=\"294\">MPPT Efficiency</td>\n<td width=\"872\">&gt;99%</td>\n</tr>\n<tr>\n<td colspan=\"2\">\n<p></p>\n<p><strong>Equipment Protection</strong></p>\n</td>\n</tr>\n<tr>\n<td width=\"294\">DC Reverse Polarity Protection</td>\n<td width=\"872\">YES</td>\n</tr>\n<tr>\n<td width=\"294\">AC Output Overcurrent Protection</td>\n<td width=\"872\">YES</td>\n</tr>\n<tr>\n<td width=\"294\">AC Output Overvoltage Protection</td>\n<td width=\"872\">YES</td>\n</tr>\n<tr>\n<td width=\"294\">AC Output Short Circuit Protection</td>\n<td width=\"872\">YES</td>\n</tr>\n<tr>\n<td width=\"294\">Thermal Protection</td>\n<td width=\"872\">YES</td>\n</tr>\n<tr>\n<td width=\"294\">Insulation Impedance Detection</td>\n<td width=\"872\">YES</td>\n</tr>\n<tr>\n<td width=\"294\">Anti-islanding Protection</td>\n<td width=\"872\">YES</td>\n</tr>\n<tr>\n<td width=\"294\">Surge Protection Level</td>\n<td width=\"872\">TYPE II(AC)</td>\n</tr>\n<tr>\n<td colspan=\"2\">\n<p></p>\n<p><strong>Interface</strong></p>\n</td>\n</tr>\n<tr>\n<td width=\"294\">Communication Interface</td>\n<td width=\"872\">Wi-Fi</td>\n</tr>\n<tr>\n<td colspan=\"2\">\n<p></p>\n<p><strong>General Data</strong></p>\n</td>\n</tr>\n<tr>\n<td width=\"294\">Operating Temperature Range (&#176;C)</td>\n<td width=\"872\">-40 to +65&#8451;, &gt;45&#8451; Derating</td>\n</tr>\n<tr>\n<td width=\"294\">Permissible Ambient Humidity</td>\n<td width=\"872\">0&#126;100%</td>\n</tr>\n<tr>\n<td width=\"294\">Permissible Altitude (m)</td>\n<td width=\"872\">2000m</td>\n</tr>\n<tr>\n<td width=\"294\">Noise (dB)</td>\n<td width=\"872\">&#8804; 25</td>\n</tr>\n<tr>\n<td width=\"294\">Ingress Protection(IP) Rating</td>\n<td width=\"872\">IP 67</td>\n</tr>\n<tr>\n<td width=\"294\">Inverter Topology</td>\n<td width=\"872\">Isolated</td>\n</tr>\n<tr>\n<td width=\"294\">Over Voltage Category</td>\n<td width=\"872\">OVC II(DC),OVC III(AC)</td>\n</tr>\n<tr>\n<td width=\"294\">Cabinet Size&#65288;W*H*D&#65289;[mm]</td>\n<td width=\"720\">311&#215;250.5&#215;36.5</td>\n</tr>\n<tr>\n<td width=\"294\">Weight [kg]</td>\n<td width=\"720\">5.1&#160;</td>\n</tr>\n<tr>\n<td width=\"294\">Warranty [year]</td>\n<td width=\"872\">10 Years</td>\n</tr>\n<tr>\n<td width=\"294\">Type Of Cooling</td>\n<td width=\"872\">natural cooling</td>\n</tr>\n<tr>\n<td width=\"294\">Grid Regulation</td>\n<td width=\"872\">IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002, G99, VDE-AR-N 4105</td>\n</tr>\n<tr>\n<td width=\"294\">Safety EMC/Standard</td>\n<td width=\"872\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</td>\n</tr>\n</tbody>\n</table>', 2, 'SUN-M160G4-EU-Q0 | Micro Inverter | 4 MPPT', '<p data-start=\"0\" data-end=\"519\">This microinverter features Quad MPPT technology for maximum energy harvest, supports high DC input currents up to 18A for compatibility with powerful <span>560</span>W modules, and boasts IP67-rated protection for durability in harsh environments. It includes integrated WiFi for real-time monitoring, is easy to install with quick-plug balcony PV systems, and comes with a 10-year warranty, extendable to 15 years in Germany and Austria.</p>\n<h3>Key Features</h3>\n<ul>\n<li><strong>Quad MPPT Technology:</strong> Each microinverter is equipped with four MPP trackers, ensuring maximum energy harvest by optimizing power conversion from each PV module.</li>\n<li><strong>High DC Input Capability:</strong> Capable of handling a maximum DC input current of 18A, making it compatible with high-output PV modules up to <span>560</span>W.</li>\n<li><strong>Robust Protection:</strong> The IP67 rating provides superior resistance to dust and water, adding to the longevity and reliability of the inverter in various environmental conditions.</li>\n<li><strong>Integrated WiFi:</strong> Enables real-time system monitoring and management through an intuitive interface, ensuring optimal performance at all times.</li>\n<li><strong>Ease of Installation: I</strong>deal for quick-plug balcony PV systems, simplifying the installation process and reducing setup time.</li>\n<li><strong>Extended Warranty:</strong> Offers a 10-year warranty (with an option for a 15-year warranty in Germany and Austria), providing long-term reliability and peace of mind.</li>\n<!--100ms--></ul>\n<br />\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-013.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<p></p>\n<h3 id=\"technical-specifications\">Technical Specifications</h3>\n<ul>\n<li><strong>PV Input</strong>:\n<ul>\n<li>Max. Input Voltage: 60V</li>\n<li>Start-up Voltage: 20V</li>\n<li>MPPT Voltage Range: 25-55V</li>\n<li>Max. Operating PV Input Current: 15 + 15 + 15 + 15A</li>\n<li>Max. Input Short Circuit Current: 22.5 +&#160;22.5 +&#160;22.5 + 22.5A<br /><br /></li>\n</ul>\n</li>\n<li><strong>AC Output:</strong>\n<ul>\n<li>Rated Active Power:&#160;1600W</li>\n<li>Max. Apparent Power: <span>1600</span>VA</li>\n<li>Grid Connection: L/N/PE</li>\n<li>Rated Output Voltage: 220/230V (Range: 0.85Un-1.1Un)</li>\n<li>Rated Output Frequency: 50/60Hz</li>\n<li>Power Factor: 0.9 leading to 0.9 lagging</li>\n<li>Total Harmonic Distortion (THDi): &lt;3%</li>\n<li>Max. Efficiency: 96.5%</li>\n<li>Euro Efficiency: 96.0%</li>\n<li>MPPT Efficiency: &gt;99%</li>\n<li>Max. Units per Branch: Up to 4 units<br /><br /></li>\n</ul>\n</li>\n<li><strong>Protection Features</strong>:\n<ul>\n<li>DC Polarity Reverse Connection Protection</li>\n<li>AC Output Overcurrent Protection</li>\n<li>AC Output Overvoltage Protection</li>\n<li>AC Output Short Circuit Protection</li>\n<li>Thermal Protection</li>\n<li>DC Terminal Insulation Monitoring</li>\n<li>Power Network Monitoring</li>\n<li>Island Protection</li>\n<li>Earth Fault Detection</li>\n<li>Overvoltage Load Drop Protection<br /><br /></li>\n</ul>\n</li>\n<li><strong>Environmental Specifications</strong>:\n<ul>\n<li>Operating Temperature: -40 to +65&#176;C (Derating above 45&#176;C)</li>\n<li>Permissible Ambient Humidity: 0-100%</li>\n<li>Permissible Altitude: 2000m</li>\n<li>Noise Level: &#8804;25dB<br /><br /></li>\n</ul>\n</li>\n<li><strong>Physical Characteristics</strong>:\n<ul>\n<li>Ingress Protection Rating: IP67</li>\n<li>Cooling Method: Natural Cooling</li>\n<li>Dimensions: 311&#215;250.5&#215;36.5 mm (excluding connectors and brackets)</li>\n<li>Weight: 5.1 kg<br /><br /></li>\n</ul>\n</li>\n<li><strong>Certifications and Standards</strong>:\n<ul>\n<li>Grid Regulations: IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002, OVE-Richtlinie R25, G99, VDE-AR-N 4105</li>\n<li>Safety and EMC Standards: IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</li>\n</ul>\n</li>\n</ul>', '<span>The SUN-M160G4-EU-Q0 microinverter series represents the latest innovation in solar power technology. Featuring four Maximum Power Point (MPP) trackers, module-level monitoring, and an IP67 protection rating, this microinverter series offers unparalleled efficiency and reliability for residential and commercial photovoltaic (PV) systems.</span>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', '');
INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(566, '<table border=\"0\" width=\"1529\" height=\"1242\" style=\"width: 1529px; height: 1242px;\">\n<tbody>\n<tr>\n<td colspan=\"2\"><strong>PV String Input Data</strong></td>\n</tr>\n<tr>\n<td width=\"294\">Max. PV Input Power(W)</td>\n<td width=\"166\"><span>210-700(4 Pieces)</span></td>\n</tr>\n<tr>\n<td width=\"294\">Max. PV Input Voltage(V)</td>\n<td width=\"872\">60</td>\n</tr>\n<tr>\n<td width=\"294\">Start-up Voltage(V)</td>\n<td width=\"872\">20</td>\n</tr>\n<tr>\n<td width=\"294\">MPPT voltage range(V)</td>\n<td width=\"872\">25-55</td>\n</tr>\n<tr>\n<td width=\"294\">Rated PV Input voltage(V)</td>\n<td width=\"872\">42.5</td>\n</tr>\n<tr>\n<td width=\"294\">Max. Operating PV Input Current (A)</td>\n<td width=\"720\">15+15+15+15</td>\n</tr>\n<tr>\n<td width=\"294\">Max. Input Short Circuit Current (A)</td>\n<td width=\"720\">22.5+22.5+22.5+22.5</td>\n</tr>\n<tr>\n<td width=\"294\">No. of MPP Trackers/No. of String per MPP Tracker</td>\n<td width=\"872\" data-online-value=\"45748\">4/1</td>\n</tr>\n<tr>\n<td colspan=\"2\">\n<p></p>\n<p><strong>AC Output Side</strong></p>\n</td>\n</tr>\n<tr>\n<td width=\"294\">Rated AC Output Active Power(W)</td>\n<td width=\"166\">2000</td>\n</tr>\n<tr>\n<td width=\"294\">Max.AC Output Apparent Power(VA)</td>\n<td width=\"166\">2000</td>\n</tr>\n<tr>\n<td width=\"294\">Rated AC output current (A)</td>\n<td width=\"166\">9.1/8.7</td>\n</tr>\n<tr>\n<td width=\"294\">Max.AC Output Current(A)</td>\n<td width=\"166\">9.1/8.7</td>\n</tr>\n<tr>\n<td width=\"294\">Rated output voltage/range (V)</td>\n<td width=\"872\">220/230 0.85Un-1.1Un</td>\n</tr>\n<tr>\n<td width=\"294\">Grid Connection Form</td>\n<td width=\"872\">L/N/PE</td>\n</tr>\n<tr>\n<td width=\"294\">Rated Output Grid Frequency/range(Hz)</td>\n<td width=\"872\">50/45-55, 60/55-65</td>\n</tr>\n<tr>\n<td width=\"294\">Max. unit per branch</td>\n<td width=\"166\">3</td>\n</tr>\n<tr>\n<td width=\"294\">Power Factor Adjustment Range</td>\n<td width=\"872\">0.9 leading to 0.9 lagging</td>\n</tr>\n<tr>\n<td width=\"294\">Total Current Harmonic Distortion THDi</td>\n<td width=\"872\">&lt;3%</td>\n</tr>\n<tr>\n<td width=\"294\">DC Injection Current</td>\n<td width=\"872\">&lt;0.5%ln</td>\n</tr>\n<tr>\n<td colspan=\"2\">\n<p></p>\n<p><strong>Efficiency</strong></p>\n</td>\n</tr>\n<tr>\n<td width=\"294\">Max. Efficiency</td>\n<td width=\"872\" data-online-value=\"0.965\">96.50%</td>\n</tr>\n<tr>\n<td width=\"294\">Euro Efficiency</td>\n<td width=\"872\">96</td>\n</tr>\n<tr>\n<td width=\"294\">MPPT Efficiency</td>\n<td width=\"872\">&gt;99%</td>\n</tr>\n<tr>\n<td colspan=\"2\">\n<p></p>\n<p><strong>Equipment Protection</strong></p>\n</td>\n</tr>\n<tr>\n<td width=\"294\">DC Reverse Polarity Protection</td>\n<td width=\"872\">YES</td>\n</tr>\n<tr>\n<td width=\"294\">AC Output Overcurrent Protection</td>\n<td width=\"872\">YES</td>\n</tr>\n<tr>\n<td width=\"294\">AC Output Overvoltage Protection</td>\n<td width=\"872\">YES</td>\n</tr>\n<tr>\n<td width=\"294\">AC Output Short Circuit Protection</td>\n<td width=\"872\">YES</td>\n</tr>\n<tr>\n<td width=\"294\">Thermal Protection</td>\n<td width=\"872\">YES</td>\n</tr>\n<tr>\n<td width=\"294\">Insulation Impedance Detection</td>\n<td width=\"872\">YES</td>\n</tr>\n<tr>\n<td width=\"294\">Anti-islanding Protection</td>\n<td width=\"872\">YES</td>\n</tr>\n<tr>\n<td width=\"294\">Surge Protection Level</td>\n<td width=\"872\">TYPE II(AC)</td>\n</tr>\n<tr>\n<td colspan=\"2\">\n<p></p>\n<p><strong>Interface</strong></p>\n</td>\n</tr>\n<tr>\n<td width=\"294\">Communication Interface</td>\n<td width=\"872\">Wi-Fi</td>\n</tr>\n<tr>\n<td colspan=\"2\">\n<p></p>\n<p><strong>General Data</strong></p>\n</td>\n</tr>\n<tr>\n<td width=\"294\">Operating Temperature Range (&#176;C)</td>\n<td width=\"872\">-40 to +65&#8451;, &gt;45&#8451; Derating</td>\n</tr>\n<tr>\n<td width=\"294\">Permissible Ambient Humidity</td>\n<td width=\"872\">0&#126;100%</td>\n</tr>\n<tr>\n<td width=\"294\">Permissible Altitude (m)</td>\n<td width=\"872\">2000m</td>\n</tr>\n<tr>\n<td width=\"294\">Noise (dB)</td>\n<td width=\"872\">&#8804; 25</td>\n</tr>\n<tr>\n<td width=\"294\">Ingress Protection(IP) Rating</td>\n<td width=\"872\">IP 67</td>\n</tr>\n<tr>\n<td width=\"294\">Inverter Topology</td>\n<td width=\"872\">Isolated</td>\n</tr>\n<tr>\n<td width=\"294\">Over Voltage Category</td>\n<td width=\"872\">OVC II(DC),OVC III(AC)</td>\n</tr>\n<tr>\n<td width=\"294\">Cabinet Size&#65288;W*H*D&#65289;[mm]</td>\n<td width=\"720\">311&#215;250.5&#215;36.5</td>\n</tr>\n<tr>\n<td width=\"294\">Weight [kg]</td>\n<td width=\"720\">5.1&#160;</td>\n</tr>\n<tr>\n<td width=\"294\">Warranty [year]</td>\n<td width=\"872\">10 Years</td>\n</tr>\n<tr>\n<td width=\"294\">Type Of Cooling</td>\n<td width=\"872\">natural cooling</td>\n</tr>\n<tr>\n<td width=\"294\">Grid Regulation</td>\n<td width=\"872\">IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002, G99, VDE-AR-N 4105</td>\n</tr>\n<tr>\n<td width=\"294\">Safety EMC/Standard</td>\n<td width=\"872\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</td>\n</tr>\n</tbody>\n</table>', 2, 'SUN-M200G4-EU-Q0 | Micro Inverter | 4 MPPT', '<p data-start=\"0\" data-end=\"519\">This microinverter features Quad MPPT technology for maximum energy harvest, supports high DC input currents up to 18A for compatibility with powerful <span>560</span>W modules, and boasts IP67-rated protection for durability in harsh environments. It includes integrated WiFi for real-time monitoring, is easy to install with quick-plug balcony PV systems, and comes with a 10-year warranty, extendable to 15 years in Germany and Austria.</p>\n<h3>Key Features</h3>\n<ul>\n<li><strong>Quad MPPT Technology:</strong> Each microinverter is equipped with four MPP trackers, ensuring maximum energy harvest by optimizing power conversion from each PV module.</li>\n<li><strong>High DC Input Capability:</strong> Capable of handling a maximum DC input current of 18A, making it compatible with high-output PV modules up to <span>560</span>W.</li>\n<li><strong>Robust Protection:</strong> The IP67 rating provides superior resistance to dust and water, adding to the longevity and reliability of the inverter in various environmental conditions.</li>\n<li><strong>Integrated WiFi:</strong> Enables real-time system monitoring and management through an intuitive interface, ensuring optimal performance at all times.</li>\n<li><strong>Ease of Installation: I</strong>deal for quick-plug balcony PV systems, simplifying the installation process and reducing setup time.</li>\n<li><strong>Extended Warranty:</strong> Offers a 10-year warranty (with an option for a 15-year warranty in Germany and Austria), providing long-term reliability and peace of mind.</li>\n<!--100ms--></ul>\n<br />\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-013.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<p></p>\n<h3 id=\"technical-specifications\">Technical Specifications</h3>\n<ul>\n<li><strong>PV Input</strong>:\n<ul>\n<li>Max. Input Voltage: 60V</li>\n<li>Start-up Voltage: 20V</li>\n<li>MPPT Voltage Range: 25-55V</li>\n<li>Max. Operating PV Input Current: 15 + 15 + 15 + 15A</li>\n<li>Max. Input Short Circuit Current: 22.5 +&#160;22.5 +&#160;22.5 + 22.5A<br /><br /></li>\n</ul>\n</li>\n<li><strong>AC Output:</strong>\n<ul>\n<li>Rated Active Power: 2000W</li>\n<li>Max. Apparent Power: 20<span>00</span>VA</li>\n<li>Grid Connection: L/N/PE</li>\n<li>Rated Output Voltage: 220/230V (Range: 0.85Un-1.1Un)</li>\n<li>Rated Output Frequency: 50/60Hz</li>\n<li>Power Factor: 0.9 leading to 0.9 lagging</li>\n<li>Total Harmonic Distortion (THDi): &lt;3%</li>\n<li>Max. Efficiency: 96.5%</li>\n<li>Euro Efficiency: 96.0%</li>\n<li>MPPT Efficiency: &gt;99%</li>\n<li>Max. Units per Branch: Up to 3 units<br /><br /></li>\n</ul>\n</li>\n<li><strong>Protection Features</strong>:\n<ul>\n<li>DC Polarity Reverse Connection Protection</li>\n<li>AC Output Overcurrent Protection</li>\n<li>AC Output Overvoltage Protection</li>\n<li>AC Output Short Circuit Protection</li>\n<li>Thermal Protection</li>\n<li>DC Terminal Insulation Monitoring</li>\n<li>Power Network Monitoring</li>\n<li>Island Protection</li>\n<li>Earth Fault Detection</li>\n<li>Overvoltage Load Drop Protection<br /><br /></li>\n</ul>\n</li>\n<li><strong>Environmental Specifications</strong>:\n<ul>\n<li>Operating Temperature: -40 to +65&#176;C (Derating above 45&#176;C)</li>\n<li>Permissible Ambient Humidity: 0-100%</li>\n<li>Permissible Altitude: 2000m</li>\n<li>Noise Level: &#8804;25dB<br /><br /></li>\n</ul>\n</li>\n<li><strong>Physical Characteristics</strong>:\n<ul>\n<li>Ingress Protection Rating: IP67</li>\n<li>Cooling Method: Natural Cooling</li>\n<li>Dimensions: 311&#215;250.5&#215;36.5 mm (excluding connectors and brackets)</li>\n<li>Weight: 5.1 kg<br /><br /></li>\n</ul>\n</li>\n<li><strong>Certifications and Standards</strong>:\n<ul>\n<li>Grid Regulations: IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002, OVE-Richtlinie R25, G99, VDE-AR-N 4105</li>\n<li>Safety and EMC Standards: IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</li>\n</ul>\n</li>\n</ul>', '<span>The SUN-M200G4-EU-Q0 microinverter series represents the latest innovation in solar power technology. Featuring four Maximum Power Point (MPP) trackers, module-level monitoring, and an IP67 protection rating, this microinverter series offers unparalleled efficiency and reliability for residential and commercial photovoltaic (PV) systems.</span>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(567, '<table border=\"0\" cellspacing=\"0\" cellpadding=\"5\" height=\"208\" style=\"width: 100%;\">\n<tbody>\n<tr style=\"background-color: #0d265f; color: white;\">\n<td><strong>Battery-Model</strong></td>\n<td><strong>AE-F2.0</strong></td>\n</tr>\n<tr>\n<td style=\"width: 30%;\">\n<p></p>\n<p><strong>Battery Technical Specification</strong></p>\n</td>\n<td></td>\n</tr>\n<tr>\n<td>Battery Chemistry</td>\n<td>LiFePO&#8324;</td>\n</tr>\n<tr>\n<td>Battery Nominal Voltage</td>\n<td>51.2V</td>\n</tr>\n<tr>\n<td>Battery Nominal Energy</td>\n<td>2000Wh</td>\n</tr>\n<tr>\n<td>Max. Charging / Discharging Current</td>\n<td>50A</td>\n</tr>\n<tr>\n<td>Battery Operating Voltage</td>\n<td>44.8V &#8211; 57.6V</td>\n</tr>\n<tr>\n<td>Battery Cycle Life</td>\n<td>&#8805;6000 (@25&#176;C &#177; 2&#176;C, 0.5C / 0.5C, 70% EOL)</td>\n</tr>\n<tr>\n<td>Parallel Capability</td>\n<td>5 pcs</td>\n</tr>\n<tr>\n<td>\n<p></p>\n<p><strong>Other Technical Specification</strong></p>\n</td>\n<td></td>\n</tr>\n<tr>\n<td>Display</td>\n<td>LED (SOC, Alarm)</td>\n</tr>\n<tr>\n<td>Communication Interfaces</td>\n<td>CAN2.0, LoRa</td>\n</tr>\n<tr>\n<td>Dimensions (W x D x H)</td>\n<td>450 x 210 x 244 mm</td>\n</tr>\n<tr>\n<td>Weight (Approx)</td>\n<td>20 kg</td>\n</tr>\n<tr>\n<td>Operating Temperature Range</td>\n<td>-10&#176;C &#8211; 50&#176;C</td>\n</tr>\n<tr>\n<td>Max. Operating Altitude</td>\n<td>3000 m</td>\n</tr>\n<tr>\n<td>Relative Humidity</td>\n<td>15% &#8211; 85% (No Condensing)</td>\n</tr>\n<tr>\n<td>Certification</td>\n<td>UN38.3, IEC 62619, CE</td>\n</tr>\n<tr>\n<td>Installation Style</td>\n<td>Floor-Mounted</td>\n</tr>\n<tr>\n<td>Warranty</td>\n<td>10 Years</td>\n</tr>\n</tbody>\n</table>', 2, 'AE-F2.0 (EU) Battery Pack Module | ESS', '<p>The&#160;Deye AE-F2.0 Battery Pack Module&#160;is your ultimate partner for seamless and efficient energy management. Whether you&#8217;re building a&#160;home energy storage system (ESS)&#160;or setting up an off-grid solar solution, this advanced battery pack combines cutting-edge technology with unmatched reliability. Boasting a&#160;nominal energy capacity of 2000Wh&#160;and a&#160;discharge current of 40A, it ensures stable, long-lasting power for all your energy needs.<br /><br /></p>\n<h3 id=\"-key-features-for-complete-home-ess-solutions-\">Key Features for Complete Home ESS Solutions</h3>\n<ul>\n<li>LiFePO4 Battery Technology<br />Enjoy enhanced safety, performance, and durability with the latest in&#160;advanced lithium chemistry. Say goodbye to energy storage worries!</li>\n<li>Variable Voltage Compatibility<br />With an operational range of&#160;44.8V to 57.6V, this battery integrates effortlessly into a variety of&#160;home ESS setups, adapting to your energy needs.</li>\n<li>Long-Lasting Performance<br />Rest easy with over&#160;6000 charge cycles, retaining 70% energy capacity even after years of daily use. The Deye AE-F2.0 is built to last.</li>\n<li>Expandable Capacity<br />Scale up your energy storage by connecting up to&#160;5 battery packs in parallel, achieving a total capacity of&#160;10kWh. Perfect for growing households or larger energy demands.</li>\n</ul>\n<ul><!--100ms--></ul>\n<br />\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-014.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<p></p>\n<h3 id=\"-why-choose-deye-ae-f2-0-for-your-home-ess-\">Why Choose Deye AE-F2.0 for Your Home ESS?</h3>\n<ol>\n<li><span>User-Friendly:</span>&#160;Intuitive LED display keeps you informed about your energy levels at all times.</li>\n<li><span>Reliable Durability:</span>&#160;Built for demanding environments, from extreme temperatures to high altitudes.</li>\n<li><span>Safe and Certified:</span>&#160;Fully compliant with international safety standards, giving you peace of mind.</li>\n<li><span>Generous Warranty:</span>&#160;Backed by a&#160;<span>10-year warranty</span>, ensuring your investment is protected.</li>\n</ol>\n<p>Whether you&#8217;re looking to&#160;maximize solar energy usage, prepare for outages, or increase your home&#8217;s energy independence, the&#160;Deye AE-F2.0 Battery Pack Module delivers dependable storage and exceptional performance. Its scalability, robust features, and sustainable battery technology make it a top-tier choice for modern homes.&#160;Upgrade your home ESS today with the Deye AE-F2.0 and experience the future of energy storage.</p>', 'Deye AE-F2.0 (EU) Battery Pack Module | Balcony Energy Solution<br /><hr />\n<ul>\n<li><strong>High Capacity</strong>: 2000Wh of energy storage for reliable power supply.</li>\n<li><strong>Long Life</strong>: Over 6000 cycle life, maintaining 70% capacity for years.</li>\n<li><strong>Advanced Chemistry</strong>: Utilizes safe and efficient LiFePO4 technology.</li>\n<li><strong>Flexible Installation</strong>: Floor-mounted design for easy setup.</li>\n<li><strong>Expandable System</strong>: Connect up to 5 packs for a maximum output of 10kWh.</li>\n<li><strong>User-Friendly Interface</strong>: LED display for SOC and alarm notifications.</li>\n<li><strong>Wide Operating Range</strong>: Functions between -10&#176;C to 50&#176;C, with a maximum altitude of 3000m.</li>\n<li><strong>Durable Build</strong>: Robust design certified for quality and safety (UN383, IEC62109, CE).</li>\n<li><strong>Warranty</strong>: 10-year warranty for added peace of mind.</li>\n</ul>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(568, '<table border=\"0\" width=\"100%\" cellspacing=\"0\" cellpadding=\"5\">\n<tbody>\n<tr style=\"background-color: #0d265f; color: white;\">\n<td><strong>System-Model</strong></td>\n<td><strong>AE-FS2.0-2H2&#160;</strong></td>\n</tr>\n<tr>\n<td>\n<p></p>\n<p><strong>AC Technical Specifications</strong></p>\n</td>\n<td></td>\n</tr>\n<tr>\n<td>Nominal Input / Output Power / USP Power</td>\n<td>1000 / 1000W</td>\n</tr>\n<tr>\n<td>AC Input / Output Frequency and Voltage</td>\n<td>50Hz (45h - 55h), 60h (55h - 65h), L / N (PE), 220 / 230 Vac</td>\n</tr>\n<tr>\n<td>Grip Type</td>\n<td>Single Phase</td>\n</tr>\n<tr>\n<td>Rated Grip Input / Output Current</td>\n<td>4.6A / 4.4A</td>\n</tr>\n<tr>\n<td>Max. Grid Input / Output Current</td>\n<td>5.0A / 4.8A</td>\n</tr>\n<tr>\n<td>Peak Power (off-grid)</td>\n<td>2 times rated power, 10s</td>\n</tr>\n<tr>\n<td>Power Factor Adjustment Range</td>\n<td>0.8 leading to 0.8 lagging</td>\n</tr>\n<tr>\n<td>Max. Bypass Grid to Load</td>\n<td>10A</td>\n</tr>\n<tr>\n<td>DC Injection current</td>\n<td>THD &lt; 3% ( Linear load &lt; 1.5% ) mA</td>\n</tr>\n<tr>\n<td>\n<p></p>\n<p><strong>DC Technical Specifications</strong></p>\n</td>\n<td></td>\n</tr>\n<tr>\n<td>Max. PV Access Power</td>\n<td>2200W</td>\n</tr>\n<tr>\n<td>Max. PV Input Power</td>\n<td>1600W</td>\n</tr>\n<tr>\n<td>Max. PV Input Voltage</td>\n<td>60V</td>\n</tr>\n<tr>\n<td>Start-up Voltage</td>\n<td>25V</td>\n</tr>\n<tr>\n<td>MPPT Voltage Range</td>\n<td>20 - 55V</td>\n</tr>\n<tr>\n<td>Full Load MPPT Voltage Range</td>\n<td>30 - 55V</td>\n</tr>\n<tr>\n<td>Rated PV Input Voltage</td>\n<td>42.5V</td>\n</tr>\n<tr>\n<td>Max. Input Short-Circuit Current</td>\n<td>27 + 27A</td>\n</tr>\n<tr>\n<td>Max. Operating PV Input Current</td>\n<td>18 + 18A</td>\n</tr>\n<tr>\n<td>No. of MPP Trackers / Strings per Tracker</td>\n<td>2 / 1</td>\n</tr>\n<tr>\n<td>\n<p></p>\n<p><strong>Battery Technical Specification</strong></p>\n</td>\n<td></td>\n</tr>\n<tr>\n<td>Battery Chemistry</td>\n<td>LiFePO&#8324;</td>\n</tr>\n<tr>\n<td>Battery Nominal Voltage</td>\n<td>51.2V</td>\n</tr>\n<tr>\n<td>Battery Nominal Energy</td>\n<td>2000Wh</td>\n</tr>\n<tr>\n<td>Max. Charging / Discharging Current</td>\n<td>25A</td>\n</tr>\n<tr>\n<td>Battery Operating Voltage</td>\n<td>44.8V &#8211; 57.6V</td>\n</tr>\n<tr>\n<td>Battery Cycle Life</td>\n<td>&#8805;6000 (@25&#176;C &#177; 2&#176;C, 0.5C / 0.5C, 70% EOL)</td>\n</tr>\n<tr>\n<td>Parallel Capability</td>\n<td>Supports up to 4 AE-F2.0 Smart Extra Batteries (max 10kWh)</td>\n</tr>\n<tr>\n<td>\n<p></p>\n<p><strong>USB Port Technical Specifications</strong></p>\n</td>\n<td></td>\n</tr>\n<tr>\n<td>USB-A Output</td>\n<td>2 ports, 5V, 2.4A, 12W Max per port</td>\n</tr>\n<tr>\n<td>USB-C Output</td>\n<td>2 ports, 5V, 3.0A, 15W Max per port</td>\n</tr>\n<tr>\n<td>\n<p></p>\n<p><strong>Other Technical Specification</strong></p>\n</td>\n<td></td>\n</tr>\n<tr>\n<td>Display</td>\n<td>Colorful Touch LCD &amp; APP &amp; Battery LED (SOC, Alarm)</td>\n</tr>\n<tr>\n<td>Communication Interfaces</td>\n<td>Wi-Fi, Bluetooth</td>\n</tr>\n<tr>\n<td>Dimensions (W x D x H)</td>\n<td>450 x 210 x 312 mm</td>\n</tr>\n<tr>\n<td>Weight (Approx)</td>\n<td>26 kg</td>\n</tr>\n<tr>\n<td>Operating Temperature Range</td>\n<td>-10&#176;C &#8211; 50&#176;C</td>\n</tr>\n<tr>\n<td>Max. Operating Altitude</td>\n<td>2000 m</td>\n</tr>\n<tr>\n<td>Relative Humidity</td>\n<td>0 &#8211; 95% (No Condensing)</td>\n</tr>\n<tr>\n<td>Safety / EMC Standards</td>\n<td>IEC2619, UN38.3, IEC/EN62109-1/2, IEC/EN61000-6-1/2/3/4</td>\n</tr>\n<tr>\n<td>Grid Regulation</td>\n<td>VDE4105, IEC61727/62116, VDE0126, AS4777.2, CEI0-21, EN50549-1, G98, G99, C10-11, UNE217002, NBR16149/16150</td>\n</tr>\n<tr>\n<td>Battery Certification</td>\n<td>UN38.3, IEC 62619</td>\n</tr>\n<tr>\n<td style=\"width: 30%;\">Installation Style</td>\n<td>Floor-Mounted</td>\n</tr>\n<tr>\n<td>Warranty</td>\n<td>5 Years</td>\n</tr>\n</tbody>\n</table>\n<p></p>\n<p></p>\n<p></p>\n<table border=\"0\" cellspacing=\"0\" cellpadding=\"5\" height=\"208\" style=\"width: 100%;\">\n<tbody>\n<tr style=\"background-color: #0d265f; color: white;\">\n<td><strong>Battery-Model</strong></td>\n<td><strong>AE-F2.0</strong></td>\n</tr>\n<tr>\n<td style=\"width: 30%;\">\n<p></p>\n<p><strong>Battery Technical Specification</strong></p>\n</td>\n<td></td>\n</tr>\n<tr>\n<td>Battery Chemistry</td>\n<td>LiFePO&#8324;</td>\n</tr>\n<tr>\n<td>Battery Nominal Voltage</td>\n<td>51.2V</td>\n</tr>\n<tr>\n<td>Battery Nominal Energy</td>\n<td>2000Wh</td>\n</tr>\n<tr>\n<td>Max. Charging / Discharging Current</td>\n<td>50A</td>\n</tr>\n<tr>\n<td>Battery Operating Voltage</td>\n<td>44.8V &#8211; 57.6V</td>\n</tr>\n<tr>\n<td>Battery Cycle Life</td>\n<td>&#8805;6000 (@25&#176;C &#177; 2&#176;C, 0.5C / 0.5C, 70% EOL)</td>\n</tr>\n<tr>\n<td>Parallel Capability</td>\n<td>5 pcs</td>\n</tr>\n<tr>\n<td>\n<p></p>\n<p><strong>Other Technical Specification</strong></p>\n</td>\n<td></td>\n</tr>\n<tr>\n<td>Display</td>\n<td>LED (SOC, Alarm)</td>\n</tr>\n<tr>\n<td>Communication Interfaces</td>\n<td>CAN2.0, LoRa</td>\n</tr>\n<tr>\n<td>Dimensions (W x D x H)</td>\n<td>450 x 210 x 244 mm</td>\n</tr>\n<tr>\n<td>Weight (Approx)</td>\n<td>20 kg</td>\n</tr>\n<tr>\n<td>Operating Temperature Range</td>\n<td>-10&#176;C &#8211; 50&#176;C</td>\n</tr>\n<tr>\n<td>Max. Operating Altitude</td>\n<td>3000 m</td>\n</tr>\n<tr>\n<td>Relative Humidity</td>\n<td>15% &#8211; 85% (No Condensing)</td>\n</tr>\n<tr>\n<td>Certification</td>\n<td>UN38.3, IEC 62619, CE</td>\n</tr>\n<tr>\n<td>Installation Style</td>\n<td>Floor-Mounted</td>\n</tr>\n<tr>\n<td>Warranty</td>\n<td>10 Years</td>\n</tr>\n</tbody>\n</table>', 2, 'AE-FS2.0-2H2 (EU) Home Solar Battery System | ESS', '<p><span>Deye is proud to unveil the AE-F(S) 2.0-2H2, a groundbreaking&#160;home solar battery system&#160;designed to meet the energy needs of the modern world. Engineered with precision and built to last, this system is a testament to Deye&#8217;s commitment to innovation, sustainability, and reliability. Whether for residential applications seeking robust&#160;solar power batteries for home, commercial setups, or portable outdoor use, the AE-F(S) 2.0-2H2 is your trusted partner in harnessing the power of renewable energy through an advanced&#160;home solar battery system.</span><br /><br /></p>\n<h3 id=\"-key-features-for-complete-home-ess-solutions-\">Key Features for Complete Home ESS Solutions</h3>\n<ul>\n<li data-block-id=\"49ac95e2-dfdf-4975-b63d-fec3b69e25c5\"><span>Durable &amp; Safe:</span>&#160;Features an IP65 waterproof rating, a 10-year warranty, and a 6000-cycle lifespan. Certified with UN38.3 and IEC62619, it&#8217;s a reliable home solar battery system.</li>\n<li data-block-id=\"db8e3465-6d21-49de-b7c7-d7ecc41063c8\"><span>High Performance:</span>&#160;Equipped with a 2kWh LFP battery, it supports 1000W PV input and 800W AC/DC output. Its rapid 4ms UPS switch ensures uninterrupted power, crucial for effective solar power storage batteries.</li>\n<li data-block-id=\"1f51c842-d86c-4eb2-bf25-3b40556cf5a3\"><span>Smart &amp; Connected:</span>&#160;Easily manage your home solar battery system via Bluetooth, WiFi, and a mobile app for seamless monitoring.</li>\n<li data-block-id=\"b4250b1e-4c69-4317-b572-39401f59f545\"><span>User-Friendly &amp; Versatile:</span>&#160;An intuitive LCD and app interface, compact design (450x210x321mm, &#126;24kg), and wide operating temperature range (-10&#176;C to 50&#176;C) make it adaptable to various environments.</li>\n<li data-block-id=\"3dcaa49d-56b5-4cf2-92f7-5cdd174002f3\"><span>Technical Excellence:</span>&#160;Offers 800W nominal power, 50Hz AC (220/230V), and a 51.2V, 2000Wh LiFePO4 battery, meeting diverse energy demands for your solar power batteries for home.</li>\n</ul>\n<ul><!--100ms--></ul>\n<br />\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-014.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<p></p>\n<h3>Technical Highlights</h3>\n<ul>\n<li>Advanced LiFePO4 battery technology</li>\n<li>Rapid 4ms UPS switching for uninterrupted power</li>\n<li>Comprehensive safety certifications (UN38.3, IEC62619)</li>\n<li>Maximum operating altitude of 3000m</li>\n</ul>\n<p data-block-id=\"dabbef10-dbe2-4c46-b901-b78724324ff5\">The AE-F(S) 2.0-2H2&#160;home solar battery system&#160;represents the future of residential energy storage. With industry-leading specifications and smart features, this system provides the reliable&#160;solar power batteries for home&#160;that today&#8217;s energy-conscious homeowners demand.</p>', 'AE-FS2.0-2H2 (EU) Home Solar Battery System | Energy Storage Solution (ESS)<br /><hr />\n<ul>\n<li><span>Robust Energy Storage</span>: 2kWh LFP battery at the core of this advanced&#160;<span>home solar battery system</span></li>\n<li><span>Powerful Performance</span>: Supports 1000W PV MPPT input &amp; 800W bidirectional AC/DC output</li>\n<li><span>Uninterrupted Power</span>: Rapid 4ms UPS load support for critical applications</li>\n<li><span>Built to Last</span>: IP65 waterproof, 10-year warranty, and a 6000-cycle lifespan</li>\n<li><span>Smart &amp; Connected</span>: Bluetooth, WiFi, and mobile app for easy monitoring and control</li>\n<li><span>User-Friendly Design</span>: Intuitive LCD, compact (450x210x321mm), and &#126;24kg</li>\n<li><span>All-Weather Ready</span>: Operates from -10&#176;C to 50&#176;C and up to 3000m altitude</li>\n<li><span>Certified Safety</span>: Meets UN38.3, IEC62619, and other key safety standards</li>\n</ul>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(569, '<table border=\"0\" width=\"100%\" cellspacing=\"0\" cellpadding=\"5\">\n<tbody>\n<tr style=\"background-color: #0d265f; color: white;\">\n<td><strong>Model</strong></td>\n<td><strong>AI-W5.1-PDU1-B + Base</strong></td>\n</tr>\n<tr>\n<td><strong>Function</strong></td>\n<td>Battery Power and Communication Interface with LED Status Display</td>\n</tr>\n<tr>\n<td><strong>Application</strong></td>\n<td>Connects Battery Modules to Hybrid Inverter &amp; System Display</td>\n</tr>\n<tr>\n<td><strong>Included Components</strong></td>\n<td>PDU (Power Distribution Unit) + Bottom Support Base + 1.5m Power Cable</td>\n</tr>\n<tr>\n<td><strong>Communication Interface</strong></td>\n<td>RS485 / CAN (depends on inverter)</td>\n</tr>\n<tr>\n<td><strong>Display</strong></td>\n<td>LED Indicators for System Status</td>\n</tr>\n<tr>\n<td><strong>Cable Type</strong></td>\n<td>Battery Power &amp; Communication Cable (1.5m)</td>\n</tr>\n<tr>\n<td><strong>Installation Style</strong></td>\n<td>Floor-Mounted (Bottom Base Included)</td>\n</tr>\n<tr>\n<td><strong>Compatibility</strong></td>\n<td>AI-W5.1-B Scalable LFP Battery System</td>\n</tr>\n<tr>\n<td><strong>Included in Package</strong></td>\n<td>PDU Unit, Base, Cable (AI-W5.1-PCable1500)</td>\n</tr>\n<tr>\n<td><strong>Certification</strong></td>\n<td>UN38.3, CE</td>\n</tr>\n<tr>\n<td><strong>Warranty</strong></td>\n<td>10 Years</td>\n</tr>\n</tbody>\n</table>', 2, 'AI-W5.1-PDU1-B+Base | ESS', '<p data-start=\"223\" data-end=\"532\">The Deye&#160;<strong data-start=\"227\" data-end=\"252\">AI-W5.1-PDU1-B+Base</strong> is an essential component of the <strong data-start=\"286\" data-end=\"299\">AI-W5.1-B</strong> scalable lithium-ion battery energy storage system designed for residential and commercial applications. This integrated unit ensures efficient communication and power distribution between the inverter and connected battery modules. The PDU (Power Distribution Unit) serves as a central hub for power and data management, connecting the inverter to the battery stack while providing a built-in LED display for live system status. The Base ensures stable installation and alignment for stacked battery modules, promoting safety and modular scalability.</p>\n<p></p>\n<h3 id=\"-key-features-for-complete-home-ess-solutions-\">Key Features for Complete Home ESS Solutions</h3>\n<ul>\n<li data-start=\"1569\" data-end=\"1664\">\n<p data-start=\"1571\" data-end=\"1664\"><strong data-start=\"1574\" data-end=\"1601\">Plug &amp; Play Integration:&#160;</strong>Pre-configured with PDU, base, and cabling for fast setup.</p>\n</li>\n<li data-start=\"1665\" data-end=\"1745\">\n<p data-start=\"1667\" data-end=\"1745\"><strong data-start=\"1670\" data-end=\"1685\">LED Display:&#160;</strong>Real-time system status monitoring directly on the PDU.</p>\n</li>\n<li data-start=\"1746\" data-end=\"1845\">\n<p data-start=\"1748\" data-end=\"1845\"><strong data-start=\"1751\" data-end=\"1777\">Seamless Communication:&#160;</strong>Reliable data and power interface between battery and inverter.</p>\n</li>\n<li data-start=\"1846\" data-end=\"1933\">\n<p data-start=\"1848\" data-end=\"1933\"><strong data-start=\"1850\" data-end=\"1865\">High Safety:&#160;</strong>Ensures stable stacking and reduces risk with a dedicated base.</p>\n</li>\n<li data-start=\"1934\" data-end=\"2015\">\n<p data-start=\"1936\" data-end=\"2015\"><strong data-start=\"1939\" data-end=\"1958\">Scalable Design:&#160;</strong>Compatible with AI-W5.1-B stackable battery modules.</p>\n</li>\n<li data-start=\"2016\" data-end=\"2115\">\n<p data-start=\"2018\" data-end=\"2115\"><strong data-start=\"2021\" data-end=\"2053\">Residential &amp; Commercial Use:&#160;</strong>Suitable for various installation sizes and requirements.</p>\n</li>\n<li data-start=\"2116\" data-end=\"2201\">\n<p data-start=\"2118\" data-end=\"2201\"><strong data-start=\"2121\" data-end=\"2146\">Hybrid Inverter Ready:&#160;</strong>Fully prepared for use with hybrid inverter systems.</p>\n</li>\n</ul>\n<ul><!--100ms--></ul>\n<br />\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-015.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<p></p>\n<h3 data-start=\"867\" data-end=\"899\"><strong data-start=\"874\" data-end=\"899\">Technical Description</strong></h3>\n<ul data-start=\"901\" data-end=\"1509\">\n<li data-start=\"901\" data-end=\"1147\">\n<p data-start=\"903\" data-end=\"943\"><strong data-start=\"903\" data-end=\"941\">Power Distribution Unit I (PDU1-B)</strong></p>\n<ul data-start=\"946\" data-end=\"1147\">\n<li data-start=\"946\" data-end=\"1036\">\n<p data-start=\"948\" data-end=\"1036\"><strong data-start=\"948\" data-end=\"961\">Function:</strong> Handles power and data communication between inverter and battery stack</p>\n</li>\n<li data-start=\"1039\" data-end=\"1086\">\n<p data-start=\"1041\" data-end=\"1086\"><strong data-start=\"1041\" data-end=\"1053\">Display:</strong> Integrated LED status monitor</p>\n</li>\n<li data-start=\"1089\" data-end=\"1147\">\n<p data-start=\"1091\" data-end=\"1147\"><strong data-start=\"1091\" data-end=\"1105\">Interface:</strong> Battery and inverter communication ports<br /><br /></p>\n</li>\n</ul>\n</li>\n<li data-start=\"1149\" data-end=\"1346\">\n<p data-start=\"1151\" data-end=\"1180\"><strong data-start=\"1151\" data-end=\"1178\">Battery Base (Included)</strong></p>\n<ul data-start=\"1183\" data-end=\"1346\">\n<li data-start=\"1183\" data-end=\"1275\">\n<p data-start=\"1185\" data-end=\"1275\"><strong data-start=\"1185\" data-end=\"1198\">Function:</strong> Mechanical support for the battery stack, ensures stability and alignment</p>\n</li>\n<li data-start=\"1278\" data-end=\"1346\">\n<p data-start=\"1280\" data-end=\"1346\"><strong data-start=\"1280\" data-end=\"1297\">Installation:</strong> Floor-mounted; compatible with modular stacking<br /><br /></p>\n</li>\n</ul>\n</li>\n<li data-start=\"1348\" data-end=\"1509\">\n<p data-start=\"1350\" data-end=\"1385\"><strong data-start=\"1350\" data-end=\"1383\">AI-W5.1-PCable1500 (Included)</strong></p>\n<ul data-start=\"1388\" data-end=\"1509\">\n<li data-start=\"1388\" data-end=\"1485\">\n<p data-start=\"1390\" data-end=\"1485\"><strong data-start=\"1390\" data-end=\"1403\">Function:</strong> Pre-wired power and communication cable to connect PDU1-B with hybrid inverter</p>\n</li>\n<li data-start=\"1488\" data-end=\"1509\">\n<p data-start=\"1490\" data-end=\"1509\"><strong data-start=\"1490\" data-end=\"1501\">Length:</strong> 1500mm</p>\n</li>\n</ul>\n</li>\n</ul>', 'The Deye AI-W5.1-PDU1-B+Base is a key component of the AI-W5.1-B battery system, enabling efficient power and data management between the inverter and battery modules. It features an integrated LED display for real-time system status and provides a stable, secure base for stacked installations, supporting both safety and modular scalability.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', '');
INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(570, '<table border=\"0\" cellpadding=\"6\" cellspacing=\"0\" style=\"width: 100%;\">\n<tbody>\n<tr>\n<td>Battery Chemistry</td>\n<td colspan=\"6\" style=\"text-align: center;\">LiFePO4</td>\n</tr>\n<tr>\n<td>Built-in Circuit Breaker</td>\n<td colspan=\"6\" style=\"text-align: center;\">125A 2P, 60Vdc</td>\n</tr>\n<tr>\n<td>Battery Module Energy (kWh)</td>\n<td colspan=\"6\" style=\"text-align: center;\">5.12</td>\n</tr>\n<tr>\n<td>Battery Module Voltage (V)</td>\n<td colspan=\"6\" style=\"text-align: center;\">51.2</td>\n</tr>\n<tr>\n<td>Battery Module Capacity (Ah)</td>\n<td colspan=\"6\" style=\"text-align: center;\">100</td>\n</tr>\n<tr>\n<td>Scalability (Modules)</td>\n<td style=\"text-align: center;\">1</td>\n<td style=\"text-align: center;\">2</td>\n<td style=\"text-align: center;\">3</td>\n<td style=\"text-align: center;\">4</td>\n<td style=\"text-align: center;\">5</td>\n<td style=\"text-align: center;\">6</td>\n</tr>\n<tr>\n<td>Nominal Voltage (V)</td>\n<td colspan=\"6\" style=\"text-align: center;\">51.2</td>\n</tr>\n<tr>\n<td>Operating Voltage (V)</td>\n<td colspan=\"6\" style=\"text-align: center;\">43.2 &#126; 57.6</td>\n</tr>\n<tr>\n<td>Nominal Energy (kWh)</td>\n<td style=\"text-align: center;\">5.12</td>\n<td style=\"text-align: center;\">10.24</td>\n<td style=\"text-align: center;\">15.36</td>\n<td style=\"text-align: center;\">20.48</td>\n<td style=\"text-align: center;\">25.6</td>\n<td style=\"text-align: center;\">30.72</td>\n</tr>\n<tr>\n<td>Usable Energy (kWh)</td>\n<td style=\"text-align: center;\">4.6</td>\n<td style=\"text-align: center;\">9.2</td>\n<td style=\"text-align: center;\">13.8</td>\n<td style=\"text-align: center;\">18.4</td>\n<td style=\"text-align: center;\">23</td>\n<td style=\"text-align: center;\">27.6</td>\n</tr>\n<tr>\n<td>Charge/Discharge Current (A) - Recommend</td>\n<td style=\"text-align: center;\">50</td>\n<td style=\"text-align: center;\">100</td>\n<td style=\"text-align: center;\">150</td>\n<td style=\"text-align: center;\">200</td>\n<td style=\"text-align: center;\">250</td>\n<td style=\"text-align: center;\">250</td>\n</tr>\n<tr>\n<td>Charge/Discharge Current (A) - Max.</td>\n<td style=\"text-align: center;\">100</td>\n<td style=\"text-align: center;\">180</td>\n<td style=\"text-align: center;\">250</td>\n<td style=\"text-align: center;\">250</td>\n<td style=\"text-align: center;\">250</td>\n<td style=\"text-align: center;\">250</td>\n</tr>\n<tr>\n<td>Charge/Discharge Current (A) - Peak (10s, 25&#8451;)</td>\n<td style=\"text-align: center;\">150</td>\n<td style=\"text-align: center;\">270</td>\n<td style=\"text-align: center;\">360</td>\n<td style=\"text-align: center;\">360</td>\n<td style=\"text-align: center;\">360</td>\n<td style=\"text-align: center;\">360</td>\n</tr>\n<tr><th colspan=\"7\">\n<p></p>\n<p>Other Parameters</p>\n</th></tr>\n<tr>\n<td>Recommend Depth of Discharge</td>\n<td colspan=\"6\" style=\"text-align: center;\">90%</td>\n</tr>\n<tr>\n<td>System Dimension (W/D/H, mm)</td>\n<td style=\"text-align: center;\">720&#215;255&#215;569</td>\n<td style=\"text-align: center;\">720&#215;255&#215;850</td>\n<td style=\"text-align: center;\">720&#215;255&#215;1131</td>\n<td style=\"text-align: center;\">720&#215;255&#215;1412</td>\n<td style=\"text-align: center;\">720&#215;255&#215;1693</td>\n<td style=\"text-align: center;\">720&#215;255&#215;1974</td>\n</tr>\n<tr>\n<td>System Weight (kg)</td>\n<td style=\"text-align: center;\">74.5</td>\n<td style=\"text-align: center;\">127.5</td>\n<td style=\"text-align: center;\">180.5</td>\n<td style=\"text-align: center;\">233.5</td>\n<td style=\"text-align: center;\">286.5</td>\n<td style=\"text-align: center;\">339.5</td>\n</tr>\n<tr>\n<td>Battery Module Dimension (W/D/H, mm)</td>\n<td colspan=\"6\" style=\"text-align: center;\">720&#215;255&#215;300 (without terminal parts)</td>\n</tr>\n<tr>\n<td style=\"width: 30%;\">Battery Module Weight (kg)</td>\n<td colspan=\"6\" style=\"text-align: center;\">55kg per module</td>\n</tr>\n<tr>\n<td>Master LED Indicator</td>\n<td colspan=\"6\" style=\"text-align: center;\">Battery module: 3 LEDs (working, alarming, protecting)<br /> PDU module: 5 LEDs (SOC: 20%&#126;100%) + 3 LEDs (working, alarming, protecting)</td>\n</tr>\n<tr>\n<td>IP Rating of Enclosure</td>\n<td colspan=\"6\" style=\"text-align: center;\">IP65 (after stacking)</td>\n</tr>\n<tr>\n<td>Operating Temperature</td>\n<td colspan=\"6\" style=\"text-align: center;\">Charge: 0&#126;55&#8451; / Discharge: -20&#126;55&#8451;</td>\n</tr>\n<tr>\n<td>Storage Temperature</td>\n<td colspan=\"6\" style=\"text-align: center;\">0&#8451;&#126;35&#8451;</td>\n</tr>\n<tr>\n<td>Humidity</td>\n<td colspan=\"6\" style=\"text-align: center;\">5% &#126; 95%</td>\n</tr>\n<tr>\n<td>Altitude</td>\n<td colspan=\"6\" style=\"text-align: center;\">&#8804;2000 m</td>\n</tr>\n<tr>\n<td>Installation</td>\n<td colspan=\"6\" style=\"text-align: center;\">Wall-Mounted, Floor-Mounted</td>\n</tr>\n<tr>\n<td>Communication Port</td>\n<td colspan=\"6\" style=\"text-align: center;\">CAN2.0, RS485</td>\n</tr>\n<tr>\n<td>Cycle Life</td>\n<td colspan=\"6\" style=\"text-align: center;\">&#8805;6000 (25&#8451;&#177;2&#8451;, 0.5C/0.5C, 90% DOD, 70% EOL)</td>\n</tr>\n<tr>\n<td>Energy Throughput</td>\n<td colspan=\"6\" style=\"text-align: center;\">16 MWh (Battery Module @70% EOL)</td>\n</tr>\n<tr>\n<td>Warranty Period</td>\n<td colspan=\"6\" style=\"text-align: center;\">10 years</td>\n</tr>\n<tr>\n<td>Certification</td>\n<td colspan=\"6\" style=\"text-align: center;\">UN38.3, IEC62619, CE, UK, VDE2510-50, CEI 0-21, CE-LVD, CEC</td>\n</tr>\n</tbody>\n</table>\n<p></p>', 2, 'AI-W5.1-B (EU) Solar Battery System | ESS', '<p data-start=\"223\" data-end=\"532\"><span>The&#160;</span><span>Deye <strong>AI-W5.1-B</strong></span><span>&#160;Solar Battery System is a cutting-edge, eco-friendly energy storage solution designed for both residential and commercial applications. Featuring a modular stackable design, this system provides unparalleled flexibility and scalability, allowing up to 6 clusters in parallel (36 units total) to achieve a maximum energy capacity of&#160;</span><span>184kWh</span><span>. Its sleek floor-mounted form ensures simple, wire-free installation, while the high-performanc</span><span>e LFP lithium-ion battery</span><span>&#160;chemistry ensures safety, reliability, and long-term durability.</span></p>\n<h3 id=\"-key-features-\"><span>Key Features for AI-W5.1-B (EU)</span></h3>\n<ul>\n<li><strong>Modular and Flexible Design:</strong> Each module offers&#160;<span>5.12 kWh</span>&#160;of nominal energy, stackable up to a maximum&#160;<span>30.72 kWh</span>&#160;per system (6 modules). Expand as your energy needs grow.<br /><br /></li>\n<li><strong>Eco-Friendly:</strong> Non-toxic, pollution-free materials, with a cobalt-free LFP battery that ensures a safer and greener energy solution.<br /><br /></li>\n<li><strong>Reliable Performance:</strong>\n<ul>\n<li>High discharge power with&#160;IP65&#160;protection, enabling indoor and outdoor usage.</li>\n<li>Wide operating temperature range from&#160;<span>-20&#176;C to 55&#176;C</span>, ensuring consistent operation in diverse conditions.</li>\n<li>Precision-engineered&#160;<span>Battery Management System (BMS)</span>&#160;prolongs lifespan and optimizes efficiency.<br /><br /></li>\n</ul>\n</li>\n<li><strong>Advanced Features</strong>:\n<ul>\n<li>Remote monitoring and firmware upgrades for hassle-free performance optimization.</li>\n<li>Intelligent auto-networking for seamless system integration.</li>\n</ul>\n</li>\n</ul>\n<p></p>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-015.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<h3 data-start=\"867\" data-end=\"899\"><strong data-start=\"874\" data-end=\"899\">Technical Description&#160;AI-W5.1-B (EU)</strong></h3>\n<ul style=\"list-style-type: disc;\">\n<li><strong data-start=\"174\" data-end=\"187\">Function:</strong> Stores and delivers energy as part of a modular lithium-ion storage system</li>\n<li><strong data-start=\"264\" data-end=\"286\">Battery Chemistry:</strong> LiFePO&#8324; (LFP)</li>\n<li><strong data-start=\"303\" data-end=\"322\">Nominal Energy:</strong> 5.12 kWh (per module)</li>\n<li><strong data-start=\"347\" data-end=\"365\">Usable Energy:</strong> 4.6 kWh (90% Depth of Discharge)</li>\n<li><strong data-start=\"401\" data-end=\"421\">Nominal Voltage:</strong> 51.2 V</li>\n<li><strong data-start=\"431\" data-end=\"459\">Operating Voltage Range:</strong> 44.8 V &#8211; 57.6 V</li>\n<li><strong data-start=\"478\" data-end=\"497\">Rated DC Power:</strong> 2.5 kW per module</li>\n<li><strong data-start=\"518\" data-end=\"540\">Peak Power Output:</strong> 100 A (10s @ 25&#176;C)</li>\n<li><strong data-start=\"562\" data-end=\"577\">Cycle Life:</strong> &#8805;6000 cycles (at 70% End of Life capacity)</li>\n<li><strong data-start=\"623\" data-end=\"636\">Warranty:</strong> 10 years</li>\n<li><strong data-start=\"649\" data-end=\"671\">Protection Rating:</strong> IP65 (dust- and water-resistant)</li>\n<li><strong data-start=\"707\" data-end=\"722\">Dimensions:</strong> 720 &#215; 255 &#215; 300 mm</li>\n<li><strong data-start=\"744\" data-end=\"755\">Weight:</strong> 55 kg per module</li>\n</ul>\n<h3 id=\"-why-choose-the-ai-w5-1-b-\"><span>Why Choose the AI-W5.1-B?</span></h3>\n<p>The AI-W5.1-B provides a scalable,&#160;eco-conscious solution to energy storage, with a focus on safety, reliability, and user convenience. Its zero-cobalt&#160;LFP lithium-ion battery&#160;design, superior lifespan, and adaptable configuration make it ideal for powering homes, businesses, or hybrid energy setups. Whether you&#8217;re preparing for off-grid independence or supplementing solar power systems, the&#160;AI-W5.1-B&#160;is a future-proof investment.&#160;The AI-W5.1-B is a versatile, reliable, and sustainable energy storage solution, perfectly suited for modern energy demands. With a 10-year warranty, eco-friendly materials, and advanced features like remote monitoring, it&#8217;s crafted for long-term efficiency, leveraging the benefits of its&#160;LFP lithium-ion battery.</p>', '<ul>\n<li><strong>Safe &amp; Reliable:</strong>&#160;LFP chemistry and an intelligent BMS</li>\n<li><strong>Scalable Capacity:</strong>&#160;30.72 kWh, multiple modules in parallel</li>\n<li><strong>Wide Operating Temperature:</strong>&#160;-20&#176;C to 55&#176;C</li>\n<li><strong>Easy Installation:</strong>&#160;Wall/floor mountable, no wiring required</li>\n<li><strong>Eco-Friendly Design:&#160;</strong>non-toxic, pollution-free materials</li>\n<li><strong>Long Cycle Life:</strong>&#160;Excellent lifespan for long-term energy storage</li>\n<li><strong>10-Year Warranty:</strong>&#160;Ensuring long-term reliability</li>\n<li><span><strong>Suitable Deye Inverter Model:</strong></span>\n<ul>\n<li><span>SUN-7/7.6/8/10K-5G05LP1-EU-SM2</span></li>\n<li><span>SUN-12/14/16K-SGO1LP1-EU</span></li>\n<li><span>SUN-5/6/8/10/12K-SG04LP3-EU</span></li>\n<li><span>SUN-3/4/5/6/8/10/12K-SG05LP3-EU-SM2</span></li>\n<li><span>SUN-14/15/16/18/20K-SG05LP3-EU-SM2</span></li>\n</ul>\n</li>\n</ul>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(571, '<table border=\"0\" cellpadding=\"6\" cellspacing=\"0\" style=\"width: 100%;\">\n<tbody>\n<tr>\n<td>Cell Chemistry</td>\n<td colspan=\"3\" style=\"text-align: center;\">LiFePO4</td>\n</tr>\n<tr>\n<td>Module Energy (kWh)</td>\n<td colspan=\"3\" style=\"text-align: center;\">7.68</td>\n</tr>\n<tr>\n<td>Module Nominal Voltage (V)</td>\n<td colspan=\"3\" style=\"text-align: center;\">38.4</td>\n</tr>\n<tr>\n<td>Module Capacity (Ah)</td>\n<td colspan=\"3\" style=\"text-align: center;\">200</td>\n</tr>\n<tr>\n<td>Module Dimensions (W &#215; D &#215; H, mm)</td>\n<td colspan=\"3\" style=\"text-align: center;\">601.5 &#215; 520 &#215; 135</td>\n</tr>\n<tr>\n<td>Module Weight (approx., kg)</td>\n<td colspan=\"3\" style=\"text-align: center;\">70</td>\n</tr>\n<tr>\n<td>Battery Modules in Series (optional)</td>\n<td style=\"text-align: center;\">7</td>\n<td style=\"text-align: center;\">13</td>\n<td style=\"text-align: center;\">21</td>\n</tr>\n<tr>\n<td>System Nominal Voltage (V)</td>\n<td style=\"text-align: center;\">268.8</td>\n<td style=\"text-align: center;\">499.2</td>\n<td style=\"text-align: center;\">806.4</td>\n</tr>\n<tr>\n<td>System Operating Voltage (V)</td>\n<td style=\"text-align: center;\">235.2 &#126; 306.6</td>\n<td style=\"text-align: center;\">436.8 &#126; 569.4</td>\n<td style=\"text-align: center;\">705.6 &#126; 920.7</td>\n</tr>\n<tr>\n<td>System Energy (kWh)</td>\n<td style=\"text-align: center;\">53.76</td>\n<td style=\"text-align: center;\">99.84</td>\n<td style=\"text-align: center;\">161.28</td>\n</tr>\n<tr>\n<td>Usable System Energy (kWh)</td>\n<td style=\"text-align: center;\">48.38</td>\n<td style=\"text-align: center;\">89.85</td>\n<td style=\"text-align: center;\">145.15</td>\n</tr>\n<tr>\n<td style=\"width: 30%;\">Charge/Discharge Current (A) - Recommended</td>\n<td colspan=\"3\" style=\"text-align: center;\">100</td>\n</tr>\n<tr>\n<td>Charge/Discharge Current (A) - Max.</td>\n<td colspan=\"3\" style=\"text-align: center;\">160</td>\n</tr>\n<tr>\n<td>Operating Temperature (&#8451;)</td>\n<td colspan=\"3\" style=\"text-align: center;\">Charge: 0 &#126; 55 / Discharge: -20 &#126; 55</td>\n</tr>\n<tr>\n<td>Status Indicator</td>\n<td colspan=\"3\" style=\"text-align: center;\">Yellow: Battery HV On. Red: System Alarm</td>\n</tr>\n<tr>\n<td>Communication Port</td>\n<td colspan=\"3\" style=\"text-align: center;\">CAN2.0</td>\n</tr>\n<tr>\n<td>Humidity</td>\n<td colspan=\"3\" style=\"text-align: center;\">5% &#126; 85% RH</td>\n</tr>\n<tr>\n<td>Altitude (above sea level)</td>\n<td colspan=\"3\" style=\"text-align: center;\">&#8804;3000 m</td>\n</tr>\n<tr>\n<td>IP Rating of Enclosure</td>\n<td colspan=\"3\" style=\"text-align: center;\">IP20</td>\n</tr>\n<tr>\n<td>System Dimensions (W &#215; D &#215; H, mm)</td>\n<td style=\"text-align: center;\">610 &#215; 610 &#215; 1450</td>\n<td style=\"text-align: center;\">610 &#215; 610 &#215; 2350</td>\n<td style=\"text-align: center;\">610 &#215; 610 &#215; 3650</td>\n</tr>\n<tr>\n<td>System Weight (approx., kg)</td>\n<td style=\"text-align: center;\">530</td>\n<td style=\"text-align: center;\">985</td>\n<td style=\"text-align: center;\">1590</td>\n</tr>\n<tr>\n<td>Installation</td>\n<td colspan=\"3\" style=\"text-align: center;\">Rack Mount</td>\n</tr>\n<tr>\n<td>Storage Temperature (&#8451;)</td>\n<td colspan=\"3\" style=\"text-align: center;\">0 &#126; 35</td>\n</tr>\n<tr>\n<td>Recommended Depth of Discharge</td>\n<td colspan=\"3\" style=\"text-align: center;\">90%</td>\n</tr>\n<tr>\n<td>Cycle Life</td>\n<td colspan=\"3\" style=\"text-align: center;\">&#8805;6000 (25&#177;2&#8451;, 0.5C/0.5C, EOL 70%)</td>\n</tr>\n<tr>\n<td>Warranty</td>\n<td colspan=\"3\" style=\"text-align: center;\">10 years</td>\n</tr>\n<tr>\n<td>Certification</td>\n<td colspan=\"3\" style=\"text-align: center;\">CE / IEC 62619 / IEC 62040 / UN38.3 / VDE-2510</td>\n</tr>\n</tbody>\n</table>', 2, 'BOS-A-Pack (EU) [7.68kWh] High-Performance Commercial Battery Storage Module | ESS', '<p>Deye BOS-A is a high-performance, embedded LiFePO4 battery module engineered for robust commercial battery storage. It offers quick installation and maintenance, advanced safety features, an intelligent BMS, and an eco-friendly design, making it an ideal choice for power backup and renewable&#160;commercial energy storage.</p>\n<h3 id=\"key-features-\">Key Features:</h3>\n<ul>\n<li><strong>High Performance:</strong> With a capacity of&#160;<span>7.68 kWh</span>&#160;and the potential for &gt;6000 cycles, the BOS-A guarantees long-lasting energy support, ensuring that your operations run smoothly without interruptions.</li>\n<li><strong>Intelligent Management:</strong> Equipped with smart cloud-based monitoring, the BOS-A enables real-time tracking of your energy consumption and battery status, optimizing performance and lowering electricity bills.</li>\n<li><strong>Flexible Configuration:</strong> Capable of supporting multiple racks with up to&#160;<span>13 battery modules</span>&#160;in series, this system provides adaptability to meet your growing energy demands.</li>\n<li><strong>Effortless Installation:</strong> The lightweight design, at just&#160;<span>70 kg</span>&#160;per module, paired with a detailed user manual, ensures a straightforward installation process.</li>\n<li><strong>Safety First:</strong> Featuring an intelligent battery management system (BMS) and comprehensive safety protocols to prevent over-discharge, over-charge, and short circuits, the BOS-A prioritizes the longevity and safety of your power system.</li>\n<li><strong>Robust Design:</strong> Built to withstand various environmental conditions, the BOS-A has a high IP rating and can function effectively in a range of temperatures, ensuring durability in any setting.</li>\n<li><strong>Warranty Assurance:</strong> Enjoy peace of mind with a&#160;<span>10-year warranty</span>, providing you with a full replacement guarantee for up to&#160;<span>6000 cycles</span>&#160;of use.<br /><br /></li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-016.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<h3 id=\"technical-specifications-\">Technical Specifications:</h3>\n<ul>\n<li><strong>Cell Chemistry:</strong> LiFePO&#8324;</li>\n<li><strong>Battery Dimensions</strong>: 601.5 mm x 520 mm x 135 mm</li>\n<li><strong>Weight:</strong> Approx. 70 kg per rack</li>\n<li><strong>Energy Efficiency:</strong> Over 90% at standard operational conditions</li>\n<li><strong>Communication Port:</strong> CAN2.0, offering seamless integration with other Deye devices</li>\n</ul>\n<h3 id=\"installation-and-support-\">Installation and Support:</h3>\n<p>The BOS-A is designed for rack-mounted environments, making it an ideal solution for&#160;commercial battery storage systems&#160;in commercial buildings and industrial facilities. Comprehensive support for your&#160;commercial energy storage&#160;solution is available via the Deye Cloud platform, enabling convenient remote monitoring and control.</p>', '<ul>\n<li><strong>High Capacity</strong>: 7.68 kWh, supports up to 6000 cycles</li>\n<li><strong>Smart Monitoring</strong>: Cloud-based tracking, real-time energy management</li>\n<li><strong>Flexible Configuration</strong>: Supports up to 13 battery modules in series</li>\n<li><strong>Easy Installation</strong>: Lightweight design (approx. 70 kg)</li>\n<li><strong>Safety Assurance</strong>: BMS, against overcharge and short circuits</li>\n<li><strong>Warranty Coverage</strong>: 10-year warranty</li>\n<li><strong>User-Friendly Interface</strong>: Seamlessly integrates with the Deye Cloud</li>\n<li><span><strong>Suitable Deye Inverter Model:</strong></span>\n<ul>\n<li><span>SUN-30K-SG01HP3-EU-BM3</span></li>\n<li><span>SUN-40K/50K-SG01HP3-EU-BM4</span></li>\n<li><span>SUN-60K-SG02HP3-EU-EM4</span></li>\n<li><span>SUN-80K-SG02HP3-EU-EM6</span></li>\n<li><span>SUN-100K-PCSL01HP3-AU</span></li>\n</ul>\n</li>\n</ul>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(572, '<table border=\"0\" cellpadding=\"6\" cellspacing=\"0\" style=\"width: 100%;\">\n<tbody>\n<tr>\n<td style=\"width: 30%;\">Cell Chemistry</td>\n<td colspan=\"3\" style=\"text-align: center;\">Lithium-ion</td>\n</tr>\n<tr>\n<td>Nominal Capacity (Ah)</td>\n<td colspan=\"3\" style=\"text-align: center;\">280</td>\n</tr>\n<tr>\n<td>Nominal Energy (kWh)</td>\n<td colspan=\"3\" style=\"text-align: center;\">14.3</td>\n</tr>\n<tr>\n<td>Nominal Voltage (V)</td>\n<td colspan=\"3\" style=\"text-align: center;\">51.2</td>\n</tr>\n<tr>\n<td>Charge/Discharge Current (A) - Nominal</td>\n<td colspan=\"3\" style=\"text-align: center;\">168</td>\n</tr>\n<tr>\n<td>Charge/Discharge Current (A) - Max.</td>\n<td colspan=\"3\" style=\"text-align: center;\">168</td>\n</tr>\n<tr>\n<td>Ingress Protection</td>\n<td colspan=\"3\" style=\"text-align: center;\">IP20</td>\n</tr>\n<tr>\n<td>Operating Temperature (&#8451;)</td>\n<td colspan=\"3\" style=\"text-align: center;\">Charge: 0 &#126; 55 / Discharge: -20 &#126; 55</td>\n</tr>\n<tr>\n<td>Storage Temperature (&#8451;)</td>\n<td colspan=\"3\" style=\"text-align: center;\">0 &#126; 35</td>\n</tr>\n<tr>\n<td>System Energy per Cluster (kWh)</td>\n<td colspan=\"3\" style=\"text-align: center;\">215</td>\n</tr>\n<tr>\n<td>System Dimensions (W &#215; H &#215; D, mm)</td>\n<td colspan=\"3\" style=\"text-align: center;\">788.6 &#215; 526 &#215; 167.2</td>\n</tr>\n<tr>\n<td>System Weight (approx., kg)</td>\n<td colspan=\"3\" style=\"text-align: center;\">32</td>\n</tr>\n<tr>\n<td>Cycle Life</td>\n<td colspan=\"3\" style=\"text-align: center;\">&#8805;6000 (25&#177;2&#8451;, 0.5C/0.5C, EOL 70%)</td>\n</tr>\n<tr>\n<td>Communication Interfaces</td>\n<td colspan=\"3\" style=\"text-align: center;\">TCP / RS485 / CAN</td>\n</tr>\n<tr>\n<td>Certification</td>\n<td colspan=\"3\" style=\"text-align: center;\">CE / IEC62619 / IEC62040 / UN38.3</td>\n</tr>\n</tbody>\n</table>', 2, 'BOS-B-Pack (EU) [14.30kWh] High-Performance Commercial Battery Storage Module | ESS', '<p><span>The&#160;BOS-B Battery&#160;from Deye is a high-performance&#160;lithium ion solar battery&#160;solution designed for commercial and industrial (C&amp;I) applications. Engineered for exceptional scalability and efficiency, this advanced&#160;lithium ion solar battery&#160;system is an ideal choice for businesses seeking reliable and robust energy management.</span></p>\n<h3 id=\"key-features-\">Key Features:</h3>\n<ul>\n<li><strong>Powerful &amp; Scalable&#160;Lithium Ion Solar Battery:</strong>&#160;Delivers&#160;215 kWh per cluster, scalable up to&#160;16 packs per PCS.</li>\n<li><strong>High Efficiency:&#160;</strong>Complements&#160;98.5% PCS&#160;and over&#160;99% MPPT efficiency.</li>\n<li><strong>Intelligent Control:</strong>&#160;Integrated EMS in this&#160;lithium ion solar battery&#160;enables zero-export, time-of-use functions, and easy remote/local management.</li>\n<li><strong>Fast &amp; Reliable Switching:&#160;</strong>Sub-<span>10ms</span>&#160;transitions (on-grid, off-grid, diesel) with robust&#160;500kW/625kW&#160;independent power paths.</li>\n<li><strong>Advanced Energy Storage:&#160;</strong>Provides up to&#160;32 hours backup; smart BMS enhances the lifespan of this&#160;lithium ion solar battery, a key benefit for&#160;lithium solar batteries.</li>\n<li><strong>Rugged &amp; Reliable:&#160;</strong><span>IP65-rated</span>&#160;PCS/MPPT; supports 110% overload and 170% peak power.</li>\n<li><strong>Efficient PV Integration:&#160;</strong>Wide MPPT range (180-850V),&#160;200 kW PV input,&#160;8 MPPT channels (40A each) for optimal&#160;charging.<br /><br /></li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-017.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<p>Deye BOS-B Battery System, a premier&#160;lithium ion solar battery, is ideally suited for a range of C&amp;I applications, providing reliable energy storage, seamless power transition, and smart energy management. BOS-B Battery System&#160;from Deye stands out with its high-performance as a&#160;lithium ion solar battery, exceptional scalability, and intelligent control features, making it a robust choice for efficient and reliable energy management in commercial and industrial settings.</p>', '<ul>\n<li><strong>Powerful Capacity:</strong>&#160;Delivers 215 kWh per cluster, expandable with up to 16 packs per PCS</li>\n<li><strong>High Efficiency:</strong>&#160;98.5% PCS efficiency and over 99% MPPT efficiency</li>\n<li><strong>Integrated EMS:</strong>&#160;Zero-export and time-of-use charging/discharging</li>\n<li><strong>User-Friendly Management:</strong>&#160;Color touchscreen for local/remote adjustments</li>\n<li><strong>Seamless Switching:</strong>&#160;STS module switches modes in &lt;10ms</li>\n<li><strong>Extended Backup:</strong>&#160;Up to 32 hours with 16 racks per PCS</li>\n<li><strong>Smart Balancing:</strong>&#160;Independent BMS for optimal charge distribution</li>\n<li><strong>Rugged Design:</strong>&#160;IP65 protection and 110% overload support</li>\n<li><strong>Efficient PV Integration:</strong>&#160;200 kW PV input with an 180-850V MPPT range</li>\n<li><span><strong>Suitable Deye Inverter Model:</strong></span>\n<ul>\n<li><span>SUN-100K-PCSL01HP3-AU</span></li>\n</ul>\n</li>\n</ul>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(573, '<table border=\"0\" cellpadding=\"6\" cellspacing=\"0\" style=\"width: 100%; border-collapse: collapse; font-family: Arial, sans-serif; font-size: 14px;\">\n<tbody>\n<tr>\n<td style=\"width: 30%;\">Battery Type</td>\n<td>LiFePO<sub>4</sub> (LFP)</td>\n</tr>\n<tr>\n<td>Nominal Voltage</td>\n<td>51.2 Vdc</td>\n</tr>\n<tr>\n<td>Rated Capacity</td>\n<td>100 Ah</td>\n</tr>\n<tr>\n<td>Rated Energy</td>\n<td>5.12 kWh</td>\n</tr>\n<tr>\n<td>Nominal Charge/Discharge Current</td>\n<td>100 A</td>\n</tr>\n<tr>\n<td>Peak Discharge Current</td>\n<td>120 A</td>\n</tr>\n<tr>\n<td>Charge Temperature</td>\n<td>0 &#126; 55&#176;C</td>\n</tr>\n<tr>\n<td>Discharge Temperature</td>\n<td>-20&#176;C &#126; 55&#176;C</td>\n</tr>\n<tr>\n<td>Storage Temperature</td>\n<td>0&#176;C &#126; 35&#176;C</td>\n</tr>\n<tr>\n<td>Ingress Protection</td>\n<td>IP20</td>\n</tr>\n<tr>\n<td>Dimension (W&#215;D&#215;H)</td>\n<td>440 &#215; 585 &#215; 133 mm</td>\n</tr>\n<tr>\n<td>Weight Approximate</td>\n<td>46 kg</td>\n</tr>\n</tbody>\n</table>', 2, 'BOS-G-Pack Pro (EU) [5.10kWh] High-Performance Commercial Battery Storage Module | ESS', '<p><span>Introducing the Deye BOS-G Pro, a cutting-edge small-scale Commercial and Industrial Energy Storage System (ESS) designed for efficient energy management and sustainability. With its advanced features and robust design, the BOS-G Pro is ideal for various applications, providing reliable power storage and management solutions.</span></p>\n<h3 id=\"key-features-\">Key Features:</h3>\n<ul>\n<li><strong>Convenient Installation:</strong> The Deye BOS-G Pro comes with a 19-inch embedded design, ensuring quick and easy installation and maintenance, making it suitable for various setups.</li>\n<li><strong>Safety and Reliability:</strong> Utilizing LiFePO4 (Lithium Iron Phosphate) cathode materials, this module offers enhanced safety performance and a long cycle life. It features minimal self-discharge rates, lasting up to six months without charging, and is free from memory effects, ensuring excellent shallow charge and discharge performance.</li>\n<li><strong>Intelligent Battery Management System (BMS):</strong> The integrated BMS provides comprehensive protection functions against over-discharge, over-charge, over-current, and extreme temperature conditions. It automatically manages the charge and discharge states while balancing the current and voltage across each cell for optimal performance.</li>\n<li><strong>Eco-Friendly Design:</strong> The entire module is non-toxic, non-polluting, and environmentally friendly, aligning with modern sustainability goals.</li>\n<li><strong>Flexible Configuration:</strong> The system supports multiple battery modules in parallel, allowing for capacity and power expansion. It also features USB and remote upgrade capabilities, ensuring compatibility with Deye inverters.</li>\n<li><strong>Wide Operating Temperature Range:</strong> The BOS-G Pro operates efficiently in a temperature range from -20&#176;C to 55&#176;C, providing excellent discharge performance and cycle life under varying environmental conditions.<br /><br /></li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-018.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<p><span>The Deye BOS-G Pro is designed for a wide range of applications, including commercial energy storage, renewable energy integration, and backup power solutions. It supports up to 16 racks of batteries in parallel and can operate with up to 10 inverters in AC parallel operation, making it a versatile choice for energy management.</span></p>', '<ul>\n<li><strong>Quick Installation</strong>: 19-inch embedded for easy setup</li>\n<li><strong>Safe &amp; Reliable</strong>: LiFePO4 for enhanced safety and long cycle life</li>\n<li><strong>Intelligent BMS</strong>: Automatic management of charge/discharge states</li>\n<li><strong>Eco-Friendly</strong>: Non-toxic and non-polluting materials</li>\n<li><strong>Flexible Configuration</strong>: Supports multiple battery modules in parallel</li>\n<li><strong>Wide Operating Range</strong>: Functions effectively between -20&#176;C to 55&#176;C</li>\n<li><strong>Long Cycle Life</strong>: Over 6000 cycles at 25&#176;C with up to 90% DoD</li>\n<li><strong>10-Year Warranty</strong>: Long-term reliability and performance</li>\n<li><span><strong>Suitable Deye Inverter Model:</strong></span>\n<ul>\n<li><span>SUN-30K-SG01HP3-EU-BM3</span></li>\n<li><span>SUN-40K/50K-SG01HP3-EU-BM4</span></li>\n<li><span>SUN-60K-SG02HP3-EU-EM4</span></li>\n<li><span>SUN-80K-SG02HP3-EU-EM6</span></li>\n<li><span>SUN-100K-PCSL01HP3-AU</span></li>\n</ul>\n</li>\n</ul>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(574, '<table border=\"0\" cellpadding=\"6\" cellspacing=\"0\" style=\"width: 100%; border-collapse: collapse; font-family: Arial, sans-serif; font-size: 14px;\">\n<tbody>\n<tr>\n<td>Model</td>\n<td>BOS-A-PDU-2</td>\n</tr>\n<tr>\n<td style=\"width: 30%;\">DC Input Voltage</td>\n<td>200 &#8211; 1000 V DC</td>\n</tr>\n<tr>\n<td>Max. DC Charge/Discharge Current</td>\n<td>160 A</td>\n</tr>\n<tr>\n<td>Internal Operating Voltage</td>\n<td>12 V DC (&#177;2%) at 4.15 A</td>\n</tr>\n<tr>\n<td>Operating Temperature Range</td>\n<td>-20&#176;C to +65&#176;C</td>\n</tr>\n<tr>\n<td>Ingress Protection Rating</td>\n<td>IP20</td>\n</tr>\n<tr>\n<td>Dimensions (W &#215; H &#215; D)</td>\n<td>632 &#215; 572 &#215; 142.2 mm</td>\n</tr>\n<tr>\n<td>Weight</td>\n<td>21 kg</td>\n</tr>\n</tbody>\n</table>', 2, 'BOS-A-PDU-2 High-Performance Power Distribution Unit (PDU) | ESS', '<p data-start=\"124\" data-end=\"334\">The <strong data-start=\"128\" data-end=\"147\">Deye BOS-A-PDU-2</strong> is an intelligent Power Distribution Unit (PDU) that provides centralized control, monitoring, and protection functions for Deye high-voltage battery storage systems of the BOS-A series.&#160;As an integral part of the high-voltage storage system, the BOS-A-PDU2 optimizes the operation of connected battery modules, ensures their safety, and enables efficient energy management. It acts as a communication interface and control unit for the entire battery network.</p>\n<h3 id=\"key-features-\">Key Features:</h3>\n<ul>\n<li data-start=\"656\" data-end=\"897\">\n<p data-start=\"658\" data-end=\"897\"><strong data-start=\"658\" data-end=\"697\">Centralized Control and Monitoring:</strong><br data-start=\"697\" data-end=\"700\" /> The PDU enables comprehensive monitoring of voltage, current, temperature, and the status of all connected battery modules. This ensures optimal operation and early detection of potential issues.</p>\n</li>\n<li data-start=\"899\" data-end=\"1089\">\n<p data-start=\"901\" data-end=\"1089\"><strong data-start=\"901\" data-end=\"936\">Intelligent Battery Management:</strong><br data-start=\"936\" data-end=\"939\" /> Integrated algorithms ensure efficient charging and discharging of the battery modules, maximizing their lifespan and optimizing system performance.</p>\n</li>\n<li data-start=\"1091\" data-end=\"1323\">\n<p data-start=\"1093\" data-end=\"1323\"><strong data-start=\"1093\" data-end=\"1132\">Comprehensive Protection Functions:</strong><br data-start=\"1132\" data-end=\"1135\" /> The BOS-A-PDU-2 offers multi-level protection mechanisms against overcharge, deep discharge, overcurrent, short circuit, and overheating to ensure the safety of the entire battery system.</p>\n</li>\n<li data-start=\"1325\" data-end=\"1538\">\n<p data-start=\"1327\" data-end=\"1538\"><strong data-start=\"1327\" data-end=\"1352\">Seamless Integration:</strong><br data-start=\"1352\" data-end=\"1355\" /> Specifically developed for Deye BOS-A high-voltage battery modules, the PDU guarantees smooth communication and compatibility with the battery modules and associated Deye inverters.</p>\n</li>\n<li data-start=\"1540\" data-end=\"1775\">\n<p data-start=\"1542\" data-end=\"1775\"><strong data-start=\"1542\" data-end=\"1574\">Supports Parallel Operation:</strong><br data-start=\"1574\" data-end=\"1577\" /> The PDU is essential for the parallel operation of multiple Deye BOS-A battery modules, enabling flexible scaling of storage capacity and ensuring balanced operation of parallel-connected modules.</p>\n</li>\n<li data-start=\"1777\" data-end=\"1950\">\n<p data-start=\"1779\" data-end=\"1950\"><strong data-start=\"1779\" data-end=\"1808\">Communication Interfaces:</strong><br data-start=\"1808\" data-end=\"1811\" /> The PDU provides the necessary communication interfaces for connection to Deye inverters and, if needed, higher-level management systems.</p>\n</li>\n<li data-start=\"1952\" data-end=\"2111\">\n<p data-start=\"1954\" data-end=\"2111\"><strong data-start=\"1954\" data-end=\"1994\">Easy Installation and Configuration:</strong><br data-start=\"1994\" data-end=\"1997\" /> The PDU&#8217;s design allows for straightforward installation and configuration of the entire battery storage system.<br /><br /></p>\n</li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-016.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>', 'The Deye BOS-A-PDU-2 is an advanced Power Distribution Unit designed specifically for Deye high-voltage (HV) battery systems. It serves as the central control and communication hub, ensuring safe, efficient, and intelligent operation of all connected battery modules. With real-time monitoring, optimized charging and discharging algorithms, and robust multi-level protection, the BOS-A-PDU2 enables seamless system integration and scalable energy storage. Ideal for demanding energy applications, it supports parallel module configurations and smooth communication with Deye inverters.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', '');
INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(575, '<table border=\"0\" cellspacing=\"0\" cellpadding=\"8\" style=\"width: 100%;\">\n<tbody>\n<tr>\n<td style=\"width: 30%;\">Model</td>\n<td>BOS-B-PDU-2</td>\n</tr>\n<tr>\n<td>Battery Type</td>\n<td>High Voltage</td>\n</tr>\n<tr>\n<td>Life Cycle</td>\n<td>6000 cycles</td>\n</tr>\n<tr>\n<td>Operating Voltage Range</td>\n<td>200&#8211;1000 V</td>\n</tr>\n<tr>\n<td>Discharge Cutoff Voltage</td>\n<td>200 V</td>\n</tr>\n<tr>\n<td>Max Charging Current</td>\n<td>175 A</td>\n</tr>\n<tr>\n<td>Recommended Discharge Current</td>\n<td>140 A</td>\n</tr>\n<tr>\n<td>Max Discharge Cutoff Current</td>\n<td>175 A</td>\n</tr>\n<tr>\n<td>Terminal Type</td>\n<td>Proprietary</td>\n</tr>\n<tr>\n<td>Cooling Method</td>\n<td>Active</td>\n</tr>\n<tr>\n<td>Recommended Charging Temp.</td>\n<td>0&#176;C to +55&#176;C</td>\n</tr>\n<tr>\n<td>Recommended Discharging Temp.</td>\n<td>-20&#176;C to +55&#176;C</td>\n</tr>\n<tr>\n<td>Recommended Storage Temp.</td>\n<td>0&#176;C to +35&#176;C</td>\n</tr>\n<tr>\n<td>Enclosure Material</td>\n<td>Metal</td>\n</tr>\n<tr>\n<td>Dimensions (mm)</td>\n<td>797 &#215; 526 &#215; 275</td>\n</tr>\n<tr>\n<td>Weight (kg)</td>\n<td>20</td>\n</tr>\n<tr>\n<td>Warranty</td>\n<td>10 Years</td>\n</tr>\n<tr>\n<td>Package Contents</td>\n<td>Control module, 4 lower covers, 3 upper covers, 16 cover feet,<br /> 1 communication cable, 1x 180mm negative power cord,<br /> 1 auxiliary power supply cable, 1 positive power cord,<br /> 1 emergency shutdown interface, 1 PCS positive cable,<br /> 1 PCS negative cable, 3x 1000mm inter-rack power cables,<br /> 1 inverter communication cable, 3x 1000mm inter-rack comm. cables,<br /> 1 optional Wi-Fi antenna, 4 grounding cables,<br /> 1 terminal resistor 120&#937;, PCS terminal connectors,<br /> 16 mounting screws</td>\n</tr>\n</tbody>\n</table>', 2, 'BOS-B-PDU-2 High-Performance Power Distribution Unit (PDU) | ESS', '<p data-start=\"252\" data-end=\"599\">The <strong data-start=\"256\" data-end=\"276\">Deye BOS-B-PDU-2</strong> is a cutting-edge Battery Management System (BMS) designed for high-voltage energy storage applications. It serves as the control hub for Deye\'s BOS-B series, offering advanced monitoring, safety, and integration features to ensure reliable and efficient energy storage system performance, even under demanding conditions.&#160;With its extended voltage range of 200&#8211;1000 V and high discharge threshold of up to 175 A, this BMS is tailored for large-scale installations. Engineered with active cooling and durable metal housing, the BOS-B-PDU-2 delivers both power and protection. Its smart connectivity options&#8212;including USB, Bluetooth, Ethernet, and COMM1&#8211;COMM3 channels&#8212;make integration seamless. This makes it the ideal choice for professionals requiring robust and scalable battery control.</p>\n<h3 id=\"key-features-\">Key Features:</h3>\n<ul>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"1098\" data-end=\"1273\"><strong data-start=\"1098\" data-end=\"1140\">Wide Voltage and High Current Capacity</strong><br data-start=\"1140\" data-end=\"1143\" /> Operates within a range of 200&#8211;1000 V and supports up to 175 A charge/discharge currents&#8212;perfect for large, high-demand systems.</p>\n</li>\n<li data-start=\"1275\" data-end=\"1441\">\n<p data-start=\"1277\" data-end=\"1441\"><strong data-start=\"1277\" data-end=\"1307\">Advanced Safety Mechanisms</strong><br data-start=\"1307\" data-end=\"1310\" /> Active cooling and high cutoff current (175 A) provide solid protection against overcurrent, overheating, and system instability.</p>\n</li>\n<li data-start=\"1443\" data-end=\"1561\">\n<p data-start=\"1445\" data-end=\"1561\"><strong data-start=\"1445\" data-end=\"1466\">Long Battery Life</strong><br data-start=\"1466\" data-end=\"1469\" /> Supports up to 6000 charge cycles, ensuring long-term reliability and minimal maintenance.</p>\n</li>\n<li data-start=\"1563\" data-end=\"1689\">\n<p data-start=\"1565\" data-end=\"1689\"><strong data-start=\"1565\" data-end=\"1589\">Durable Construction</strong><br data-start=\"1589\" data-end=\"1592\" /> Housed in a sturdy metal enclosure, designed for tough environments and consistent performance.</p>\n</li>\n<li data-start=\"1691\" data-end=\"1848\">\n<p data-start=\"1693\" data-end=\"1848\"><strong data-start=\"1693\" data-end=\"1733\">Comprehensive Monitoring and Control</strong><br data-start=\"1733\" data-end=\"1736\" /> Built-in display, LED status indicators, and intelligent internal diagnostics for easy system status tracking.</p>\n</li>\n<li data-start=\"1850\" data-end=\"2012\">\n<p data-start=\"1852\" data-end=\"2012\"><strong data-start=\"1852\" data-end=\"1890\">Versatile Communication Interfaces</strong><br data-start=\"1890\" data-end=\"1893\" /> USB, Bluetooth, Ethernet, and three COMM channels offer excellent system integration and remote management potential.</p>\n</li>\n<li data-start=\"2014\" data-end=\"2170\">\n<p data-start=\"2016\" data-end=\"2170\"><strong data-start=\"2016\" data-end=\"2045\">Professional-Grade Design</strong><br data-start=\"2045\" data-end=\"2048\" /> Includes proprietary terminals, logical cable management, and intuitive layout for efficient installation and operation.</p>\n</li>\n<li data-start=\"2172\" data-end=\"2317\">\n<p data-start=\"2174\" data-end=\"2317\"><strong data-start=\"2174\" data-end=\"2208\">Full Installation Kit Included</strong><br data-start=\"2208\" data-end=\"2211\" /> Comes with all essential cables, covers, screws, and communication lines&#8212;ready for immediate deployment.<br /><br /></p>\n</li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-017.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>', 'The Deye BOS-B-PDU-2 is a high-performance Battery Management System (BMS) designed for high-voltage energy storage solutions. With a wide operating range of 200&#8211;1000 V, 175 A max current, and advanced safety features including active cooling and smart monitoring, it ensures efficient, stable, and secure system control. Ideal for large-scale installations and professional applications.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(576, '<div>\n<table border=\"0\" cellpadding=\"8\" style=\"width: 100%;\">\n<tbody>\n<tr><th style=\"width: 30%; text-align: left;\">Model</th>\n<td style=\"text-align: left;\">SUN-STS500L</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Switching Capacity</th>\n<td>500 kW (standard) / 650 kW (peak)</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Switching Time</th>\n<td>&lt; 10 ms</td>\n</tr>\n<tr style=\"text-align: left;\"><th>AC Ports</th>\n<td>GEN, Load, Grid, STS AC Parallel</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Protection</th>\n<td>Overcurrent, Overvoltage, Short-circuit, Earth-fault, Islanding</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Cooling</th>\n<td>Intelligent air cooling</td>\n</tr>\n<tr style=\"text-align: left;\"><th>IP Rating</th>\n<td>IP20</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Operating Temperature</th>\n<td>-25&#176;C to +60&#176;C</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Humidity</th>\n<td>0&#8211;95%</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Altitude</th>\n<td>&#8804; 4000 m</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Dimensions (W&#215;H&#215;D)</th>\n<td>543 &#215; 575 &#215; 866 mm</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Weight</th>\n<td>Not specified</td>\n</tr>\n</tbody>\n</table>\n</div>', 2, 'BOS-B | SUN-STS500L Static Transfer Switch (STS) Module | ESS', '<p data-start=\"252\" data-end=\"599\">The SUN-STS500L is a high-performance Static Transfer Switch (STS) designed for Deye energy storage systems. It ensures fast and reliable switching between grid, diesel generator, and load in under 10 milliseconds, offering seamless operation for hybrid energy systems. As a key component of the system architecture, the STS Module guarantees power continuity, protects against grid disturbances, and supports stable energy transition.</p>\n<h3 id=\"key-features-\">Key Features:</h3>\n<ul>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"638\" data-end=\"775\"><strong data-start=\"638\" data-end=\"667\">Ultra-Fast Transfer Time:</strong><br data-start=\"667\" data-end=\"670\" /> Switches between power sources in less than 10&#8239;ms, ensuring uninterrupted power supply to critical loads.</p>\n<p data-start=\"777\" data-end=\"915\"><strong data-start=\"777\" data-end=\"801\">High Power Capacity:</strong><br data-start=\"801\" data-end=\"804\" /> Supports up to 500&#8239;kW (650&#8239;kW peak), with independent full-capacity paths for grid, diesel generator, and load.</p>\n<p data-start=\"917\" data-end=\"1098\"><strong data-start=\"917\" data-end=\"951\">Integrated Protection Systems:</strong><br data-start=\"951\" data-end=\"954\" /> Provides overcurrent, overvoltage, short-circuit, earth-fault detection, insulation monitoring, and surge protection according to IEC standards.</p>\n<p data-start=\"1100\" data-end=\"1249\"><strong data-start=\"1100\" data-end=\"1130\">Advanced Safety Functions:</strong><br data-start=\"1130\" data-end=\"1133\" /> Built-in arc-fault circuit interrupter (optional), islanding protection, DC polarity and residual current detection.</p>\n<p data-start=\"1251\" data-end=\"1378\"><strong data-start=\"1251\" data-end=\"1283\">Scalable Parallel Operation:</strong><br data-start=\"1283\" data-end=\"1286\" /> Allows multiple STS units to be used in parallel, expanding system flexibility and capacity.</p>\n<p data-start=\"1380\" data-end=\"1519\"><strong data-start=\"1380\" data-end=\"1398\">Rugged Design:</strong><br data-start=\"1398\" data-end=\"1401\" /> Reliable performance under harsh conditions: wide temperature range, high humidity tolerance, and intelligent cooling.</p>\n<p data-start=\"1521\" data-end=\"1661\"><strong data-start=\"1521\" data-end=\"1542\">Easy Integration:</strong><br data-start=\"1542\" data-end=\"1545\" /> Ideal for use with Deye&#8217;s PCS and battery systems, offering direct interface for seamless communication and control.<br /><br /></p>\n</li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-017.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>', 'The SUN-STS500L is a high-performance Static Transfer Switch designed for seamless energy transitions in Deye hybrid storage systems. With ultra-fast switching under 10&#8239;ms and a robust 500&#8239;kW capacity, it ensures uninterrupted power, advanced protection, and reliable performance&#8212;even under demanding conditions. Ideal for grid-diesel hybrid setups requiring maximum continuity and safety.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(577, '<table border=\"0\" cellpadding=\"8\" style=\"width: 100%;\">\n<tbody>\n<tr><th style=\"width: 30%;\">\n<div style=\"text-align: left;\">Model</div>\n</th>\n<td style=\"text-align: left;\">\n<div>SUN-MPPT-L01-EU-AM8</div>\n</td>\n</tr>\n<tr style=\"text-align: left;\"><th>\n<div>Max PV Power</div>\n</th>\n<td>\n<div>200 kW</div>\n</td>\n</tr>\n<tr style=\"text-align: left;\"><th>\n<div>MPPT Channels</div>\n</th>\n<td>\n<div>8 (2 inputs per channel)</div>\n</td>\n</tr>\n<tr style=\"text-align: left;\"><th>\n<div>MPPT Voltage Range</div>\n</th>\n<td>\n<div>180&#8211;850 V (Full-load 450&#8211;850 V)</div>\n</td>\n</tr>\n<tr style=\"text-align: left;\"><th>\n<div>Max PV Voltage</div>\n</th>\n<td>\n<div>1000 V</div>\n</td>\n</tr>\n<tr style=\"text-align: left;\"><th>\n<div>Max Input Current per MPPT</div>\n</th>\n<td>\n<div>40 A</div>\n</td>\n</tr>\n<tr style=\"text-align: left;\"><th>\n<div>Efficiency</div>\n</th>\n<td>\n<div>&gt;99% peak, &gt;99.9% MPPT</div>\n</td>\n</tr>\n<tr style=\"text-align: left;\"><th>\n<div>Protection</div>\n</th>\n<td>\n<div>Surge, reverse polarity, insulation resistance monitoring</div>\n</td>\n</tr>\n<tr style=\"text-align: left;\"><th>\n<div>IP Rating</div>\n</th>\n<td>\n<div>IP65</div>\n</td>\n</tr>\n<tr><th style=\"text-align: left;\">\n<div>Dimensions (W&#215;H&#215;D)</div>\n</th>\n<td>\n<div style=\"text-align: left;\">543 &#215; 197.8 &#215; 700 mm</div>\n</td>\n</tr>\n</tbody>\n</table>', 2, 'BOS-B | SUN-MPPT-L01-EU-AM8 Maximum Power Point Tracking (MPPT) Module | ESS', '<p data-start=\"252\" data-end=\"599\">The SUN-MPPT-L01-EU-AM8 is an advanced MPPT (Maximum Power Point Tracking) module engineered for use in Deye&#8217;s commercial and industrial energy storage solutions. It enables efficient solar energy harvesting through multi-channel MPPT optimization, ensuring maximum energy yield under dynamic environmental conditions.</p>\n<h3 id=\"key-features-\">Key Features:</h3>\n<ul>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"2849\" data-end=\"2972\"><strong data-start=\"2849\" data-end=\"2870\">High PV Capacity:</strong><br data-start=\"2870\" data-end=\"2873\" /> Supports up to 200&#8239;kW of solar PV input with 8 independent MPPT channels, each handling up to 40&#8239;A.</p>\n</li>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"2849\" data-end=\"2972\"><strong data-start=\"2974\" data-end=\"2994\">Wide MPPT Range:<br /></strong>Provides a broad tracking range of 180&#8239;V to 850&#8239;V, ensuring compatibility with various PV array configurations.</p>\n</li>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"2849\" data-end=\"2972\"><strong data-start=\"3110\" data-end=\"3130\">High Efficiency:<br /></strong>Delivers peak conversion efficiency above 99% with MPPT accuracy over 99.9%, ensuring minimal energy loss.</p>\n</li>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"2849\" data-end=\"2972\"><strong data-start=\"3241\" data-end=\"3269\">Multiple Input Channels:<br /></strong>Each MPPT channel includes 2 inputs (16 in total), enabling flexible PV string design and simplified layout.</p>\n</li>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"2849\" data-end=\"2972\"><strong data-start=\"3382\" data-end=\"3407\">Built-in Protections:<br /></strong>Includes surge protection, DC reverse polarity protection, and insulation resistance monitoring.</p>\n</li>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"2849\" data-end=\"2972\"><strong data-start=\"3508\" data-end=\"3532\">Rugged Construction:<br /></strong>IP65-rated enclosure protects against dust and water ingress, ideal for indoor and sheltered outdoor use.</p>\n</li>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"2849\" data-end=\"2972\"><strong data-start=\"3642\" data-end=\"3667\">Ease of Installation:<br /></strong>Compact design allows for quick and straightforward integration into PV and battery systems.</p>\n<p data-start=\"1521\" data-end=\"1661\"></p>\n</li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-017.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>', 'The SUN-MPPT-L01-EU-AM8 is a high-efficiency MPPT module tailored for Deye\'s commercial and industrial solar storage systems. Featuring 8 independent MPPT channels and a total PV input capacity of up to 200&#8239;kW, it maximizes solar energy harvest under varying conditions. With advanced protection, precision tracking, and a rugged IP65 design, it ensures reliable and optimized PV performance in any setup.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(578, '<div>\n<table border=\"0\" cellpadding=\"8\" style=\"width: 100%;\">\n<tbody>\n<tr><th style=\"text-align: left;\">Model</th>\n<td style=\"text-align: left;\">SUN-100K/125K-PCSL01HP3</td>\n</tr>\n<tr style=\"text-align: left;\"><th style=\"width: 30%;\">Nominal Power</th>\n<td>100 kW / 125 kW</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Max Units in Parallel</th>\n<td>Up to 20 units (2.5 MW total)</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Max Charge/Discharge Current</th>\n<td>220 A</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Efficiency</th>\n<td>98.5% peak, 97.8% Euro</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Grid Frequency</th>\n<td>45&#8211;65 Hz</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Power Factor</th>\n<td>Adjustable from &#8211;1 to 1</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Harmonic Distortion</th>\n<td>&lt;3% THDi</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Interfaces</th>\n<td>LCD, LED, RS485, CAN, Meter, Wi-Fi</td>\n</tr>\n<tr style=\"text-align: left;\"><th>IP Rating</th>\n<td>IP65</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Dimensions (W&#215;H&#215;D)</th>\n<td>543 &#215; 310 &#215; 775 mm</td>\n</tr>\n</tbody>\n</table>\n</div>', 2, 'BOS-B | SUN-100K/125K-PCSL01HP3 Power Conversion System (PCS) Module | ESS', '<p data-start=\"252\" data-end=\"599\">The Deye SUN-PCS (<span>Power Conversion System)&#160;</span>Module (available in 100&#8239;kW and 125&#8239;kW variants) is a core component of Deye\'s Power Conversion System. It enables bidirectional power conversion between DC batteries and the AC grid, supporting advanced energy management strategies in commercial and industrial applications. The PCS module is designed to work in grid-connected and off-grid scenarios, offering high flexibility and robust performance.</p>\n<h3 id=\"key-features-\">Key Features:</h3>\n<ul>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"4958\" data-end=\"5085\"><strong data-start=\"4958\" data-end=\"4995\">High Efficiency Power Conversion:</strong><br data-start=\"4995\" data-end=\"4998\" /> Peak conversion efficiency up to 98.5%, ensuring minimal losses during energy transfer.</p>\n</li>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"4958\" data-end=\"5085\"><strong data-start=\"5087\" data-end=\"5120\">Scalable System Architecture:<br /></strong>Multiple PCS units can be connected in parallel, scaling system capacity up to 2.5&#8239;MW.</p>\n</li>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"4958\" data-end=\"5085\"><strong data-start=\"5211\" data-end=\"5241\">Advanced Grid Interaction:<br /></strong>Supports reactive power control, zero-export mode, and time-of-use strategies for optimized grid interaction.</p>\n</li>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"4958\" data-end=\"5085\"><strong data-start=\"5355\" data-end=\"5382\">High Discharge Current:<br /></strong>Up to 220&#8239;A charging/discharging, with support for 110% overload and 170% peak output for short durations.</p>\n</li>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"4958\" data-end=\"5085\"><strong data-start=\"5493\" data-end=\"5517\">Flexible Interfaces:<br /></strong>Equipped with RS485, CAN, Wi-Fi, LCD/LED display, and metering interface for seamless control and monitoring.</p>\n</li>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"4958\" data-end=\"5085\"><strong data-start=\"5631\" data-end=\"5665\">Comprehensive Safety Measures:<br /></strong>Features include DC residual current detection, arc-fault circuit interrupter (optional), insulation monitoring, and short-circuit protection.</p>\n</li>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"4958\" data-end=\"5085\"><strong data-start=\"5812\" data-end=\"5833\">Robust Enclosure:<br /></strong>IP65 protection for reliable outdoor or indoor deployment.</p>\n<p data-start=\"5812\" data-end=\"5894\"></p>\n</li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-017.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>', 'The SUN-100K/125K-PCSL01HP3 is a high-performance Power Conversion System (PCS) module from Deye, available in 100&#8239;kW and 125&#8239;kW variants. It enables efficient bidirectional energy flow between DC battery storage and the AC grid, supporting both on-grid and off-grid applications. With advanced grid features, scalable architecture up to 2.5&#8239;MW, and robust protection systems, it is an ideal choice for commercial and industrial energy storage solutions.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(579, '<table border=\"0\" cellpadding=\"8\" cellspacing=\"0\" style=\"border-collapse: collapse; width: 100%;\">\n<tbody>\n<tr>\n<td style=\"width: 30%;\"><strong>Model</strong></td>\n<td>HVB750V/100A-EU</td>\n</tr>\n<tr>\n<td>Operating Voltage</td>\n<td>120&#8211;750&#8239;V DC</td>\n</tr>\n<tr>\n<td>Nominal Charge/Discharge Current</td>\n<td>100&#8239;A</td>\n</tr>\n<tr>\n<td>Max. Charge/Discharge Current</td>\n<td>125&#8239;A</td>\n</tr>\n<tr>\n<td>DC Input Rating</td>\n<td>12&#8239;V&#8239;&#177;&#8239;2% / 4.15&#8239;A</td>\n</tr>\n<tr>\n<td>Operating Temperature Range</td>\n<td>&#8211;20&#8239;&#176;C to +65&#8239;&#176;C</td>\n</tr>\n<tr>\n<td>Ingress Protection</td>\n<td>IP20</td>\n</tr>\n<tr>\n<td>Dimensions (mm)</td>\n<td>440 &#215; 570 &#215; 150</td>\n</tr>\n<tr>\n<td>Weight</td>\n<td>15&#8239;kg</td>\n</tr>\n<tr><th colspan=\"2\" style=\"text-align: left;\">Included in Delivery</th></tr>\n<tr>\n<td colspan=\"2\">\n<ul style=\"margin: 0; padding-left: 20px;\">\n<li>120-ohm termination resistor</li>\n<li>140&#8239;mm communication cable</li>\n<li>220&#8239;mm power cable</li>\n<li>2.1&#8239;m power cable (EU version)</li>\n<li>Power plug</li>\n</ul>\n</td>\n</tr>\n</tbody>\n</table>', 2, 'BOS-G-PDU-2 High-Performance Power Distribution Unit (PDU) | ESS', '<p>The <strong data-start=\"258\" data-end=\"273\">BOS-G-PDU-2</strong> is a high-performance Power Distribution Unit designed to manage and monitor high-voltage battery storage systems with precision and safety. It supports a wide input voltage range and high current loads while ensuring system protection and seamless communication with Deye inverters. Housed in a compact, rack-mountable chassis, it is ideal for professional energy storage projects requiring long-term stability, scalability, and intelligent control.</p>\n<h3 id=\"key-features-\">Key Features:</h3>\n<ul>\n<li data-start=\"754\" data-end=\"958\">\n<p data-start=\"756\" data-end=\"958\"><strong data-start=\"756\" data-end=\"802\">Wide Voltage Range &amp; High Current Handling</strong><br data-start=\"802\" data-end=\"805\" /> Operates from <strong data-start=\"821\" data-end=\"840\">120 to 750&#8239;V DC</strong> (up to <strong data-start=\"848\" data-end=\"858\">1000&#8239;V</strong> in select configurations) with <strong data-start=\"890\" data-end=\"907\">100&#8239;A nominal</strong> and <strong data-start=\"912\" data-end=\"932\">125&#8239;A short-term</strong> charge/discharge current.</p>\n</li>\n<li data-start=\"960\" data-end=\"1168\">\n<p data-start=\"962\" data-end=\"1168\"><strong data-start=\"962\" data-end=\"1001\">Centralized Monitoring &amp; Protection</strong><br data-start=\"1001\" data-end=\"1004\" /> Tracks voltage, current, and temperature per module; integrated safety features protect against overvoltage, undervoltage, overcurrent, overtemperature, and more.</p>\n</li>\n<li data-start=\"1170\" data-end=\"1347\">\n<p data-start=\"1172\" data-end=\"1347\"><strong data-start=\"1172\" data-end=\"1203\">Seamless System Integration</strong><br data-start=\"1203\" data-end=\"1206\" /> Designed for the <strong data-start=\"1225\" data-end=\"1245\">BOS&#8209;G Pro series</strong>; communicates via <strong data-start=\"1264\" data-end=\"1285\">CAN&#8239;2.0 and RS485</strong> with full compatibility with <strong data-start=\"1315\" data-end=\"1323\">Deye</strong> energy storage systems.</p>\n</li>\n<li data-start=\"1349\" data-end=\"1466\">\n<p data-start=\"1351\" data-end=\"1466\"><strong data-start=\"1351\" data-end=\"1379\">Visual Status Indicators</strong><br data-start=\"1379\" data-end=\"1382\" /> <strong data-start=\"1384\" data-end=\"1402\">LED indicators</strong> show system states: yellow for HV power active, red for alarms.</p>\n</li>\n<li data-start=\"1468\" data-end=\"1601\">\n<p data-start=\"1470\" data-end=\"1601\"><strong data-start=\"1470\" data-end=\"1506\">Wide Operating Temperature Range</strong><br data-start=\"1506\" data-end=\"1509\" /> Ensures reliable operation from <strong data-start=\"1543\" data-end=\"1563\">&#8211;20&#8239;&#176;C to +65&#8239;&#176;C</strong>, ideal for industrial and indoor use.</p>\n</li>\n<li data-start=\"1603\" data-end=\"1773\">\n<p data-start=\"1605\" data-end=\"1773\"><strong data-start=\"1605\" data-end=\"1643\">Compact and Rack-Compatible Design</strong><br data-start=\"1643\" data-end=\"1646\" /> Measures <strong data-start=\"1657\" data-end=\"1679\">440 &#215; 570 &#215; 150 mm</strong>, weighs <strong data-start=\"1688\" data-end=\"1697\">19&#8239;kg</strong>, and fits <strong data-start=\"1708\" data-end=\"1730\">standard 19&#8221; racks</strong> for easy integration into cabinet systems.</p>\n</li>\n<li data-start=\"1775\" data-end=\"1961\">\n<p data-start=\"1777\" data-end=\"1961\"><strong data-start=\"1777\" data-end=\"1815\">Complete Installation Kit Included</strong><br data-start=\"1815\" data-end=\"1818\" /> Delivered with <strong data-start=\"1835\" data-end=\"1869\">power and communication cables</strong>, <strong data-start=\"1871\" data-end=\"1896\">termination resistors</strong>, and <strong data-start=\"1902\" data-end=\"1926\">mounting accessories</strong> for quick and secure installation.</p>\n<p data-start=\"473\" data-end=\"568\"></p>\n</li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-018.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>', 'The BOS-G-PDU-2 is a high-performance Power Distribution Unit engineered for safe, precise, and intelligent control of high-voltage battery storage systems. With wide voltage compatibility (120&#8211;750&#8239;V DC), robust 100&#8239;A nominal current handling, and seamless integration with Deye inverters, it ensures centralized monitoring, system protection, and long-term reliability. Its compact 19&#8221; rack-mountable design and complete installation kit make it ideal for scalable industrial energy storage applications.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(580, '<table border=\"0\" cellspacing=\"0\" cellpadding=\"8\" style=\"width: 100%;\">\n<tbody>\n<tr>\n<td>Model</td>\n<td>GE-F60</td>\n</tr>\n<tr>\n<td>Cell Chemistry</td>\n<td>LiFePO4</td>\n</tr>\n<tr>\n<td>Module Energy (kWh)</td>\n<td>5.12</td>\n</tr>\n<tr>\n<td>Module Nominal Voltage (V)</td>\n<td>51.2</td>\n</tr>\n<tr>\n<td>Module Capacity (Ah)</td>\n<td>100</td>\n</tr>\n<tr>\n<td>Battery Module Qty in Series</td>\n<td>12</td>\n</tr>\n<tr>\n<td>System Nominal Voltage (V)</td>\n<td>614.4</td>\n</tr>\n<tr>\n<td>System Operating Voltage (V)</td>\n<td>480 &#126; 700</td>\n</tr>\n<tr>\n<td>System Energy (kWh)</td>\n<td>61.44</td>\n</tr>\n<tr>\n<td style=\"width: 30%;\">System Usable Energy (kWh)</td>\n<td>55.29</td>\n</tr>\n<tr>\n<td>Rated DC Power</td>\n<td>61.44</td>\n</tr>\n<tr>\n<td>Recommend Charge/Discharge Current (A)</td>\n<td>50</td>\n</tr>\n<tr>\n<td>Nominal Charge/Discharge Current (A)</td>\n<td>100</td>\n</tr>\n<tr>\n<td>Peak Discharge (2 mins, 25&#176;C)</td>\n<td>125</td>\n</tr>\n<tr>\n<td>Status Indicator</td>\n<td>Yellow: Battery High Voltage Power On<br />Red: Battery System Alarm</td>\n</tr>\n<tr>\n<td>Communication Port</td>\n<td>CAN2.0 / RS485</td>\n</tr>\n<tr>\n<td>Humidity</td>\n<td>5% &#126; 85% RH</td>\n</tr>\n<tr>\n<td>Altitude</td>\n<td>&#8804; 2000 m</td>\n</tr>\n<tr>\n<td>IP Rating of Enclosure</td>\n<td>IP55</td>\n</tr>\n<tr>\n<td>Dimension (W &#215; D &#215; H, mm)</td>\n<td>783 &#215; 1059 &#215; 2235</td>\n</tr>\n<tr>\n<td>Weight Approximate (kg)</td>\n<td>10.7</td>\n</tr>\n<tr>\n<td>Installation Method</td>\n<td>Floor-Mounted</td>\n</tr>\n<tr>\n<td>Storage Temperature (&#176;C)</td>\n<td>0 &#126; 35</td>\n</tr>\n<tr>\n<td>Operating Temperature (&#176;C)</td>\n<td>-30 &#126; 60 (&#65310;45 derating)</td>\n</tr>\n<tr>\n<td>Recommended Depth of Discharge</td>\n<td>90%</td>\n</tr>\n<tr>\n<td>Cycle Life</td>\n<td>&#8805; 6000 (25&#177;2&#176;C, 0.5C / 0.5C, EOL 70%)</td>\n</tr>\n<tr>\n<td>Warranty</td>\n<td>10 years</td>\n</tr>\n<tr>\n<td>Certification</td>\n<td>UN38.3 / CB / CE / CEC / IEC 62040</td>\n</tr>\n</tbody>\n</table>', 2, 'GE-F60 (EU) [55.29 kWh] Small-Scale Commercial & Industrial (C&I) Battery Storage Module | ESS', '<p>The Deye GE-F60 is a cutting-edge small-scale Commercial &amp; Industrial Energy Storage System (ESS) designed for exceptional performance, safety, and flexibility. Powered by advanced&#160;LiFePO&#8324; (Lithium Iron Phosphate)&#160;technology, this reliable, floor-mounted energy storage solution is ideal for applications requiring efficiency, safety, and long-term durability.</p>\n<h3 id=\"key-features-\">Key Features:</h3>\n<ul style=\"list-style-type: disc;\">\n<li><strong>Total Protection</strong><br /><span></span>Combustible gas, smoke, and temperature detection for enhanced safety.<br />Integrated active exhaust and fire alarm systems.<br />Five-level extreme safety protection ensures peace of mind.<br /><br /></li>\n<li><strong>Superior Safety</strong><br /><span></span>Utilizes&#160;LiFePO&#8324; battery technology, offering high thermal stability and durability.<br />Aerosol fire suppression system for battery packs and systems guarantees robust fire safety protocols.<br /><br /></li>\n<li><strong>Integrated Technology</strong><br />Equipped with an advanced&#160;EMS, hybrid inverter, and&#160;BMS integration technology&#160;for seamless operation.<br />Supports black start functionality and off-grid operations for enhanced reliability.<br />Engineered with redundancy design for consistent power availability.<br /><br /></li>\n<li><strong>Flexible Expansion</strong><br />Scalable design supports battery expansion up to&#160;3600 kWh, perfect for growing power needs.<br />Delivers modular usability for both on-grid and off-grid applications.<br /><br /></li>\n</ul>\n<div style=\"padding-left: 30px;\"></div>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-019.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<h3 id=\"-performance-specifications-\"><span>Performance &amp; Specifications:</span></h3>\n<ul>\n<li><span>Energy Capacity</span>: Usable energy of&#160;<span>55.29 kWh</span>&#160;with total energy at&#160;<span>61.44 kWh</span>.</li>\n<li><span>Cycle Life</span>: Over&#160;<span>6000 cycles</span>&#160;at 70% End of Life (EOL), providing lasting performance.</li>\n<li><span>Power Output</span>: Rated DC power of&#160;<span>61.44 kW</span>&#160;with a nominal discharge current of&#160;<span>100 A</span>.</li>\n<li><span>Voltage Range</span>: Operates efficiently within&#160;<span>480&#8211;700 V</span>.</li>\n<li><span>IP Rating</span>:&#160;<span>IP55</span>-rated enclosure for protection against dust and water.</li>\n</ul>\n<h3 id=\"-technical-details-\"><span>Technical Details:</span></h3>\n<ul>\n<li><span>Operating Temperature</span>: -30&#176;C to 60&#176;C for versatile environments.</li>\n<li><span>Dimensions</span>: Compact size of&#160;<span>783 x 1059 x 2235 mm</span>&#160;and a weight of approximately&#160;<span>1070 kg</span>.</li>\n<li><span>Warranty</span>: Backed by a&#160;<span>10-year warranty</span>&#160;for long-term assurance.</li>\n<li><span>Certifications</span>: Certified under&#160;<span>UN38.3, CB, CE, CEC, IEC 62040</span>&#160;standards for quality and safety compliance.</li>\n</ul>\n<h3 id=\"-why-choose-ge-f60-\"><span>Why Choose GE-F60?</span></h3>\n<p>The Deye GE-F60 is tailored to meet the demands of diverse industrial and commercial energy storage needs, offering:</p>\n<ul>\n<li>Long-lasting reliability from&#160;<span>LiFePO&#8324; battery chemistry</span>.</li>\n<li>Scalable and flexible design to adapt to future energy capacity upgrades.</li>\n<li>Unmatched safety with advanced fire suppression and monitoring systems.</li>\n</ul>\n<p><span>Empower your energy storage solutions with the Deye GE-F60, combining advanced safety features, flexible scalability, and high efficiency for optimal performance.</span></p>', '<ul>\n<li><strong>High Capacity:</strong>&#160;55.29 kWh usable energy, expandable to 3600 kWh.</li>\n<li><strong>Long-Lasting:</strong>&#160;Over 6000 cycles with &#8805;70% EOL.</li>\n<li><strong>Advanced Safety:</strong>&#160;5-level protection with fire suppression.</li>\n<li><strong>Smart Tech:</strong>&#160;Integrated EMS, BMS, and hybrid inverter.</li>\n<li><strong>Durable Design:</strong>&#160;IP55-rated, -30&#176;C to 60&#176;C operation.</li>\n<li><strong>Warranty:</strong>&#160;10 years, globally certified.</li>\n<li><span><strong>Suitable Deye Inverter Model:</strong></span>\n<ul>\n<li><span>SUN-29.9/30/35K-SG01HP3-EU-BM3</span></li>\n<li><span>SUN-40/50K-SG01HP3-EU-BM4</span></li>\n</ul>\n</li>\n</ul>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', '');
INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(581, '<div>\n<table border=\"0\" cellpadding=\"8\" cellspacing=\"0\" style=\"width: 100%;\">\n<tbody><!-- System Specification -->\n<tr><th colspan=\"2\" style=\"text-align: left;\">System Specification</th></tr>\n<tr>\n<td>Model</td>\n<td>GE-F120-2H2</td>\n</tr>\n<tr>\n<td>Nominal Output Power / UPS Power (W)</td>\n<td>50,000</td>\n</tr>\n<tr>\n<td>AC Output Frequency and Voltage</td>\n<td>50/60Hz; 220/380, 230/400Vac</td>\n</tr>\n<tr>\n<td>Grid Type</td>\n<td>3L/N/PE</td>\n</tr>\n<tr>\n<td>Number of Parallel (Off-grid)</td>\n<td>10</td>\n</tr>\n<tr>\n<td>Energy Configuration (kWh)</td>\n<td>122.8</td>\n</tr>\n<tr>\n<td>Dimension (W x D x H, mm)</td>\n<td>1780 &#215; 1056 &#215; 2235</td>\n</tr>\n<tr>\n<td>Weight Approx. (kg)</td>\n<td>2090</td>\n</tr>\n<tr>\n<td>AC Output Rated Current (A)</td>\n<td>75.8</td>\n</tr>\n<tr>\n<td>Battery Operating Voltage (V)</td>\n<td>500 &#126; 700</td>\n</tr>\n<tr>\n<td>Max. RTE</td>\n<td>89%</td>\n</tr>\n<tr>\n<td>Battery Chemistry</td>\n<td>LiFePO4</td>\n</tr>\n<tr>\n<td>IP Rating of Enclosure</td>\n<td>IP55</td>\n</tr>\n<tr>\n<td>Installation Style</td>\n<td>Floor-Mounted</td>\n</tr>\n<tr>\n<td>Storage Temperature (&#176;C)</td>\n<td>-20 &#126; 45 (&#65310;45 derating)</td>\n</tr>\n<tr>\n<td>Warranty</td>\n<td>10 years</td>\n</tr>\n<!-- Inverter Technical Specification -->\n<tr><th colspan=\"2\" style=\"text-align: left;\"><br />Inverter Technical Specification</th></tr>\n<tr>\n<td>Max. PV Input Power (W)</td>\n<td>65,000</td>\n</tr>\n<tr>\n<td>Max. PV Input Current (A)</td>\n<td>36 + 36 + 36 + 36</td>\n</tr>\n<tr>\n<td>Rated PV Input Voltage (Vdc)</td>\n<td>600</td>\n</tr>\n<tr>\n<td>Start Up DC Voltage (Vdc)</td>\n<td>180</td>\n</tr>\n<tr>\n<td>MPPT Voltage Range (Vdc)</td>\n<td>150 &#126; 850</td>\n</tr>\n<tr>\n<td>Max. PV Short-circuit Current (A)</td>\n<td>55 + 55 + 55 + 55</td>\n</tr>\n<tr>\n<td>Number of MPPT</td>\n<td>4</td>\n</tr>\n<tr>\n<td>Peak Power (off-grid)</td>\n<td>1.5 times rated power, 10s</td>\n</tr>\n<tr>\n<td>Power Factor</td>\n<td>0.8 leading to 0.8 lagging</td>\n</tr>\n<tr>\n<td>THD</td>\n<td>&lt;3%</td>\n</tr>\n<tr>\n<td>DC Injection Current (mA)</td>\n<td>&lt;0.5%ln</td>\n</tr>\n<tr>\n<td>Display</td>\n<td>LCD</td>\n</tr>\n<tr>\n<td>Operating Temperature Range (&#176;C)</td>\n<td>-40 &#126; 60 (&#65310;45 derating)</td>\n</tr>\n<tr>\n<td>Relative Humidity</td>\n<td>15% &#126; 85% (No Condensing)</td>\n</tr>\n<tr>\n<td>Dimension (W x D x H, mm)</td>\n<td>527 &#215; 294 &#215; 894</td>\n</tr>\n<tr>\n<td>Communication</td>\n<td>CAN, RS485, WIFI, ETH</td>\n</tr>\n<tr>\n<td style=\"width: 30%;\">Grid Regulation</td>\n<td>VDE4105, IEC61727/62116, VDE0126, AS4777.2, CEI0 21, EN50549-1, G98, G99, C10-11, UNE217002, NBR16149/NBR16150</td>\n</tr>\n<tr>\n<td>Max. Efficiency</td>\n<td>97.6%</td>\n</tr>\n<tr>\n<td>MPPT Efficiency</td>\n<td>99.9%</td>\n</tr>\n<!-- Battery Technical Specification -->\n<tr><th colspan=\"2\" style=\"text-align: left;\"><br />Battery Technical Specification</th></tr>\n<tr>\n<td>Battery Module Nominal Voltage (V)</td>\n<td>51.2</td>\n</tr>\n<tr>\n<td>Battery Module Energy (kWh)</td>\n<td>5.12</td>\n</tr>\n<tr>\n<td>BMS Communication</td>\n<td>CAN</td>\n</tr>\n<tr>\n<td>Battery Module Dimension (W x D x H, mm)</td>\n<td>440 &#215; 570 &#215; 133</td>\n</tr>\n<tr>\n<td>Battery Module Weight (kg)</td>\n<td>44</td>\n</tr>\n<tr>\n<td>Operating Temperature Range</td>\n<td>Charge: 0 &#126; 55 / Discharge: -20 &#126; 55</td>\n</tr>\n<tr>\n<td>Cycle Life</td>\n<td>&#8805;6000 (@25&#176;C&#177;2&#176;C, 0.5C/0.5C, 70% EOL)</td>\n</tr>\n<tr>\n<td>Battery Module Certification</td>\n<td>UN38.3, IEC62619, IEC61000</td>\n</tr>\n</tbody>\n</table>\n</div>', 2, 'GE-F120-2H2 (EU) [120 kWh] High Voltage All-In-One Hybrid Battery Storage System | ESS', '<p>Discover the future of energy management with the <strong data-start=\"127\" data-end=\"147\">Deye GE-F120-2H2</strong>, a state-of-the-art hybrid energy storage system that redefines efficiency and reliability for residential, commercial, and industrial applications. The meticulously engineered GE-F120-2H2 is designed to meet high energy demands while offering seamless integration and advanced performance features.<br /><br /></p>\n<h3 data-start=\"449\" data-end=\"466\">Key Features:</h3>\n<ul data-start=\"468\" data-end=\"1984\">\n<li data-start=\"468\" data-end=\"702\">\n<p data-start=\"470\" data-end=\"702\"><strong data-start=\"470\" data-end=\"496\">Impressive Rated Power</strong>:<br data-start=\"497\" data-end=\"500\" /> With a robust rated output of <strong data-start=\"532\" data-end=\"541\">50&#8239;kW</strong>, the GE-F120-2H2 can effortlessly power everything from household appliances to large industrial machinery, making it the ideal choice for diverse energy needs.</p>\n</li>\n<li data-start=\"704\" data-end=\"883\">\n<p data-start=\"706\" data-end=\"883\"><strong data-start=\"706\" data-end=\"735\">Generous Storage Capacity</strong>:<br data-start=\"736\" data-end=\"739\" /> Boasting an impressive <strong data-start=\"764\" data-end=\"775\">120&#8239;kWh</strong> of storage capacity, this system ensures you have ample energy to handle even the most demanding scenarios.</p>\n</li>\n<li data-start=\"885\" data-end=\"1160\">\n<p data-start=\"887\" data-end=\"1160\"><strong data-start=\"887\" data-end=\"924\">High-Rate Charge/Discharge Cycles</strong>:<br data-start=\"925\" data-end=\"928\" /> Designed for high-performance applications, the GE-F120-2H2 supports rapid energy cycling, enabling swift transitions between charging and discharging. This is especially beneficial in environments with fluctuating energy demands.</p>\n</li>\n<li data-start=\"1162\" data-end=\"1373\">\n<p data-start=\"1164\" data-end=\"1373\"><strong data-start=\"1164\" data-end=\"1197\">Redundant Power Supply Design</strong>:<br data-start=\"1198\" data-end=\"1201\" /> Enjoy uninterrupted power with an innovative power redundancy feature that ensures reliable energy delivery during critical operations, even under challenging conditions.</p>\n</li>\n<li data-start=\"1375\" data-end=\"1581\">\n<p data-start=\"1377\" data-end=\"1581\"><strong data-start=\"1377\" data-end=\"1403\">Black Start Capability</strong>:<br data-start=\"1404\" data-end=\"1407\" /> Thanks to its black start function, the system can reboot independently without relying on external power sources&#8212;greatly enhancing reliability and operational flexibility.</p>\n</li>\n<li data-start=\"1583\" data-end=\"1806\">\n<p data-start=\"1585\" data-end=\"1806\"><strong data-start=\"1585\" data-end=\"1645\">Advanced Lithium Iron Phosphate (LFP) Battery Technology</strong>:<br data-start=\"1646\" data-end=\"1649\" /> Using high-quality LFP batteries, the system offers exceptional safety, long lifespan, and thermal stability, ensuring top-tier performance and durability.</p>\n</li>\n<li data-start=\"1808\" data-end=\"1984\">\n<p data-start=\"1810\" data-end=\"1984\"><strong data-start=\"1810\" data-end=\"1840\">Expandable Energy Capacity</strong>:<br data-start=\"1841\" data-end=\"1844\" /> Future-proof your energy system with the ability to scale battery capacity up to <strong data-start=\"1927\" data-end=\"1938\">120&#8239;kWh</strong>, adapting over time to evolving energy needs.<br /><br /></p>\n</li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-020.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<h3 id=\"-performance-specifications-\"><span>Performance &amp; Specifications:</span></h3>\n<ul>\n<li data-start=\"2007\" data-end=\"2033\">\n<p data-start=\"2009\" data-end=\"2033\"><strong data-start=\"2009\" data-end=\"2018\">Model</strong>: GE-F120-2H2</p>\n</li>\n<li data-start=\"2034\" data-end=\"2076\">\n<p data-start=\"2036\" data-end=\"2076\"><strong data-start=\"2036\" data-end=\"2048\">Category</strong>: High Voltage Series (HV)</p>\n</li>\n<li data-start=\"2077\" data-end=\"2127\">\n<p data-start=\"2079\" data-end=\"2127\"><strong data-start=\"2079\" data-end=\"2095\">Battery Type</strong>: Lithium Iron Phosphate (LFP)</p>\n</li>\n<li data-start=\"2128\" data-end=\"2229\">\n<p data-start=\"2130\" data-end=\"2229\"><strong data-start=\"2130\" data-end=\"2157\">Dynamic Charge Capacity</strong>: Designed for fast cycling without compromising safety or efficiency.</p>\n</li>\n<li data-start=\"2230\" data-end=\"2340\">\n<p data-start=\"2232\" data-end=\"2340\"><strong data-start=\"2232\" data-end=\"2263\">Operating Temperature Range</strong>: Engineered for effective performance in various environmental conditions.</p>\n</li>\n<li data-start=\"2341\" data-end=\"2425\">\n<p data-start=\"2343\" data-end=\"2425\"><strong data-start=\"2343\" data-end=\"2366\">Dimensions &amp; Weight</strong>: (Specific dimensions and weight available upon request)</p>\n</li>\n<li data-start=\"2426\" data-end=\"2501\">\n<p data-start=\"2428\" data-end=\"2501\"><strong data-start=\"2428\" data-end=\"2449\">Installation Type</strong>: (Installation requirements available upon request)</p>\n</li>\n</ul>\n<p><strong data-start=\"2508\" data-end=\"2577\">Experience unmatched energy management with the Deye GE-F120-2H2.&#160;</strong>This innovative hybrid energy storage system is not just a solution&#8212;it&#8217;s a commitment to safety, performance, and efficiency in every application. Embrace the future of energy with confidence!</p>', '<ul>\n<li>50KW rated power and 120KWh storage capacity</li>\n<li>Suitable for high-rate cyclic charging and discharging scenarios</li>\n<li>All-in-One integrated technology: PCs, inverters, BMS, and EMS</li>\n<li>Power supply redundancy design, black start function, and off-grid operation</li>\n<li>Lithium Iron Phosphate (LFP) battery with aerosol fire-extinguishing solution</li>\n<li>Safety features: combustible gas, smoke, and temperature detection, active exhaust, and fire alarm</li>\n<li>Expandable battery capacity up to 120KWh</li>\n<li>Maximum battery temperature remains below 35&#8451; during rated power operation</li>\n</ul>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(582, '<table border=\"0\" cellspacing=\"0\" cellpadding=\"8\" style=\"width: 100%;\">\n<tbody>\n<tr>\n<td style=\"width: 30%;\">Model</td>\n<td>RW-F10.2</td>\n</tr>\n<tr>\n<td>Battery Chemistry</td>\n<td>LiFePO4</td>\n</tr>\n<tr>\n<td>Capacity (Ah)</td>\n<td>200</td>\n</tr>\n<tr>\n<td>Scalability</td>\n<td>Max. 32 pcs pack (Max. 326 kWh) in parallel</td>\n</tr>\n<tr>\n<td>Nominal Voltage (V)</td>\n<td>51.2</td>\n</tr>\n<tr>\n<td>Operating Voltage (V)</td>\n<td>44.8 &#126; 57.6</td>\n</tr>\n<tr>\n<td>Energy (kWh)</td>\n<td>10.2</td>\n</tr>\n<tr>\n<td>Usable Energy (kWh) [1]</td>\n<td>9.2</td>\n</tr>\n<tr>\n<td>Rated DC Power (kW)</td>\n<td>6 / 7</td>\n</tr>\n<tr>\n<td>Max DC Power (kW)</td>\n<td>12</td>\n</tr>\n<tr>\n<td>Charge/Discharge Current (A) - Recommend [2]</td>\n<td>Charge: 100 / Discharge: 100</td>\n</tr>\n<tr>\n<td>Charge/Discharge Current (A) - Max [2]</td>\n<td>Charge: 198 / Discharge: 240</td>\n</tr>\n<tr><th colspan=\"2\" style=\"text-align: left;\">\n<p></p>\n<p>Other Parameter</p>\n</th></tr>\n<tr>\n<td>Recommended Depth of Discharge</td>\n<td>90%</td>\n</tr>\n<tr>\n<td>Dimension (W/H/D, mm)</td>\n<td>600 &#215; 760 &#215; 200 (Without hanging board)</td>\n</tr>\n<tr>\n<td>Weight Approximate (kg)</td>\n<td>10.4</td>\n</tr>\n<tr>\n<td>Master LED Indicator</td>\n<td>5 LED (SOC: 20% &#126; 100%), 2 LED (working, protecting)</td>\n</tr>\n<tr>\n<td>IP Rating of Enclosure</td>\n<td>IP65</td>\n</tr>\n<tr>\n<td>Working Temperature</td>\n<td>Charge: 0&#65374;55&#8451; / Discharge: -20&#65374;55&#8451;</td>\n</tr>\n<tr>\n<td>Storage Temperature</td>\n<td>0&#65374;35&#8451;</td>\n</tr>\n<tr>\n<td>Humidity</td>\n<td>5% &#126; 95%</td>\n</tr>\n<tr>\n<td>Altitude</td>\n<td>&#8804; 3000 m</td>\n</tr>\n<tr>\n<td>Installation</td>\n<td>Wall-Mounted, Floor-Mounted</td>\n</tr>\n<tr>\n<td>Communication Port</td>\n<td>CAN2.0, RS485</td>\n</tr>\n<tr>\n<td>Warranty Period [3]</td>\n<td>10 years</td>\n</tr>\n<tr>\n<td>Certification</td>\n<td>UN38.3, IEC62619, CE, CEI 0-21, VDE2510-50, CEC</td>\n</tr>\n</tbody>\n</table>', 2, 'RW-F10.2 (EU) [10.2 kWh] Battery Storage System | ESS', '<p data-start=\"96\" data-end=\"627\">The Deye RW-F10.2 is a new standard in energy storage with our advanced lithium iron phosphate (LFP) battery system&#8212;engineered for safety, performance, and versatility. Designed with a cobalt-free chemistry, this battery ensures enhanced safety, long-term durability, and high energy density. Its low-voltage safety connections and integrated Battery Management System (BMS) offer intelligent protection, while the natural cooling design and IP65-rated enclosure provide reliable performance across a wide temperature range from -20&#176;C to 55&#176;C.&#160;Ideal for both residential and commercial use, the modular system supports up to 32 units in parallel, scaling to an impressive 326 kWh of capacity. With up to 6000 cycles at 90% depth of discharge and support for 1C charging and 1.2C discharging, it guarantees exceptional performance backed by a 10-year standard warranty. Installation is simple and flexible thanks to its flat form factor, which supports both wall-mounted and floor-standing setups. Seamless integration with Deye inverters, remote monitoring, auto-networking, and environmentally friendly materials make this battery a smart, sustainable choice for powering the future.</p>\n<p data-start=\"96\" data-end=\"627\"></p>\n<h3 data-start=\"449\" data-end=\"466\">Key Features:</h3>\n<ul data-start=\"468\" data-end=\"1984\">\n<li><span><strong>Enhanced Safety: </strong><br />Our cobalt-free LFP chemistry ensures a safer battery with a long lifespan and high energy density. The low voltage safety connection further enhances the overall safety of the system.<br /><br /></span></li>\n<li><span><strong>Exceptional Performance: </strong><br />With support for maximum 1C charge and 1.2C discharge rates, this battery delivers outstanding performance. It boasts an impressive 6000 cycles at 90% DOD and comes with a 10-year standard warranty.<br /><br /></span></li>\n<li><span><strong>Built-in Protection: </strong><br />The integrated intelligent Battery Management System (BMS) provides comprehensive protection for your battery. The natural cooling design, IP65 rating, and a wide operating temperature range of -20&#176;C to 55&#176;C ensure reliable operation in various conditions.<br /><br /></span></li>\n<li><span><strong>Modular and Expandable: </strong><br />The modular design allows for easy expansion, with a maximum of 32 units in parallel, providing up to 326 kWh of capacity. This flexibility makes it perfect for both residential and commercial applications, enabling you to increase your self-consumption ratio.<br /><br /></span></li>\n<li><span><strong>User-Friendly:</strong><br />The battery modules feature auto-networking, eliminating the need for DIP switch coding. Easy maintenance, remote monitoring, and upgrades are supported through the Deye platform. The battery also seamlessly integrates with Deye inverters to form an all-in-one stacked system.<br /><br /></span></li>\n<li><span><strong>Environmentally Friendly:</strong><br />We use environmentally friendly materials to ensure the entire module is non-toxic and pollution-free, promoting a greener future.<br /><br /></span></li>\n<li><span><strong>Versatile Installation:</strong><br />The flat design allows for both wall-mounted (with a wall bracket) and floor-standing (with a removable base) installations, saving valuable space<br /><br /></span></li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-021.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<h3><span>Technical Specifications:</span></h3>\n<ul class=\"list-outside list-disc pl-8\">\n<li><span>Battery Chemistry: LiFePO4</span></li>\n<li><span>Built-in Circuit Breaker: 125A 4P, 60Vdc</span></li>\n<li><span>Nominal Capacity: 200Ah</span></li>\n<li><span>Nominal Voltage: 51.2V</span></li>\n<li><span>Operating Voltage: 43.2V &#126; 57.6V</span></li>\n<li><span>Nominal Energy: 10.2 kWh</span></li>\n<li><span>Usable Energy: 9.2 kWh (90% DOD)</span></li>\n</ul>\n<p><span>Invest in the Deye RW-F10.2 LFP Battery and take control of your energy future. With its superior safety, performance, and flexibility, this battery is the ideal choice for powering your home or business while reducing your carbon footprint. Experience the difference of Deye&#8217;s cutting-edge energy storage technology today.</span></p>', '<span>The RW-F10.2 Lithium Iron Phosphate (LFP) Battery is a safer, high-performance, and eco-friendly energy storage solution for your residential or commercial needs. This state-of-the-art battery is designed to maximize your energy independence and support your transition to clean, renewable power.</span>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(583, '<div>\n<table border=\"0\" cellspacing=\"0\" cellpadding=\"8\" style=\"width: 100%;\">\n<tbody>\n<tr>\n<td style=\"width: 30%; text-align: left;\">Model</td>\n<td style=\"text-align: left;\">RW-F16</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Battery Chemistry</td>\n<td>LiFePO4</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Built-in Circuit Breaker</td>\n<td>125A 2P, 60Vdc</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Capacity (Ah) [1]</td>\n<td>314</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Scalability</td>\n<td>Max. 32 pcs pack (Max. 512 kWh) in parallel</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Nominal Voltage (V)</td>\n<td>51.2</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Operating Voltage (V)</td>\n<td>44.8 &#126; 57.6</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Nominal Energy (kWh) [1]</td>\n<td>16</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Usable Energy (kWh @ 90% DoD)</td>\n<td>14.4</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Charge/Discharge Current (A) - Max. Continuous [2]</td>\n<td>160 / 160</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Charge/Discharge Current (A) - Peak (10 sec)</td>\n<td>300 / 300</td>\n</tr>\n<tr style=\"text-align: left;\"><th colspan=\"2\">\n<p></p>\n<p>Other Parameter</p>\n</th></tr>\n<tr style=\"text-align: left;\">\n<td>Recommended Depth of Discharge</td>\n<td>90%</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Dimension (W/H/D, mm)</td>\n<td>480 &#215; 830 &#215; 235 (Without hanging board and base)</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Weight Approximate</td>\n<td>122 kg</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Master LCD Indicator</td>\n<td>LCD (SOC and working state)</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>IP Rating of Enclosure</td>\n<td>IP20</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Working Temperature</td>\n<td>Charge: 0&#8451;&#65374;55&#8451; / Discharge: -20&#8451;&#65374;55&#8451;</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Recommended Operating Temperature</td>\n<td>15&#8451;&#65374;35&#8451;</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Storage Temperature</td>\n<td>0&#8451;&#65374;35&#8451;</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Relative Humidity</td>\n<td>95%</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Altitude</td>\n<td>&#8804; 2000 m</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Cycle Life</td>\n<td>&#8805; 6000 (25&#8451;&#177;2&#8451;, 0.5C/0.5C, 90% DOD, 70% EOL)</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Installation</td>\n<td>Wall-Mounted, Floor-Mounted</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Communication Port</td>\n<td>CAN2.0, RS485</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Energy Throughput</td>\n<td>52.5 MWh (25&#8451;, 0.5C/0.5C, 70% EOL)</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Certification</td>\n<td>UN38.3, MSDS</td>\n</tr>\n</tbody>\n</table>\n</div>', 2, 'RW-F16 (EU) [16 kWh] Battery Storage System | ESS', '<p data-start=\"96\" data-end=\"627\"><span>Introducing the Deye RW-F16, an advanced residential energy storage solution designed to provide reliable, safe, and efficient power backup for your home. Featuring cutting-edge LiFePO4 battery technology, the RW-F16 is built to deliver sustainable energy solutions while ensuring maximum performance and user convenience.</span></p>\n<p data-start=\"96\" data-end=\"627\"></p>\n<h3 data-start=\"449\" data-end=\"466\">Key Features:</h3>\n<ul data-start=\"468\" data-end=\"1984\">\n<li><strong>Maximum Output Power:</strong><br />8 kW with the ability to connect up to 32 units in parallel, providing scalability up to 512 kWh, perfect for larger energy needs.<br /><br /></li>\n<li><strong>Battery Chemistry:</strong><br />Employing Lithium Iron Phosphate (LiFePO4) technology, known for its safety and longevity, with over 6000 cycles at 90% Depth of Discharge (DoD).<br /><br /></li>\n<li><strong>Robust Built-in Protection:</strong><br />Equipped with a built-in circuit breaker for added safety during charging (160A) and discharging (160A).<br /><br /></li>\n<li><strong>Versatile Operating Conditions:</strong><br />Charge from 0&#8451; to 55&#8451; and discharge in extreme conditions from -20&#8451; to 55&#8451;, ensuring efficiency in varying climates.<br /><br /></li>\n<li><strong>Remote Monitoring and Firmware Upgrade:</strong><br />Supports remote management and firmware upgrades via Deye inverter, allowing for effortless monitoring and maintenance.<br /><br /></li>\n<li><strong>Flexible Installation Options:</strong><br />Wall and floor-mounted configurations fit seamlessly into residential settings.<br /><br /></li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-022.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<h3 id=\"specifications-\">Technical Specifications:</h3>\n<ul>\n<li><span>Nominal Voltage</span>: 60 Vdc</li>\n<li><span>Capacity</span>: 125 Ah (usable energy 14.4 kWh @ 90% DoD)</li>\n<li><span>Energy Efficiency</span>: 90% round-trip efficiency with a cycle life of &#8805;6000 at 25&#8451;.</li>\n<li><span>Physical Dimensions</span>: 480 mm (W) x 830 mm (H) x 235 mm (D)</li>\n<li><span>Weight</span>: Approximately 122 kg</li>\n<li><span>Environmental Ratings</span>: IP20 rating for indoor use with a temperature range of -20&#8451; to 55&#8451;.</li>\n<li><span>Humidity and Altitude</span>: Humidity tolerance up to 95% and operates effectively below 2000 m altitude.</li>\n<li><span>Warranty Period</span>: 5 years, ensuring peace of mind and reliability.</li>\n</ul>\n<h3 id=\"typical-applications-\">Typical Applications:</h3>\n<p>The Deye RW-F16 is perfect for residential energy backup, ensuring you stay powered during outages and can optimize your energy consumption sustainably. Invest in the Deye RW-F16 for a smart, safe, and efficient energy storage solution that supports your active lifestyle while being friendly to the environment.</p>', '<ul>\n<li><span>High Power Output</span>: Delivers up to 8 kW with the ability to connect up to 32 units, scalable to 512 kWh.</li>\n<li><span>Long-lasting Battery Life</span>: Utilizes LiFePO4 technology with over 6000 cycles, ensuring durability and longevity.</li>\n<li><span>Built-in Circuit Protection</span>: Features a built-in circuit breaker for safe charging (160A) and discharging (160A).</li>\n<li><span>Wide Operating Range</span>: Capable of charging from 0&#8451; to 55&#8451; and discharging from -20&#8451; to 55&#8451;.</li>\n<li><span>Remote Management</span>: Supports remote monitoring and firmware upgrades via Deye inverter.</li>\n<li><span>Flexible Installation</span>: Suitable for both wall-mounted and floor-mounted setups.</li>\n<li><span>Efficient Energy Use</span>: Achieves 90% round-trip efficiency with a nominal usable energy of 14.4 kWh.</li>\n<li><span>Robust Design</span>: IP20 rating, designed for indoor use with high humidity tolerance (up to 95%).</li>\n</ul>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(584, '<div>\n<table border=\"0\" cellspacing=\"0\" cellpadding=\"8\" style=\"width: 100%;\">\n<tbody>\n<tr>\n<td style=\"width: 30%; text-align: left;\">Model</td>\n<td style=\"text-align: left;\">RW-F16</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Battery Chemistry</td>\n<td>LiFePO4</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Built-in Circuit Breaker</td>\n<td>125A 2P, 60Vdc</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Capacity (Ah) [1]</td>\n<td>314</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Scalability</td>\n<td>Max. 32 pcs pack (Max. 512 kWh) in parallel</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Nominal Voltage (V)</td>\n<td>51.2</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Operating Voltage (V)</td>\n<td>44.8 &#126; 57.6</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Nominal Energy (kWh) [1]</td>\n<td>16</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Usable Energy (kWh @ 90% DoD)</td>\n<td>14.4</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Charge/Discharge Current (A) - Max. Continuous [2]</td>\n<td>160 / 160</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Charge/Discharge Current (A) - Peak (10 sec)</td>\n<td>300 / 300</td>\n</tr>\n<tr style=\"text-align: left;\"><th colspan=\"2\">\n<p></p>\n<p>Other Parameter</p>\n</th></tr>\n<tr style=\"text-align: left;\">\n<td>Recommended Depth of Discharge</td>\n<td>90%</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Dimension (W/H/D, mm)</td>\n<td>480 &#215; 830 &#215; 235 (Without hanging board and base)</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Weight Approximate</td>\n<td>122 kg</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Master LCD Indicator</td>\n<td>LCD (SOC and working state)</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>IP Rating of Enclosure</td>\n<td>IP20</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Working Temperature</td>\n<td>Charge: 0&#8451;&#65374;55&#8451; / Discharge: -20&#8451;&#65374;55&#8451;</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Recommended Operating Temperature</td>\n<td>15&#8451;&#65374;35&#8451;</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Storage Temperature</td>\n<td>0&#8451;&#65374;35&#8451;</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Relative Humidity</td>\n<td>95%</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Altitude</td>\n<td>&#8804; 2000 m</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Cycle Life</td>\n<td>&#8805; 6000 (25&#8451;&#177;2&#8451;, 0.5C/0.5C, 90% DOD, 70% EOL)</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Installation</td>\n<td>Wall-Mounted, Floor-Mounted</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Communication Port</td>\n<td>CAN2.0, RS485</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Energy Throughput</td>\n<td>52.5 MWh (25&#8451;, 0.5C/0.5C, 70% EOL)</td>\n</tr>\n<tr style=\"text-align: left;\">\n<td>Certification</td>\n<td>UN38.3, MSDS</td>\n</tr>\n</tbody>\n</table>\n</div>', 2, 'RW-F16 (EU) [16 kWh] Battery Storage System | ESS', '<p data-start=\"96\" data-end=\"627\"><span>Introducing the Deye RW-F16, an advanced residential energy storage solution designed to provide reliable, safe, and efficient power backup for your home. Featuring cutting-edge LiFePO4 battery technology, the RW-F16 is built to deliver sustainable energy solutions while ensuring maximum performance and user convenience.</span></p>\n<p data-start=\"96\" data-end=\"627\"></p>\n<h3 data-start=\"449\" data-end=\"466\">Key Features:</h3>\n<ul data-start=\"468\" data-end=\"1984\">\n<li><strong>Maximum Output Power:</strong><br />8 kW with the ability to connect up to 32 units in parallel, providing scalability up to 512 kWh, perfect for larger energy needs.<br /><br /></li>\n<li><strong>Battery Chemistry:</strong><br />Employing Lithium Iron Phosphate (LiFePO4) technology, known for its safety and longevity, with over 6000 cycles at 90% Depth of Discharge (DoD).<br /><br /></li>\n<li><strong>Robust Built-in Protection:</strong><br />Equipped with a built-in circuit breaker for added safety during charging (160A) and discharging (160A).<br /><br /></li>\n<li><strong>Versatile Operating Conditions:</strong><br />Charge from 0&#8451; to 55&#8451; and discharge in extreme conditions from -20&#8451; to 55&#8451;, ensuring efficiency in varying climates.<br /><br /></li>\n<li><strong>Remote Monitoring and Firmware Upgrade:</strong><br />Supports remote management and firmware upgrades via Deye inverter, allowing for effortless monitoring and maintenance.<br /><br /></li>\n<li><strong>Flexible Installation Options:</strong><br />Wall and floor-mounted configurations fit seamlessly into residential settings.<br /><br /></li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-022.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<h3 id=\"specifications-\">Technical Specifications:</h3>\n<ul>\n<li><span>Nominal Voltage</span>: 60 Vdc</li>\n<li><span>Capacity</span>: 125 Ah (usable energy 14.4 kWh @ 90% DoD)</li>\n<li><span>Energy Efficiency</span>: 90% round-trip efficiency with a cycle life of &#8805;6000 at 25&#8451;.</li>\n<li><span>Physical Dimensions</span>: 480 mm (W) x 830 mm (H) x 235 mm (D)</li>\n<li><span>Weight</span>: Approximately 122 kg</li>\n<li><span>Environmental Ratings</span>: IP20 rating for indoor use with a temperature range of -20&#8451; to 55&#8451;.</li>\n<li><span>Humidity and Altitude</span>: Humidity tolerance up to 95% and operates effectively below 2000 m altitude.</li>\n<li><span>Warranty Period</span>: 5 years, ensuring peace of mind and reliability.</li>\n</ul>\n<h3 id=\"typical-applications-\">Typical Applications:</h3>\n<p>The Deye RW-F16 is perfect for residential energy backup, ensuring you stay powered during outages and can optimize your energy consumption sustainably. Invest in the Deye RW-F16 for a smart, safe, and efficient energy storage solution that supports your active lifestyle while being friendly to the environment.</p>', '<ul>\n<li><span>High Power Output</span>: Delivers up to 8 kW with the ability to connect up to 32 units, scalable to 512 kWh.</li>\n<li><span>Long-lasting Battery Life</span>: Utilizes LiFePO4 technology with over 6000 cycles, ensuring durability and longevity.</li>\n<li><span>Built-in Circuit Protection</span>: Features a built-in circuit breaker for safe charging (160A) and discharging (160A).</li>\n<li><span>Wide Operating Range</span>: Capable of charging from 0&#8451; to 55&#8451; and discharging from -20&#8451; to 55&#8451;.</li>\n<li><span>Remote Management</span>: Supports remote monitoring and firmware upgrades via Deye inverter.</li>\n<li><span>Flexible Installation</span>: Suitable for both wall-mounted and floor-mounted setups.</li>\n<li><span>Efficient Energy Use</span>: Achieves 90% round-trip efficiency with a nominal usable energy of 14.4 kWh.</li>\n<li><span>Robust Design</span>: IP20 rating, designed for indoor use with high humidity tolerance (up to 95%).</li>\n</ul>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(585, '<div>\n<table border=\"0\" cellpadding=\"8\" style=\"width: 100%;\">\n<tbody>\n<tr><th style=\"text-align: left;\">Model</th>\n<td style=\"text-align: left;\">SUN-100K/125K-PCSL01HP3</td>\n</tr>\n<tr style=\"text-align: left;\"><th style=\"width: 30%;\">Nominal Power</th>\n<td>100 kW / 125 kW</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Max Units in Parallel</th>\n<td>Up to 20 units (2.5 MW total)</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Max Charge/Discharge Current</th>\n<td>220 A</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Efficiency</th>\n<td>98.5% peak, 97.8% Euro</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Grid Frequency</th>\n<td>45&#8211;65 Hz</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Power Factor</th>\n<td>Adjustable from &#8211;1 to 1</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Harmonic Distortion</th>\n<td>&lt;3% THDi</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Interfaces</th>\n<td>LCD, LED, RS485, CAN, Meter, Wi-Fi</td>\n</tr>\n<tr style=\"text-align: left;\"><th>IP Rating</th>\n<td>IP65</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Dimensions (W&#215;H&#215;D)</th>\n<td>543 &#215; 310 &#215; 775 mm</td>\n</tr>\n</tbody>\n</table>\n</div>', 2, 'BOS-B | SUN-100K/125K-PCSL01HP3 Power Conversion System (PCS) Module | ESS', '<p data-start=\"252\" data-end=\"599\">The Deye SUN-PCS (<span>Power Conversion System)&#160;</span>Module (available in 100&#8239;kW and 125&#8239;kW variants) is a core component of Deye\'s Power Conversion System. It enables bidirectional power conversion between DC batteries and the AC grid, supporting advanced energy management strategies in commercial and industrial applications. The PCS module is designed to work in grid-connected and off-grid scenarios, offering high flexibility and robust performance.</p>\n<h3 id=\"key-features-\">Key Features:</h3>\n<ul>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"4958\" data-end=\"5085\"><strong data-start=\"4958\" data-end=\"4995\">High Efficiency Power Conversion:</strong><br data-start=\"4995\" data-end=\"4998\" /> Peak conversion efficiency up to 98.5%, ensuring minimal losses during energy transfer.</p>\n</li>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"4958\" data-end=\"5085\"><strong data-start=\"5087\" data-end=\"5120\">Scalable System Architecture:<br /></strong>Multiple PCS units can be connected in parallel, scaling system capacity up to 2.5&#8239;MW.</p>\n</li>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"4958\" data-end=\"5085\"><strong data-start=\"5211\" data-end=\"5241\">Advanced Grid Interaction:<br /></strong>Supports reactive power control, zero-export mode, and time-of-use strategies for optimized grid interaction.</p>\n</li>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"4958\" data-end=\"5085\"><strong data-start=\"5355\" data-end=\"5382\">High Discharge Current:<br /></strong>Up to 220&#8239;A charging/discharging, with support for 110% overload and 170% peak output for short durations.</p>\n</li>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"4958\" data-end=\"5085\"><strong data-start=\"5493\" data-end=\"5517\">Flexible Interfaces:<br /></strong>Equipped with RS485, CAN, Wi-Fi, LCD/LED display, and metering interface for seamless control and monitoring.</p>\n</li>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"4958\" data-end=\"5085\"><strong data-start=\"5631\" data-end=\"5665\">Comprehensive Safety Measures:<br /></strong>Features include DC residual current detection, arc-fault circuit interrupter (optional), insulation monitoring, and short-circuit protection.</p>\n</li>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"4958\" data-end=\"5085\"><strong data-start=\"5812\" data-end=\"5833\">Robust Enclosure:<br /></strong>IP65 protection for reliable outdoor or indoor deployment.</p>\n<p data-start=\"5812\" data-end=\"5894\"></p>\n</li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-017.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>', 'The SUN-100K/125K-PCSL01HP3 is a high-performance Power Conversion System (PCS) module from Deye, available in 100&#8239;kW and 125&#8239;kW variants. It enables efficient bidirectional energy flow between DC battery storage and the AC grid, supporting both on-grid and off-grid applications. With advanced grid features, scalable architecture up to 2.5&#8239;MW, and robust protection systems, it is an ideal choice for commercial and industrial energy storage solutions.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', '');
INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(586, '<table border=\"0\" cellpadding=\"8\" style=\"width: 100%;\">\n<tbody>\n<tr><th style=\"width: 30%;\">\n<div style=\"text-align: left;\">Model</div>\n</th>\n<td style=\"text-align: left;\">\n<div>SUN-MPPT-L01-EU-AM8</div>\n</td>\n</tr>\n<tr style=\"text-align: left;\"><th>\n<div>Max PV Power</div>\n</th>\n<td>\n<div>200 kW</div>\n</td>\n</tr>\n<tr style=\"text-align: left;\"><th>\n<div>MPPT Channels</div>\n</th>\n<td>\n<div>8 (2 inputs per channel)</div>\n</td>\n</tr>\n<tr style=\"text-align: left;\"><th>\n<div>MPPT Voltage Range</div>\n</th>\n<td>\n<div>180&#8211;850 V (Full-load 450&#8211;850 V)</div>\n</td>\n</tr>\n<tr style=\"text-align: left;\"><th>\n<div>Max PV Voltage</div>\n</th>\n<td>\n<div>1000 V</div>\n</td>\n</tr>\n<tr style=\"text-align: left;\"><th>\n<div>Max Input Current per MPPT</div>\n</th>\n<td>\n<div>40 A</div>\n</td>\n</tr>\n<tr style=\"text-align: left;\"><th>\n<div>Efficiency</div>\n</th>\n<td>\n<div>&gt;99% peak, &gt;99.9% MPPT</div>\n</td>\n</tr>\n<tr style=\"text-align: left;\"><th>\n<div>Protection</div>\n</th>\n<td>\n<div>Surge, reverse polarity, insulation resistance monitoring</div>\n</td>\n</tr>\n<tr style=\"text-align: left;\"><th>\n<div>IP Rating</div>\n</th>\n<td>\n<div>IP65</div>\n</td>\n</tr>\n<tr><th style=\"text-align: left;\">\n<div>Dimensions (W&#215;H&#215;D)</div>\n</th>\n<td>\n<div style=\"text-align: left;\">543 &#215; 197.8 &#215; 700 mm</div>\n</td>\n</tr>\n</tbody>\n</table>', 2, 'BOS-B | SUN-MPPT-L01-EU-AM8 Maximum Power Point Tracking (MPPT) Module | ESS', '<p data-start=\"252\" data-end=\"599\">The SUN-MPPT-L01-EU-AM8 is an advanced MPPT (Maximum Power Point Tracking) module engineered for use in Deye&#8217;s commercial and industrial energy storage solutions. It enables efficient solar energy harvesting through multi-channel MPPT optimization, ensuring maximum energy yield under dynamic environmental conditions.</p>\n<h3 id=\"key-features-\">Key Features:</h3>\n<ul>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"2849\" data-end=\"2972\"><strong data-start=\"2849\" data-end=\"2870\">High PV Capacity:</strong><br data-start=\"2870\" data-end=\"2873\" /> Supports up to 200&#8239;kW of solar PV input with 8 independent MPPT channels, each handling up to 40&#8239;A.</p>\n</li>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"2849\" data-end=\"2972\"><strong data-start=\"2974\" data-end=\"2994\">Wide MPPT Range:<br /></strong>Provides a broad tracking range of 180&#8239;V to 850&#8239;V, ensuring compatibility with various PV array configurations.</p>\n</li>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"2849\" data-end=\"2972\"><strong data-start=\"3110\" data-end=\"3130\">High Efficiency:<br /></strong>Delivers peak conversion efficiency above 99% with MPPT accuracy over 99.9%, ensuring minimal energy loss.</p>\n</li>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"2849\" data-end=\"2972\"><strong data-start=\"3241\" data-end=\"3269\">Multiple Input Channels:<br /></strong>Each MPPT channel includes 2 inputs (16 in total), enabling flexible PV string design and simplified layout.</p>\n</li>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"2849\" data-end=\"2972\"><strong data-start=\"3382\" data-end=\"3407\">Built-in Protections:<br /></strong>Includes surge protection, DC reverse polarity protection, and insulation resistance monitoring.</p>\n</li>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"2849\" data-end=\"2972\"><strong data-start=\"3508\" data-end=\"3532\">Rugged Construction:<br /></strong>IP65-rated enclosure protects against dust and water ingress, ideal for indoor and sheltered outdoor use.</p>\n</li>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"2849\" data-end=\"2972\"><strong data-start=\"3642\" data-end=\"3667\">Ease of Installation:<br /></strong>Compact design allows for quick and straightforward integration into PV and battery systems.</p>\n<p data-start=\"1521\" data-end=\"1661\"></p>\n</li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-017.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>', 'The SUN-MPPT-L01-EU-AM8 is a high-efficiency MPPT module tailored for Deye\'s commercial and industrial solar storage systems. Featuring 8 independent MPPT channels and a total PV input capacity of up to 200&#8239;kW, it maximizes solar energy harvest under varying conditions. With advanced protection, precision tracking, and a rugged IP65 design, it ensures reliable and optimized PV performance in any setup.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(587, '<div>\n<table border=\"0\" cellpadding=\"8\" style=\"width: 100%;\">\n<tbody>\n<tr><th style=\"width: 30%; text-align: left;\">Model</th>\n<td style=\"text-align: left;\">SUN-STS500L</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Switching Capacity</th>\n<td>500 kW (standard) / 650 kW (peak)</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Switching Time</th>\n<td>&lt; 10 ms</td>\n</tr>\n<tr style=\"text-align: left;\"><th>AC Ports</th>\n<td>GEN, Load, Grid, STS AC Parallel</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Protection</th>\n<td>Overcurrent, Overvoltage, Short-circuit, Earth-fault, Islanding</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Cooling</th>\n<td>Intelligent air cooling</td>\n</tr>\n<tr style=\"text-align: left;\"><th>IP Rating</th>\n<td>IP20</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Operating Temperature</th>\n<td>-25&#176;C to +60&#176;C</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Humidity</th>\n<td>0&#8211;95%</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Altitude</th>\n<td>&#8804; 4000 m</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Dimensions (W&#215;H&#215;D)</th>\n<td>543 &#215; 575 &#215; 866 mm</td>\n</tr>\n<tr style=\"text-align: left;\"><th>Weight</th>\n<td>Not specified</td>\n</tr>\n</tbody>\n</table>\n</div>', 2, 'BOS-B | SUN-STS500L Static Transfer Switch (STS) Module | ESS', '<p data-start=\"252\" data-end=\"599\">The SUN-STS500L is a high-performance Static Transfer Switch (STS) designed for Deye energy storage systems. It ensures fast and reliable switching between grid, diesel generator, and load in under 10 milliseconds, offering seamless operation for hybrid energy systems. As a key component of the system architecture, the STS Module guarantees power continuity, protects against grid disturbances, and supports stable energy transition.</p>\n<h3 id=\"key-features-\">Key Features:</h3>\n<ul>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"638\" data-end=\"775\"><strong data-start=\"638\" data-end=\"667\">Ultra-Fast Transfer Time:</strong><br data-start=\"667\" data-end=\"670\" /> Switches between power sources in less than 10&#8239;ms, ensuring uninterrupted power supply to critical loads.</p>\n<p data-start=\"777\" data-end=\"915\"><strong data-start=\"777\" data-end=\"801\">High Power Capacity:</strong><br data-start=\"801\" data-end=\"804\" /> Supports up to 500&#8239;kW (650&#8239;kW peak), with independent full-capacity paths for grid, diesel generator, and load.</p>\n<p data-start=\"917\" data-end=\"1098\"><strong data-start=\"917\" data-end=\"951\">Integrated Protection Systems:</strong><br data-start=\"951\" data-end=\"954\" /> Provides overcurrent, overvoltage, short-circuit, earth-fault detection, insulation monitoring, and surge protection according to IEC standards.</p>\n<p data-start=\"1100\" data-end=\"1249\"><strong data-start=\"1100\" data-end=\"1130\">Advanced Safety Functions:</strong><br data-start=\"1130\" data-end=\"1133\" /> Built-in arc-fault circuit interrupter (optional), islanding protection, DC polarity and residual current detection.</p>\n<p data-start=\"1251\" data-end=\"1378\"><strong data-start=\"1251\" data-end=\"1283\">Scalable Parallel Operation:</strong><br data-start=\"1283\" data-end=\"1286\" /> Allows multiple STS units to be used in parallel, expanding system flexibility and capacity.</p>\n<p data-start=\"1380\" data-end=\"1519\"><strong data-start=\"1380\" data-end=\"1398\">Rugged Design:</strong><br data-start=\"1398\" data-end=\"1401\" /> Reliable performance under harsh conditions: wide temperature range, high humidity tolerance, and intelligent cooling.</p>\n<p data-start=\"1521\" data-end=\"1661\"><strong data-start=\"1521\" data-end=\"1542\">Easy Integration:</strong><br data-start=\"1542\" data-end=\"1545\" /> Ideal for use with Deye&#8217;s PCS and battery systems, offering direct interface for seamless communication and control.<br /><br /></p>\n</li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-017.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>', 'The SUN-STS500L is a high-performance Static Transfer Switch designed for seamless energy transitions in Deye hybrid storage systems. With ultra-fast switching under 10&#8239;ms and a robust 500&#8239;kW capacity, it ensures uninterrupted power, advanced protection, and reliable performance&#8212;even under demanding conditions. Ideal for grid-diesel hybrid setups requiring maximum continuity and safety.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(588, '<table border=\"0\" cellspacing=\"0\" cellpadding=\"8\" style=\"width: 100%;\">\n<tbody>\n<tr>\n<td style=\"width: 30%;\">Model</td>\n<td>BOS-B-PDU-2</td>\n</tr>\n<tr>\n<td>Battery Type</td>\n<td>High Voltage</td>\n</tr>\n<tr>\n<td>Life Cycle</td>\n<td>6000 cycles</td>\n</tr>\n<tr>\n<td>Operating Voltage Range</td>\n<td>200&#8211;1000 V</td>\n</tr>\n<tr>\n<td>Discharge Cutoff Voltage</td>\n<td>200 V</td>\n</tr>\n<tr>\n<td>Max Charging Current</td>\n<td>175 A</td>\n</tr>\n<tr>\n<td>Recommended Discharge Current</td>\n<td>140 A</td>\n</tr>\n<tr>\n<td>Max Discharge Cutoff Current</td>\n<td>175 A</td>\n</tr>\n<tr>\n<td>Terminal Type</td>\n<td>Proprietary</td>\n</tr>\n<tr>\n<td>Cooling Method</td>\n<td>Active</td>\n</tr>\n<tr>\n<td>Recommended Charging Temp.</td>\n<td>0&#176;C to +55&#176;C</td>\n</tr>\n<tr>\n<td>Recommended Discharging Temp.</td>\n<td>-20&#176;C to +55&#176;C</td>\n</tr>\n<tr>\n<td>Recommended Storage Temp.</td>\n<td>0&#176;C to +35&#176;C</td>\n</tr>\n<tr>\n<td>Enclosure Material</td>\n<td>Metal</td>\n</tr>\n<tr>\n<td>Dimensions (mm)</td>\n<td>797 &#215; 526 &#215; 275</td>\n</tr>\n<tr>\n<td>Weight (kg)</td>\n<td>20</td>\n</tr>\n<tr>\n<td>Warranty</td>\n<td>10 Years</td>\n</tr>\n<tr>\n<td>Package Contents</td>\n<td>Control module, 4 lower covers, 3 upper covers, 16 cover feet,<br /> 1 communication cable, 1x 180mm negative power cord,<br /> 1 auxiliary power supply cable, 1 positive power cord,<br /> 1 emergency shutdown interface, 1 PCS positive cable,<br /> 1 PCS negative cable, 3x 1000mm inter-rack power cables,<br /> 1 inverter communication cable, 3x 1000mm inter-rack comm. cables,<br /> 1 optional Wi-Fi antenna, 4 grounding cables,<br /> 1 terminal resistor 120&#937;, PCS terminal connectors,<br /> 16 mounting screws</td>\n</tr>\n</tbody>\n</table>', 2, 'BOS-B-PDU-2 High-Performance Power Distribution Unit (PDU) | ESS', '<p data-start=\"252\" data-end=\"599\">The <strong data-start=\"256\" data-end=\"276\">Deye BOS-B-PDU-2</strong> is a cutting-edge Battery Management System (BMS) designed for high-voltage energy storage applications. It serves as the control hub for Deye\'s BOS-B series, offering advanced monitoring, safety, and integration features to ensure reliable and efficient energy storage system performance, even under demanding conditions.&#160;With its extended voltage range of 200&#8211;1000 V and high discharge threshold of up to 175 A, this BMS is tailored for large-scale installations. Engineered with active cooling and durable metal housing, the BOS-B-PDU-2 delivers both power and protection. Its smart connectivity options&#8212;including USB, Bluetooth, Ethernet, and COMM1&#8211;COMM3 channels&#8212;make integration seamless. This makes it the ideal choice for professionals requiring robust and scalable battery control.</p>\n<h3 id=\"key-features-\">Key Features:</h3>\n<ul>\n<li data-start=\"1096\" data-end=\"1273\">\n<p data-start=\"1098\" data-end=\"1273\"><strong data-start=\"1098\" data-end=\"1140\">Wide Voltage and High Current Capacity</strong><br data-start=\"1140\" data-end=\"1143\" /> Operates within a range of 200&#8211;1000 V and supports up to 175 A charge/discharge currents&#8212;perfect for large, high-demand systems.</p>\n</li>\n<li data-start=\"1275\" data-end=\"1441\">\n<p data-start=\"1277\" data-end=\"1441\"><strong data-start=\"1277\" data-end=\"1307\">Advanced Safety Mechanisms</strong><br data-start=\"1307\" data-end=\"1310\" /> Active cooling and high cutoff current (175 A) provide solid protection against overcurrent, overheating, and system instability.</p>\n</li>\n<li data-start=\"1443\" data-end=\"1561\">\n<p data-start=\"1445\" data-end=\"1561\"><strong data-start=\"1445\" data-end=\"1466\">Long Battery Life</strong><br data-start=\"1466\" data-end=\"1469\" /> Supports up to 6000 charge cycles, ensuring long-term reliability and minimal maintenance.</p>\n</li>\n<li data-start=\"1563\" data-end=\"1689\">\n<p data-start=\"1565\" data-end=\"1689\"><strong data-start=\"1565\" data-end=\"1589\">Durable Construction</strong><br data-start=\"1589\" data-end=\"1592\" /> Housed in a sturdy metal enclosure, designed for tough environments and consistent performance.</p>\n</li>\n<li data-start=\"1691\" data-end=\"1848\">\n<p data-start=\"1693\" data-end=\"1848\"><strong data-start=\"1693\" data-end=\"1733\">Comprehensive Monitoring and Control</strong><br data-start=\"1733\" data-end=\"1736\" /> Built-in display, LED status indicators, and intelligent internal diagnostics for easy system status tracking.</p>\n</li>\n<li data-start=\"1850\" data-end=\"2012\">\n<p data-start=\"1852\" data-end=\"2012\"><strong data-start=\"1852\" data-end=\"1890\">Versatile Communication Interfaces</strong><br data-start=\"1890\" data-end=\"1893\" /> USB, Bluetooth, Ethernet, and three COMM channels offer excellent system integration and remote management potential.</p>\n</li>\n<li data-start=\"2014\" data-end=\"2170\">\n<p data-start=\"2016\" data-end=\"2170\"><strong data-start=\"2016\" data-end=\"2045\">Professional-Grade Design</strong><br data-start=\"2045\" data-end=\"2048\" /> Includes proprietary terminals, logical cable management, and intuitive layout for efficient installation and operation.</p>\n</li>\n<li data-start=\"2172\" data-end=\"2317\">\n<p data-start=\"2174\" data-end=\"2317\"><strong data-start=\"2174\" data-end=\"2208\">Full Installation Kit Included</strong><br data-start=\"2208\" data-end=\"2211\" /> Comes with all essential cables, covers, screws, and communication lines&#8212;ready for immediate deployment.<br /><br /></p>\n</li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-017.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>', 'The Deye BOS-B-PDU-2 is a high-performance Battery Management System (BMS) designed for high-voltage energy storage solutions. With a wide operating range of 200&#8211;1000 V, 175 A max current, and advanced safety features including active cooling and smart monitoring, it ensures efficient, stable, and secure system control. Ideal for large-scale installations and professional applications.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(589, '<table border=\"0\" cellpadding=\"6\" cellspacing=\"0\" style=\"width: 100%;\">\n<tbody>\n<tr>\n<td>Cell Chemistry</td>\n<td colspan=\"3\" style=\"text-align: center;\">LiFePO4</td>\n</tr>\n<tr>\n<td>Module Energy (kWh)</td>\n<td colspan=\"3\" style=\"text-align: center;\">7.68</td>\n</tr>\n<tr>\n<td>Module Nominal Voltage (V)</td>\n<td colspan=\"3\" style=\"text-align: center;\">38.4</td>\n</tr>\n<tr>\n<td>Module Capacity (Ah)</td>\n<td colspan=\"3\" style=\"text-align: center;\">200</td>\n</tr>\n<tr>\n<td>Module Dimensions (W &#215; D &#215; H, mm)</td>\n<td colspan=\"3\" style=\"text-align: center;\">601.5 &#215; 520 &#215; 135</td>\n</tr>\n<tr>\n<td>Module Weight (approx., kg)</td>\n<td colspan=\"3\" style=\"text-align: center;\">70</td>\n</tr>\n<tr>\n<td>Battery Modules in Series (optional)</td>\n<td style=\"text-align: center;\">7</td>\n<td style=\"text-align: center;\">13</td>\n<td style=\"text-align: center;\">21</td>\n</tr>\n<tr>\n<td>System Nominal Voltage (V)</td>\n<td style=\"text-align: center;\">268.8</td>\n<td style=\"text-align: center;\">499.2</td>\n<td style=\"text-align: center;\">806.4</td>\n</tr>\n<tr>\n<td>System Operating Voltage (V)</td>\n<td style=\"text-align: center;\">235.2 &#126; 306.6</td>\n<td style=\"text-align: center;\">436.8 &#126; 569.4</td>\n<td style=\"text-align: center;\">705.6 &#126; 920.7</td>\n</tr>\n<tr>\n<td>System Energy (kWh)</td>\n<td style=\"text-align: center;\">53.76</td>\n<td style=\"text-align: center;\">99.84</td>\n<td style=\"text-align: center;\">161.28</td>\n</tr>\n<tr>\n<td>Usable System Energy (kWh)</td>\n<td style=\"text-align: center;\">48.38</td>\n<td style=\"text-align: center;\">89.85</td>\n<td style=\"text-align: center;\">145.15</td>\n</tr>\n<tr>\n<td style=\"width: 30%;\">Charge/Discharge Current (A) - Recommended</td>\n<td colspan=\"3\" style=\"text-align: center;\">100</td>\n</tr>\n<tr>\n<td>Charge/Discharge Current (A) - Max.</td>\n<td colspan=\"3\" style=\"text-align: center;\">160</td>\n</tr>\n<tr>\n<td>Operating Temperature (&#8451;)</td>\n<td colspan=\"3\" style=\"text-align: center;\">Charge: 0 &#126; 55 / Discharge: -20 &#126; 55</td>\n</tr>\n<tr>\n<td>Status Indicator</td>\n<td colspan=\"3\" style=\"text-align: center;\">Yellow: Battery HV On. Red: System Alarm</td>\n</tr>\n<tr>\n<td>Communication Port</td>\n<td colspan=\"3\" style=\"text-align: center;\">CAN2.0</td>\n</tr>\n<tr>\n<td>Humidity</td>\n<td colspan=\"3\" style=\"text-align: center;\">5% &#126; 85% RH</td>\n</tr>\n<tr>\n<td>Altitude (above sea level)</td>\n<td colspan=\"3\" style=\"text-align: center;\">&#8804;3000 m</td>\n</tr>\n<tr>\n<td>IP Rating of Enclosure</td>\n<td colspan=\"3\" style=\"text-align: center;\">IP20</td>\n</tr>\n<tr>\n<td>System Dimensions (W &#215; D &#215; H, mm)</td>\n<td style=\"text-align: center;\">610 &#215; 610 &#215; 1450</td>\n<td style=\"text-align: center;\">610 &#215; 610 &#215; 2350</td>\n<td style=\"text-align: center;\">610 &#215; 610 &#215; 3650</td>\n</tr>\n<tr>\n<td>System Weight (approx., kg)</td>\n<td style=\"text-align: center;\">530</td>\n<td style=\"text-align: center;\">985</td>\n<td style=\"text-align: center;\">1590</td>\n</tr>\n<tr>\n<td>Installation</td>\n<td colspan=\"3\" style=\"text-align: center;\">Rack Mount</td>\n</tr>\n<tr>\n<td>Storage Temperature (&#8451;)</td>\n<td colspan=\"3\" style=\"text-align: center;\">0 &#126; 35</td>\n</tr>\n<tr>\n<td>Recommended Depth of Discharge</td>\n<td colspan=\"3\" style=\"text-align: center;\">90%</td>\n</tr>\n<tr>\n<td>Cycle Life</td>\n<td colspan=\"3\" style=\"text-align: center;\">&#8805;6000 (25&#177;2&#8451;, 0.5C/0.5C, EOL 70%)</td>\n</tr>\n<tr>\n<td>Warranty</td>\n<td colspan=\"3\" style=\"text-align: center;\">10 years</td>\n</tr>\n<tr>\n<td>Certification</td>\n<td colspan=\"3\" style=\"text-align: center;\">CE / IEC 62619 / IEC 62040 / UN38.3 / VDE-2510</td>\n</tr>\n</tbody>\n</table>', 2, 'TEST BOS-A-Pack (EU) [7.68kWh] High-Performance Commercial Battery Storage Module | ESS TEST', '<p>Deye BOS-A is a high-performance, embedded LiFePO4 battery module engineered for robust commercial battery storage. It offers quick installation and maintenance, advanced safety features, an intelligent BMS, and an eco-friendly design, making it an ideal choice for power backup and renewable&#160;commercial energy storage.</p>\n<h3 id=\"key-features-\">Key Features:</h3>\n<ul>\n<li><strong>High Performance:</strong> With a capacity of&#160;<span>7.68 kWh</span>&#160;and the potential for &gt;6000 cycles, the BOS-A guarantees long-lasting energy support, ensuring that your operations run smoothly without interruptions.</li>\n<li><strong>Intelligent Management:</strong> Equipped with smart cloud-based monitoring, the BOS-A enables real-time tracking of your energy consumption and battery status, optimizing performance and lowering electricity bills.</li>\n<li><strong>Flexible Configuration:</strong> Capable of supporting multiple racks with up to&#160;<span>13 battery modules</span>&#160;in series, this system provides adaptability to meet your growing energy demands.</li>\n<li><strong>Effortless Installation:</strong> The lightweight design, at just&#160;<span>70 kg</span>&#160;per module, paired with a detailed user manual, ensures a straightforward installation process.</li>\n<li><strong>Safety First:</strong> Featuring an intelligent battery management system (BMS) and comprehensive safety protocols to prevent over-discharge, over-charge, and short circuits, the BOS-A prioritizes the longevity and safety of your power system.</li>\n<li><strong>Robust Design:</strong> Built to withstand various environmental conditions, the BOS-A has a high IP rating and can function effectively in a range of temperatures, ensuring durability in any setting.</li>\n<li><strong>Warranty Assurance:</strong> Enjoy peace of mind with a&#160;<span>10-year warranty</span>, providing you with a full replacement guarantee for up to&#160;<span>6000 cycles</span>&#160;of use.<br /><br /></li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-016.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<h3 id=\"technical-specifications-\">Technical Specifications:</h3>\n<ul>\n<li><strong>Cell Chemistry:</strong> LiFePO&#8324;</li>\n<li><strong>Battery Dimensions</strong>: 601.5 mm x 520 mm x 135 mm</li>\n<li><strong>Weight:</strong> Approx. 70 kg per rack</li>\n<li><strong>Energy Efficiency:</strong> Over 90% at standard operational conditions</li>\n<li><strong>Communication Port:</strong> CAN2.0, offering seamless integration with other Deye devices</li>\n</ul>\n<h3 id=\"installation-and-support-\">Installation and Support:</h3>\n<p>The BOS-A is designed for rack-mounted environments, making it an ideal solution for&#160;commercial battery storage systems&#160;in commercial buildings and industrial facilities. Comprehensive support for your&#160;commercial energy storage&#160;solution is available via the Deye Cloud platform, enabling convenient remote monitoring and control.</p>', '<ul>\n<li><strong>High Capacity</strong>: 7.68 kWh, supports up to 6000 cycles</li>\n<li><strong>Smart Monitoring</strong>: Cloud-based tracking, real-time energy management</li>\n<li><strong>Flexible Configuration</strong>: Supports up to 13 battery modules in series</li>\n<li><strong>Easy Installation</strong>: Lightweight design (approx. 70 kg)</li>\n<li><strong>Safety Assurance</strong>: BMS, against overcharge and short circuits</li>\n<li><strong>Warranty Coverage</strong>: 10-year warranty</li>\n<li><strong>User-Friendly Interface</strong>: Seamlessly integrates with the Deye Cloud</li>\n<li><span><strong>Suitable Deye Inverter Model:</strong></span>\n<ul>\n<li><span>SUN-30K-SG01HP3-EU-BM3</span></li>\n<li><span>SUN-40K/50K-SG01HP3-EU-BM4</span></li>\n<li><span>SUN-60K-SG02HP3-EU-EM4</span></li>\n<li><span>SUN-80K-SG02HP3-EU-EM6</span></li>\n<li><span>SUN-100K-PCSL01HP3-AU</span></li>\n</ul>\n</li>\n</ul>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(590, '<table border=\"0\" cellspacing=\"0\" cellpadding=\"8\" style=\"width: 100%;\">\n<tbody>\n<tr>\n<td>Model</td>\n<td>RW-M6.1-B</td>\n</tr>\n<tr>\n<td>Battery Chemistry</td>\n<td>LiFePO4</td>\n</tr>\n<tr>\n<td>Capacity (Ah)</td>\n<td>120</td>\n</tr>\n<tr>\n<td>Scalability</td>\n<td>Max. 32 pcs in parallel (196 kWh)</td>\n</tr>\n<tr>\n<td>Nominal Voltage (V)</td>\n<td>51.2</td>\n</tr>\n<tr>\n<td>Operating Voltage (V)</td>\n<td>43.2 &#126; 57.6</td>\n</tr>\n<tr>\n<td>Energy (kWh)</td>\n<td>6.14</td>\n</tr>\n<tr>\n<td>Usable Energy (kWh) [1]</td>\n<td>5.53</td>\n</tr>\n<tr>\n<td>Charge/Discharge Current (A) - Recommend [2]</td>\n<td>60</td>\n</tr>\n<tr>\n<td>Charge/Discharge Current (A) - Max. [2]</td>\n<td>100</td>\n</tr>\n<tr>\n<td>Peak Discharge (2 mins, 25&#8451;)</td>\n<td>150</td>\n</tr>\n<tr><th colspan=\"2\" style=\"text-align: left;\">\n<p></p>\n<p>Other Parameter</p>\n</th></tr>\n<tr>\n<td>Recommended Depth of Discharge</td>\n<td>90%</td>\n</tr>\n<tr>\n<td>Dimension (W/H/D, mm)</td>\n<td>510 &#215; 740 &#215; 145 (Without Base, depth of 161 mm with Hanging Board)</td>\n</tr>\n<tr>\n<td>Weight Approximate (kg)</td>\n<td>60</td>\n</tr>\n<tr>\n<td>Master LED Indicator</td>\n<td>5 LED (SOC 20%&#126;100%)<br />3 LED (working, alarming, protecting)</td>\n</tr>\n<tr>\n<td>IP Rating of Enclosure</td>\n<td>IP65</td>\n</tr>\n<tr>\n<td>Working Temperature</td>\n<td>Charge: 0&#8451;&#65374;+55&#8451;<br />Discharge: -20&#8451;&#65374;+55&#8451;</td>\n</tr>\n<tr>\n<td>Storage Temperature</td>\n<td>0&#8451;&#65374;35&#8451;</td>\n</tr>\n<tr>\n<td>Humidity</td>\n<td>5%&#126;95%</td>\n</tr>\n<tr>\n<td>Altitude</td>\n<td>&#8804; 2000 m</td>\n</tr>\n<tr>\n<td>Installation</td>\n<td>Wall-Mounted, Floor-Mounted</td>\n</tr>\n<tr>\n<td>Communication Port</td>\n<td>CAN2.0, RS485</td>\n</tr>\n<tr>\n<td>Certification</td>\n<td>UN38.3, IEC62619, CE</td>\n</tr>\n</tbody>\n</table>', 2, 'RW-M6.1-B (EU) [6.1 kWh] Battery Storage System | ESS', '<p data-start=\"96\" data-end=\"627\"><span>The Deye RW-M 6.1-B is a state-of-the-art Lithium Iron Phosphate (LFP) battery designed to provide reliable, safe, and high-efficiency power storage solutions for both residential and commercial applications. With its advanced Battery Management System (BMS) and modular design, this battery ensures long lifespan, high power density, and complete protection for your energy storage needs.</span></p>\n<p data-start=\"96\" data-end=\"627\"></p>\n<h3 data-start=\"449\" data-end=\"466\">Key Features:</h3>\n<ul data-start=\"468\" data-end=\"1984\">\n<li><strong>Safety and Longevity:</strong>\n<ul>\n<li>Cobalt-free LFP chemistry ensures safer operation.</li>\n<li>Intelligent BMS provides comprehensive protection and extends cycle life.</li>\n<li>High discharge power support ensures reliability.<br /><br /></li>\n</ul>\n</li>\n<li><strong>High Efficiency:</strong>\n<ul>\n<li>High-power density for efficient energy storage.</li>\n<li>Operating voltage range from 43.2V to 57.6V.</li>\n<li>Usable energy capacity of 5.53 kWh with a nominal voltage of 51.2V.<br /><br /></li>\n</ul>\n</li>\n<li><strong>Flexible and Scalable:</strong>\n<ul>\n<li>Modular design allows for easy expansion, supporting up to 32 units in parallel.</li>\n<li>Maximum capacity of 196 kWh.</li>\n<li>Suitable for various applications with limited installation space and restricted load-bearing.<br /><br /></li>\n</ul>\n</li>\n<li><strong>Convenient and Intelligent:</strong>\n<ul>\n<li>Auto-networking battery modules for effortless maintenance.</li>\n<li>Remote monitoring and firmware upgrades via USB drive.</li>\n<li>CAN 2.0 and RS485 communication ports for seamless integration.<br /><br /></li>\n</ul>\n</li>\n<li><strong>Eco-Friendly:</strong>\n<ul>\n<li>Made from non-toxic, pollution-free materials.</li>\n<li>Designed to be environmentally friendly.<br /><br /></li>\n</ul>\n</li>\n<li><strong>Versatile Installation:</strong>\n<ul>\n<li>Supports both wall-mounted and floor-mounted setups.</li>\n<li>Saves installation space with a flat design.<br /><br /></li>\n</ul>\n</li>\n<li><strong>Robust Construction:</strong>\n<ul>\n<li>IP65 rating for a robust enclosure.</li>\n<li>Operates efficiently within a wide temperature range (-20&#8451; to 55&#8451;).</li>\n<li>Cycle life of &#8805; 6000 cycles at 25&#8451;.<br /><br /></li>\n</ul>\n</li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-023.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<h3><span>Technical Specifications:</span></h3>\n<ul>\n<li><span>Battery Chemistry:</span>&#160;LiFePO4</li>\n<li><span>Capacity:</span>&#160;120 Ah</li>\n<li><span>Energy:</span>&#160;6.14 kWh</li>\n<li><span>Rated DC Power:</span>&#160;Peak (2 mins, 25&#8451;) 150 kW</li>\n<li><span>Dimension (W/H/D):</span>&#160;510 mm&#160;<em>740 mm&#160;</em>145 mm (without base)</li>\n<li><span>Weight:</span>&#160;Approx. 58 kg</li>\n<li><span>Operating Temperature:</span>&#160;Charge: 0&#65374;55&#8451; / Discharge: -20&#8451;&#65374;55&#8451;</li>\n<li><span>Storage Temperature:</span>&#160;0&#8451;&#65374;35&#8451;</li>\n<li><span>Humidity:</span>&#160;5%&#65374;95%</li>\n<li><span>Altitude:</span>&#160;&#8804; 2000 m</li>\n<li><span>Warranty Period:</span>&#160;10 years</li>\n<li><span>Energy Throughput:</span>&#160;20 MWh @ 70% EOL</li>\n<li><span>Certifications:</span>&#160;UN38.3, IEC62619, CE, CEI 0-21, VDE2510-50</li>\n</ul>\n<h3><span>Accessories Included:</span></h3>\n<ul>\n<li><span>Battery Hanging Board (RW-M6.1-B-Hboard):</span>&#160;For wall mounting.</li>\n<li><span>Hybrid Inverter Cable (RW-M6.1-B-PCable1500):</span>&#160;1500mm length, waterproof terminals.</li>\n<li><span>Battery Parallel Cable (RW-M6.1-B-BCable300):</span>&#160;300mm length, waterproof terminals.</li>\n<li><span>Fixed Supports (RW-M6.1-B-Fixed support):</span>&#160;For securing the battery when floor-mounted.</li>\n</ul>', '<span>The Deye RW-M 6.1-B LFP battery is the perfect solution for those seeking a reliable, flexible, and eco-friendly energy storage system with advanced features for optimal performance and safety.</span>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(591, '<table border=\"0\" cellspacing=\"0\" cellpadding=\"8\" style=\"width: 100%;\">\n<tbody>\n<tr>\n<td style=\"width: 30%;\">Model</td>\n<td>SE-G5.1 Pro-B</td>\n</tr>\n<tr>\n<td>Battery Chemistry</td>\n<td>LiFePO4</td>\n</tr>\n<tr>\n<td>Capacity (Ah)</td>\n<td>100</td>\n</tr>\n<tr>\n<td>Scalability</td>\n<td>Max. 64 pcs pack (327 kWh) in parallel (Max. 32 pcs without external setup)</td>\n</tr>\n<tr>\n<td>Nominal Voltage (V)</td>\n<td>51.2</td>\n</tr>\n<tr>\n<td>Operating Voltage (V)</td>\n<td>43.2 &#126; 57.6</td>\n</tr>\n<tr>\n<td>Energy (kWh)</td>\n<td>5.12</td>\n</tr>\n<tr>\n<td>Usable Energy (kWh) [1]</td>\n<td>4.61</td>\n</tr>\n<tr>\n<td>Charge/Discharge Current (A) - Recommend [2]</td>\n<td>50</td>\n</tr>\n<tr>\n<td>Charge/Discharge Current (A) - Max. [2]</td>\n<td>100</td>\n</tr>\n<tr>\n<td>Peak (2 mins, 25&#8451;)</td>\n<td>150</td>\n</tr>\n<tr><th colspan=\"2\" style=\"text-align: left;\">\n<p></p>\n<p>Other Parameter</p>\n</th></tr>\n<tr>\n<td style=\"text-align: left;\">Recommended Depth of Discharge</td>\n<td>90%</td>\n</tr>\n<tr>\n<td>Dimension (W/H/D, mm)</td>\n<td>445 &#215; 133 &#215; 540</td>\n</tr>\n<tr>\n<td>Weight Approximate (kg)</td>\n<td>45</td>\n</tr>\n<tr>\n<td>Master LED Indicator</td>\n<td>5 LED (SOC: 20%&#126;100%)<br /> 3 LED (working, alarming, protecting)</td>\n</tr>\n<tr>\n<td>IP Rating of Enclosure</td>\n<td>IP20</td>\n</tr>\n<tr>\n<td>Working Temperature</td>\n<td>Charge: 0&#8451;&#65374;55&#8451;<br />Discharge: -20&#8451;&#65374;55&#8451;</td>\n</tr>\n<tr>\n<td>Storage Temperature</td>\n<td>0&#8451;&#65374;35&#8451;</td>\n</tr>\n<tr>\n<td>Humidity</td>\n<td>5% &#126; 95%</td>\n</tr>\n<tr>\n<td>Altitude</td>\n<td>&#8804; 2000 m</td>\n</tr>\n<tr>\n<td>Cycle Life</td>\n<td>&#8805;6000 (25&#176;C &#177;2&#176;C, 0.5C/0.5C, 90% DOD, 70% EOL)</td>\n</tr>\n<tr>\n<td>Installation</td>\n<td>Wall-Mounted, Floor-Mounted, Rack-Mounted (19-inch standard cabinet, cabinet depth &#8805;600 mm)</td>\n</tr>\n<tr>\n<td>Communication Port</td>\n<td>CAN2.0, RS485</td>\n</tr>\n<tr>\n<td>Certification</td>\n<td>UN38.3, IEC62619, CE, UKCA, VDE2510-50, FCC, UL1973, UL9540A, REACH, ROHS</td>\n</tr>\n</tbody>\n</table>', 2, 'SE-G5.1-Pro-B (EU) [5,12 kWh] Battery Storage System | ESS', '<p data-start=\"96\" data-end=\"627\"><span>The Deye RW-M 6.1-B is a state-of-the-art Lithium Iron Phosphate (LFP) battery designed to provide reliable, safe, and high-efficiency power storage solutions for both residential and commercial applications. With its advanced Battery Management System (BMS) and modular design, this battery ensures long lifespan, high power density, and complete protection for your energy storage needs.</span></p>\n<p data-start=\"96\" data-end=\"627\"></p>\n<h3 data-start=\"449\" data-end=\"466\">Key Features:</h3>\n<ul style=\"list-style-type: disc;\">\n<li><span><strong>Safer: </strong><br />Our cobalt-free LFP battery offers enhanced safety and a long lifespan, with high efficiency and power density. The intelligent Battery Management System (BMS) provides complete protection for your peace of mind.</span></li>\n</ul>\n<ul data-start=\"468\" data-end=\"1984\">\n<li><span><strong>Reliable: </strong><br />The SE-G5.1 Pro-B supports high discharge power and operates in a wide temperature range of -20&#176;C to 55&#176;C. With an IP20 rating and natural cooling, this battery is built to last.<br /></span><span></span></li>\n<li><span><strong>Flexible: </strong><br />The modular design allows for easy expansion, with a maximum of 64 units in parallel, providing up to 327 kWh of storage capacity. This flexibility makes it ideal for various applications and energy needs.<br /><br /></span></li>\n<li><span><strong>Convenient: </strong><br />The battery modules feature auto-networking for easy maintenance, and support remote monitoring and firmware upgrades via USB drive, ensuring a hassle-free experience.<br /><br /></span></li>\n<li><span><strong>Eco-Friendly: </strong><br />We use environmentally friendly materials, ensuring the entire module is non-toxic and pollution-free, promoting a greener future.<br /><br /></span></li>\n<li><span><strong>Three Mounting Methods: </strong><br />With a 19-inch standard design, the SE-G5.1 Pro-B supports rack-mounting, wall-mounting, and floor-mounting, saving valuable installation space and adapting to your specific requirements.<br /><br /></span></li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-024.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<h3><span>Technical Specifications:</span></h3>\n<ul class=\"list-outside list-disc pl-8\">\n<li><span>Battery Chemistry: LiFePO4</span></li>\n<li><span>Capacity: 100 Ah</span></li>\n<li><span>Nominal Voltage: 51.2 V</span></li>\n<li><span>Nominal Energy: 5.12 kWh</span></li>\n<li><span>Usable Energy: 4.6 kWh</span></li>\n<li><span>Dimensions: 440 x 133 x 540 mm</span></li>\n<li><span>Weight: Approximately 45 kg</span></li>\n<li><span>Warranty Period: 10 years</span></li>\n</ul>\n<p><span>Invest in the Deye SE-G5.1 Pro-B LFP Battery for a safe, reliable, and flexible energy storage solution that adapts to your needs and contributes to a more sustainable future.</span></p>', '<p><span class=\"animate-in fade-in-25 duration-700\">&#160;The Deye SE-G5.1 Pro-B is a cutting-edge lithium iron phosphate (LFP) battery designed for safe, reliable, and flexible energy storage solutions.</span><span class=\"animate-in fade-in-25 duration-700\">&#160;This</span><span class=\"animate-in fade-in-25 duration-700\">&#160;modular battery</span><span class=\"animate-in fade-in-25 duration-700\">&#160;system is perfect</span><span class=\"animate-in fade-in-25 duration-700\">&#160;for both residential</span><span class=\"animate-in fade-in-25 duration-700\">&#160;and commercial</span><span class=\"animate-in fade-in-25 duration-700\">&#160;applications</span><span class=\"animate-in fade-in-25 duration-700\">, allowing you</span><span class=\"animate-in fade-in-25 duration-700\">&#160;to increase your</span><span class=\"animate-in fade-in-25 duration-700\">&#160;self-consumption ratio</span><span class=\"animate-in fade-in-25 duration-700\">&#160;and optimize</span><span class=\"animate-in fade-in-25 duration-700\">&#160;your energy usage</span><span class=\"animate-in fade-in-25 duration-700\">.</span></p>\n<strong class=\"font-serif text-lg font-medium\">Safety:</strong>&#160;LFP chemistry + advanced BMS monitoring<br /><strong class=\"font-serif text-lg font-medium\">Power:</strong>&#160;51.2V | 100Ah | 5.12kWh output<br /><strong class=\"font-serif text-lg font-medium\">Scalability:</strong>&#160;Up to 64 units (327kWh total)<br /><strong class=\"font-serif text-lg font-medium\">Temperature Range:</strong>&#160;-20&#176;C to 55&#176;C<br /><strong class=\"font-serif text-lg font-medium\">Protection:</strong>&#160;IP20-rated enclosure<br /><strong class=\"font-serif text-lg font-medium\">Mounting:</strong>&#160;Wall, floor, or rack options<br /><span><strong>Suitable Deye Inverter Model:</strong></span>\n<ul>\n<li><span>SUN-3.6/5/6/7/7.6/8/10K-SG05LP1-EU-SM2-P</span></li>\n<li><span>SUN-3.6/5/6/7/7.6/8/10K-SG05LP1-EU-AM2-P</span></li>\n<li><span>SUN-5/6/7.6/8K-SG02LP2-US-AM2</span></li>\n<li><span>SUN-10/12K-SG02LP2-US-AM3</span></li>\n<li><span>SUN-7.6/8K-SG02LP1-EU-AM2-P</span></li>\n<li><span>SUN-10/12K-SG02LP1-EU-AM3-P</span></li>\n<li><span>SUN-12/14/16/18K-SG01LP1-EU-AM3-P</span></li>\n<li><span>SUN-5/6/8/10/12K-SG04LP3-EU-AM2-P</span></li>\n<li><span>SUN-3/4/5/6/8/10/12K-SG05LP3-EU-SM2</span></li>\n<li><span>SUN-14/15/16/18/20K-SG05LP3-EU-SM2</span></li>\n</ul>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', '');
INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(592, '<div>\n<table border=\"0\" cellpadding=\"8\" style=\"width: 100%;\">\n<tbody>\n<tr style=\"background-color: black; color: white;\"><th style=\"width: 30%; text-align: left;\">Main Parameter&#160;</th>\n<td><strong>GB-L-Pro</strong></td>\n</tr>\n<tr><th style=\"width: 30%; text-align: left;\">Cell Chemistry</th>\n<td>LiFePO&#8324;</td>\n</tr>\n<tr><th style=\"text-align: left;\">Module Model</th>\n<td>GB-L-PACK 4.0</td>\n</tr>\n<tr><th style=\"text-align: left;\">Module Energy (kWh)</th>\n<td>4</td>\n</tr>\n<tr><th style=\"text-align: left;\">Module Nominal Voltage (V)</th>\n<td>102.4</td>\n</tr>\n<tr><th style=\"text-align: left;\">Module Capacity (Ah)</th>\n<td>40</td>\n</tr>\n<tr><th style=\"text-align: left;\">Battery System Models</th>\n<td>GB-L8 PRO, GB-L12 PRO, GB-L16 PRO, GB-L20 PRO, GB-L24 PRO</td>\n</tr>\n<tr><th style=\"text-align: left;\">Battery Module Qty in Series (Optional)</th>\n<td>2, 3, 4, 5, 6</td>\n</tr>\n<tr><th style=\"text-align: left;\">System Nominal Voltage (V)</th>\n<td>204.8, 307.2, 409.6, 512, 614.4</td>\n</tr>\n<tr><th style=\"text-align: left;\">System Operating Voltage (V)</th>\n<td>166.4 &#126; 700</td>\n</tr>\n<tr><th style=\"text-align: left;\">System Energy (kWh)</th>\n<td>8, 12, 16, 20, 24</td>\n</tr>\n<tr><th style=\"text-align: left;\">System Usable Energy (kWh)</th>\n<td>7.2, 10.8, 14.4, 18, 21.6</td>\n</tr>\n<tr><th style=\"text-align: left;\">Charge / Discharge Current (A)</th>\n<td>Recommend: 20, Nominal: 40, Peak (2 mins, 25&#176;C): 50</td>\n</tr>\n<tr><th style=\"text-align: left;\">Working Temperature (&#176;C)</th>\n<td>Charge: -10 &#126; 55 / Discharge: -20 &#126; 55</td>\n</tr>\n<tr><th style=\"text-align: left;\">LCD Display</th>\n<td>SOC%, Power, Total Voltage</td>\n</tr>\n<tr><th style=\"text-align: left;\">Communication Port</th>\n<td>CAN2.0, RS485</td>\n</tr>\n<tr><th style=\"text-align: left;\">Humidity</th>\n<td>5% &#126; 90%</td>\n</tr>\n<tr><th style=\"text-align: left;\">Altitude</th>\n<td>&#8804;2000m</td>\n</tr>\n<tr><th style=\"text-align: left;\">IP Rating of Enclosure</th>\n<td>IP65</td>\n</tr>\n<tr><th style=\"text-align: left;\">Storage Temperature (&#176;C)</th>\n<td>0 &#126; 35</td>\n</tr>\n<tr><th style=\"text-align: left;\">Dimensions (W &#215; D &#215; H, mm)</th>\n<td>540&#215;385&#215;650 (GB-L8 PRO)<br /> 540&#215;385&#215;870 (GB-L12 PRO)<br /> 540&#215;385&#215;1090 (GB-L16 PRO)<br /> 540&#215;385&#215;1310 (GB-L20 PRO)<br /> 540&#215;385&#215;1530 (GB-L24 PRO)</td>\n</tr>\n<tr><th style=\"text-align: left;\">Weight (kg)</th>\n<td>97, 136, 175, 214, 253</td>\n</tr>\n<tr><th style=\"text-align: left;\">Installation Location</th>\n<td>Floor Mount</td>\n</tr>\n<tr><th style=\"text-align: left;\">Recommended Depth of Discharge</th>\n<td>0.9</td>\n</tr>\n<tr><th style=\"text-align: left;\">Cycle Life</th>\n<td>&#8805;6000 (25&#177;2&#176;C, 0.5C / 0.5C, EOL70%)</td>\n</tr>\n<tr><th style=\"text-align: left;\">Warranty</th>\n<td>10 years</td>\n</tr>\n<tr><th style=\"text-align: left;\">Certification</th>\n<td>CE, IEC62619, VDE 2510-50, UN38.3</td>\n</tr>\n</tbody>\n</table>\n</div>\n<hr />\n<div>\n<table border=\"0\" cellpadding=\"8\" style=\"width: 100%;\">\n<tbody>\n<tr style=\"background-color: black; color: white;\"><th style=\"width: 30%; text-align: left;\">Control Box / PDU</th>\n<td><strong>GB-LBS-PRO</strong></td>\n</tr>\n<tr><th style=\"width: 30%; text-align: left;\">Operating Voltage</th>\n<td>120 &#126; 750 Vdc</td>\n</tr>\n<tr><th style=\"text-align: left;\">Nominal Charge / Discharge Current</th>\n<td>40 A</td>\n</tr>\n<tr><th style=\"text-align: left;\">Max Charge / Discharge Current</th>\n<td>50 A</td>\n</tr>\n<tr><th style=\"text-align: left;\">Operating Temperature Range</th>\n<td>-20 &#126; 65 &#176;C</td>\n</tr>\n<tr><th style=\"text-align: left;\">Ingress Protection</th>\n<td>IP65</td>\n</tr>\n<tr><th style=\"text-align: left;\">Dimension (W &#215; D &#215; H)</th>\n<td>540 &#215; 385 &#215; 110 mm</td>\n</tr>\n<tr><th style=\"text-align: left;\">Weight</th>\n<td>Approx. 12 kg</td>\n</tr>\n</tbody>\n</table>\n</div>\n<hr />\n<div>\n<table border=\"0\" cellpadding=\"8\" style=\"width: 100%;\">\n<tbody>\n<tr style=\"background-color: black; color: white;\"><th style=\"width: 30%; text-align: left;\">Module Battery</th>\n<td><strong>GB-LM4.0-PRO</strong></td>\n</tr>\n<tr><th style=\"width: 30%; text-align: left;\">Battery Type</th>\n<td>LiFePO&#8324; (LFP)</td>\n</tr>\n<tr><th style=\"text-align: left;\">Nominal Voltage</th>\n<td>102.4&#8239;Vdc</td>\n</tr>\n<tr><th style=\"text-align: left;\">Rated Capacity</th>\n<td>40&#8239;Ah</td>\n</tr>\n<tr><th style=\"text-align: left;\">Rated Energy</th>\n<td>4&#8239;kWh</td>\n</tr>\n<tr><th style=\"text-align: left;\">Nominal Charge/Discharge Current</th>\n<td>40&#8239;A</td>\n</tr>\n<tr><th style=\"text-align: left;\">Peak Discharge Current</th>\n<td>50&#8239;A</td>\n</tr>\n<tr><th style=\"text-align: left;\">Charge Temperature</th>\n<td>-20&#8451;&#65374;55&#8451;</td>\n</tr>\n<tr><th style=\"text-align: left;\">Discharge Temperature</th>\n<td>-20&#8451;&#65374;55&#8451;</td>\n</tr>\n<tr><th style=\"text-align: left;\">Storage Temperature</th>\n<td>0&#8451;&#65374;35&#8451;</td>\n</tr>\n<tr><th style=\"text-align: left;\">Ingress Protection</th>\n<td>IP65</td>\n</tr>\n<tr><th style=\"text-align: left;\">Dimension (W &#215; D &#215; H)</th>\n<td>540 &#215; 385 &#215; 220&#8239;mm</td>\n</tr>\n<tr><th style=\"text-align: left;\">Weight</th>\n<td>Approx. 40.5&#8239;kg</td>\n</tr>\n</tbody>\n</table>\n</div>\n<hr />\n<div>\n<table border=\"0\" cellpadding=\"8\" style=\"width: 100%;\">\n<tbody>\n<tr style=\"background-color: black; color: white;\"><th style=\"width: 30%; text-align: left;\">Module Base</th>\n<td><strong>GB-LBase</strong></td>\n</tr>\n<tr><th style=\"width: 30%; text-align: left;\">Component</th>\n<td>Battery Module Base</td>\n</tr>\n<tr><th style=\"text-align: left;\">Dimension (W &#215; D &#215; H)</th>\n<td>540 &#215; 385 &#215; 100&#8239;mm</td>\n</tr>\n<tr><th style=\"text-align: left;\">Weight</th>\n<td>Approx. 7&#8239;kg</td>\n</tr>\n</tbody>\n</table>\n</div>', 2, 'GB-L PRO | GB-LM4.0-PRO [4 kWh] Battery Storage System | ESS', '<p>The <strong data-start=\"297\" data-end=\"313\">GB-LM4.0-PRO</strong> is a high-performance LiFePO&#8324; (LFP) battery module designed exclusively as part of the <strong data-start=\"401\" data-end=\"422\">GB-L Pro (EU) Set</strong>. With a compact footprint and robust protection (IP65-rated), this module is ideal for demanding residential and commercial energy storage needs. It delivers reliable, safe, and long-lasting energy with a total capacity of 4 kWh, making it a perfect fit for scalable systems.</p>\n<h3 data-start=\"449\" data-end=\"466\">Key Features:</h3>\n<ul data-start=\"468\" data-end=\"1984\">\n<li data-start=\"727\" data-end=\"813\">\n<p data-start=\"729\" data-end=\"813\">Lithium Iron Phosphate (LiFePO&#8324;) chemistry ensures high safety and long cycle life</p>\n</li>\n<li data-start=\"814\" data-end=\"857\">\n<p data-start=\"816\" data-end=\"857\">4 kWh rated energy with a 40Ah capacity</p>\n</li>\n<li data-start=\"858\" data-end=\"899\">\n<p data-start=\"860\" data-end=\"899\">Compact and lightweight: only 40.5 kg</p>\n</li>\n<li data-start=\"900\" data-end=\"954\">\n<p data-start=\"902\" data-end=\"954\">IP65-rated enclosure for dust and water resistance</p>\n</li>\n<li data-start=\"955\" data-end=\"1008\">\n<p data-start=\"957\" data-end=\"1008\">Wide operating temperature range (-20&#176;C to +55&#176;C)</p>\n</li>\n<li data-start=\"1009\" data-end=\"1042\">\n<p data-start=\"1011\" data-end=\"1042\">Peak discharge current of 50A</p>\n</li>\n<li data-start=\"1043\" data-end=\"1099\">\n<p data-start=\"1045\" data-end=\"1099\">Part of the GB-L Pro (EU) Set &#8211; modular and scalable</p>\n</li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-025.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<p>The Deye GB-L-PRO is a cutting-edge residential energy storage system (ESS). Designed meticulously to cater to the modern needs of energy consumers, the GB-L-PRO offers a reliable, efficient, and intelligent solution for those looking to harness the power of renewable energy sources effectively. This high-voltage battery system is engineered to provide unparalleled performance, safety, and adaptability, making it the perfect choice for both residential and commercial applications.</p>\n<h3 id=\"key-features-\">Deye GB-L-PRO SET:</h3>\n<ul>\n<li><span>Safety Assurance</span>: The GB-L-PRO is equipped with built-in explosion relief devices and fire protection mechanisms that quickly isolate fire sources, ensuring user safety.</li>\n<li><span>High-Efficiency Design</span>: Utilizing a high-voltage stack configuration with modules connected in series without cable connections, the system maximizes operational efficiency.</li>\n<li><span>Thermal Management</span>: Continuous temperature monitoring of critical components, including cells and power plug-ins, provides robust thermal management for enhanced performance.</li>\n<li><span>Wide Operating Temperature Range</span>: The system can operate in temperatures ranging from -20&#176;C to 55&#176;C, with optional heating functionality to address low-temperature scenarios.</li>\n<li><span>Environmentally Friendly</span>: Rated at IP65 for dust and water resistance and with an anti-corrosion grade of &#8805;C2, the GB-L-PRO embodies ecological responsibility with its environmentally friendly battery technology.</li>\n<li><span>Intelligent Monitoring</span>: Features remote firmware upgrades, real-time battery status notifications, and an LCD display to provide vital information including state of charge (SOC), power levels, and total voltage.</li>\n</ul>\n<h3 id=\"technical-specifications-\">Technical Specifications:</h3>\n<ul>\n<li><span>Cell Chemistry</span>: Lithium Iron Phosphate (LiFePO4)</li>\n<li><span>Module Capacity</span>: 4 kWh</li>\n<li><span>System Configurations</span>: Available in various models including GB-L8 PRO, GB-L12 PRO, GB-L16 PRO, GB-L20 PRO, and GB-L24 PRO, facilitating different energy requirements.</li>\n<li><span>Nominal Voltage</span>: Ranges from 204.8V to 614.4V, depending on the model.</li>\n<li><span>Usable Energy</span>: Varies from 8 kWh to 24 kWh based on configuration.</li>\n<li><span>Charge/Discharge Current</span>: Nominal current of 40A, with a peak discharge capacity of 50A for short bursts.</li>\n<li><span>Cycle Life</span>: Rated for over 6000 cycles at 25 &#177; 2&#176;C, maintaining 70% capacity at end-of-life.</li>\n<li><span>Warranty</span>: Comprehensive 10-year warranty covering specified conditions.</li>\n</ul>\n<h3>Physical Dimensions and Installation</h3>\n<p>The physical attributes of the GB-L-PRO are thoughtfully designed to facilitate seamless installation and integration into various spaces:</p>\n<ul>\n<li><span>Dimensions</span>: The system is available in several sizes, ranging from compact models measuring 540 &#215; 385 &#215; 650 mm to larger models measuring 540 &#215; 385 &#215; 1530 mm, accommodating different installation needs and spatial constraints.</li>\n<li><span>Weight</span>: Depending on the configuration, weights range from 97 kg to 253 kg, ensuring structural integrity and stability during operation.</li>\n<li><span>Installation</span>: The battery system is specifically designed for floor mounting, making it suitable for both residential and commercial applications.</li>\n</ul>\n<p>Deye GB-L-PRO is not just a battery system; it represents a comprehensive energy storage solution that combines reliability, efficiency, safety, and advanced technology. It is the ideal choice for those seeking to enhance their energy management, reduce dependency on grid power, and contribute to a more sustainable future. Experience the power of intelligent energy storage with the Deye GB-L-PRO for energy management and sustainability.</p>', '<p>The <strong data-start=\"98\" data-end=\"114\" data-is-only-node=\"\">GB-LM4.0-PRO</strong> is a compact and efficient 4&#8239;kWh LiFePO&#8324; battery module designed for high safety, durability, and performance. Ideal for modular energy storage systems, it offers IP65 protection, a wide temperature range, and reliable output, making it a perfect fit for residential and commercial use as part of the GB-L Pro (EU) Set.</p>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(593, '<div>\n<table border=\"0\" cellpadding=\"8\" style=\"width: 100%;\">\n<tbody>\n<tr style=\"background-color: black; color: white;\"><th style=\"width: 30%; text-align: left;\">Main Parameter&#160;</th>\n<td><strong>GB-L-Pro</strong></td>\n</tr>\n<tr><th style=\"width: 30%; text-align: left;\">Cell Chemistry</th>\n<td>LiFePO&#8324;</td>\n</tr>\n<tr><th style=\"text-align: left;\">Module Model</th>\n<td>GB-L-PACK 4.0</td>\n</tr>\n<tr><th style=\"text-align: left;\">Module Energy (kWh)</th>\n<td>4</td>\n</tr>\n<tr><th style=\"text-align: left;\">Module Nominal Voltage (V)</th>\n<td>102.4</td>\n</tr>\n<tr><th style=\"text-align: left;\">Module Capacity (Ah)</th>\n<td>40</td>\n</tr>\n<tr><th style=\"text-align: left;\">Battery System Models</th>\n<td>GB-L8 PRO, GB-L12 PRO, GB-L16 PRO, GB-L20 PRO, GB-L24 PRO</td>\n</tr>\n<tr><th style=\"text-align: left;\">Battery Module Qty in Series (Optional)</th>\n<td>2, 3, 4, 5, 6</td>\n</tr>\n<tr><th style=\"text-align: left;\">System Nominal Voltage (V)</th>\n<td>204.8, 307.2, 409.6, 512, 614.4</td>\n</tr>\n<tr><th style=\"text-align: left;\">System Operating Voltage (V)</th>\n<td>166.4 &#126; 700</td>\n</tr>\n<tr><th style=\"text-align: left;\">System Energy (kWh)</th>\n<td>8, 12, 16, 20, 24</td>\n</tr>\n<tr><th style=\"text-align: left;\">System Usable Energy (kWh)</th>\n<td>7.2, 10.8, 14.4, 18, 21.6</td>\n</tr>\n<tr><th style=\"text-align: left;\">Charge / Discharge Current (A)</th>\n<td>Recommend: 20, Nominal: 40, Peak (2 mins, 25&#176;C): 50</td>\n</tr>\n<tr><th style=\"text-align: left;\">Working Temperature (&#176;C)</th>\n<td>Charge: -10 &#126; 55 / Discharge: -20 &#126; 55</td>\n</tr>\n<tr><th style=\"text-align: left;\">LCD Display</th>\n<td>SOC%, Power, Total Voltage</td>\n</tr>\n<tr><th style=\"text-align: left;\">Communication Port</th>\n<td>CAN2.0, RS485</td>\n</tr>\n<tr><th style=\"text-align: left;\">Humidity</th>\n<td>5% &#126; 90%</td>\n</tr>\n<tr><th style=\"text-align: left;\">Altitude</th>\n<td>&#8804;2000m</td>\n</tr>\n<tr><th style=\"text-align: left;\">IP Rating of Enclosure</th>\n<td>IP65</td>\n</tr>\n<tr><th style=\"text-align: left;\">Storage Temperature (&#176;C)</th>\n<td>0 &#126; 35</td>\n</tr>\n<tr><th style=\"text-align: left;\">Dimensions (W &#215; D &#215; H, mm)</th>\n<td>540&#215;385&#215;650 (GB-L8 PRO)<br /> 540&#215;385&#215;870 (GB-L12 PRO)<br /> 540&#215;385&#215;1090 (GB-L16 PRO)<br /> 540&#215;385&#215;1310 (GB-L20 PRO)<br /> 540&#215;385&#215;1530 (GB-L24 PRO)</td>\n</tr>\n<tr><th style=\"text-align: left;\">Weight (kg)</th>\n<td>97, 136, 175, 214, 253</td>\n</tr>\n<tr><th style=\"text-align: left;\">Installation Location</th>\n<td>Floor Mount</td>\n</tr>\n<tr><th style=\"text-align: left;\">Recommended Depth of Discharge</th>\n<td>0.9</td>\n</tr>\n<tr><th style=\"text-align: left;\">Cycle Life</th>\n<td>&#8805;6000 (25&#177;2&#176;C, 0.5C / 0.5C, EOL70%)</td>\n</tr>\n<tr><th style=\"text-align: left;\">Warranty</th>\n<td>10 years</td>\n</tr>\n<tr><th style=\"text-align: left;\">Certification</th>\n<td>CE, IEC62619, VDE 2510-50, UN38.3</td>\n</tr>\n</tbody>\n</table>\n</div>\n<hr />\n<div>\n<table border=\"0\" cellpadding=\"8\" style=\"width: 100%;\">\n<tbody>\n<tr style=\"background-color: black; color: white;\"><th style=\"width: 30%; text-align: left;\">Control Box / PDU</th>\n<td><strong>GB-LBS-PRO</strong></td>\n</tr>\n<tr><th style=\"width: 30%; text-align: left;\">Operating Voltage</th>\n<td>120 &#126; 750 Vdc</td>\n</tr>\n<tr><th style=\"text-align: left;\">Nominal Charge / Discharge Current</th>\n<td>40 A</td>\n</tr>\n<tr><th style=\"text-align: left;\">Max Charge / Discharge Current</th>\n<td>50 A</td>\n</tr>\n<tr><th style=\"text-align: left;\">Operating Temperature Range</th>\n<td>-20 &#126; 65 &#176;C</td>\n</tr>\n<tr><th style=\"text-align: left;\">Ingress Protection</th>\n<td>IP65</td>\n</tr>\n<tr><th style=\"text-align: left;\">Dimension (W &#215; D &#215; H)</th>\n<td>540 &#215; 385 &#215; 110 mm</td>\n</tr>\n<tr><th style=\"text-align: left;\">Weight</th>\n<td>Approx. 12 kg</td>\n</tr>\n</tbody>\n</table>\n</div>\n<hr />\n<div>\n<table border=\"0\" cellpadding=\"8\" style=\"width: 100%;\">\n<tbody>\n<tr style=\"background-color: black; color: white;\"><th style=\"width: 30%; text-align: left;\">Module Battery</th>\n<td><strong>GB-LM4.0-PRO</strong></td>\n</tr>\n<tr><th style=\"width: 30%; text-align: left;\">Battery Type</th>\n<td>LiFePO&#8324; (LFP)</td>\n</tr>\n<tr><th style=\"text-align: left;\">Nominal Voltage</th>\n<td>102.4&#8239;Vdc</td>\n</tr>\n<tr><th style=\"text-align: left;\">Rated Capacity</th>\n<td>40&#8239;Ah</td>\n</tr>\n<tr><th style=\"text-align: left;\">Rated Energy</th>\n<td>4&#8239;kWh</td>\n</tr>\n<tr><th style=\"text-align: left;\">Nominal Charge/Discharge Current</th>\n<td>40&#8239;A</td>\n</tr>\n<tr><th style=\"text-align: left;\">Peak Discharge Current</th>\n<td>50&#8239;A</td>\n</tr>\n<tr><th style=\"text-align: left;\">Charge Temperature</th>\n<td>-20&#8451;&#65374;55&#8451;</td>\n</tr>\n<tr><th style=\"text-align: left;\">Discharge Temperature</th>\n<td>-20&#8451;&#65374;55&#8451;</td>\n</tr>\n<tr><th style=\"text-align: left;\">Storage Temperature</th>\n<td>0&#8451;&#65374;35&#8451;</td>\n</tr>\n<tr><th style=\"text-align: left;\">Ingress Protection</th>\n<td>IP65</td>\n</tr>\n<tr><th style=\"text-align: left;\">Dimension (W &#215; D &#215; H)</th>\n<td>540 &#215; 385 &#215; 220&#8239;mm</td>\n</tr>\n<tr><th style=\"text-align: left;\">Weight</th>\n<td>Approx. 40.5&#8239;kg</td>\n</tr>\n</tbody>\n</table>\n</div>\n<hr />\n<div>\n<table border=\"0\" cellpadding=\"8\" style=\"width: 100%;\">\n<tbody>\n<tr style=\"background-color: black; color: white;\"><th style=\"width: 30%; text-align: left;\">Module Base</th>\n<td><strong>GB-LBase</strong></td>\n</tr>\n<tr><th style=\"width: 30%; text-align: left;\">Component</th>\n<td>Battery Module Base</td>\n</tr>\n<tr><th style=\"text-align: left;\">Dimension (W &#215; D &#215; H)</th>\n<td>540 &#215; 385 &#215; 100&#8239;mm</td>\n</tr>\n<tr><th style=\"text-align: left;\">Weight</th>\n<td>Approx. 7&#8239;kg</td>\n</tr>\n</tbody>\n</table>\n</div>', 2, 'GB-L PRO | GB-LBS-PRO+GB-LBase | ESS', '<p>The <strong data-start=\"278\" data-end=\"292\">GB-LBS-PRO</strong> control box and the <strong data-start=\"313\" data-end=\"325\">GB-LBase</strong> mounting platform together form the foundation of a modular, high-performance lithium battery energy system. Designed with flexibility, safety, and space efficiency in mind, this combination ensures stable operation, simple installation, and optimal performance in both residential and commercial energy storage applications. Whether deployed as part of a scalable battery rack or a standalone unit, the GB-LBS-PRO and GB-LBase provide the essential structure and intelligence required to manage and support the energy modules above.</p>\n<h3 data-start=\"449\" data-end=\"466\">Key Features:</h3>\n<ul data-start=\"468\" data-end=\"1984\">\n<li data-start=\"888\" data-end=\"1076\">\n<p data-start=\"890\" data-end=\"1076\"><strong data-start=\"890\" data-end=\"914\">Robust Control Unit:</strong><br data-start=\"914\" data-end=\"917\" /> The GB-LBS-PRO operates across a wide voltage range (120 &#8211; 750 Vdc), managing charge/discharge processes with up to 50 A for peak performance and efficiency.</p>\n</li>\n<li data-start=\"1078\" data-end=\"1283\">\n<p data-start=\"1080\" data-end=\"1283\"><strong data-start=\"1080\" data-end=\"1114\">Intelligent System Management:</strong><br data-start=\"1114\" data-end=\"1117\" /> Integrated with advanced protection features, real-time monitoring, and multiple communication interfaces (CAN2.0, RS485), ensuring smart system control and safety.</p>\n</li>\n<li data-start=\"1285\" data-end=\"1470\">\n<p data-start=\"1287\" data-end=\"1470\"><strong data-start=\"1287\" data-end=\"1313\">IP65-Rated Protection:</strong><br data-start=\"1313\" data-end=\"1316\" /> Both the GB-LBS-PRO and GB-LBase are built with IP65 ingress protection, making them suitable for challenging environments with dust and water exposure.</p>\n</li>\n<li data-start=\"1472\" data-end=\"1653\">\n<p data-start=\"1474\" data-end=\"1653\"><strong data-start=\"1474\" data-end=\"1505\">Compact and Modular Design:</strong><br data-start=\"1505\" data-end=\"1508\" /> The GB-LBase serves as a durable and space-saving foundation, perfectly supporting battery modules while simplifying installation and stacking.</p>\n</li>\n<li data-start=\"1655\" data-end=\"1843\">\n<p data-start=\"1657\" data-end=\"1843\"><strong data-start=\"1657\" data-end=\"1694\">Thermal and Mechanical Stability:</strong><br data-start=\"1694\" data-end=\"1697\" /> The GB-LBS-PRO operates in harsh temperature conditions (-20&#176;C to +65&#176;C), and the GB-LBase provides structural integrity even under heavy loads.</p>\n</li>\n<li data-start=\"1845\" data-end=\"2053\">\n<p data-start=\"1847\" data-end=\"2053\"><strong data-start=\"1847\" data-end=\"1878\">Space-Efficient Dimensions:</strong><br data-start=\"1878\" data-end=\"1881\" /> Designed to match battery module footprints precisely &#8212; GB-LBS-PRO: 540 &#215; 385 &#215; 110 mm, GB-LBase: 540 &#215; 385 &#215; 100 mm &#8212; ensuring a seamless and professional system layout.</p>\n<p data-start=\"729\" data-end=\"813\"></p>\n</li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-025.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\n<p>The Deye GB-L-PRO is a cutting-edge residential energy storage system (ESS). Designed meticulously to cater to the modern needs of energy consumers, the GB-L-PRO offers a reliable, efficient, and intelligent solution for those looking to harness the power of renewable energy sources effectively. This high-voltage battery system is engineered to provide unparalleled performance, safety, and adaptability, making it the perfect choice for both residential and commercial applications.</p>\n<h3 id=\"key-features-\">Deye GB-L-PRO SET:</h3>\n<ul>\n<li><span>Safety Assurance</span>: The GB-L-PRO is equipped with built-in explosion relief devices and fire protection mechanisms that quickly isolate fire sources, ensuring user safety.</li>\n<li><span>High-Efficiency Design</span>: Utilizing a high-voltage stack configuration with modules connected in series without cable connections, the system maximizes operational efficiency.</li>\n<li><span>Thermal Management</span>: Continuous temperature monitoring of critical components, including cells and power plug-ins, provides robust thermal management for enhanced performance.</li>\n<li><span>Wide Operating Temperature Range</span>: The system can operate in temperatures ranging from -20&#176;C to 55&#176;C, with optional heating functionality to address low-temperature scenarios.</li>\n<li><span>Environmentally Friendly</span>: Rated at IP65 for dust and water resistance and with an anti-corrosion grade of &#8805;C2, the GB-L-PRO embodies ecological responsibility with its environmentally friendly battery technology.</li>\n<li><span>Intelligent Monitoring</span>: Features remote firmware upgrades, real-time battery status notifications, and an LCD display to provide vital information including state of charge (SOC), power levels, and total voltage.</li>\n</ul>\n<h3 id=\"technical-specifications-\">Technical Specifications:</h3>\n<ul>\n<li><span>Cell Chemistry</span>: Lithium Iron Phosphate (LiFePO4)</li>\n<li><span>Module Capacity</span>: 4 kWh</li>\n<li><span>System Configurations</span>: Available in various models including GB-L8 PRO, GB-L12 PRO, GB-L16 PRO, GB-L20 PRO, and GB-L24 PRO, facilitating different energy requirements.</li>\n<li><span>Nominal Voltage</span>: Ranges from 204.8V to 614.4V, depending on the model.</li>\n<li><span>Usable Energy</span>: Varies from 8 kWh to 24 kWh based on configuration.</li>\n<li><span>Charge/Discharge Current</span>: Nominal current of 40A, with a peak discharge capacity of 50A for short bursts.</li>\n<li><span>Cycle Life</span>: Rated for over 6000 cycles at 25 &#177; 2&#176;C, maintaining 70% capacity at end-of-life.</li>\n<li><span>Warranty</span>: Comprehensive 10-year warranty covering specified conditions.</li>\n</ul>\n<h3>Physical Dimensions and Installation</h3>\n<p>The physical attributes of the GB-L-PRO are thoughtfully designed to facilitate seamless installation and integration into various spaces:</p>\n<ul>\n<li><span>Dimensions</span>: The system is available in several sizes, ranging from compact models measuring 540 &#215; 385 &#215; 650 mm to larger models measuring 540 &#215; 385 &#215; 1530 mm, accommodating different installation needs and spatial constraints.</li>\n<li><span>Weight</span>: Depending on the configuration, weights range from 97 kg to 253 kg, ensuring structural integrity and stability during operation.</li>\n<li><span>Installation</span>: The battery system is specifically designed for floor mounting, making it suitable for both residential and commercial applications.</li>\n</ul>\n<p>Deye GB-L-PRO is not just a battery system; it represents a comprehensive energy storage solution that combines reliability, efficiency, safety, and advanced technology. It is the ideal choice for those seeking to enhance their energy management, reduce dependency on grid power, and contribute to a more sustainable future. Experience the power of intelligent energy storage with the Deye GB-L-PRO for energy management and sustainability.</p>', '<p>The <strong data-start=\"162\" data-end=\"176\">GB-LBS-PRO</strong> control box and <strong data-start=\"193\" data-end=\"205\">GB-LBase</strong> platform form the essential base unit of the GB-L energy storage system. Together, they provide smart power management, robust protection, and a stable foundation for modular battery stacks&#8212;perfectly suited for scalable residential and commercial energy applications.</p>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(594, '<table border=\"0\" cellpadding=\"8\" cellspacing=\"0\" style=\"border-collapse: collapse; font-family: Arial, sans-serif; width: 100%;\">\n<tbody>\n<tr>\n<td style=\"width: 30%;\"><strong>Model</strong></td>\n<td>3U-HRack</td>\n</tr>\n<tr>\n<td><strong>Rack Type</strong></td>\n<td>Standard 19-inch</td>\n</tr>\n<tr>\n<td><strong>Battery Capacity</strong></td>\n<td>Holds 12 batteries + 1 HV control box</td>\n</tr>\n<tr>\n<td><strong>Dimensions (W&#215;D&#215;H)</strong></td>\n<td>589 &#215; 590 &#215; 2240 mm</td>\n</tr>\n<tr>\n<td><strong>Weight</strong></td>\n<td>Approx. 85 kg</td>\n</tr>\n<tr>\n<td><strong>Compatibility</strong></td>\n<td>Optional for BOS-G systems</td>\n</tr>\n</tbody>\n</table>', 2, 'BOS-G | 3U-HRack | Rack', '<p>The <strong data-start=\"136\" data-end=\"148\">3U-HRack</strong> is a high-capacity, standard 19-inch rack solution designed for seamless integration of up to 12 battery modules and 1 high-voltage battery cluster control box. With its optimized footprint and robust steel construction, this rack provides a compact and efficient platform for high-voltage energy storage systems. Engineered for reliability and scalability, the 3U-HRack is the ideal choice for commercial or industrial BOS-G energy setups.</p>\n<h3 data-start=\"449\" data-end=\"466\">Key Features:</h3>\n<ul data-start=\"468\" data-end=\"1984\">\n<li data-start=\"620\" data-end=\"698\">\n<p data-start=\"622\" data-end=\"698\"><strong data-start=\"622\" data-end=\"650\">Standard 19\" Rack Design</strong> &#8211; Compatible with industry-standard equipment</p>\n</li>\n<li data-start=\"699\" data-end=\"773\">\n<p data-start=\"701\" data-end=\"773\"><strong data-start=\"701\" data-end=\"718\">High Capacity</strong> &#8211; Accommodates 12 battery modules + 1 HV control box</p>\n</li>\n<li data-start=\"774\" data-end=\"833\">\n<p data-start=\"776\" data-end=\"833\"><strong data-start=\"776\" data-end=\"797\">Compact Footprint</strong> &#8211; Dimensions: 589 &#215; 590 &#215; 2240 mm</p>\n</li>\n<li data-start=\"834\" data-end=\"906\">\n<p data-start=\"836\" data-end=\"906\"><strong data-start=\"836\" data-end=\"853\">Durable Build</strong> &#8211; Approx. weight: 85 kg, built for stable stacking</p>\n</li>\n<li data-start=\"907\" data-end=\"987\">\n<p data-start=\"909\" data-end=\"987\"><strong data-start=\"909\" data-end=\"932\">Optimized for BOS-G</strong> &#8211; Optional enclosure for BOS-G system configurations</p>\n</li>\n<li data-start=\"988\" data-end=\"1067\">\n<p data-start=\"990\" data-end=\"1067\"><strong data-start=\"990\" data-end=\"1019\">Vertical Space Efficiency</strong> &#8211; Ideal for limited floor space installations</p>\n</li>\n<li data-start=\"1068\" data-end=\"1149\">\n<p data-start=\"1070\" data-end=\"1149\"><strong data-start=\"1070\" data-end=\"1090\">Easy Integration</strong> &#8211; Pre-configured layout for high-voltage energy clusters</p>\n</li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-018.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>', '<p><strong data-start=\"64\" data-end=\"80\">The 3U-HRack</strong> is a robust 19-inch standard rack designed to accommodate up to 12 battery units and 1 high-voltage cluster control box. With its space-efficient design and durable construction, it\'s an ideal solution for high-capacity energy storage setups. Fully compatible with the BOS-G system.</p>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(595, '<table border=\"0\" cellpadding=\"8\" style=\"width: 100%; border-collapse: collapse; border: 1px solid #ccc;\">\n<thead>\n<tr><th style=\"text-align: left; width: 40%;\">Model</th><th style=\"text-align: left;\">3U-LRack</th></tr>\n</thead>\n<tbody>\n<tr>\n<td style=\"width: 30%;\">Rack Type</td>\n<td>Standard 19-inch</td>\n</tr>\n<tr>\n<td>Battery Capacity</td>\n<td>Up to 8 batteries</td>\n</tr>\n<tr>\n<td>Cluster Control Support</td>\n<td>1 &#215; High Voltage Battery Cluster Control Box</td>\n</tr>\n<tr>\n<td>Dimensions (W &#215; D &#215; H)</td>\n<td>589 &#215; 590 &#215; 1640 mm</td>\n</tr>\n<tr>\n<td>Weight</td>\n<td>Approx. 65 kg</td>\n</tr>\n<tr>\n<td>System Compatibility</td>\n<td>Optional for BOS-G</td>\n</tr>\n</tbody>\n</table>', 2, 'BOS-G | 3U-LRack | Rack', '<p>The <strong data-start=\"436\" data-end=\"448\">3U-LRack</strong> provides a dependable and scalable housing solution for energy storage systems requiring moderate capacity. With support for up to 8 batteries and a high-voltage battery cluster control box, it offers the same professional-level build quality as its larger counterpart while reducing space and weight. It is ideal for applications where footprint matters but performance cannot be compromised.</p>\n<h3 data-start=\"449\" data-end=\"466\">Key Features:</h3>\n<ul data-start=\"468\" data-end=\"1984\" style=\"list-style-type: disc;\">\n<li data-start=\"870\" data-end=\"957\">\n<p data-start=\"872\" data-end=\"957\"><strong data-start=\"875\" data-end=\"896\">Standard 19\" Rack</strong> &#8211; Designed for compatibility with industry-standard setups</p>\n</li>\n<li data-start=\"958\" data-end=\"1045\">\n<p data-start=\"960\" data-end=\"1045\"><strong data-start=\"963\" data-end=\"990\">Holds up to 8 Batteries</strong> &#8211; Suitable for medium-scale energy storage solutions</p>\n</li>\n<li data-start=\"1046\" data-end=\"1145\">\n<p data-start=\"1048\" data-end=\"1145\"><strong data-start=\"1051\" data-end=\"1093\">Includes 1 HV Cluster Control Box Slot</strong> &#8211; Seamlessly integrates with high-voltage systems</p>\n</li>\n<li data-start=\"1146\" data-end=\"1197\">\n<p data-start=\"1148\" data-end=\"1197\"><strong data-start=\"1151\" data-end=\"1173\">Compact Dimensions</strong> &#8211; 589 &#215; 590 &#215; 1640 mm</p>\n</li>\n<li data-start=\"1198\" data-end=\"1243\">\n<p data-start=\"1200\" data-end=\"1243\"><strong data-start=\"1203\" data-end=\"1225\">Lightweight Design</strong> &#8211; Approx. 65 kg</p>\n</li>\n<li data-start=\"1198\" data-end=\"1243\">\n<p data-start=\"1200\" data-end=\"1243\"><strong data-start=\"1249\" data-end=\"1269\">BOS-G Compatible</strong> &#8211; Fully optional for BOS-G integration setups</p>\n<p data-start=\"622\" data-end=\"698\"></p>\n</li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-018.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>', '<p data-start=\"107\" data-end=\"397\"><strong data-start=\"107\" data-end=\"123\">The 3U-LRack</strong> is a standard 19-inch rack designed to hold up to 8 battery units and 1 high-voltage cluster control box. Its compact, space-saving structure makes it an excellent choice for flexible and medium-capacity energy storage installations. Fully compatible with the BOS-G system.</p>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', ''),
(596, '<table border=\"0\" cellpadding=\"8\" style=\"width: 100%; border-collapse: collapse; border: 1px solid #ccc;\">\n<thead>\n<tr><th style=\"text-align: left; width: 40%;\">Model</th><th style=\"text-align: left;\">BOS-A-Rack11</th></tr>\n</thead>\n<tbody>\n<tr>\n<td style=\"width: 30%;\">Rack Type</td>\n<td>Standard 19-inch</td>\n</tr>\n<tr>\n<td>Battery Capacity</td>\n<td>Up to 10 batteries</td>\n</tr>\n<tr>\n<td>Cluster Control Support</td>\n<td>1 &#215; High Voltage Battery Cluster Control Box</td>\n</tr>\n<tr>\n<td>Dimensions (W &#215; D &#215; H)</td>\n<td>610 &#215; 610 &#215; 1900 mm</td>\n</tr>\n<tr>\n<td>Weight</td>\n<td>Approx. 47 kg</td>\n</tr>\n<tr>\n<td>System Compatibility</td>\n<td>BOS Compatible</td>\n</tr>\n</tbody>\n</table>', 2, 'BOS-A | BOS-A-Rack11 | Rack', '<p>The <strong data-start=\"507\" data-end=\"523\">BOS-A-Rack11</strong> offers a reliable housing for up to 10 battery units and a high-voltage cluster control box, providing a solid balance between capacity and compactness. Its dimensions and weight optimize installation flexibility while maintaining BOS system compatibility, making it suitable for various energy storage needs.</p>\n<h3 data-start=\"449\" data-end=\"466\">Key Features:</h3>\n<ul data-start=\"468\" data-end=\"1984\" style=\"list-style-type: disc;\">\n<li data-start=\"850\" data-end=\"882\">\n<p data-start=\"852\" data-end=\"882\">Standard 19-inch rack design</p>\n</li>\n<li data-start=\"883\" data-end=\"914\">\n<p data-start=\"885\" data-end=\"914\">Supports up to 10 batteries</p>\n</li>\n<li data-start=\"915\" data-end=\"979\">\n<p data-start=\"917\" data-end=\"979\">Includes slot for 1 high-voltage battery cluster control box</p>\n</li>\n<li data-start=\"980\" data-end=\"1015\">\n<p data-start=\"982\" data-end=\"1015\">Dimensions: 610 &#215; 610 &#215; 1900 mm</p>\n</li>\n<li data-start=\"1016\" data-end=\"1048\">\n<p data-start=\"1018\" data-end=\"1048\">Lightweight at approx. 47 kg</p>\n</li>\n<li data-start=\"1049\" data-end=\"1098\">\n<p data-start=\"1051\" data-end=\"1098\">Fully compatible with BOS system architecture</p>\n<p data-start=\"872\" data-end=\"957\"></p>\n</li>\n</ul>\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-016.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>', '<p data-start=\"107\" data-end=\"397\">The <strong data-start=\"184\" data-end=\"200\">BOS-A-Rack11</strong> is a robust 19-inch rack solution designed for medium-sized energy storage setups, accommodating 10 batteries alongside a high-voltage battery cluster control box. Its compact footprint and lightweight design make it a versatile choice for efficient energy system installations.</p>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', 'Dies ist ein Platzhalter Artikel für div. Möglichkeiten.', '');
