<table style="width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); font-size: 16px;">
<tbody>
<tr style="background: #30358C; color: white;"><th style="padding: 18px 20px; text-align: left; font-weight: 600;">Parameter</th><th style="padding: 18px 20px; text-align: left; font-weight: 600;">Value</th></tr>
<tr>
<td colspan="2" style="background: #30358C; color: white; padding: 14px 20px; font-weight: bold; font-size: 17px;">Deye SUN-100K/125K-PCSL01HP3 Power Conversion System</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Model</td>
<td style="padding: 14px 20px;">SUN-100K/125K-PCSL01HP3</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Rated Power</td>
<td style="padding: 14px 20px;">100 kW or 125 kW</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. Units in Parallel</td>
<td style="padding: 14px 20px;">Up to 20 units &#8594; 2.5 MW total</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. Charge/Discharge Current</td>
<td style="padding: 14px 20px;">220 A</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Overload Capability</td>
<td style="padding: 14px 20px;">110 % continuous &#183; 170 % peak (short-term)</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Peak Efficiency</td>
<td style="padding: 14px 20px;">98.5 %</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">European Efficiency</td>
<td style="padding: 14px 20px;">97.8 %</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Grid Frequency</td>
<td style="padding: 14px 20px;">45 &#8211; 65 Hz</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Power Factor</td>
<td style="padding: 14px 20px;">&#8211;1 to +1 (fully adjustable)</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Total Harmonic Distortion (THDi)</td>
<td style="padding: 14px 20px;">&lt; 3 % at rated power</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Display &amp; Interfaces</td>
<td style="padding: 14px 20px;">LCD + LED, RS485, CAN, Wi-Fi, Meter interface</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Protection Rating</td>
<td style="padding: 14px 20px;">IP65 (outdoor)</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Dimensions (W &#215; H &#215; D)</td>
<td style="padding: 14px 20px;">543 &#215; 775 &#215; 310 mm</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Weight (approx.)</td>
<td style="padding: 14px 20px;">75 kg</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Operating Temperature</td>
<td style="padding: 14px 20px;">&#8211;25 &#176;C to +60 &#176;C (&gt;45 &#176;C derating)</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Cooling</td>
<td style="padding: 14px 20px;">Intelligent forced air cooling</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Safety Features</td>
<td style="padding: 14px 20px;">DC RCD, optional AFCI, insulation monitoring, anti-islanding, short-circuit protection</td>
</tr>
</tbody>
</table>