INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(1018, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Parameter</th><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Specification</th></tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Three-Phase Hybrid Inverter SUN-10K-SG01HP3-EU</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Battery Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Battery Type</td>\n<td style=\"padding: 14px 20px;\">Lithium-ion (160&#8211;700 V)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Charging/Discharging Current</td>\n<td style=\"padding: 14px 20px;\">37 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Number of Battery Inputs</td>\n<td style=\"padding: 14px 20px;\">1</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Charging Strategy</td>\n<td style=\"padding: 14px 20px;\">Self-adaptive to BMS</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">PV String Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Access Power</td>\n<td style=\"padding: 14px 20px;\">20 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. PV Input Power</td>\n<td style=\"padding: 14px 20px;\">16 kW</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">1000 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Start-up Voltage</td>\n<td style=\"padding: 14px 20px;\">180 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range</td>\n<td style=\"padding: 14px 20px;\">150&#8211;850 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Rated DC Input Voltage</td>\n<td style=\"padding: 14px 20px;\">600 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Number of MPP Trackers / Strings per MPPT</td>\n<td style=\"padding: 14px 20px;\">2 / 1+1</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current</td>\n<td style=\"padding: 14px 20px;\">20 A + 20 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Short-Circuit Current</td>\n<td style=\"padding: 14px 20px;\">30 A + 30 A</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">AC Output Data (On-Grid)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Output Power</td>\n<td style=\"padding: 14px 20px;\">10 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Apparent Power</td>\n<td style=\"padding: 14px 20px;\">11 kVA</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Current (400 V / 380 V)</td>\n<td style=\"padding: 14px 20px;\">14.5 A / 15.2 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Current</td>\n<td style=\"padding: 14px 20px;\">16.0 A / 16.7 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Peak Power (Off-Grid)</td>\n<td style=\"padding: 14px 20px;\">1.5 &#215; rated power, 10 s</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Continuous AC Passthrough</td>\n<td style=\"padding: 14px 20px;\">40 A</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Efficiency</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Efficiency</td>\n<td style=\"padding: 14px 20px;\">97.6 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">European Efficiency</td>\n<td style=\"padding: 14px 20px;\">97.0 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Efficiency</td>\n<td style=\"padding: 14px 20px;\">&gt; 99 %</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">General Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Dimensions (W &#215; H &#215; D)</td>\n<td style=\"padding: 14px 20px;\">408 &#215; 638 &#215; 237 mm</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Weight</td>\n<td style=\"padding: 14px 20px;\">30.5 kg</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Cooling</td>\n<td style=\"padding: 14px 20px;\">Intelligent air cooling</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Noise Level</td>\n<td style=\"padding: 14px 20px;\">&#8804; 55 dB</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Protection Rating</td>\n<td style=\"padding: 14px 20px;\">IP65</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">5 years (extendable to 10 years)</td>\n</tr>\n</tbody>\n</table>', 3, 'SUN-10K-SG01HP3-EU-AM2 | Three-Phase Hybrid Inverter | 2 MPPT | HV Battery Supported', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye SUN-10K-SG01HP3-EU is a compact yet extremely powerful 10 kW three-phase high-voltage hybrid inverter &#8211; perfect for modern homes, small businesses and agricultural operations. With 2 independent MPPTs (1+1 strings), up to 20 kW PV access power and high-voltage battery support (160&#8211;700 V), it delivers maximum yield even on complex roofs. 100 % unbalanced load (each phase independently up to 5 kW), AC coupling for retrofitting, parallel operation of up to 10 units, 37 A charge/discharge current and full diesel generator compatibility make it one of the most flexible inverters in its class. Six programmable time slots and intelligent energy management ensure optimal self-consumption and the lowest possible electricity costs.</p>\n<div style=\"margin: 70px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-005.jpg\" alt=\"Deye SUN-10K-SG01HP3-EU 10kW Hybrid Inverter\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Advantages</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">100 % Unbalanced Load</strong><br />Each phase up to 5 kW independently</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">2 MPPTs &#8211; 20 kW PV Access</strong><br />Ideal for east-west roofs &amp; shading</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">AC Coupling</strong><br />Perfect retrofit solution</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">37 A Battery Current</strong><br />Fast charging &amp; discharging</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">High-Voltage Battery 160&#8211;700 V</strong><br />Higher efficiency, lower cable losses</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Parallel up to 10 Units</strong><br />Scalable to 100 kW</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Diesel Generator Compatible</strong><br />Stores generator power</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Only 30.5 kg &amp; IP65</strong><br />Easy installation, outdoor suitable</div>\n</div>\n<div style=\"margin: 70px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"Deye 10kW Hybrid Installation\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5; margin: 70px 0;\">\n<p>Deye SUN-10K-SG01HP3-EU &#8211; The Smart 10 kW Three-Phase High-Voltage Hybrid</p>\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">2 MPPT &#183; 20 kW PV &#183; 100 % unbalanced &#183; 37 A &#183; Parallel 10&#215; &#183; Diesel-ready &#183; IP65</p>\n</div>\n</div>', 'Deye SUN-10K-SG01HP3-EU 10kW Three-Phase High-Voltage Hybrid Inverter<br /><br />Compact 10 kW hybrid inverter with 2 MPPTs (20 kW PV access), 100 % unbalanced load (5 kW per phase), 37 A battery current, AC coupling, parallel up to 10 units and diesel generator compatibility. Only 30.5 kg, IP65, extremely quiet &#8211; ideal for homes and small commercial applications.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(1019, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Parameter</th><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Specification</th></tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Three-Phase Hybrid Inverter SUN-12K-SG01HP3-EU</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Battery Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Battery Type</td>\n<td style=\"padding: 14px 20px;\">Lithium-ion (160&#8211;700 V)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Charging/Discharging Current</td>\n<td style=\"padding: 14px 20px;\">37 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Number of Battery Inputs</td>\n<td style=\"padding: 14px 20px;\">1</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Charging Strategy</td>\n<td style=\"padding: 14px 20px;\">Self-adaptive to BMS</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">PV String Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Access Power</td>\n<td style=\"padding: 14px 20px;\">24 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. PV Input Power</td>\n<td style=\"padding: 14px 20px;\">19.2 kW</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">1000 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Start-up Voltage</td>\n<td style=\"padding: 14px 20px;\">180 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range</td>\n<td style=\"padding: 14px 20px;\">150&#8211;850 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Rated DC Input Voltage</td>\n<td style=\"padding: 14px 20px;\">600 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Number of MPP Trackers / Strings per MPPT</td>\n<td style=\"padding: 14px 20px;\">2 / 2+1</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current</td>\n<td style=\"padding: 14px 20px;\">26 A + 20 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Short-Circuit Current</td>\n<td style=\"padding: 14px 20px;\">39 A + 30 A</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">AC Output Data (On-Grid)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Output Power</td>\n<td style=\"padding: 14px 20px;\">12 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Apparent Power</td>\n<td style=\"padding: 14px 20px;\">13.2 kVA</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Current (400 V / 380 V)</td>\n<td style=\"padding: 14px 20px;\">17.4 A / 18.2 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Current</td>\n<td style=\"padding: 14px 20px;\">19.2 A / 20 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Peak Power (Off-Grid)</td>\n<td style=\"padding: 14px 20px;\">1.5 &#215; rated power, 10 s</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Continuous AC Passthrough</td>\n<td style=\"padding: 14px 20px;\">80 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Grid Voltage</td>\n<td style=\"padding: 14px 20px;\">220/380 V, 230/400 V (3L+N+PE)</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Efficiency</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Efficiency</td>\n<td style=\"padding: 14px 20px;\">97.6 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">European Efficiency</td>\n<td style=\"padding: 14px 20px;\">97.0 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Efficiency</td>\n<td style=\"padding: 14px 20px;\">&gt; 99 %</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Protection &amp; Features</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">100 % Unbalanced Output</td>\n<td style=\"padding: 14px 20px;\">Yes (each phase up to 50 %)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Parallel Operation</td>\n<td style=\"padding: 14px 20px;\">Up to 10 units</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Diesel Generator Compatible</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">General Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Dimensions (W &#215; H &#215; D)</td>\n<td style=\"padding: 14px 20px;\">408 &#215; 638 &#215; 237 mm</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Weight</td>\n<td style=\"padding: 14px 20px;\">30.5 kg</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Cooling</td>\n<td style=\"padding: 14px 20px;\">Intelligent air cooling</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Noise Level</td>\n<td style=\"padding: 14px 20px;\">&#8804; 55 dB</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Protection Rating</td>\n<td style=\"padding: 14px 20px;\">IP65</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">5 years (extendable to 10 years)</td>\n</tr>\n</tbody>\n</table>', 3, 'SUN-12K-SG01HP3-EU-AM2 | Three-Phase Hybrid Inverter | 2 MPPT | HV Battery Supported', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye SUN-12K-SG01HP3-EU is a compact yet extremely powerful 12 kW three-phase high-voltage hybrid inverter &#8211; the ideal solution for large residential systems and smaller commercial projects. With 2 MPPTs (2+1 strings), up to 24 kW PV access power and high-voltage battery support (160&#8211;700 V), it offers maximum flexibility. 100 % unbalanced output (each phase independently up to 50 % rated power), AC coupling for retrofitting, parallel operation of up to 10 units (on- and off-grid), 37 A charge/discharge current and diesel generator compatibility make this inverter unbeatable in its class. Six freely programmable time slots and a full energy management system ensure maximum self-consumption and optimal electricity cost savings.</p>\n<div style=\"margin: 70px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-005.jpg\" alt=\"Deye SUN-12K-SG01HP3-EU 12kW Hybrid Inverter\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Advantages</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">100 % Unbalanced Output</strong><br />Each phase independently up to 50 % rated power</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">2 MPPTs &#8211; 3 Strings</strong><br />24 kW PV access &#8211; perfect for complex roofs</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">AC Coupling</strong><br />Ideal retrofit for existing systems</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">37 A Charge/Discharge</strong><br />Fast battery cycles</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">High-Voltage Battery 160&#8211;700 V</strong><br />Higher efficiency, lower losses</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Parallel up to 10 Units</strong><br />On-grid &amp; off-grid &#8211; up to 120 kW total</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Diesel Generator Compatible</strong><br />Stores energy from generators</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Six Time Slots</strong><br />Perfect tariff optimisation</div>\n</div>\n<div style=\"margin: 70px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"Deye Hybrid Inverter Installation\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5; margin: 70px 0;\">\n<p>Deye SUN-12K-SG01HP3-EU &#8211; Compact 12 kW Three-Phase High-Voltage Hybrid Powerhouse</p>\n<p style=\"font-size: 21px; opacity: 0.95; margin-top: 15px;\">2 MPPT &#183; 24 kW PV &#183; 100 % Unbalanced &#183; 37 A &#183; Parallel 10&#215; &#183; Diesel Compatible &#183; IP65</p>\n</div>\n</div>', 'Deye SUN-12K-SG01HP3-EU 12kW Three-Phase High-Voltage Hybrid Inverter<br /><br />Compact 12 kW hybrid inverter with 2 MPPTs (24 kW PV access), 100 % unbalanced output, 37 A battery current, high-voltage storage (160&#8211;700 V), AC coupling, parallel up to 10 units, diesel generator compatible, full EMS. Only 30.5 kg, IP65, extremely quiet &#8804;55 dB &#8211; perfect for large homes and small commercial systems.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(1020, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Parameter</th><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Specification</th></tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Three-Phase Hybrid Inverter SUN-15K-SG01HP3-EU</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Battery Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Battery Type</td>\n<td style=\"padding: 14px 20px;\">Lithium-ion (160&#8211;700 V)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Charging/Discharging Current</td>\n<td style=\"padding: 14px 20px;\">37 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Number of Battery Inputs</td>\n<td style=\"padding: 14px 20px;\">1</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Charging Strategy</td>\n<td style=\"padding: 14px 20px;\">Self-adaptive to BMS</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">PV String Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Access Power</td>\n<td style=\"padding: 14px 20px;\">30 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. PV Input Power</td>\n<td style=\"padding: 14px 20px;\">24 kW</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">1000 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Start-up Voltage</td>\n<td style=\"padding: 14px 20px;\">180 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range</td>\n<td style=\"padding: 14px 20px;\">150&#8211;850 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Rated DC Input Voltage</td>\n<td style=\"padding: 14px 20px;\">600 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Number of MPP Trackers / Strings per MPPT</td>\n<td style=\"padding: 14px 20px;\">2 / 2+1</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current</td>\n<td style=\"padding: 14px 20px;\">26 A + 20 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Short-Circuit Current</td>\n<td style=\"padding: 14px 20px;\">39 A + 30 A</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">AC Output Data (On-Grid)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Output Power</td>\n<td style=\"padding: 14px 20px;\">15 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Apparent Power</td>\n<td style=\"padding: 14px 20px;\">16.5 kVA</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Current (400 V / 380 V)</td>\n<td style=\"padding: 14px 20px;\">21.8 A / 22.8 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Current</td>\n<td style=\"padding: 14px 20px;\">24 A / 25 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Peak Power (Off-Grid)</td>\n<td style=\"padding: 14px 20px;\">1.5 &#215; rated power, 10 s</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Continuous AC Passthrough</td>\n<td style=\"padding: 14px 20px;\">80 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Grid Voltage</td>\n<td style=\"padding: 14px 20px;\">220/380 V, 230/400 V (3L+N+PE)</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Efficiency</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Efficiency</td>\n<td style=\"padding: 14px 20px;\">97.6 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">European Efficiency</td>\n<td style=\"padding: 14px 20px;\">97.0 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Efficiency</td>\n<td style=\"padding: 14px 20px;\">&gt; 99 %</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Protection &amp; Features</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">100 % Unbalanced Output</td>\n<td style=\"padding: 14px 20px;\">Yes (each phase up to 50 %)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Parallel Operation</td>\n<td style=\"padding: 14px 20px;\">Up to 10 units</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Diesel Generator Compatible</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">General Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Dimensions (W &#215; H &#215; D)</td>\n<td style=\"padding: 14px 20px;\">408 &#215; 638 &#215; 237 mm</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Weight</td>\n<td style=\"padding: 14px 20px;\">30.5 kg</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Cooling</td>\n<td style=\"padding: 14px 20px;\">Intelligent air cooling</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Noise Level</td>\n<td style=\"padding: 14px 20px;\">&#8804; 55 dB</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Protection Rating</td>\n<td style=\"padding: 14px 20px;\">IP65</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">5 years (extendable to 10 years)</td>\n</tr>\n</tbody>\n</table>', 3, 'SUN-15K-SG01HP3-EU-AM2 | Three-Phase Hybrid Inverter | 2 MPPT | HV Battery Supported', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye SUN-15K-SG01HP3-EU is a compact yet powerful 15 kW three-phase high-voltage hybrid inverter &#8211; the ideal solution for large residential homes, multi-family houses and smaller commercial buildings. With 2 MPPTs (2+1 strings), up to 30 kW PV access, high-voltage battery support (160&#8211;700 V), 100 % unbalanced output, AC coupling and 37 A charge/discharge current, it offers maximum flexibility. Parallel operation of up to 10 units (on- &amp; off-grid), diesel generator compatibility and six freely programmable time slots guarantee perfect energy management and highest possible self-consumption.</p>\n<div style=\"margin: 70px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-005.jpg\" alt=\"Deye SUN-15K-SG01HP3-EU 15kW Hybrid Inverter\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Advantages</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">100 % Unbalanced Output</strong><br />Each phase up to 50 % independently</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">2 MPPTs &#8211; 3 Strings</strong><br />30 kW PV access &#8211; perfect for east/west roofs</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">AC Coupling</strong><br />Simple retrofit of existing systems</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">37 A Charge/Discharge</strong><br />Fast battery cycles</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">High-Voltage Battery 160&#8211;700 V</strong><br />Higher efficiency, lower losses</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Parallel up to 10 Units</strong><br />On- &amp; off-grid &#8211; up to 150 kW total</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Diesel Generator Compatible</strong><br />Stores generator power</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Six Time Slots</strong><br />Optimal tariff management</div>\n</div>\n<div style=\"margin: 70px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"Deye Hybrid Inverter Installation\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5; margin: 70px 0;\">\n<p>Deye SUN-15K-SG01HP3-EU &#8211; The 15 kW Three-Phase High-Voltage Hybrid All-Rounder</p>\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">2 MPPT &#183; 30 kW PV &#183; 100 % unbalanced &#183; 37 A &#183; Parallel 10&#215; &#183; Diesel compatible &#183; IP65</p>\n</div>\n</div>', '<p dir=\"auto\" style=\"white-space: pre-wrap;\">Deye SUN-15K-SG01HP3-EU 15kW Three-Phase High-Voltage Hybrid Inverter &#8211; 2 MPPTs (30 kW PV), 100 % unbalanced load, 37 A battery current, AC coupling, parallel up to 10 units, diesel compatible, only 30.5 kg, IP65, extremely quiet &#8804;55 dB.</p>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(1021, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Parameter</th><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Specification</th></tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Three-Phase Hybrid Inverter SUN-20K-SG01HP3-EU</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Battery Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Battery Type</td>\n<td style=\"padding: 14px 20px;\">Lithium-ion (160&#8211;700 V)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Charging/Discharging Current</td>\n<td style=\"padding: 14px 20px;\">37 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Number of Battery Inputs</td>\n<td style=\"padding: 14px 20px;\">1</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Charging Strategy</td>\n<td style=\"padding: 14px 20px;\">Self-adaptive to BMS</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">PV String Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Access Power</td>\n<td style=\"padding: 14px 20px;\">40 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. PV Input Power</td>\n<td style=\"padding: 14px 20px;\">32 kW</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">1000 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Start-up Voltage</td>\n<td style=\"padding: 14px 20px;\">180 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range</td>\n<td style=\"padding: 14px 20px;\">150&#8211;850 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Rated DC Input Voltage</td>\n<td style=\"padding: 14px 20px;\">600 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Number of MPP Trackers / Strings per MPPT</td>\n<td style=\"padding: 14px 20px;\">2 / 2+2</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current</td>\n<td style=\"padding: 14px 20px;\">26 A + 26 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Short-Circuit Current</td>\n<td style=\"padding: 14px 20px;\">39 A + 39 A</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">AC Output Data (On-Grid)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Output Power</td>\n<td style=\"padding: 14px 20px;\">20 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Apparent Power</td>\n<td style=\"padding: 14px 20px;\">22 kVA</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Current (400 V / 380 V)</td>\n<td style=\"padding: 14px 20px;\">29 A / 30.4 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Current</td>\n<td style=\"padding: 14px 20px;\">31.9 A / 33.4 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Peak Power (Off-Grid)</td>\n<td style=\"padding: 14px 20px;\">1.5 &#215; rated power, 10 s</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Continuous AC Passthrough</td>\n<td style=\"padding: 14px 20px;\">80 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Grid Voltage</td>\n<td style=\"padding: 14px 20px;\">220/380 V, 230/400 V (3L+N+PE)</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Efficiency</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Efficiency</td>\n<td style=\"padding: 14px 20px;\">97.6 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">European Efficiency</td>\n<td style=\"padding: 14px 20px;\">97.0 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Efficiency</td>\n<td style=\"padding: 14px 20px;\">&gt; 99 %</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Protection &amp; Features</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">100 % Unbalanced Output</td>\n<td style=\"padding: 14px 20px;\">Yes (each phase up to 50 %)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Parallel Operation</td>\n<td style=\"padding: 14px 20px;\">Up to 10 units</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Diesel Generator Compatible</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">General Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Dimensions (W &#215; H &#215; D)</td>\n<td style=\"padding: 14px 20px;\">408 &#215; 638 &#215; 237 mm</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Weight</td>\n<td style=\"padding: 14px 20px;\">30.5 kg</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Cooling</td>\n<td style=\"padding: 14px 20px;\">Intelligent air cooling</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Noise Level</td>\n<td style=\"padding: 14px 20px;\">&#8804; 55 dB</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Protection Rating</td>\n<td style=\"padding: 14px 20px;\">IP65</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">5 years (extendable to 10 years)</td>\n</tr>\n</tbody>\n</table>', 3, 'SUN-20K-SG01HP3-EU-AM2 | Three-Phase Hybrid Inverter | 2 MPPT | HV Battery Supported', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye SUN-20K-SG01HP3-EU is a powerful 20 kW three-phase high-voltage hybrid inverter &#8211; the ideal solution for large residential and small commercial systems. With 2 independent MPPTs (2 strings each), up to 40 kW PV access, high-voltage battery support (160&#8211;700 V) and 100 % unbalanced output (each phase up to 50 % of rated power), it offers maximum flexibility. AC coupling for retrofitting, parallel operation of up to 10 units (on- &amp; off-grid), 37 A charge/discharge current, diesel generator compatibility and six programmable time slots make this inverter the perfect all-rounder for intelligent energy management and highest self-consumption.</p>\n<div style=\"margin: 70px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-005.jpg\" alt=\"Deye SUN-20K-SG01HP3-EU 20kW Hybrid Inverter\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Advantages</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">100 % Unbalanced Output</strong><br />Each phase independently up to 50 % rated power</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">2 MPPTs &#8211; 4 Strings</strong><br />40 kW PV access &#8211; perfect for complex roofs</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">AC Coupling</strong><br />Seamless retrofit of existing systems</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">37 A Charge/Discharge</strong><br />Fast battery cycles</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">High-Voltage Battery 160&#8211;700 V</strong><br />Higher efficiency, lower losses</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Parallel up to 10 Units</strong><br />On-grid &amp; off-grid &#8211; up to 200 kW total</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Diesel Generator Compatible</strong><br />Stores energy from generators</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Six Time Slots</strong><br />Perfect tariff optimisation</div>\n</div>\n<div style=\"margin: 70px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"Deye Hybrid Inverter Installation\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5; margin: 70px 0;\">\n<p>Deye SUN-20K-SG01HP3-EU &#8211; The 20 kW Three-Phase High-Voltage Hybrid Powerhouse</p>\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">2 MPPT &#183; 40 kW PV &#183; 100 % Unbalanced &#183; 37 A &#183; Parallel 10&#215; &#183; Diesel Compatible &#183; IP65</p>\n</div>\n</div>', 'Deye SUN-20K-SG01HP3-EU 20kW Three-Phase High-Voltage Hybrid Inverter<br /><br />Professional 20 kW hybrid inverter with 2 MPPTs (40 kW PV access), 100 % unbalanced load, 37 A battery current, high-voltage storage (160&#8211;700 V), AC coupling, parallel operation up to 10 units, diesel generator compatibility and full EMS. Compact 30.5 kg, IP65, extremely quiet &#8804;55 dB &#8211; ideal for large homes and small commercial applications.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', '');
INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(1022, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;\">\r\n<tbody>\r\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Parameter</th><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Specification</th></tr>\r\n<tr style=\"background: #30358C; color: white;\">\r\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Three-Phase Hybrid Inverter SUN-25K-SG01HP3-EU</td>\r\n</tr>\r\n<tr style=\"background: #30358C; color: white;\">\r\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Battery Input Data</td>\r\n</tr>\r\n<tr style=\"background: #f8f9fc;\">\r\n<td style=\"padding: 14px 20px;\">Battery Type</td>\r\n<td style=\"padding: 14px 20px;\">Lithium-ion (160&#8211;700 V)</td>\r\n</tr>\r\n<tr>\r\n<td style=\"padding: 14px 20px;\">Max. Charging/Discharging Current</td>\r\n<td style=\"padding: 14px 20px;\">50 A</td>\r\n</tr>\r\n<tr style=\"background: #f8f9fc;\">\r\n<td style=\"padding: 14px 20px;\">Number of Battery Inputs</td>\r\n<td style=\"padding: 14px 20px;\">1</td>\r\n</tr>\r\n<tr>\r\n<td style=\"padding: 14px 20px;\">Charging Strategy</td>\r\n<td style=\"padding: 14px 20px;\">Self-adaptive to BMS</td>\r\n</tr>\r\n<tr style=\"background: #30358C; color: white;\">\r\n<td colspan=\"2\" style=\"padding: 16px 20px;\">PV String Input Data</td>\r\n</tr>\r\n<tr style=\"background: #f8f9fc;\">\r\n<td style=\"padding: 14px 20px;\">Max. PV Access Power</td>\r\n<td style=\"padding: 14px 20px;\">50 kW</td>\r\n</tr>\r\n<tr>\r\n<td style=\"padding: 14px 20px;\">Max. PV Input Power</td>\r\n<td style=\"padding: 14px 20px;\">40 kW</td>\r\n</tr>\r\n<tr style=\"background: #f8f9fc;\">\r\n<td style=\"padding: 14px 20px;\">Max. PV Input Voltage</td>\r\n<td style=\"padding: 14px 20px;\">1000 V</td>\r\n</tr>\r\n<tr>\r\n<td style=\"padding: 14px 20px;\">Start-up Voltage</td>\r\n<td style=\"padding: 14px 20px;\">180 V</td>\r\n</tr>\r\n<tr style=\"background: #f8f9fc;\">\r\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range</td>\r\n<td style=\"padding: 14px 20px;\">150&#8211;850 V</td>\r\n</tr>\r\n<tr>\r\n<td style=\"padding: 14px 20px;\">Rated DC Input Voltage</td>\r\n<td style=\"padding: 14px 20px;\">600 V</td>\r\n</tr>\r\n<tr style=\"background: #f8f9fc;\">\r\n<td style=\"padding: 14px 20px;\">Number of MPP Trackers / Strings per MPPT</td>\r\n<td style=\"padding: 14px 20px;\">2 / 2+2</td>\r\n</tr>\r\n<tr>\r\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current</td>\r\n<td style=\"padding: 14px 20px;\">26 A + 26 A</td>\r\n</tr>\r\n<tr style=\"background: #f8f9fc;\">\r\n<td style=\"padding: 14px 20px;\">Max. PV Short-Circuit Current</td>\r\n<td style=\"padding: 14px 20px;\">39 A + 39 A</td>\r\n</tr>\r\n<tr style=\"background: #30358C; color: white;\">\r\n<td colspan=\"2\" style=\"padding: 16px 20px;\">AC Output Data (On-Grid)</td>\r\n</tr>\r\n<tr style=\"background: #f8f9fc;\">\r\n<td style=\"padding: 14px 20px;\">Rated Output Power</td>\r\n<td style=\"padding: 14px 20px;\">25 kW</td>\r\n</tr>\r\n<tr>\r\n<td style=\"padding: 14px 20px;\">Max. Apparent Power</td>\r\n<td style=\"padding: 14px 20px;\">27.5 kVA</td>\r\n</tr>\r\n<tr style=\"background: #f8f9fc;\">\r\n<td style=\"padding: 14px 20px;\">Rated AC Current (400 V / 380 V)</td>\r\n<td style=\"padding: 14px 20px;\">36.3 A / 37.9 A</td>\r\n</tr>\r\n<tr>\r\n<td style=\"padding: 14px 20px;\">Max. AC Current</td>\r\n<td style=\"padding: 14px 20px;\">39.9 A / 41.7 A</td>\r\n</tr>\r\n<tr style=\"background: #f8f9fc;\">\r\n<td style=\"padding: 14px 20px;\">Peak Power (Off-Grid)</td>\r\n<td style=\"padding: 14px 20px;\">1.5 &#215; rated power, 10 s</td>\r\n</tr>\r\n<tr>\r\n<td style=\"padding: 14px 20px;\">Max. Continuous AC Passthrough</td>\r\n<td style=\"padding: 14px 20px;\">80 A</td>\r\n</tr>\r\n<tr style=\"background: #f8f9fc;\">\r\n<td style=\"padding: 14px 20px;\">Rated Grid Voltage</td>\r\n<td style=\"padding: 14px 20px;\">220/380 V, 230/400 V (3L+N+PE)</td>\r\n</tr>\r\n<tr style=\"background: #30358C; color: white;\">\r\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Efficiency</td>\r\n</tr>\r\n<tr style=\"background: #f8f9fc;\">\r\n<td style=\"padding: 14px 20px;\">Max. Efficiency</td>\r\n<td style=\"padding: 14px 20px;\">97.6 %</td>\r\n</tr>\r\n<tr>\r\n<td style=\"padding: 14px 20px;\">European Efficiency</td>\r\n<td style=\"padding: 14px 20px;\">97.0 %</td>\r\n</tr>\r\n<tr style=\"background: #f8f9fc;\">\r\n<td style=\"padding: 14px 20px;\">MPPT Efficiency</td>\r\n<td style=\"padding: 14px 20px;\">&gt; 99 %</td>\r\n</tr>\r\n<tr style=\"background: #30358C; color: white;\">\r\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Protection &amp; Features</td>\r\n</tr>\r\n<tr style=\"background: #f8f9fc;\">\r\n<td style=\"padding: 14px 20px;\">100 % Unbalanced Output</td>\r\n<td style=\"padding: 14px 20px;\">Yes (each phase up to 50 %)</td>\r\n</tr>\r\n<tr>\r\n<td style=\"padding: 14px 20px;\">Parallel Operation</td>\r\n<td style=\"padding: 14px 20px;\">Up to 10 units</td>\r\n</tr>\r\n<tr style=\"background: #f8f9fc;\">\r\n<td style=\"padding: 14px 20px;\">Diesel Generator Compatible</td>\r\n<td style=\"padding: 14px 20px;\">Yes</td>\r\n</tr>\r\n<tr style=\"background: #30358C; color: white;\">\r\n<td colspan=\"2\" style=\"padding: 16px 20px;\">General Data</td>\r\n</tr>\r\n<tr style=\"background: #f8f9fc;\">\r\n<td style=\"padding: 14px 20px;\">Dimensions (W &#215; H &#215; D)</td>\r\n<td style=\"padding: 14px 20px;\">408 &#215; 638 &#215; 237 mm</td>\r\n</tr>\r\n<tr>\r\n<td style=\"padding: 14px 20px;\">Weight</td>\r\n<td style=\"padding: 14px 20px;\">30.5 kg</td>\r\n</tr>\r\n<tr style=\"background: #f8f9fc;\">\r\n<td style=\"padding: 14px 20px;\">Cooling</td>\r\n<td style=\"padding: 14px 20px;\">Intelligent air cooling</td>\r\n</tr>\r\n<tr>\r\n<td style=\"padding: 14px 20px;\">Noise Level</td>\r\n<td style=\"padding: 14px 20px;\">&#8804; 55 dB</td>\r\n</tr>\r\n<tr style=\"background: #f8f9fc;\">\r\n<td style=\"padding: 14px 20px;\">Protection Rating</td>\r\n<td style=\"padding: 14px 20px;\">IP65</td>\r\n</tr>\r\n<tr>\r\n<td style=\"padding: 14px 20px;\">Warranty</td>\r\n<td style=\"padding: 14px 20px;\">5 years (extendable to 10 years)</td>\r\n</tr>\r\n</tbody>\r\n</table>', 3, 'SUN-25K-SG01HP3-EU-AM2 | Three-Phase Hybrid Inverter | 2 MPPT | HV Battery Supported', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\r\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye SUN-25K-SG01HP3-EU is a powerful 25 kW three-phase high-voltage hybrid inverter &#8211; perfect for large residential systems, commercial buildings and small industrial plants. Equipped with 2 independent MPPTs (2 strings each), a huge PV input of up to 50 kW and high-voltage battery support (160&#8211;700 V), it extracts every available watt. 100 % unbalanced output (each phase independently up to 50 % of rated power), AC coupling for easy retrofitting, parallel operation of up to 10 units (on-grid &amp; off-grid), 50 A charging/discharging current and diesel generator compatibility make this inverter unbeatable in flexibility and reliability. Six freely programmable time slots and full energy management system (EMS) guarantee maximum self-consumption and perfect electricity cost optimisation.</p>\r\n<div style=\"margin: 70px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-005.jpg\" alt=\"Deye SUN-25K-SG01HP3-EU 25kW Hybrid Inverter\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\r\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Advantages</h3>\r\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\r\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">100 % Unbalanced Output</strong><br />Each phase independently up to 50 % rated power</div>\r\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">2 MPPTs &#8211; 4 Strings</strong><br />50 kW PV access, ideal for complex roofs</div>\r\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">AC Coupling</strong><br />Perfect retrofit for existing systems</div>\r\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">50 A Charge/Discharge</strong><br />Extremely fast battery cycles</div>\r\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">High-Voltage Battery 160&#8211;700 V</strong><br />Higher efficiency, lower losses</div>\r\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Parallel up to 10 Units</strong><br />On-grid &amp; off-grid &#8211; up to 250 kW total</div>\r\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Diesel Generator Compatible</strong><br />Stores energy from generators</div>\r\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Six Time Slots</strong><br />Perfect tariff optimisation</div>\r\n</div>\r\n<div style=\"margin: 70px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"Deye Hybrid Inverter Installation\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\r\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5; margin: 70px 0;\">\r\n<p>Deye SUN-25K-SG01HP3-EU &#8211; The 25 kW Three-Phase High-Voltage Hybrid Powerhouse</p>\r\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">2 MPPT &#183; 50 kW PV &#183; 100 % Unbalanced &#183; 50 A &#183; Parallel 10&#215; &#183; Diesel Compatible &#183; IP65</p>\r\n</div>\r\n</div>', 'Deye SUN-25K-SG01HP3-EU 25kW Three-Phase High-Voltage Hybrid Inverter<br /><br />Professional 25 kW hybrid inverter with 2 MPPTs (50 kW PV access), 100 % unbalanced load, 50 A battery current, high-voltage storage (160&#8211;700 V), AC coupling, parallel operation up to 10 units, diesel generator compatibility and full EMS. Compact, only 30.5 kg, IP65, extremely quiet &#8804;55 dB &#8211; ideal for large homes and commercial applications.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\r\n\r\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\r\n\r\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\r\n\r\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\r\n\r\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\r\n\r\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\r\n\r\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(1023, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Parameter</th><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Specification</th></tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Three-Phase Hybrid Inverter SUN-29.9K-SG01HP3-EU-BM3</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Battery Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Battery Type</td>\n<td style=\"padding: 14px 20px;\">Lithium-ion (160&#8211;800 V)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Charging/Discharging Current</td>\n<td style=\"padding: 14px 20px;\">50 A + 50 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Number of Battery Inputs</td>\n<td style=\"padding: 14px 20px;\">2</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Charging Strategy</td>\n<td style=\"padding: 14px 20px;\">Self-adaptive to BMS</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">PV String Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Access Power</td>\n<td style=\"padding: 14px 20px;\">59.8 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. PV Input Power</td>\n<td style=\"padding: 14px 20px;\">47.84 kW</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">1000 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Start-up Voltage</td>\n<td style=\"padding: 14px 20px;\">180 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range</td>\n<td style=\"padding: 14px 20px;\">150&#8211;850 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Rated PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">600 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Number of MPP Trackers / Strings per MPPT</td>\n<td style=\"padding: 14px 20px;\">3 / 2+2+2</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current</td>\n<td style=\"padding: 14px 20px;\">36 A &#215; 3</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Short-Circuit Current</td>\n<td style=\"padding: 14px 20px;\">55 A &#215; 3</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">AC Output Data (On-Grid)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Output Power</td>\n<td style=\"padding: 14px 20px;\">29.9 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Apparent Power</td>\n<td style=\"padding: 14px 20px;\">29.9 kVA</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Current (400 V / 380 V)</td>\n<td style=\"padding: 14px 20px;\">43.4 A / 45.4 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Current</td>\n<td style=\"padding: 14px 20px;\">43.4 A / 45.4 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Peak Power (Off-Grid)</td>\n<td style=\"padding: 14px 20px;\">1.5 &#215; rated power, 10 s</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Continuous AC Passthrough</td>\n<td style=\"padding: 14px 20px;\">200 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Grid Voltage</td>\n<td style=\"padding: 14px 20px;\">220/380 V, 230/400 V (3L+N+PE)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Power Factor</td>\n<td style=\"padding: 14px 20px;\">0.8 leading to 0.8 lagging</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Efficiency</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Efficiency</td>\n<td style=\"padding: 14px 20px;\">97.6 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">European Efficiency</td>\n<td style=\"padding: 14px 20px;\">97.0 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Efficiency</td>\n<td style=\"padding: 14px 20px;\">&gt; 99 %</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Protection &amp; Features</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">100 % Unbalanced Output</td>\n<td style=\"padding: 14px 20px;\">Yes (each phase up to 50 %)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Parallel Operation</td>\n<td style=\"padding: 14px 20px;\">Up to 10 units (on-grid &amp; off-grid)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Diesel Generator Energy Storage</td>\n<td style=\"padding: 14px 20px;\">Supported</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Surge Protection</td>\n<td style=\"padding: 14px 20px;\">Type II (DC + AC)</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">General Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Dimensions (W &#215; H &#215; D)</td>\n<td style=\"padding: 14px 20px;\">527 &#215; 894 &#215; 294 mm (excl. connectors)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Weight</td>\n<td style=\"padding: 14px 20px;\">80 kg</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Cooling</td>\n<td style=\"padding: 14px 20px;\">Intelligent air cooling</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Noise Emission</td>\n<td style=\"padding: 14px 20px;\">&#8804; 65 dB</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Protection Degree</td>\n<td style=\"padding: 14px 20px;\">IP65</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Operating Temperature Range</td>\n<td style=\"padding: 14px 20px;\">-40 &#176;C to +60 &#176;C (&gt;45 &#176;C derating)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Communication</td>\n<td style=\"padding: 14px 20px;\">RS485 / RS232 / CAN + Wi-Fi / GPRS / 4G / LAN (optional)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">5 years (10 years depending on installation location)</td>\n</tr>\n</tbody>\n</table>', 3, 'SUN-29.9K-SG01HP3-EU-BM3 | Three-Phase Hybrid Inverter | 3 MPPT | HV Battery Supported', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye SUN-29.9K-SG01HP3-EU-BM3 is a powerful 30 kW three-phase high-voltage hybrid inverter &#8211; the perfect choice for large homes, commercial buildings and small industrial applications. With 3 independent MPPTs (2 strings each), an impressive PV input of up to 59.8 kW and high-voltage battery support (160&#8211;800 V), it extracts maximum yield even from complex roofs. 100 % unbalanced output (each phase independently up to 50 % of rated power), AC coupling for easy retrofitting, parallel operation of up to 10 units (on-grid &amp; off-grid), dual 50 A + 50 A battery paths and diesel generator compatibility make this inverter extremely versatile and future-proof. Six freely programmable time slots and full energy management system (EMS) ensure optimal electricity cost reduction and maximum self-consumption.</p>\n<div style=\"margin: 70px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-006.jpg\" alt=\"Deye SUN-29.9K-SG01HP3-EU-BM3 30kW Hybrid Inverter\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Advantages</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">100 % Unbalanced Output</strong><br />Each phase independently up to 50 % rated power</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">3 MPPTs &#8211; 6 Strings</strong><br />Up to 59.8 kW PV input, ideal for complex roofs</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">AC Coupling</strong><br />Perfect retrofit for existing systems</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">50 A + 50 A Charge/Discharge</strong><br />Fast battery cycles, dual battery paths</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">High-Voltage Battery 160&#8211;800 V</strong><br />Higher efficiency, lower losses</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Parallel up to 10 Units</strong><br />On-grid &amp; off-grid &#8211; up to 300 kW total</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Diesel Generator Compatible</strong><br />Stores energy from generators</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Six Programmable Time Slots</strong><br />Perfect tariff optimisation</div>\n</div>\n<div style=\"margin: 70px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"Deye Hybrid Inverter Installation\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5; margin: 70px 0;\">\n<p>Deye SUN-29.9K-SG01HP3-EU-BM3 &#8211; The 30 kW Three-Phase High-Voltage Hybrid Powerhouse</p>\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">3 MPPT &#183; 59.8 kW PV &#183; 100 % Unbalanced &#183; 50+50 A &#183; Parallel 10&#215; &#183; Diesel Compatible &#183; IP65</p>\n</div>\n</div>', 'Deye SUN-29.9K-SG01HP3-EU-BM3 30kW Three-Phase High-Voltage Hybrid Inverter<br /><br />Professional 30 kW hybrid inverter with 3 MPPTs (59.8 kW PV access), 100 % unbalanced load, 50+50 A battery current, high-voltage storage (160&#8211;800 V), AC coupling, parallel operation up to 10 units, diesel generator compatibility and full EMS. Perfect for large homes, commercial and light industry. IP65, intelligent cooling, &#8804;65 dB.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(1024, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Parameter</th><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Specification</th></tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Three-Phase Hybrid Inverter SUN-30K-SG01HP3-EU-BM3</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Battery Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Battery Type</td>\n<td style=\"padding: 14px 20px;\">Lithium-ion (160&#8211;800 V)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Charging/Discharging Current</td>\n<td style=\"padding: 14px 20px;\">75 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Number of Battery Inputs</td>\n<td style=\"padding: 14px 20px;\">1</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Charging Strategy</td>\n<td style=\"padding: 14px 20px;\">Self-adaptive to BMS</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">PV String Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Access Power</td>\n<td style=\"padding: 14px 20px;\">60 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. PV Input Power</td>\n<td style=\"padding: 14px 20px;\">48 kW (30 kW rated + 60% oversizing)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">1000 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Start-up Voltage</td>\n<td style=\"padding: 14px 20px;\">180 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range</td>\n<td style=\"padding: 14px 20px;\">150&#8211;850 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Rated PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">600 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Number of MPP Trackers / Strings per MPPT</td>\n<td style=\"padding: 14px 20px;\">3 / 2+2+2</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current</td>\n<td style=\"padding: 14px 20px;\">55 A &#215; 3</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Short-Circuit Current</td>\n<td style=\"padding: 14px 20px;\">36 A &#215; 3</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">AC Output Data (On-Grid)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Output Power</td>\n<td style=\"padding: 14px 20px;\">30 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Apparent Power</td>\n<td style=\"padding: 14px 20px;\">33 kVA</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Current (400 V / 380 V)</td>\n<td style=\"padding: 14px 20px;\">45.5 A / 47.9 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Current</td>\n<td style=\"padding: 14px 20px;\">50 A / 52.6 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Peak Power (Off-Grid)</td>\n<td style=\"padding: 14px 20px;\">1.5 &#215; rated power, 10 s</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Continuous AC Passthrough</td>\n<td style=\"padding: 14px 20px;\">200 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Grid Voltage</td>\n<td style=\"padding: 14px 20px;\">220/380 V, 230/400 V (3L+N+PE)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Power Factor</td>\n<td style=\"padding: 14px 20px;\">0.8 leading to 0.8 lagging</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Efficiency</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Efficiency</td>\n<td style=\"padding: 14px 20px;\">97.6 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">European Efficiency</td>\n<td style=\"padding: 14px 20px;\">97.0 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Efficiency</td>\n<td style=\"padding: 14px 20px;\">&gt; 99 %</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Protection &amp; Features</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">100 % Unbalanced Output</td>\n<td style=\"padding: 14px 20px;\">Yes (each phase up to 50 %)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Parallel Operation</td>\n<td style=\"padding: 14px 20px;\">Up to 10 units (on-grid &amp; off-grid)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Diesel Generator Energy Storage</td>\n<td style=\"padding: 14px 20px;\">Supported</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Surge Protection</td>\n<td style=\"padding: 14px 20px;\">Type II (DC + AC)</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">General Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Dimensions (W &#215; H &#215; D)</td>\n<td style=\"padding: 14px 20px;\">527 &#215; 894 &#215; 294 mm (excl. connectors)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Weight</td>\n<td style=\"padding: 14px 20px;\">80 kg</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Cooling</td>\n<td style=\"padding: 14px 20px;\">Intelligent air cooling</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Noise Emission</td>\n<td style=\"padding: 14px 20px;\">&#8804; 65 dB</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Protection Degree</td>\n<td style=\"padding: 14px 20px;\">IP65</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Operating Temperature Range</td>\n<td style=\"padding: 14px 20px;\">-40 &#176;C to +60 &#176;C (&gt;45 &#176;C derating)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Communication</td>\n<td style=\"padding: 14px 20px;\">RS485 / RS232 / CAN + Wi-Fi / GPRS / 4G / LAN (optional)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">5 years (extendable)</td>\n</tr>\n</tbody>\n</table>', 3, 'SUN-30K-SG02HP3-EU-AM3 | Three-Phase Hybrid Inverter | 3 MPPT | HV Battery Supported', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye SUN-30K-SG01HP3-EU-BM3 is a powerful 30 kW three-phase high-voltage hybrid inverter of the latest generation &#8211; ideal for large residential homes and small to medium commercial projects. With 3 independent MPPTs (2 strings each), up to 60 kW PV input and high-voltage battery support (160&#8211;800 V), it delivers maximum yields even on complex roofs. 100 % unbalanced output (each phase up to 50 % rated power independently), AC coupling for easy retrofitting of existing systems, parallel operation of up to 10 units (on-grid &amp; off-grid) and diesel generator compatibility make it extremely flexible and future-proof. Maximum charge/discharge current of 50 A + 50 A, six programmable time-of-use periods and intelligent energy management ensure maximum self-consumption and perfect electricity cost savings.</p>\n<div style=\"margin: 70px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-006.jpg\" alt=\"Deye SUN-30K-SG01HP3-EU-BM3 Hybrid Inverter\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Advantages</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">100 % Unbalanced Output</strong><br />Each phase independently up to 50 % rated power</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">3 MPPTs &#8211; 6 Strings</strong><br />60 kW PV access, perfect for east-west and complex roofs</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">AC Coupling</strong><br />Easy retrofit of existing PV systems</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">50 A + 50 A Charge/Discharge</strong><br />Fast battery cycles</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">High-Voltage Battery 160&#8211;800 V</strong><br />Higher efficiency, lower losses</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Parallel up to 10 Units</strong><br />Up to 300 kW total (on-grid &amp; off-grid)</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Diesel Generator Compatible</strong><br />Stores energy from generators</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Six Time Slots</strong><br />Perfect tariff optimisation &amp; self-consumption</div>\n</div>\n<div style=\"margin: 70px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"Deye Hybrid Inverter Installation\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5; margin: 70px 0;\">\n<p>Deye SUN-30K-SG01HP3-EU-BM3 &#8211; The 30 kW Three-Phase High-Voltage Hybrid Pro</p>\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">3 MPPT &#183; 60 kW PV &#183; 100 % Unbalanced &#183; 50+50 A &#183; Parallel 10&#215; &#183; Diesel Compatible &#183; IP65</p>\n</div>\n</div>', 'Deye SUN-30K-SG01HP3-EU-BM3 30 kW Three-Phase High-Voltage Hybrid Inverter<br /><br />Powerful 30 kW hybrid inverter with 3 MPPTs (60 kW PV access), 100 % unbalanced output, 50+50 A battery current, high-voltage storage support (160&#8211;800 V), AC coupling, parallel operation of up to 10 units, diesel generator compatibility and full energy management system. Perfect for large residential and commercial projects. IP65, intelligent cooling, &#8804;65 dB.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', '');
INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(1025, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Parameter</th><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Value</th></tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Three-Phase Hybrid Inverter SUN-50K-SG01HP3-EU-BM4</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Battery Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Battery Type</td>\n<td style=\"padding: 14px 20px;\">Li-ion</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Battery Voltage Range (V)</td>\n<td style=\"padding: 14px 20px;\">160-800</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Charging Current (A)</td>\n<td style=\"padding: 14px 20px;\">50+50</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Discharging Current (A)</td>\n<td style=\"padding: 14px 20px;\">50+50</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Charging Strategy for Li-Ion Battery</td>\n<td style=\"padding: 14px 20px;\">Self-adaptation to BMS</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Number of Battery Inputs</td>\n<td style=\"padding: 14px 20px;\">2</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">PV String Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Access Power (W)</td>\n<td style=\"padding: 14px 20px;\">100000</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. DC Input Power (W)</td>\n<td style=\"padding: 14px 20px;\">80000</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. DC Input Voltage (V)</td>\n<td style=\"padding: 14px 20px;\">1000</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Start Voltage (V)</td>\n<td style=\"padding: 14px 20px;\">180</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range (V)</td>\n<td style=\"padding: 14px 20px;\">150-800</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Rated DC Input Voltage (V)</td>\n<td style=\"padding: 14px 20px;\">600</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current (A)</td>\n<td style=\"padding: 14px 20px;\">36+36+36+36</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Input Short-Circuit Current (A)</td>\n<td style=\"padding: 14px 20px;\">55+55+55+55</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Number of MPP Trackers / Number of Strings per MPP Tracker</td>\n<td style=\"padding: 14px 20px;\">4/2+2+2+2</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">AC Input/Output Side</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Input/Output Active Power</td>\n<td style=\"padding: 14px 20px;\">50000</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Input/Output Apparent Power</td>\n<td style=\"padding: 14px 20px;\">55000</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">AC Input/Output Rated Current (A)</td>\n<td style=\"padding: 14px 20px;\">75.8/72.5</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Input/Output Current (A)</td>\n<td style=\"padding: 14px 20px;\">83.4/79.8</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Continuous AC Passthrough (Grid for Charging)</td>\n<td style=\"padding: 14px 20px;\">200</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Peak Power (off-grid)</td>\n<td style=\"padding: 14px 20px;\">1.5 times rated output power, 10 s</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Power Factor Adjustment Range</td>\n<td style=\"padding: 14px 20px;\">0.8 leading to 0.8 lagging</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Rated Input/Output Voltage/Range (V)</td>\n<td style=\"padding: 14px 20px;\">220/380V, 230/400V 0.85Un-1.1Un</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Input/Output Grid Frequency/Range (Hz)</td>\n<td style=\"padding: 14px 20px;\">50/45-55, 60/55-65</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Connection Type</td>\n<td style=\"padding: 14px 20px;\">3L+N+PE</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Total Harmonic Current Distortion (THDi)</td>\n<td style=\"padding: 14px 20px;\">&lt;3% (Rated Power)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">DC Current Injection</td>\n<td style=\"padding: 14px 20px;\">&lt;0.5% In</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Efficiency</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Efficiency</td>\n<td style=\"padding: 14px 20px;\">97.6%</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Euro Efficiency</td>\n<td style=\"padding: 14px 20px;\">97.0%</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Efficiency</td>\n<td style=\"padding: 14px 20px;\">&gt;99%</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Device Protection</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Integrated</td>\n<td style=\"padding: 14px 20px;\">DC Polarity Reverse Connection Protection, AC Output Overcurrent Protection, Thermal Protection, AC Output Overvoltage Protection, AC Output Short-Circuit Protection, DC Component Monitoring, Overvoltage Load Drop Protection, Ground Fault Current Monitoring, Arc Fault Current Interrupter (optional), Grid Monitoring, Anti-Island Protection Monitoring, Ground Fault Detection, DC Input Switch, DC Insulation Impedance Monitoring, Backfeed Detection (RCD), Overvoltage Protection Level</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Overvoltage Protection Level</td>\n<td style=\"padding: 14px 20px;\">TYPE II (DC), TYPE II (AC)</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Interface</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">LCD/LED Display</td>\n<td style=\"padding: 14px 20px;\">LCD</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Communication Interface</td>\n<td style=\"padding: 14px 20px;\">WIFI, RS485, CAN</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Monitoring Mode</td>\n<td style=\"padding: 14px 20px;\">GPRS/WIFI/Bluetooth/4G/LAN (optional)</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">General Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Operating Temperature Range (&#176;C)</td>\n<td style=\"padding: 14px 20px;\">-40 to +60&#176;C, &gt;45&#176;C Power Derating</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Permissible Ambient Humidity</td>\n<td style=\"padding: 14px 20px;\">0-100%</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Permissible Altitude</td>\n<td style=\"padding: 14px 20px;\">2000m</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Noise (dB)</td>\n<td style=\"padding: 14px 20px;\">&lt;65 db=\"\" a=\"\" td=\"\"&gt; <!--65--><!--65--></td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Protection Rating</td>\n<td style=\"padding: 14px 20px;\">IP 65</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Inverter Topology</td>\n<td style=\"padding: 14px 20px;\">Non-isolated</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Overvoltage Category</td>\n<td style=\"padding: 14px 20px;\">OVC II (DC), OVC III (AC)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Dimensions (WxHxD mm)</td>\n<td style=\"padding: 14px 20px;\">527&#215;894&#215;294 (Without connectors and brackets)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Weight (kg)</td>\n<td style=\"padding: 14px 20px;\">80</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Cooling Mode</td>\n<td style=\"padding: 14px 20px;\">Intelligent Cooling</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">5-year/10-year warranty period depends on installation conditions of the inverter. For details, see the general warranty conditions.</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Regulation</td>\n<td style=\"padding: 14px 20px;\">IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002, OVE Guideline R25, G99, VDE-AR-N 4105</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Safety EMC / Standard</td>\n<td style=\"padding: 14px 20px;\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</td>\n</tr>\n</tbody>\n</table>', 3, 'SUN-50K-SG01HP3-EU-BM4 | Three-Phase Hybrid Inverter | 4 MPPT | HV Battery Supported', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye SUN-50K-SG01HP3-EU-BM4 is a powerful 50 kW three-phase high-voltage hybrid inverter &#8211; perfect for large residential homes, commercial operations, and small industrial facilities. With 4 independent MPPTs (2 strings each), up to 100 kW PV access, and high-voltage battery support (160&#8211;800 V), it maximizes yield even on complex roof structures. 100 % unbalanced load (each phase can independently deliver up to 50 % of rated power), AC coupling for easy retrofitting of existing PV systems, parallel operation of up to 10 units (on-grid &amp; off-grid), and diesel generator compatibility make it extremely flexible and future-proof. Maximum charging/discharging power of 50 A + 50 A, six freely programmable time slots, and intelligent energy management ensure optimal cost savings and maximum self-consumption.</p>\n<div style=\"margin: 70px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-006.jpg\" alt=\"Deye SUN-50K-SG01HP3-EU-BM3 50kW Hybrid Inverter\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Advantages</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">100 % Unbalanced Output</strong><br />Each phase independently up to 50 % rated power</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">4 MPPTs &#8211; 8 Strings</strong><br />100 kW PV access, ideal for east-west and shaded roofs</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">AC Coupling</strong><br />Perfect retrofit for existing PV systems</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">50 A + 50 A Charge/Discharge</strong><br />Fast battery cycling</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">High-Voltage Battery 160&#8211;800 V</strong><br />Higher efficiency, lower losses</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Parallel up to 10 Units</strong><br />On-grid &amp; off-grid &#8211; up to 500 kW total</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Diesel Generator Compatible</strong><br />Stores generator energy</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Six Time Slots</strong><br />Perfect tariff and self-consumption optimization</div>\n</div>\n<div style=\"margin: 70px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"Deye Hybrid Inverter Installation\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5; margin: 70px 0;\">\n<p>Deye SUN-50K-SG01HP3-EU-BM4 &#8211; The 50 kW Three-Phase High-Voltage Hybrid Pro</p>\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">4 MPPT &#183; 100 kW PV &#183; 100 % Unbalanced &#183; 50+50 A &#183; Parallel 10&#215; &#183; Diesel Compatible &#183; IP65</p>\n</div>\n</div>', '<p>Deye SUN-50K-SG01HP3-EU-BM4 50kW</p>\n<p>Three-Phase High-Voltage Hybrid InverterPowerful 50 kW hybrid inverter with 4 MPPTs (100 kW PV access), 100% unbalanced load, 50+50 A battery current, high-voltage storage (160&#8211;800 V), AC coupling, parallel operation up to 10 units, diesel generator compatibility, and full EMS. Ideal for large homes, commercial, and small industrial applications. IP65, intelligent cooling,&#160;&lt;65 dB.</p>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(1026, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Parameter</th><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Value</th></tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Three-Phase Hybrid Inverter SUN-80K-SG02HP3-EU-EM6</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Battery Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Battery Type</td>\n<td style=\"padding: 14px 20px;\">Lithium-ion (160&#8211;1000 V)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Charging / Discharging Current</td>\n<td style=\"padding: 14px 20px;\">80 A + 80 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Number of Battery Inputs</td>\n<td style=\"padding: 14px 20px;\">2</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Charging Strategy</td>\n<td style=\"padding: 14px 20px;\">Self-adaptive to BMS</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">PV String Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Access Power</td>\n<td style=\"padding: 14px 20px;\">160 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. PV Input Power</td>\n<td style=\"padding: 14px 20px;\">128 kW</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">1000 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Start-up Voltage</td>\n<td style=\"padding: 14px 20px;\">180 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range</td>\n<td style=\"padding: 14px 20px;\">150&#8211;850 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Rated PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">650 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">No. of MPP Trackers / Strings per MPPT</td>\n<td style=\"padding: 14px 20px;\">6 / 2+2+2+2+2+2</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current</td>\n<td style=\"padding: 14px 20px;\">36 A &#215; 6</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Short-Circuit Current</td>\n<td style=\"padding: 14px 20px;\">54 A &#215; 6</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">AC Output Data (On-Grid)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Output Power</td>\n<td style=\"padding: 14px 20px;\">80 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Apparent Power</td>\n<td style=\"padding: 14px 20px;\">88 kVA</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Current (400 V / 380 V)</td>\n<td style=\"padding: 14px 20px;\">115.9 A / 121.3 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Current</td>\n<td style=\"padding: 14px 20px;\">127.6 A / 133.4 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Peak Power (Off-Grid)</td>\n<td style=\"padding: 14px 20px;\">1.5 &#215; rated power, 10 s</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Continuous AC Passthrough</td>\n<td style=\"padding: 14px 20px;\">200 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Grid Voltage</td>\n<td style=\"padding: 14px 20px;\">220/380 V, 230/400 V (3L+N+PE)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Power Factor</td>\n<td style=\"padding: 14px 20px;\">0.8 leading &#8211; 0.8 lagging</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Efficiency</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Efficiency</td>\n<td style=\"padding: 14px 20px;\">97.6 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">European Efficiency</td>\n<td style=\"padding: 14px 20px;\">97.0 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Efficiency</td>\n<td style=\"padding: 14px 20px;\">&gt; 99 %</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">Protection &amp; Features</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">100 % Unbalanced Load Support</td>\n<td style=\"padding: 14px 20px;\">Yes (each phase up to 50 %)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Parallel Operation</td>\n<td style=\"padding: 14px 20px;\">Up to 10 units (on- &amp; off-grid)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Diesel Generator Energy Storage</td>\n<td style=\"padding: 14px 20px;\">Supported</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Surge Protection</td>\n<td style=\"padding: 14px 20px;\">Type II (DC + AC)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">AFCI (Arc Fault Protection)</td>\n<td style=\"padding: 14px 20px;\">Optional</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px;\">General Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Dimensions (W &#215; H &#215; D)</td>\n<td style=\"padding: 14px 20px;\">606 &#215; 927 &#215; 314 mm (excl. connectors)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Weight</td>\n<td style=\"padding: 14px 20px;\">105 kg</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Cooling</td>\n<td style=\"padding: 14px 20px;\">Intelligent air cooling</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Noise Level</td>\n<td style=\"padding: 14px 20px;\">&#8804; 65 dB</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Protection Rating</td>\n<td style=\"padding: 14px 20px;\">IP65</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Operating Temperature</td>\n<td style=\"padding: 14px 20px;\">-40 &#176;C to +60 &#176;C (&gt;45 &#176;C derating)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Communication</td>\n<td style=\"padding: 14px 20px;\">RS485 / RS232 / CAN + Wi-Fi / GPRS / 4G / LAN (optional)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">5 years (extendable to 10 years depending on region)</td>\n</tr>\n</tbody>\n</table>', 3, 'SUN-80K-SG02HP3-EU-EM6 | Three-Phase Hybrid Inverter | 6 MPPT | HV Battery Supported', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye SUN-80K-SG02HP3-EU-EM6 is a powerful 80 kW three-phase high-voltage hybrid inverter &#8211; the perfect solution for large residential systems, commercial buildings and small industrial plants. With 6 independent MPPTs (2 strings each), a gigantic PV input of up to 160 kW and high-voltage battery support (160&#8211;1000 V), it extracts every watt from the roof. 100 % unbalanced output (each phase can deliver up to 50 % of rated power independently), AC coupling for easy retrofitting of existing PV systems, parallel operation of up to 10 units (on-grid &amp; off-grid) and diesel generator compatibility make this inverter unbeatable in flexibility and reliability. Maximum charging/discharging power of 80 A + 80 A, six freely configurable time slots and full EMS functionality ensure perfect energy management according to electricity tariffs and self-consumption requirements.</p>\n<div style=\"margin: 70px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-006.jpg\" alt=\"Deye SUN-80K-SG02HP3-EU-EM6 80kW Hybrid Inverter\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Advantages</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">100 % Unbalanced Output</strong><br />Each phase independently up to 50 % rated power</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">6 MPPTs &#8211; 12 Strings</strong><br />160 kW PV access, ideal for complex roofs</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">AC Coupling</strong><br />Perfect retrofit for existing PV systems</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">80 A + 80 A Charge/Discharge</strong><br />Extremely fast battery cycles</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">High-Voltage Battery 160&#8211;1000 V</strong><br />Higher efficiency, lower losses</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Parallel up to 10 Units</strong><br />On-grid &amp; off-grid &#8211; up to 800 kW total</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Diesel Generator Compatible</strong><br />Stores energy from generators</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Six Time Slots</strong><br />Perfect tariff optimisation</div>\n</div>\n<div style=\"margin: 70px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"Deye Hybrid Inverter Installation\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5; margin: 70px 0;\">\n<p>Deye SUN-80K-SG02HP3-EU-EM6 &#8211; The 80 kW Three-Phase High-Voltage Hybrid Powerhouse</p>\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">6 MPPT &#183; 160 kW PV &#183; 100 % Unbalanced &#183; 80+80 A &#183; Parallel 10&#215; &#183; Diesel Compatible &#183; IP65</p>\n</div>\n</div>', 'Deye SUN-80K-SG02HP3-EU-EM6 80kW Three-Phase High-Voltage Hybrid Inverter<br /><br />Professional 80 kW hybrid inverterr three-phase hybrid inverter with 6 MPPTs (160 kW PV access), 100 % unbalanced output, 80+80 A battery current, high-voltage storage (160&#8211;1000 V), AC coupling, parallel operation up to 10 units, diesel generator compatibility and full EMS functions. Perfect for large homes, commercial buildings and industrial applications. IP65, intelligent cooling, &#8804;65 dB.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(1027, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Parameter</th><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Value</th></tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Single-Phase String Inverter SUN-2K-G04P1-EU-AM1</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">PV String Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Input Power</td>\n<td style=\"padding: 14px 20px;\">2.6 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">550 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Start-up Voltage</td>\n<td style=\"padding: 14px 20px;\">80 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range</td>\n<td style=\"padding: 14px 20px;\">70&#8211;500 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">360 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current</td>\n<td style=\"padding: 14px 20px;\">20 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Input Short Circuit Current</td>\n<td style=\"padding: 14px 20px;\">30 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">No. of MPP Trackers / Strings per MPP Tracker</td>\n<td style=\"padding: 14px 20px;\">1 / 1</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">AC Output Side</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Active Power</td>\n<td style=\"padding: 14px 20px;\">2 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Apparent Power</td>\n<td style=\"padding: 14px 20px;\">2.2 kVA</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Current (230 V / 220 V)</td>\n<td style=\"padding: 14px 20px;\">8.7 A / 9.1 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Current (230 V / 220 V)</td>\n<td style=\"padding: 14px 20px;\">9.6 A / 10 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Output Voltage / Range</td>\n<td style=\"padding: 14px 20px;\">220/230 V (0.85 Un &#8211; 1.1 Un)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Connection Form</td>\n<td style=\"padding: 14px 20px;\">L+N+PE</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Grid Frequency / Range</td>\n<td style=\"padding: 14px 20px;\">50/60 Hz (45&#8211;55 / 55&#8211;65 Hz)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Power Factor Adjustment Range</td>\n<td style=\"padding: 14px 20px;\">0.8 leading &#8211; 0.8 lagging</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Total Harmonic Distortion (THDi)</td>\n<td style=\"padding: 14px 20px;\">&lt; 3 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">DC Injection Current</td>\n<td style=\"padding: 14px 20px;\">&lt; 0.5 % In</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Efficiency</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Efficiency</td>\n<td style=\"padding: 14px 20px;\">97.3 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">European Efficiency</td>\n<td style=\"padding: 14px 20px;\">96.9 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Efficiency</td>\n<td style=\"padding: 14px 20px;\">&gt; 99 %</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Equipment Protection</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Polarity Reverse Connection Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Output Overcurrent Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">AC Output Overvoltage Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Output Short Circuit Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Thermal Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Insulation Impedance Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Component Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Arc Fault Circuit Interrupter (AFCI)</td>\n<td style=\"padding: 14px 20px;\">Optional</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Anti-Islanding Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Residual Current Detection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Surge Protection Level</td>\n<td style=\"padding: 14px 20px;\">Type II (DC), Type II (AC)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">DC Switch</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Interface</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Communication Interface</td>\n<td style=\"padding: 14px 20px;\">RS485 / RS232</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Monitoring Mode</td>\n<td style=\"padding: 14px 20px;\">GPRS / Wi-Fi / Bluetooth / 4G / LAN (optional)</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">General Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Operating Temperature Range</td>\n<td style=\"padding: 14px 20px;\">-25 &#176;C to +65 &#176;C (&gt;45 &#176;C derating)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Permissible Ambient Humidity</td>\n<td style=\"padding: 14px 20px;\">0&#8211;100 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Permissible Altitude</td>\n<td style=\"padding: 14px 20px;\">2000 m</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Noise Emission</td>\n<td style=\"padding: 14px 20px;\">&#8804; 35 dB</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Ingress Protection Rating</td>\n<td style=\"padding: 14px 20px;\">IP65</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Cabinet Size (W &#215; H &#215; D)</td>\n<td style=\"padding: 14px 20px;\">280 &#215; 310 &#215; 184 mm (excl. connectors and brackets)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Weight</td>\n<td style=\"padding: 14px 20px;\">6.35 kg</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Type of Cooling</td>\n<td style=\"padding: 14px 20px;\">Natural Cooling</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">5 years</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Regulation</td>\n<td style=\"padding: 14px 20px;\">IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002, G98, G99, VDE-AR-N 4105</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Safety EMC / Standard</td>\n<td style=\"padding: 14px 20px;\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1/2</td>\n</tr>\n</tbody>\n</table>', 3, 'SUN-2K-G04P1-EU-AM1 | Single Phase String Inverter | 1 MPPT', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye SUN-2K-G04P1-EU-AM1 is a compact, state-of-the-art 2 kW single-phase string inverter &#8211; perfect for very small residential systems, extensions, or balcony power plants. With a peak efficiency of 97.3 % and a European efficiency of 96.9 %, it delivers excellent performance in its class. Thanks to an extremely low start-up voltage of only 80 V, it produces power even in low-light conditions. Zero-export capability, VSG grid support, optional string-level monitoring and optional anti-PID function make it highly flexible and future-proof. Weighing just 6.35 kg, with ultra-compact dimensions of 280 &#215; 310 &#215; 184 mm, natural cooling (barely audible &#8804; 35 dB) and IP65 protection, it can be installed by one person &#8211; indoors or outdoors. Extensive communication options and full certification to all major European standards complete this outstanding package.</p>\n<div style=\"margin: 60px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-007.jpg\" alt=\"Deye SUN-2K-G04P1-EU-AM1 2kW Single-Phase Inverter\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Advantages</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Excellent Efficiency</strong><br />97.3 % peak &#183; 96.9 % European</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Extremely Early Start</strong><br />Only 80 V start-up voltage</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Zero Export &amp; VSG</strong><br />Maximum self-consumption + grid support</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Barely Audible</strong><br />Natural cooling, &#8804; 35 dB</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Feather-Light &amp; Compact</strong><br />Only 6.35 kg, 280 &#215; 310 &#215; 184 mm, IP65</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Full Protection Suite</strong><br />Type II SPD (DC+AC), optional AFCI</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Smart Monitoring</strong><br />Wi-Fi / 4G / Bluetooth optional</div>\n</div>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5; margin: 70px 0;\">\n<p>Deye SUN-2K-G04P1-EU-AM1 &#8211; The Ultra-Light 2 kW Premium Single-Phase Inverter</p>\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">97.3 % Efficiency &#183; 80 V Start &#183; Zero Export &#183; VSG &#183; &#8804; 35 dB &#183; Only 6.35 kg &#183; IP65</p>\n</div>\n</div>', 'Deye SUN-2K-G04P1-EU-AM1 2kW Single-Phase String Inverter (EU)<br /><br />Ultra-light 2 kW single-phase inverter with 97.3 % efficiency, extremely early start at 80 V, zero-export &amp; VSG function, only 6.35 kg, virtually silent (&#8804; 35 dB), IP65, Type II SPD on both sides, fully certified (G99, VDE-AR-N 4105 etc.). Ideal for very small residential systems, extensions, and balcony power plants.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', '');
INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(1028, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Parameter</th><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Value</th></tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Single-Phase String Inverter SUN-3K-G04P1-EU-AM1</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">PV String Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Input Power</td>\n<td style=\"padding: 14px 20px;\">3.9 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">550 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Start-up Voltage</td>\n<td style=\"padding: 14px 20px;\">80 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range</td>\n<td style=\"padding: 14px 20px;\">70&#8211;500 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">360 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current</td>\n<td style=\"padding: 14px 20px;\">20 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Input Short Circuit Current</td>\n<td style=\"padding: 14px 20px;\">30 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">No. of MPP Trackers / Strings per MPP Tracker</td>\n<td style=\"padding: 14px 20px;\">1 / 1</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">AC Output Side</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Active Power</td>\n<td style=\"padding: 14px 20px;\">3 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Apparent Power</td>\n<td style=\"padding: 14px 20px;\">3.3 kVA</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Current (230 V / 220 V)</td>\n<td style=\"padding: 14px 20px;\">13.1 A / 13.7 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Current (230 V / 220 V)</td>\n<td style=\"padding: 14px 20px;\">14.4 A / 15 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Output Voltage / Range</td>\n<td style=\"padding: 14px 20px;\">220/230 V (0.85 Un &#8211; 1.1 Un)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Connection Form</td>\n<td style=\"padding: 14px 20px;\">L+N+PE</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Grid Frequency / Range</td>\n<td style=\"padding: 14px 20px;\">50/60 Hz (45&#8211;55 / 55&#8211;65 Hz)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Power Factor Adjustment Range</td>\n<td style=\"padding: 14px 20px;\">0.8 leading &#8211; 0.8 lagging</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Total Harmonic Distortion (THDi)</td>\n<td style=\"padding: 14px 20px;\">&lt; 3 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">DC Injection Current</td>\n<td style=\"padding: 14px 20px;\">&lt; 0.5 % In</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Efficiency</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Efficiency</td>\n<td style=\"padding: 14px 20px;\">97.5 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">European Efficiency</td>\n<td style=\"padding: 14px 20px;\">97.0 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Efficiency</td>\n<td style=\"padding: 14px 20px;\">&gt; 99 %</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Equipment Protection</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Polarity Reverse Connection Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Output Overcurrent Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">AC Output Overvoltage Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Output Short Circuit Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Thermal Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Insulation Impedance Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Component Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Arc Fault Circuit Interrupter (AFCI)</td>\n<td style=\"padding: 14px 20px;\">Optional</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Anti-Islanding Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Residual Current Detection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Surge Protection Level</td>\n<td style=\"padding: 14px 20px;\">Type II (DC), Type II (AC)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">DC Switch</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Interface</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Communication Interface</td>\n<td style=\"padding: 14px 20px;\">RS485 / RS232</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Monitoring Mode</td>\n<td style=\"padding: 14px 20px;\">GPRS / Wi-Fi / Bluetooth / 4G / LAN (optional)</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">General Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Operating Temperature Range</td>\n<td style=\"padding: 14px 20px;\">-25 &#176;C to +65 &#176;C (&gt;45 &#176;C derating)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Permissible Ambient Humidity</td>\n<td style=\"padding: 14px 20px;\">0&#8211;100 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Permissible Altitude</td>\n<td style=\"padding: 14px 20px;\">2000 m</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Noise Emission</td>\n<td style=\"padding: 14px 20px;\">&#8804; 35 dB</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Ingress Protection Rating</td>\n<td style=\"padding: 14px 20px;\">IP65</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Cabinet Size (W &#215; H &#215; D)</td>\n<td style=\"padding: 14px 20px;\">280 &#215; 310 &#215; 184 mm (excl. connectors and brackets)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Weight</td>\n<td style=\"padding: 14px 20px;\">6.35 kg</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Type of Cooling</td>\n<td style=\"padding: 14px 20px;\">Natural Cooling</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">5 years</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Regulation</td>\n<td style=\"padding: 14px 20px;\">IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002, G98, G99, VDE-AR-N 4105</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Safety EMC / Standard</td>\n<td style=\"padding: 14px 20px;\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1/2</td>\n</tr>\n</tbody>\n</table>', 3, 'SUN-3K-G04P1-EU-AM1 | Single Phase String Inverter | 1 MPPT', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye SUN-3K-G04P1-EU-AM1 is a compact, state-of-the-art 3 kW single-phase string inverter &#8211; perfect for smaller residential homes and compact commercial systems. With a peak efficiency of 97.5 % and a European efficiency of 97.0 %, it delivers excellent performance in its class. Thanks to an extremely low start-up voltage of only 80 V, it produces power even in low-light conditions. Zero-export capability, VSG grid support, optional string-level monitoring and optional anti-PID function make it highly flexible and future-proof. Weighing just 6.35 kg, with ultra-compact dimensions of 280 &#215; 310 &#215; 184 mm, natural cooling (barely audible &#8804; 35 dB) and IP65 protection, it can be installed by one person &#8211; indoors or outdoors. Extensive communication options and full certification to all major European standards complete this outstanding package.</p>\n<div style=\"margin: 60px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-007.jpg\" alt=\"Deye SUN-3K-G04P1-EU-AM1 3kW Single-Phase Inverter\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Advantages</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Excellent Efficiency</strong><br />97.5 % peak &#183; 97.0 % European</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Extremely Early Start</strong><br />Only 80 V start-up voltage</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Zero Export &amp; VSG</strong><br />Maximum self-consumption + grid support</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Barely Audible</strong><br />Natural cooling, &#8804; 35 dB</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Feather-Light &amp; Compact</strong><br />Only 6.35 kg, 280 &#215; 310 &#215; 184 mm, IP65</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Full Protection Suite</strong><br />Type II SPD (DC+AC), optional AFCI</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Smart Monitoring</strong><br />Wi-Fi / 4G / Bluetooth optional</div>\n</div>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5; margin: 70px 0;\">\n<p>Deye SUN-3K-G04P1-EU-AM1 &#8211; The Ultra-Light 3 kW Premium Single-Phase Inverter</p>\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">97.5 % Efficiency &#183; 80 V Start &#183; Zero Export &#183; VSG &#183; &#8804; 35 dB &#183; Only 6.35 kg &#183; IP65</p>\n</div>\n</div>', 'Deye SUN-3K-G04P1-EU-AM1 3kW Single-Phase String Inverter (EU)<br /><br />Ultra-light 3 kW single-phase inverter with 97.5 % efficiency, extremely early start at 80 V, zero-export &amp; VSG function, only 6.35 kg, virtually silent (&#8804; 35 dB), IP65, Type II SPD on both sides, fully certified (G99, VDE-AR-N 4105 etc.). Perfect for small residential and compact commercial installations.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(1029, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Parameter</th><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Value</th></tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">String Inverter Model SUN-5K-G06P3-EU-AM2-P1</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">PV String Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Input Power</td>\n<td style=\"padding: 14px 20px;\">7.5 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">1100 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Start-up Voltage</td>\n<td style=\"padding: 14px 20px;\">140 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range</td>\n<td style=\"padding: 14px 20px;\">120&#8211;1000 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">600 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current</td>\n<td style=\"padding: 14px 20px;\">20 + 20 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Input Short Circuit Current</td>\n<td style=\"padding: 14px 20px;\">30 + 30 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">No. of MPP Trackers / Strings per MPP Tracker</td>\n<td style=\"padding: 14px 20px;\">2 / 1+1</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">AC Output Side</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Active Power</td>\n<td style=\"padding: 14px 20px;\">5 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Apparent Power</td>\n<td style=\"padding: 14px 20px;\">5.5 kVA</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Current (400 V / 380 V)</td>\n<td style=\"padding: 14px 20px;\">7.3 A / 7.6 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Current (400 V / 380 V)</td>\n<td style=\"padding: 14px 20px;\">8 A / 8.4 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Output Voltage / Range</td>\n<td style=\"padding: 14px 20px;\">220/380 V, 230/400 V (0.85 Un &#8211; 1.1 Un)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Connection Form</td>\n<td style=\"padding: 14px 20px;\">3L/N/PE</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Grid Frequency / Range</td>\n<td style=\"padding: 14px 20px;\">50/60 Hz (45&#8211;55 / 55&#8211;65 Hz)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Power Factor Adjustment Range</td>\n<td style=\"padding: 14px 20px;\">0.8 leading &#8211; 0.8 lagging</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Total Harmonic Distortion (THDi)</td>\n<td style=\"padding: 14px 20px;\">&lt; 3 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">DC Injection Current</td>\n<td style=\"padding: 14px 20px;\">&lt; 0.5 % In</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Efficiency</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Efficiency</td>\n<td style=\"padding: 14px 20px;\">98.2 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">European Efficiency</td>\n<td style=\"padding: 14px 20px;\">97.6 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Efficiency</td>\n<td style=\"padding: 14px 20px;\">&gt; 99 %</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Equipment Protection</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Polarity Reverse Connection Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Output Overcurrent Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">AC Output Overvoltage Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Output Short Circuit Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Thermal Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">DC Terminal Insulation Impedance Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Component Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Arc Fault Circuit Interrupter (AFCI)</td>\n<td style=\"padding: 14px 20px;\">Optional</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Ground Fault Current Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Power Network Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Island Protection Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Earth Fault Detection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Overvoltage Load Drop Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Residual Current (RCD) Detection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Surge Protection Level</td>\n<td style=\"padding: 14px 20px;\">Type II (DC), Type II (AC)</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Interface</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Communication Interface</td>\n<td style=\"padding: 14px 20px;\">RS485 / RS232</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Monitoring Mode</td>\n<td style=\"padding: 14px 20px;\">GPRS / Wi-Fi / Bluetooth / 4G / LAN (optional)</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">General Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Operating Temperature Range</td>\n<td style=\"padding: 14px 20px;\">-25 &#176;C to +60 &#176;C (&gt;45 &#176;C derating)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Permissible Ambient Humidity</td>\n<td style=\"padding: 14px 20px;\">0&#8211;100 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Permissible Altitude</td>\n<td style=\"padding: 14px 20px;\">4000 m</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Noise Emission</td>\n<td style=\"padding: 14px 20px;\">&lt; 45 dB</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Ingress Protection Rating</td>\n<td style=\"padding: 14px 20px;\">IP65</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Inverter Topology</td>\n<td style=\"padding: 14px 20px;\">Non-Isolated</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Over Voltage Category</td>\n<td style=\"padding: 14px 20px;\">OVC II (DC), OVC III (AC)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Cabinet Size (W &#215; H &#215; D)</td>\n<td style=\"padding: 14px 20px;\">283 &#215; 463 &#215; 178 mm (excl. connectors and brackets)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Weight</td>\n<td style=\"padding: 14px 20px;\">11 kg</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Type of Cooling</td>\n<td style=\"padding: 14px 20px;\">Natural Cooling</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">5 years</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Regulation</td>\n<td style=\"padding: 14px 20px;\">IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002, OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Safety EMC / Standard</td>\n<td style=\"padding: 14px 20px;\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1/2</td>\n</tr>\n</tbody>\n</table>', 3, 'SUN-5K-G06P3-EU-AM2-P1 | Three Phase String Inverter | 2 MPPT', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye SUN-5K-G06P3-EU-AM2-P1 is a state-of-the-art 5 kW three-phase string inverter of the latest generation &#8211; ideal for smaller residential homes and compact commercial installations. With a peak efficiency of 98.2 % and a European efficiency of 97.6 %, it delivers outstanding performance. Two independent MPPTs with an extremely wide voltage range of 120&#8211;1000 V and a very low start-up voltage of only 140 V guarantee maximum yield even in diffuse light conditions. Zero-export capability, integrated VSG technology for grid support, optional string-level monitoring and optional anti-PID function make this inverter future-proof and highly flexible. Weighing just 11 kg, with compact dimensions of 283 &#215; 463 &#215; 178 mm, natural cooling (completely silent) and IP65 protection, it can be installed by one person &#8211; indoors or outdoors. Extensive communication options and full certification to all major European standards complete this top-class package.</p>\n<div style=\"margin: 60px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-008.jpg\" alt=\"Deye SUN-5K-G06P3-EU-AM2-P1 5kW String Inverter\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Advantages</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Excellent Efficiency</strong><br />98.2 % peak &#183; 97.6 % European &#8211; very high yield.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Extremely Low Start-Up</strong><br />Only 140 V start, 120&#8211;1000 V MPPT range.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Zero Export &amp; VSG</strong><br />Perfect for export-limited regions + grid support.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Completely Silent</strong><br />Natural cooling, &lt; 45 dB.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Ultra-Light &amp; Compact</strong><br />Only 11 kg, 283 &#215; 463 &#215; 178 mm, IP65.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Full Protection Suite</strong><br />Type II SPD (DC+AC), optional AFCI &amp; anti-PID.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Smart Monitoring</strong><br />Optional string monitoring, Wi-Fi/4G/LAN.</div>\n</div>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5; margin: 70px 0;\">\n<p>Deye SUN-5K-G06P3-EU-AM2-P1 &#8211; The Silent 5 kW Premium String Inverter</p>\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">98.2 % Efficiency &#183; 2 MPPT &#183; Zero Export &#183; VSG &#183; Silent &#183; Only 11 kg &#183; IP65</p>\n</div>\n</div>', 'Deye SUN-5K-G06P3-EU-AM2-P1 5kW Three-Phase String Inverter (EU)<br /><br />Ultra-light and completely silent 5 kW inverter with 98.2 % efficiency, 2 MPPT (120&#8211;1000 V), zero-export &amp; VSG function, optional string monitoring, only 11 kg, natural cooling. IP65, Type II SPD both sides, fully certified (G99, VDE-AR-N 4105 etc.). Ideal for smaller residential and compact commercial systems.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(1030, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Parameter</th><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Value</th></tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">String Inverter Model SUN-6K-G06P3-EU-AM2-P1</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">PV String Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Input Power</td>\n<td style=\"padding: 14px 20px;\">9 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">1100 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Start-up Voltage</td>\n<td style=\"padding: 14px 20px;\">140 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range</td>\n<td style=\"padding: 14px 20px;\">120&#8211;1000 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">600 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current</td>\n<td style=\"padding: 14px 20px;\">20 + 20 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Input Short Circuit Current</td>\n<td style=\"padding: 14px 20px;\">30 + 30 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">No. of MPP Trackers / Strings per MPP Tracker</td>\n<td style=\"padding: 14px 20px;\">2 / 1+1</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">AC Output Side</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Active Power</td>\n<td style=\"padding: 14px 20px;\">6 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Apparent Power</td>\n<td style=\"padding: 14px 20px;\">6.6 kVA</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Current (400 V / 380 V)</td>\n<td style=\"padding: 14px 20px;\">8.7 A / 9.1 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Current (400 V / 380 V)</td>\n<td style=\"padding: 14px 20px;\">9.6 A / 10 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Output Voltage / Range</td>\n<td style=\"padding: 14px 20px;\">220/380 V, 230/400 V (0.85 Un &#8211; 1.1 Un)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Connection Form</td>\n<td style=\"padding: 14px 20px;\">3L/N/PE</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Grid Frequency / Range</td>\n<td style=\"padding: 14px 20px;\">50/60 Hz (45&#8211;55 / 55&#8211;65 Hz)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Power Factor Adjustment Range</td>\n<td style=\"padding: 14px 20px;\">0.8 leading &#8211; 0.8 lagging</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Total Harmonic Distortion (THDi)</td>\n<td style=\"padding: 14px 20px;\">&lt; 3 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">DC Injection Current</td>\n<td style=\"padding: 14px 20px;\">&lt; 0.5 % In</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Efficiency</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Efficiency</td>\n<td style=\"padding: 14px 20px;\">98.2 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">European Efficiency</td>\n<td style=\"padding: 14px 20px;\">97.6 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Efficiency</td>\n<td style=\"padding: 14px 20px;\">&gt; 99 %</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Equipment Protection</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Polarity Reverse Connection Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Output Overcurrent Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">AC Output Overvoltage Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Output Short Circuit Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Thermal Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">DC Terminal Insulation Impedance Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Component Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Arc Fault Circuit Interrupter (AFCI)</td>\n<td style=\"padding: 14px 20px;\">Optional</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Ground Fault Current Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Power Network Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Island Protection Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Earth Fault Detection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Overvoltage Load Drop Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Residual Current (RCD) Detection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Surge Protection Level</td>\n<td style=\"padding: 14px 20px;\">Type II (DC), Type II (AC)</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Interface</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Communication Interface</td>\n<td style=\"padding: 14px 20px;\">RS485 / RS232</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Monitoring Mode</td>\n<td style=\"padding: 14px 20px;\">GPRS / Wi-Fi / Bluetooth / 4G / LAN (optional)</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">General Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Operating Temperature Range</td>\n<td style=\"padding: 14px 20px;\">-25 &#176;C to +60 &#176;C (&gt;45 &#176;C derating)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Permissible Ambient Humidity</td>\n<td style=\"padding: 14px 20px;\">0&#8211;100 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Permissible Altitude</td>\n<td style=\"padding: 14px 20px;\">4000 m</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Noise Emission</td>\n<td style=\"padding: 14px 20px;\">&lt; 45 dB</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Ingress Protection Rating</td>\n<td style=\"padding: 14px 20px;\">IP65</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Inverter Topology</td>\n<td style=\"padding: 14px 20px;\">Non-Isolated</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Over Voltage Category</td>\n<td style=\"padding: 14px 20px;\">OVC II (DC), OVC III (AC)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Cabinet Size (W &#215; H &#215; D)</td>\n<td style=\"padding: 14px 20px;\">283 &#215; 463 &#215; 178 mm (excl. connectors and brackets)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Weight</td>\n<td style=\"padding: 14px 20px;\">11 kg</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Type of Cooling</td>\n<td style=\"padding: 14px 20px;\">Natural Cooling</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">5 years</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Regulation</td>\n<td style=\"padding: 14px 20px;\">IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002, OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Safety EMC / Standard</td>\n<td style=\"padding: 14px 20px;\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1/2</td>\n</tr>\n</tbody>\n</table>', 3, 'SUN-6K-G06P3-EU-AM2-P1 | Three Phase String Inverter | 2 MPPT', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye SUN-6K-G06P3-EU-AM2-P1 is a state-of-the-art 6 kW three-phase string inverter of the latest generation &#8211; the perfect choice for residential homes and small commercial solar systems. With a peak efficiency of 98.2 % and a European efficiency of 97.6 %, it delivers outstanding performance. Two independent MPPTs with an extremely wide voltage range of 120&#8211;1000 V and a very low start-up voltage of only 140 V guarantee maximum yield even in diffuse light conditions. Zero-export capability, integrated VSG technology for grid support, optional string-level monitoring and optional anti-PID function make this inverter future-proof and highly flexible. Weighing just 11 kg, with compact dimensions of 283 &#215; 463 &#215; 178 mm, natural cooling (completely silent) and IP65 protection, it can be installed by one person &#8211; indoors or outdoors. Extensive communication options and full certification to all major European standards complete this top-class package.</p>\n<div style=\"margin: 60px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-008.jpg\" alt=\"Deye SUN-6K-G06P3-EU-AM2-P1 6kW String Inverter\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Advantages</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Excellent Efficiency</strong><br />98.2 % peak &#183; 97.6 % European &#8211; very high yield.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Extremely Low Start-Up</strong><br />Only 140 V start, 120&#8211;1000 V MPPT range.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Zero Export &amp; VSG</strong><br />Perfect for export-limited regions + grid support.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Completely Silent</strong><br />Natural cooling, &lt; 45 dB.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Ultra-Light &amp; Compact</strong><br />Only 11 kg, 283 &#215; 463 &#215; 178 mm, IP65.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Full Protection Suite</strong><br />Type II SPD (DC+AC), optional AFCI &amp; anti-PID.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Smart Monitoring</strong><br />Optional string monitoring, Wi-Fi/4G/LAN.</div>\n</div>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5; margin: 70px 0;\">\n<p>Deye SUN-6K-G06P3-EU-AM2-P1 &#8211; The Silent 6 kW Premium String Inverter</p>\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">98.2 % Efficiency &#183; 2 MPPT &#183; Zero Export &#183; VSG &#183; Silent &#183; Only 11 kg &#183; IP65</p>\n</div>\n</div>', 'Deye SUN-6K-G06P3-EU-AM2-P1 6kW Three-Phase String Inverter (EU)<br /><br />Ultra-light and completely silent 6 kW inverter with 98.2 % efficiency, 2 MPPT (120&#8211;1000 V), zero-export &amp; VSG function, optional string monitoring, only 11 kg, natural cooling. IP65, Type II SPD both sides, fully certified (G99, VDE-AR-N 4105 etc.). Perfect for residential and small commercial installations.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', '');
INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(1031, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Parameter</th><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Value</th></tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">String Inverter Model SUN-8K-G06P3-EU-AM2-P1</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">PV String Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Input Power</td>\n<td style=\"padding: 14px 20px;\">12 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">1100 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Start-up Voltage</td>\n<td style=\"padding: 14px 20px;\">140 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range</td>\n<td style=\"padding: 14px 20px;\">120&#8211;1000 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">600 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current</td>\n<td style=\"padding: 14px 20px;\">20 + 20 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Input Short Circuit Current</td>\n<td style=\"padding: 14px 20px;\">30 + 30 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">No. of MPP Trackers / Strings per MPP Tracker</td>\n<td style=\"padding: 14px 20px;\">2 / 1+1</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">AC Output Side</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Active Power</td>\n<td style=\"padding: 14px 20px;\">8 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Apparent Power</td>\n<td style=\"padding: 14px 20px;\">8.8 kVA</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Current (400 V / 380 V)</td>\n<td style=\"padding: 14px 20px;\">11.6 A / 12.2 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Current (400 V / 380 V)</td>\n<td style=\"padding: 14px 20px;\">12.8 A / 13.4 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Output Voltage / Range</td>\n<td style=\"padding: 14px 20px;\">220/380 V, 230/400 V (0.85 Un &#8211; 1.1 Un)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Connection Form</td>\n<td style=\"padding: 14px 20px;\">3L/N/PE</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Grid Frequency / Range</td>\n<td style=\"padding: 14px 20px;\">50/60 Hz (45&#8211;55 / 55&#8211;65 Hz)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Power Factor Adjustment Range</td>\n<td style=\"padding: 14px 20px;\">0.8 leading &#8211; 0.8 lagging</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Total Harmonic Distortion (THDi)</td>\n<td style=\"padding: 14px 20px;\">&lt; 3 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">DC Injection Current</td>\n<td style=\"padding: 14px 20px;\">&lt; 0.5 % In</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Efficiency</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Efficiency</td>\n<td style=\"padding: 14px 20px;\">98.3 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">European Efficiency</td>\n<td style=\"padding: 14px 20px;\">97.8 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Efficiency</td>\n<td style=\"padding: 14px 20px;\">&gt; 99 %</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Equipment Protection</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Polarity Reverse Connection Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Output Overcurrent Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">AC Output Overvoltage Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Output Short Circuit Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Thermal Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">DC Terminal Insulation Impedance Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Component Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Arc Fault Circuit Interrupter (AFCI)</td>\n<td style=\"padding: 14px 20px;\">Optional</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Ground Fault Current Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Power Network Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Island Protection Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Earth Fault Detection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Overvoltage Load Drop Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Residual Current (RCD) Detection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Surge Protection Level</td>\n<td style=\"padding: 14px 20px;\">Type II (DC), Type II (AC)</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Interface</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Communication Interface</td>\n<td style=\"padding: 14px 20px;\">RS485 / RS232</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Monitoring Mode</td>\n<td style=\"padding: 14px 20px;\">GPRS / Wi-Fi / Bluetooth / 4G / LAN (optional)</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">General Data</td>\n</tr>\n</tbody>\n</table>', 3, 'SUN-8K-G06P3-EU-AM2-P1 | Three Phase String Inverter | 2 MPPT', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye SUN-8K-G06P3-EU-AM2-P1 is a state-of-the-art 8 kW three-phase string inverter of the latest generation &#8211; perfect for residential homes and smaller commercial solar systems. With a peak efficiency of 98.3 % and a European efficiency of 97.8 %, it delivers outstanding performance. Two independent MPPTs with an extremely wide voltage range of 120&#8211;1000 V and a very low start-up voltage of only 140 V guarantee maximum yield even in diffuse light conditions. Zero-export capability, integrated VSG technology for grid support, optional string-level monitoring and optional anti-PID function make this inverter future-proof and highly flexible. Weighing just 11 kg, with compact dimensions of 283 &#215; 463 &#215; 178 mm, natural cooling (completely silent) and IP65 protection, it can be installed by one person &#8211; indoors or outdoors. Extensive communication options and full certification to all major European standards complete this top-class package.</p>\n<div style=\"margin: 60px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-008.jpg\" alt=\"Deye SUN-8K-G06P3-EU-AM2-P1 8kW String Inverter\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Advantages</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Excellent Efficiency</strong><br />98.3 % peak &#183; 97.8 % European &#8211; very high yield.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Extremely Low Start-Up</strong><br />Only 140 V start, 120&#8211;1000 V MPPT range.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Zero Export &amp; VSG</strong><br />Perfect for export-limited regions + grid support.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Completely Silent</strong><br />Natural cooling, &lt; 45 dB.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Ultra-Light &amp; Compact</strong><br />Only 11 kg, 283 &#215; 463 &#215; 178 mm, IP65.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Full Protection Suite</strong><br />Type II SPD (DC+AC), optional AFCI &amp; anti-PID.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Smart Monitoring</strong><br />Optional string monitoring, Wi-Fi/4G/LAN.</div>\n</div>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5; margin: 70px 0;\">\n<p>Deye SUN-8K-G06P3-EU-AM2-P1 &#8211; The Silent 8 kW Premium String Inverter</p>\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">98.3 % Efficiency &#183; 2 MPPT &#183; Zero Export &#183; VSG &#183; Silent &#183; Only 11 kg &#183; IP65</p>\n</div>\n</div>', 'Deye SUN-8K-G06P3-EU-AM2-P1 8kW Three-Phase String Inverter (EU)<br /><br />Ultra-light and completely silent 8 kW inverter with 98.3 % efficiency, 2 MPPT (120&#8211;1000 V), zero-export &amp; VSG function, optional string monitoring, only 11 kg, natural cooling. IP65, Type II SPD both sides, fully certified (G99, VDE-AR-N 4105 etc.). Ideal for residential and small commercial installations.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(1032, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Parameter</th><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Value</th></tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">String Inverter Model SUN-10K-G06P3-EU-AM2-P1</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">PV String Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Input Power</td>\n<td style=\"padding: 14px 20px;\">15 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">1100 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Start-up Voltage</td>\n<td style=\"padding: 14px 20px;\">140 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range</td>\n<td style=\"padding: 14px 20px;\">120&#8211;1000 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">600 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current</td>\n<td style=\"padding: 14px 20px;\">20 + 20 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Input Short Circuit Current</td>\n<td style=\"padding: 14px 20px;\">30 + 30 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">No. of MPP Trackers / Strings per MPP Tracker</td>\n<td style=\"padding: 14px 20px;\">2 / 1+1</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">AC Output Side</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Active Power</td>\n<td style=\"padding: 14px 20px;\">10 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Apparent Power</td>\n<td style=\"padding: 14px 20px;\">11 kVA</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Current (400 V / 380 V)</td>\n<td style=\"padding: 14px 20px;\">14.5 A / 15.2 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Current (400 V / 380 V)</td>\n<td style=\"padding: 14px 20px;\">16 A / 16.7 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Output Voltage / Range</td>\n<td style=\"padding: 14px 20px;\">220/380 V, 230/400 V (0.85 Un &#8211; 1.1 Un)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Connection Form</td>\n<td style=\"padding: 14px 20px;\">3L/N/PE</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Grid Frequency / Range</td>\n<td style=\"padding: 14px 20px;\">50/60 Hz (45&#8211;55 / 55&#8211;65 Hz)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Power Factor Adjustment Range</td>\n<td style=\"padding: 14px 20px;\">0.8 leading &#8211; 0.8 lagging</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Total Harmonic Distortion (THDi)</td>\n<td style=\"padding: 14px 20px;\">&lt; 3 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">DC Injection Current</td>\n<td style=\"padding: 14px 20px;\">&lt; 0.5 % In</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Efficiency</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Efficiency</td>\n<td style=\"padding: 14px 20px;\">98.3 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">European Efficiency</td>\n<td style=\"padding: 14px 20px;\">97.8 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Efficiency</td>\n<td style=\"padding: 14px 20px;\">&gt; 99 %</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Equipment Protection</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Polarity Reverse Connection Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Output Overcurrent Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">AC Output Overvoltage Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Output Short Circuit Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Thermal Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">DC Terminal Insulation Impedance Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Component Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Arc Fault Circuit Interrupter (AFCI)</td>\n<td style=\"padding: 14px 20px;\">Optional</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Ground Fault Current Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Power Network Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Island Protection Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Earth Fault Detection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Overvoltage Load Drop Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Residual Current (RCD) Detection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Surge Protection Level</td>\n<td style=\"padding: 14px 20px;\">Type II (DC), Type II (AC)</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Interface</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Communication Interface</td>\n<td style=\"padding: 14px 20px;\">RS485 / RS232</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Monitoring Mode</td>\n<td style=\"padding: 14px 20px;\">GPRS / Wi-Fi / Bluetooth / 4G / LAN (optional)</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">General Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Operating Temperature Range</td>\n<td style=\"padding: 14px 20px;\">-25 &#176;C to +60 &#176;C (&gt;45 &#176;C derating)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Permissible Ambient Humidity</td>\n<td style=\"padding: 14px 20px;\">0&#8211;100 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Permissible Altitude</td>\n<td style=\"padding: 14px 20px;\">4000 m</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Noise Emission</td>\n<td style=\"padding: 14px 20px;\">&lt; 45 dB</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Ingress Protection Rating</td>\n<td style=\"padding: 14px 20px;\">IP65</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Inverter Topology</td>\n<td style=\"padding: 14px 20px;\">Non-Isolated</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Over Voltage Category</td>\n<td style=\"padding: 14px 20px;\">OVC II (DC), OVC III (AC)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Cabinet Size (W &#215; H &#215; D)</td>\n<td style=\"padding: 14px 20px;\">283 &#215; 463 &#215; 178 mm (excl. connectors and brackets)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Weight</td>\n<td style=\"padding: 14px 20px;\">11 kg</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Type of Cooling</td>\n<td style=\"padding: 14px 20px;\">Natural Cooling</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">5 years</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Regulation</td>\n<td style=\"padding: 14px 20px;\">IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002, OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Safety EMC / Standard</td>\n<td style=\"padding: 14px 20px;\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1/2</td>\n</tr>\n</tbody>\n</table>', 3, 'SUN-10K-G06P3-EU-AM2-P1 | Three Phase String Inverter | 2 MPPT', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye SUN-10K-G06P3-EU-AM2-P1 is a state-of-the-art 10 kW three-phase string inverter of the latest generation &#8211; ideal for residential and smaller commercial solar systems. With a peak efficiency of 98.3 % and a European efficiency of 97.8 %, it delivers outstanding performance. Two independent MPPTs with an extremely wide voltage range of 120&#8211;1000 V and a very low start-up voltage of only 140 V guarantee maximum yield even in diffuse light conditions. Zero-export capability, integrated VSG technology for grid support, optional string-level monitoring and optional anti-PID function make this inverter future-proof and highly flexible. Weighing just 11 kg, with compact dimensions of 283 &#215; 463 &#215; 178 mm, natural cooling (completely silent) and IP65 protection, it can be installed by one person &#8211; indoors or outdoors. Extensive communication options and full certification to all major European standards complete this top-class package.</p>\n<div style=\"margin: 60px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-008.jpg\" alt=\"Deye SUN-10K-G06P3-EU-AM2-P1 10kW String Inverter\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Advantages</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Excellent Efficiency</strong><br />98.3 % peak &#183; 97.8 % European &#8211; very high yield.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Extremely Low Start-Up</strong><br />Only 140 V start, 120&#8211;1000 V MPPT range.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Zero Export &amp; VSG</strong><br />Perfect for export-limited regions + grid support.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Completely Silent</strong><br />Natural cooling, &lt; 45 dB.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Ultra-Light &amp; Compact</strong><br />Only 11 kg, 283 &#215; 463 &#215; 178 mm, IP65.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Full Protection Suite</strong><br />Type II SPD (DC+AC), optional AFCI &amp; anti-PID.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Smart Monitoring</strong><br />Optional string monitoring, Wi-Fi/4G/LAN.</div>\n</div>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5; margin: 70px 0;\">\n<p>Deye SUN-10K-G06P3-EU-AM2-P1 &#8211; The Silent 10 kW Premium String Inverter</p>\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">98.3 % Efficiency &#183; 2 MPPT &#183; Zero Export &#183; VSG &#183; Silent &#183; Only 11 kg &#183; IP65</p>\n</div>\n</div>', 'Deye SUN-10K-G06P3-EU-AM2-P1 10kW Three-Phase String Inverter (EU)<br /><br />Ultra-light and completely silent 10 kW inverter with 98.3 % efficiency, 2 MPPT (120&#8211;1000 V), zero-export &amp; VSG function, optional string monitoring, only 11 kg, natural cooling. IP65, Type II SPD both sides, fully certified (G99, VDE-AR-N 4105 etc.). Perfect for residential and small commercial systems.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(1033, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Parameter</th><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Value</th></tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">String Inverter Model SUN-12K-G06P3-EU-AM2-P1</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">PV String Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Input Power</td>\n<td style=\"padding: 14px 20px;\">18 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">1100 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Start-up Voltage</td>\n<td style=\"padding: 14px 20px;\">140 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range</td>\n<td style=\"padding: 14px 20px;\">120&#8211;1000 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">600 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current</td>\n<td style=\"padding: 14px 20px;\">20 + 20 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Input Short Circuit Current</td>\n<td style=\"padding: 14px 20px;\">30 + 30 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">No. of MPP Trackers / Strings per MPP Tracker</td>\n<td style=\"padding: 14px 20px;\">2 / 1+1</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">AC Output Side</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Active Power</td>\n<td style=\"padding: 14px 20px;\">12 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Apparent Power</td>\n<td style=\"padding: 14px 20px;\">13.2 kVA</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Current (400 V / 380 V)</td>\n<td style=\"padding: 14px 20px;\">17.4 A / 18.2 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Current (400 V / 380 V)</td>\n<td style=\"padding: 14px 20px;\">19.2 A / 20 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Output Voltage / Range</td>\n<td style=\"padding: 14px 20px;\">220/380 V, 230/400 V (0.85 Un &#8211; 1.1 Un)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Connection Form</td>\n<td style=\"padding: 14px 20px;\">3L/N/PE</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Grid Frequency / Range</td>\n<td style=\"padding: 14px 20px;\">50/60 Hz (45&#8211;55 / 55&#8211;65 Hz)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Power Factor Adjustment Range</td>\n<td style=\"padding: 14px 20px;\">0.8 leading &#8211; 0.8 lagging</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Total Harmonic Distortion (THDi)</td>\n<td style=\"padding: 14px 20px;\">&lt; 3 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">DC Injection Current</td>\n<td style=\"padding: 14px 20px;\">&lt; 0.5 % In</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Efficiency</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Efficiency</td>\n<td style=\"padding: 14px 20px;\">98.3 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">European Efficiency</td>\n<td style=\"padding: 14px 20px;\">97.8 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Efficiency</td>\n<td style=\"padding: 14px 20px;\">&gt; 99 %</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Equipment Protection</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Polarity Reverse Connection Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Output Overcurrent Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">AC Output Overvoltage Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Output Short Circuit Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Thermal Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">DC Terminal Insulation Impedance Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Component Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Arc Fault Circuit Interrupter (AFCI)</td>\n<td style=\"padding: 14px 20px;\">Optional</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Ground Fault Current Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Power Network Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Island Protection Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Earth Fault Detection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Overvoltage Load Drop Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Residual Current (RCD) Detection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Surge Protection Level</td>\n<td style=\"padding: 14px 20px;\">Type II (DC), Type II (AC)</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Interface</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Communication Interface</td>\n<td style=\"padding: 14px 20px;\">RS485 / RS232</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Monitoring Mode</td>\n<td style=\"padding: 14px 20px;\">GPRS / Wi-Fi / Bluetooth / 4G / LAN (optional)</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">General Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Operating Temperature Range</td>\n<td style=\"padding: 14px 20px;\">-25 &#176;C to +60 &#176;C (&gt;45 &#176;C derating)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Permissible Ambient Humidity</td>\n<td style=\"padding: 14px 20px;\">0&#8211;100 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Permissible Altitude</td>\n<td style=\"padding: 14px 20px;\">4000 m</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Noise Emission</td>\n<td style=\"padding: 14px 20px;\">&lt; 45 dB</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Ingress Protection Rating</td>\n<td style=\"padding: 14px 20px;\">IP65</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Inverter Topology</td>\n<td style=\"padding: 14px 20px;\">Non-Isolated</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Over Voltage Category</td>\n<td style=\"padding: 14px 20px;\">OVC II (DC), OVC III (AC)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Cabinet Size (W &#215; H &#215; D)</td>\n<td style=\"padding: 14px 20px;\">283 &#215; 463 &#215; 178 mm (excl. connectors and brackets)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Weight</td>\n<td style=\"padding: 14px 20px;\">11 kg</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Type of Cooling</td>\n<td style=\"padding: 14px 20px;\">Natural Cooling</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">5 years</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Regulation</td>\n<td style=\"padding: 14px 20px;\">IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002, OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Safety EMC / Standard</td>\n<td style=\"padding: 14px 20px;\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1/2</td>\n</tr>\n</tbody>\n</table>', 3, 'SUN-12K-G06P3-EU-AM2-P1 | Three Phase String Inverter | 2 MPPT', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye SUN-12K-G06P3-EU-AM2-P1 is a state-of-the-art 12 kW three-phase string inverter of the latest generation &#8211; perfectly tailored for residential and smaller commercial solar systems. With a peak efficiency of 98.3 % and a European efficiency of 97.8 %, it delivers outstanding performance. Two independent MPPTs with an extremely wide voltage range of 120&#8211;1000 V and a very low start-up voltage of only 140 V ensure maximum yield even in diffuse light conditions. Zero-export capability, integrated VSG technology for grid support, optional string-level monitoring and optional anti-PID function make this inverter future-proof and highly flexible. Weighing just 11 kg, with compact dimensions of 283 &#215; 463 &#215; 178 mm, natural cooling (completely silent) and IP65 protection, it can be installed by one person &#8211; indoors or outdoors. Comprehensive communication options and full certification to all major European standards complete this top-class package.</p>\n<div style=\"margin: 60px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-008.jpg\" alt=\"Deye SUN-12K-G06P3-EU-AM2-P1 12kW String Inverter\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Advantages</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Excellent Efficiency</strong><br />98.3 % peak &#183; 97.8 % European &#8211; very high yield.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Extremely Low Start-Up</strong><br />Only 140 V start, 120&#8211;1000 V MPPT range.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Zero Export &amp; VSG</strong><br />Perfect for export-limited regions + grid support.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Completely Silent</strong><br />Natural cooling, &lt; 45 dB.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Ultra-Light &amp; Compact</strong><br />Only 11 kg, 283 &#215; 463 &#215; 178 mm, IP65.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Full Protection</strong><br />Type II SPD (DC+AC), optional AFCI &amp; anti-PID.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Smart Monitoring</strong><br />Optional string monitoring, Wi-Fi/4G/LAN.</div>\n</div>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5; margin: 70px 0;\">\n<p>Deye SUN-12K-G06P3-EU-AM2-P1 &#8211; The Silent 12 kW Premium String Inverter</p>\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">98.3 % Efficiency &#183; 2 MPPT &#183; Zero Export &#183; VSG &#183; Silent &#183; Only 11 kg &#183; IP65</p>\n</div>\n</div>', 'Deye SUN-12K-G06P3-EU-AM2-P1 12kW Three-Phase String Inverter (EU)<br /><br />Ultra-light and completely silent 12 kW inverter with 98.3 % efficiency, 2 MPPT (120&#8211;1000 V), zero-export &amp; VSG function, optional string monitoring, only 11 kg, natural cooling. IP65, Type II SPD both sides, fully certified (G99, VDE-AR-N 4105 etc.). Ideal for residential and small commercial systems.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', '');
INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(1034, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Parameter</th><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Value</th></tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">String Inverter Model SUN-15K-G06P3-EU-AM2-P1</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">PV String Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Input Power</td>\n<td style=\"padding: 14px 20px;\">22.5 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">1100 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Start-up Voltage</td>\n<td style=\"padding: 14px 20px;\">140 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range</td>\n<td style=\"padding: 14px 20px;\">120&#8211;1000 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">600 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current</td>\n<td style=\"padding: 14px 20px;\">20 + 26 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Input Short Circuit Current</td>\n<td style=\"padding: 14px 20px;\">30 + 39 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">No. of MPP Trackers / Strings per MPP Tracker</td>\n<td style=\"padding: 14px 20px;\">2 / 1+2</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">AC Output Side</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Active Power</td>\n<td style=\"padding: 14px 20px;\">15 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Apparent Power</td>\n<td style=\"padding: 14px 20px;\">16.5 kVA</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Current (400 V / 380 V)</td>\n<td style=\"padding: 14px 20px;\">21.8 A / 22.8 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Current (400 V / 380 V)</td>\n<td style=\"padding: 14px 20px;\">24 A / 25 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Output Voltage / Range</td>\n<td style=\"padding: 14px 20px;\">220/380 V, 230/400 V (0.85 Un &#8211; 1.1 Un)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Connection Form</td>\n<td style=\"padding: 14px 20px;\">3L/N/PE</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Grid Frequency / Range</td>\n<td style=\"padding: 14px 20px;\">50/60 Hz (45&#8211;55 / 55&#8211;65 Hz)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Power Factor Adjustment Range</td>\n<td style=\"padding: 14px 20px;\">0.8 leading &#8211; 0.8 lagging</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Total Harmonic Distortion (THDi)</td>\n<td style=\"padding: 14px 20px;\">&lt; 3 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">DC Injection Current</td>\n<td style=\"padding: 14px 20px;\">&lt; 0.5 % In</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Efficiency</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Efficiency</td>\n<td style=\"padding: 14px 20px;\">98.5 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">European Efficiency</td>\n<td style=\"padding: 14px 20px;\">98.0 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Efficiency</td>\n<td style=\"padding: 14px 20px;\">&gt; 99 %</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Equipment Protection</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Polarity Reverse Connection Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Output Overcurrent Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">AC Output Overvoltage Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Output Short Circuit Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Thermal Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">DC Terminal Insulation Impedance Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Component Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Arc Fault Circuit Interrupter (AFCI)</td>\n<td style=\"padding: 14px 20px;\">Optional</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Ground Fault Current Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Power Network Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Island Protection Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Earth Fault Detection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Overvoltage Load Drop Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Residual Current (RCD) Detection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Surge Protection Level</td>\n<td style=\"padding: 14px 20px;\">Type II (DC), Type II (AC)</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Interface</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Communication Interface</td>\n<td style=\"padding: 14px 20px;\">RS485 / RS232</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Monitoring Mode</td>\n<td style=\"padding: 14px 20px;\">GPRS / Wi-Fi / Bluetooth / 4G / LAN (optional)</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">General Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Operating Temperature Range</td>\n<td style=\"padding: 14px 20px;\">-25 &#176;C to +60 &#176;C (&gt;45 &#176;C derating)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Permissible Ambient Humidity</td>\n<td style=\"padding: 14px 20px;\">0&#8211;100 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Permissible Altitude</td>\n<td style=\"padding: 14px 20px;\">4000 m</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Noise Emission</td>\n<td style=\"padding: 14px 20px;\">&lt; 45 dB</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Ingress Protection Rating</td>\n<td style=\"padding: 14px 20px;\">IP65</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Inverter Topology</td>\n<td style=\"padding: 14px 20px;\">Non-Isolated</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Over Voltage Category</td>\n<td style=\"padding: 14px 20px;\">OVC II (DC), OVC III (AC)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Cabinet Size (W &#215; H &#215; D)</td>\n<td style=\"padding: 14px 20px;\">283 &#215; 463 &#215; 178 mm (excl. connectors and brackets)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Weight</td>\n<td style=\"padding: 14px 20px;\">11 kg</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Type of Cooling</td>\n<td style=\"padding: 14px 20px;\">Intelligent air cooling</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">5 years</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Regulation</td>\n<td style=\"padding: 14px 20px;\">IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002, OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Safety EMC / Standard</td>\n<td style=\"padding: 14px 20px;\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1/2</td>\n</tr>\n</tbody>\n</table>', 3, 'SUN-15K-G06P3-EU-AM2-P1 | Three Phase String Inverter | 2 MPPT', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye SUN-15K-G06P3-EU-AM2-P1 is a highly efficient 15 kW three-phase string inverter of the latest generation, specially developed for residential and smaller commercial solar systems. With a peak efficiency of 98.5 % and a European efficiency of 98 %, it delivers top performance. Two independent MPPTs with an ultra-wide voltage range of 120&#8211;1000 V and a very low start-up voltage of only 140 V guarantee maximum yield even in poor light conditions. Zero-export capability, integrated VSG (Virtual Synchronous Generator) technology for grid stabilisation, optional string-level monitoring and optional anti-PID function make this inverter future-proof and extremely versatile. At just 11 kg and with compact dimensions (283 &#215; 463 &#215; 178 mm) plus IP65 protection, it is perfect for easy wall mounting &#8211; indoors or outdoors. Extensive communication options and full certification to all major European standards round off this outstanding package.</p>\n<div style=\"margin: 60px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-008.jpg\" alt=\"Deye SUN-15K-G06P3-EU-AM2-P1 15kW String Inverter\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Advantages</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Top Efficiency</strong><br />98.5 % peak &#183; 98 % European efficiency &#8211; maximum yield.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Ultra-Low Start-Up</strong><br />Only 140 V start-up, 120&#8211;1000 V MPPT range.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Zero Export &amp; VSG</strong><br />Perfect for export-limited regions + grid support.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Extremely Light</strong><br />Only 11 kg &#8211; single-person installation.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Quiet &amp; Compact</strong><br />&lt; 45 dB, 283 &#215; 463 &#215; 178 mm, IP65.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Full Protection</strong><br />Type II SPD (DC+AC), optional AFCI, anti-PID.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Smart Monitoring</strong><br />Optional string-level monitoring, Wi-Fi/4G/LAN.</div>\n</div>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5; margin: 70px 0;\">\n<p>Deye SUN-15K-G06P3-EU-AM2-P1 &#8211; The Ultra-Compact 15 kW Premium String Inverter</p>\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">98.5 % Efficiency &#183; 2 MPPT &#183; Zero Export &#183; VSG &#183; Only 11 kg &#183; IP65</p>\n</div>\n</div>', '<p dir=\"auto\" style=\"white-space: pre-wrap;\">Deye SUN-15K-G06P3-EU-AM2-P1</p>\n<p dir=\"auto\" style=\"white-space: pre-wrap;\">15kW Three-Phase String Inverter (EU) Ultra-compact 15 kW inverter with 98.5 % efficiency, 2 MPPT (120&#8211;1000 V), zero-export &amp; VSG function, optional string monitoring, only 11 kg and &lt;45 dB. IP65, Type II SPD both sides, fully certified (G99, VDE-AR-N 4105, etc.). Perfect for residential and small commercial systems.</p>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(1035, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Parameter</th><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Value</th></tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">String Inverter Model SUN-20K-G05</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">PV String Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Input Power</td>\n<td style=\"padding: 14px 20px;\">26 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">1100 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Start-up Voltage</td>\n<td style=\"padding: 14px 20px;\">250 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range</td>\n<td style=\"padding: 14px 20px;\">200&#8211;1000 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">600 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current</td>\n<td style=\"padding: 14px 20px;\">26 + 26 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Input Short Circuit Current</td>\n<td style=\"padding: 14px 20px;\">39 + 39 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">No. of MPP Trackers / Strings per MPP Tracker</td>\n<td style=\"padding: 14px 20px;\">2 / 2+2</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">AC Output Side</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Active Power</td>\n<td style=\"padding: 14px 20px;\">20 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Apparent Power</td>\n<td style=\"padding: 14px 20px;\">22 kVA</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Current (400V / 380V)</td>\n<td style=\"padding: 14px 20px;\">29 A / 30.3 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Current (400V / 380V)</td>\n<td style=\"padding: 14px 20px;\">31.9 A / 33.3 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Output Voltage / Range</td>\n<td style=\"padding: 14px 20px;\">220/380 V, 230/400 V (0.85 Un &#8211; 1.1 Un)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Connection Form</td>\n<td style=\"padding: 14px 20px;\">3L/N/PE</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Grid Frequency / Range</td>\n<td style=\"padding: 14px 20px;\">50/60 Hz (45&#8211;55 Hz / 55&#8211;65 Hz)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Power Factor Adjustment Range</td>\n<td style=\"padding: 14px 20px;\">0.8 leading &#8211; 0.8 lagging</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Total Harmonic Distortion (THDi)</td>\n<td style=\"padding: 14px 20px;\">&lt; 3 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">DC Injection Current</td>\n<td style=\"padding: 14px 20px;\">&lt; 0.5 % In</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Efficiency</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Efficiency</td>\n<td style=\"padding: 14px 20px;\">98.5 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">European Efficiency</td>\n<td style=\"padding: 14px 20px;\">98.0 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Efficiency</td>\n<td style=\"padding: 14px 20px;\">&gt; 99 %</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Equipment Protection</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Reverse Polarity Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Output Overcurrent Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">AC Output Overvoltage Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Output Short Circuit Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Thermal Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Insulation Impedance Detection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Component Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Arc Fault Circuit Interrupter (AFCI)</td>\n<td style=\"padding: 14px 20px;\">Optional</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Anti-Islanding Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Residual Current Detection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Surge Protection Level</td>\n<td style=\"padding: 14px 20px;\">Type II (DC), Type II (AC)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">DC Switch</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Interface</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Communication Interface</td>\n<td style=\"padding: 14px 20px;\">RS485 / RS232</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Monitoring Mode</td>\n<td style=\"padding: 14px 20px;\">GPRS / Wi-Fi / Bluetooth / 4G / LAN (optional)</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">General Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Operating Temperature Range</td>\n<td style=\"padding: 14px 20px;\">-25 &#176;C to +60 &#176;C (&gt;45 &#176;C derating)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Permissible Ambient Humidity</td>\n<td style=\"padding: 14px 20px;\">0&#8211;100 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Permissible Altitude</td>\n<td style=\"padding: 14px 20px;\">4000 m</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Noise Emission</td>\n<td style=\"padding: 14px 20px;\">&#8804; 50 dB(A)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Ingress Protection Rating</td>\n<td style=\"padding: 14px 20px;\">IP65</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Inverter Topology</td>\n<td style=\"padding: 14px 20px;\">Non-Isolated</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Over Voltage Category</td>\n<td style=\"padding: 14px 20px;\">OVC II (DC), OVC III (AC)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Cabinet Size (W &#215; H &#215; D)</td>\n<td style=\"padding: 14px 20px;\">362 &#215; 527 &#215; 220 mm (excl. connectors and brackets)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Weight</td>\n<td style=\"padding: 14px 20px;\">20 kg</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Type of Cooling</td>\n<td style=\"padding: 14px 20px;\">Intelligent air cooling</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">5 years</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Regulation</td>\n<td style=\"padding: 14px 20px;\">IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002, OVE-Richtlinie R25, G99, VDE-AR-N 4105</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Safety EMC / Standard</td>\n<td style=\"padding: 14px 20px;\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1/2</td>\n</tr>\n</tbody>\n</table>', 3, 'SUN-20K-G05 | Three Phase String Inverter | 2 MPPT', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye SUN-20K-G05 is a state-of-the-art 20 kW three-phase string inverter of the latest generation for commercial and larger residential solar systems. With a peak efficiency of 98.5 % and a European efficiency of 98 %, it belongs to the absolute top class. Two independent MPPTs with an extremely wide voltage range of 200&#8211;1000 V and a start-up voltage of only 250 V guarantee maximum flexibility and highest yield under all light conditions. The comprehensive protection suite, intelligent air cooling (&#8804; 50 dB), Type II surge protection on both DC and AC sides, and optional AFCI ensure maximum safety and longevity. Weighing just 20 kg with compact dimensions (362 &#215; 527 &#215; 220 mm) and IP65 rating, it is perfect for easy outdoor wall mounting. Extensive communication options (RS485/RS232 standard, Wi-Fi/GPRS/4G/LAN optional) and certification to all major international standards (VDE-AR-N 4105, G99, EN 50549 etc.) make the SUN-20K-G05 the ideal choice for modern, future-proof solar projects.</p>\n<div style=\"margin: 60px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-009.jpg\" alt=\"Deye SUN-20K-G05 20kW String Inverter\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Advantages</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Top-Class Efficiency</strong><br />98.5 % peak &#183; 98 % European efficiency &#8211; minimal losses, maximum output.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Dual MPPT &#183; Ultra-Wide Range</strong><br />200&#8211;1000 V, starts at 250 V &#8211; ultimate design flexibility.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Ultra-Light &amp; Compact</strong><br />Only 20 kg, 362 &#215; 527 &#215; 220 mm &#8211; single-person installation.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Quiet &amp; Rugged</strong><br />&#8804; 50 dB, IP65, -25 to +60 &#176;C &#8211; ideal for outdoor use.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Full Protection Suite</strong><br />Type II SPD (DC+AC), optional AFCI, anti-islanding, RCMU, etc.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Complete Connectivity</strong><br />RS485/RS232 standard, Wi-Fi/GPRS/4G/LAN optional.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Global Certification</strong><br />VDE-AR-N 4105, G99, EN 50549, CEI 0-21, IEC 61727 and more.</div>\n</div>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5; margin: 70px 0;\">\n<p>Deye SUN-20K-G05 &#8211; The Ultra-Lightweight 20 kW Professional String Inverter</p>\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">98.5 % Efficiency &#183; 2 MPPT &#183; Only 20 kg &#183; IP65 &#183; Global Standards</p>\n</div>\n</div>', 'Deye SUN-20K-G05 20kW Three-Phase String Inverter (EU)<br /><br />Ultra-lightweight 20 kW inverter with 98.5 % peak efficiency, dual MPPT (200&#8211;1000 V), and only 20 kg. IP65, extremely quiet (&#8804;50 dB), Type II SPD (DC+AC), optional AFCI, and certified to global standards (VDE-AR-N 4105, G99, EN 50549, etc.). Perfect for commercial rooftops and large residential systems.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(1036, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Parameter</th><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Value</th></tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">String Inverter Model SUN-25K-G05</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">PV String Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Input Power</td>\n<td style=\"padding: 14px 20px;\">32.5 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">1100 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Start-up Voltage</td>\n<td style=\"padding: 14px 20px;\">250 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range</td>\n<td style=\"padding: 14px 20px;\">200&#8211;1000 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">600 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current</td>\n<td style=\"padding: 14px 20px;\">26 + 26 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Input Short Circuit Current</td>\n<td style=\"padding: 14px 20px;\">39 + 39 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">No. of MPP Trackers / Strings per Tracker</td>\n<td style=\"padding: 14px 20px;\">2 / 2+2</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">AC Output Side</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Active Power</td>\n<td style=\"padding: 14px 20px;\">25 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Apparent Power</td>\n<td style=\"padding: 14px 20px;\">27.5 kVA</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Current</td>\n<td style=\"padding: 14px 20px;\">37.9 A / 36.2 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Current</td>\n<td style=\"padding: 14px 20px;\">41.7 A / 39.8 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Output Voltage / Range</td>\n<td style=\"padding: 14px 20px;\">220/380 V, 230/400 V (0.85 Un &#8211; 1.1 Un)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Connection Form</td>\n<td style=\"padding: 14px 20px;\">3L/N/PE</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Grid Frequency / Range</td>\n<td style=\"padding: 14px 20px;\">50/60 Hz (45&#8211;55 / 55&#8211;65 Hz)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Power Factor Adjustment Range</td>\n<td style=\"padding: 14px 20px;\">0.8 leading &#8211; 0.8 lagging</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Total Harmonic Distortion (THDi)</td>\n<td style=\"padding: 14px 20px;\">&lt; 3 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">DC Injection Current</td>\n<td style=\"padding: 14px 20px;\">&lt; 0.5 % In</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Efficiency</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Efficiency</td>\n<td style=\"padding: 14px 20px;\">98.5 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Euro Efficiency</td>\n<td style=\"padding: 14px 20px;\">98.0 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Efficiency</td>\n<td style=\"padding: 14px 20px;\">&gt; 99 %</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Equipment Protection</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Reverse Polarity Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Overcurrent / Overvoltage / Short Circuit Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Thermal Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Insulation &amp; Residual Current Monitoring</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Anti-Islanding Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Surge Protection</td>\n<td style=\"padding: 14px 20px;\">Type II (DC), Type II (AC)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Switch</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Arc Fault Circuit Interrupter (AFCI)</td>\n<td style=\"padding: 14px 20px;\">Optional</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Interface &amp; General Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Communication Interface</td>\n<td style=\"padding: 14px 20px;\">RS485 / RS232</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Monitoring Modes</td>\n<td style=\"padding: 14px 20px;\">GPRS / Wi-Fi / Bluetooth / 4G / LAN (optional)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Operating Temperature Range</td>\n<td style=\"padding: 14px 20px;\">-25 &#176;C to +60 &#176;C (&gt;45 &#176;C derating)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Permissible Ambient Humidity</td>\n<td style=\"padding: 14px 20px;\">0&#8211;100 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Permissible Altitude</td>\n<td style=\"padding: 14px 20px;\">4000 m</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Noise Emission</td>\n<td style=\"padding: 14px 20px;\">&#8804; 50 dB(A)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Ingress Protection Rating</td>\n<td style=\"padding: 14px 20px;\">IP65</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Dimensions (W &#215; H &#215; D)</td>\n<td style=\"padding: 14px 20px;\">362 &#215; 527 &#215; 220 mm (excl. connectors)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Weight</td>\n<td style=\"padding: 14px 20px;\">20 kg</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Cooling</td>\n<td style=\"padding: 14px 20px;\">Intelligent air cooling</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">5 years</td>\n</tr>\n</tbody>\n</table>', 3, 'SUN-25K-G05 | Three Phase String Inverter | 2 MPPT', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye SUN-25K-G05 is a state-of-the-art 25 kW three-phase string inverter of the latest generation for commercial and larger residential solar systems. With a peak efficiency of 98.5 % and a European efficiency of 98 %, it belongs to the absolute top class. Two independent MPPTs with an extremely wide voltage range of 200&#8211;1000 V and a start-up voltage of only 250 V guarantee maximum flexibility and highest yield under all light conditions. The comprehensive protection suite, intelligent air cooling (&#8804; 50 dB), Type II surge protection on both DC and AC sides, and optional AFCI ensure maximum safety and longevity. Weighing just 20 kg with compact dimensions (362 &#215; 527 &#215; 220 mm) and IP65 rating, it is perfect for easy outdoor wall mounting. Extensive communication options (RS485/RS232 standard, Wi-Fi/GPRS/4G/LAN optional) and certification to all major international standards (VDE-AR-N 4105, G99, EN 50549 etc.) make the SUN-25K-G05 the ideal choice for modern, future-proof solar projects.</p>\n<div style=\"margin: 60px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-009.jpg\" alt=\"Deye SUN-25K-G05 25kW String Inverter\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Advantages</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Top-Class Efficiency</strong><br />98.5 % peak &#183; 98 % European efficiency &#8211; minimal losses, maximum output.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Dual MPPT &#183; Ultra-Wide Range</strong><br />200&#8211;1000 V, starts at 250 V &#8211; ultimate design flexibility.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Ultra-Light &amp; Compact</strong><br />Only 20 kg, 362 &#215; 527 &#215; 220 mm &#8211; single-person installation.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Quiet &amp; Rugged</strong><br />&#8804; 50 dB, IP65, -25 to +60 &#176;C &#8211; ideal for outdoor use.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Full Protection Suite</strong><br />Type II SPD (DC+AC), optional AFCI, anti-islanding, RCMU, etc.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Complete Connectivity</strong><br />RS485/RS232 standard, Wi-Fi/GPRS/4G/LAN optional.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Global Certification</strong><br />VDE-AR-N 4105, G99, EN 50549, CEI 0-21, IEC 61727 and more.</div>\n</div>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5; margin: 70px 0;\">\n<p>Deye SUN-25K-G05 &#8211; The Ultra-Lightweight 25 kW Professional String Inverter</p>\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">98.5 % Efficiency &#183; 2 MPPT &#183; Only 20 kg &#183; IP65 &#183; Global Standards</p>\n</div>\n</div>', 'Deye SUN-25K-G05 25kW Three-Phase String Inverter (EU)<br /><br />Ultra-lightweight 25 kW inverter with 98.5 % peak efficiency, dual MPPT (200&#8211;1000 V), and only 20 kg. IP65, extremely quiet (&#8804;50 dB), Type II SPD (DC+AC), optional AFCI, and certified to global standards (VDE-AR-N 4105, G99, EN 50549, etc.). Perfect for commercial rooftops and large residential systems.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', '');
INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(1037, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Parameter</th><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Value</th></tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">String Inverter Model SUN-30K-G04</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">PV String Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Input Power</td>\n<td style=\"padding: 14px 20px;\">39 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">1100 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Start-up Voltage</td>\n<td style=\"padding: 14px 20px;\">250 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range</td>\n<td style=\"padding: 14px 20px;\">200&#8211;1000 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">600 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current</td>\n<td style=\"padding: 14px 20px;\">40 + 40 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Input Short Circuit Current</td>\n<td style=\"padding: 14px 20px;\">60 + 60 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">No. of MPP Trackers / Strings per Tracker</td>\n<td style=\"padding: 14px 20px;\">2 / 3+3</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">AC Output Side</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Active Power</td>\n<td style=\"padding: 14px 20px;\">30 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Apparent Power</td>\n<td style=\"padding: 14px 20px;\">33 kVA</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Current</td>\n<td style=\"padding: 14px 20px;\">45.5 A / 43.5 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Current</td>\n<td style=\"padding: 14px 20px;\">50 A / 47.9 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Output Voltage / Range</td>\n<td style=\"padding: 14px 20px;\">220/380 V, 230/400 V (0.85 Un &#8211; 1.1 Un)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Connection Form</td>\n<td style=\"padding: 14px 20px;\">3L/N/PE</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Grid Frequency / Range</td>\n<td style=\"padding: 14px 20px;\">50/60 Hz (45&#8211;55 / 55&#8211;65 Hz)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Power Factor Adjustment Range</td>\n<td style=\"padding: 14px 20px;\">0.8 leading &#8211; 0.8 lagging</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Total Harmonic Distortion (THDi)</td>\n<td style=\"padding: 14px 20px;\">&lt; 3 %</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Efficiency</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Efficiency</td>\n<td style=\"padding: 14px 20px;\">98.6 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Euro Efficiency</td>\n<td style=\"padding: 14px 20px;\">98.1 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Efficiency</td>\n<td style=\"padding: 14px 20px;\">&gt; 99 %</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">General Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Operating Temperature Range</td>\n<td style=\"padding: 14px 20px;\">-25 &#176;C to +60 &#176;C (&gt;45 &#176;C derating)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Noise Emission</td>\n<td style=\"padding: 14px 20px;\">&#8804; 60 dB</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Ingress Protection Rating</td>\n<td style=\"padding: 14px 20px;\">IP65</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Dimensions (W &#215; H &#215; D)</td>\n<td style=\"padding: 14px 20px;\">330 &#215; 572 &#215; 206 mm</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Weight</td>\n<td style=\"padding: 14px 20px;\">28.7 kg</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Cooling</td>\n<td style=\"padding: 14px 20px;\">Intelligent air cooling</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">5 years</td>\n</tr>\n</tbody>\n</table>', 3, 'SUN-30K-G04 | Three Phase String Inverter | 2 MPPT', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye SUN-30K-G04 is a cutting-edge 30 kW three-phase string inverter designed for commercial and industrial solar systems. Delivering an outstanding 98.6 % maximum efficiency and 98.1 % European efficiency, it ranks among the most efficient inverters in its class. Two independent MPPTs with an ultra-wide 200&#8211;1000 V range and a start-up voltage of just 250 V ensure maximum flexibility and yield in all conditions. A comprehensive protection suite, intelligent air cooling, optional AFCI, and full connectivity make it exceptionally reliable and future-proof. Weighing only 28.7 kg with IP65 rating and operation from -25 &#176;C to +60 &#176;C, it&#8217;s perfect for demanding outdoor installations. Certified to all major global standards (VDE-AR-N 4105, G99, EN 50549, etc.), the SUN-30K-G04 is the ideal choice for high-performance solar projects.</p>\n<div style=\"margin: 60px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-010.jpg\" alt=\"Deye SUN-30K-G04 30kW String Inverter\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Advantages</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Outstanding Efficiency</strong><br />98.6 % peak and 98.1 % European efficiency &#8211; more yield, less loss.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Dual MPPT Wide Range</strong><br />200&#8211;1000 V, starts at 250 V &#8211; ultimate design flexibility.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Full Protection Suite</strong><br />Type II SPD (DC+AC), anti-islanding, RCMU, optional AFCI.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Ultra-Compact &amp; Light</strong><br />Only 28.7 kg and 330&#215;572&#215;206 mm &#8211; easy single-person installation.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Smart &amp; Quiet Cooling</strong><br />Intelligent air cooling, &#8804;60 dB &#8211; long life even in hot climates.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Full Connectivity</strong><br />RS485/RS232 standard, Wi-Fi/GPRS/4G/LAN optional &#8211; perfect remote monitoring.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Global Certification</strong><br />VDE-AR-N 4105, G99, EN 50549, CEI 0-21, IEC 61727 etc.</div>\n</div>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5; margin: 70px 0;\">\n<p>Deye SUN-30K-G04 &#8211; The Compact 30 kW Professional String Inverter</p>\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">98.6 % Efficiency &#183; 2 MPPT &#183; IP65 &#183; Only 28.7 kg &#183; Global Standards</p>\n</div>\n</div>', 'Deye SUN-30K-G04 30kW Three-Phase String Inverter (EU)<br /><br />Compact, high-performance 30 kW inverter with 98.6 % peak efficiency, dual MPPT (200&#8211;1000 V), and only 28.7 kg. IP65-rated, intelligent air cooling (&#8804;60 dB), full protection including Type II SPD, and certified to global standards (VDE-AR-N 4105, G99, EN 50549, etc.). Ideal for commercial rooftop and ground-mounted systems.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(1038, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Parameter</th><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Value</th></tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">String Inverter Model SUN-40K-G04</td>\n</tr>\n<!-- PV String Input Data -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">PV String Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Input Power</td>\n<td style=\"padding: 14px 20px;\">52 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">1100 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Start-up Voltage</td>\n<td style=\"padding: 14px 20px;\">250 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range</td>\n<td style=\"padding: 14px 20px;\">200&#8211;1000 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">600 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current</td>\n<td style=\"padding: 14px 20px;\">40 + 40 + 40 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Input Short Circuit Current</td>\n<td style=\"padding: 14px 20px;\">60 + 60 + 60 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">No. of MPP Trackers / Strings per Tracker</td>\n<td style=\"padding: 14px 20px;\">3 / 3+3+3</td>\n</tr>\n<!-- AC Output Side -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">AC Output Side</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Active Power</td>\n<td style=\"padding: 14px 20px;\">40 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Apparent Power</td>\n<td style=\"padding: 14px 20px;\">44 kVA</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Current</td>\n<td style=\"padding: 14px 20px;\">60.6 A / 58 A (220 V / 230 V)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Current</td>\n<td style=\"padding: 14px 20px;\">66.7 A / 63.8 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Output Voltage / Range</td>\n<td style=\"padding: 14px 20px;\">220/380 V, 230/400 V (0.85 Un &#8211; 1.1 Un)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Connection Form</td>\n<td style=\"padding: 14px 20px;\">3L/N/PE</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Grid Frequency / Range</td>\n<td style=\"padding: 14px 20px;\">50/60 Hz (45&#8211;55 Hz / 55&#8211;65 Hz)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Power Factor Adjustment Range</td>\n<td style=\"padding: 14px 20px;\">0.8 leading &#8211; 0.8 lagging</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Total Harmonic Distortion (THDi)</td>\n<td style=\"padding: 14px 20px;\">&lt; 3 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">DC Injection Current</td>\n<td style=\"padding: 14px 20px;\">&lt; 0.5 % In</td>\n</tr>\n<!-- Efficiency -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Efficiency</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Efficiency</td>\n<td style=\"padding: 14px 20px;\">98.7 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Euro Efficiency</td>\n<td style=\"padding: 14px 20px;\">98.1 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Efficiency</td>\n<td style=\"padding: 14px 20px;\">&gt; 99 %</td>\n</tr>\n<!-- Equipment Protection -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Equipment Protection</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Reverse Polarity Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Output Overcurrent / Overvoltage / Short Circuit Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Thermal Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Insulation Impedance / Residual Current Detection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Anti-Islanding Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Surge Protection</td>\n<td style=\"padding: 14px 20px;\">Type II (DC), Type II (AC)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Switch</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Arc Fault Circuit Interrupter (AFCI)</td>\n<td style=\"padding: 14px 20px;\">Optional</td>\n</tr>\n<!-- Interface -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Interface</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Communication Interface</td>\n<td style=\"padding: 14px 20px;\">RS485/RS232</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Monitoring Modes</td>\n<td style=\"padding: 14px 20px;\">GPRS/Wi-Fi/Bluetooth/4G/LAN (optional)</td>\n</tr>\n<!-- General Data -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">General Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Operating Temperature Range</td>\n<td style=\"padding: 14px 20px;\">-25 &#176;C to +60 &#176;C (&gt;45 &#176;C derating)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Permissible Ambient Humidity</td>\n<td style=\"padding: 14px 20px;\">0&#8211;100 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Permissible Altitude</td>\n<td style=\"padding: 14px 20px;\">4000 m</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Noise Emission</td>\n<td style=\"padding: 14px 20px;\">&lt; 65 dB</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Ingress Protection Rating</td>\n<td style=\"padding: 14px 20px;\">IP65</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Inverter Topology</td>\n<td style=\"padding: 14px 20px;\">Non-isolated</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Over Voltage Category</td>\n<td style=\"padding: 14px 20px;\">OVC II (DC), OVC III (AC)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Dimensions (W &#215; H &#215; D)</td>\n<td style=\"padding: 14px 20px;\">434 &#215; 570 &#215; 243 mm (excl. connectors)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Weight</td>\n<td style=\"padding: 14px 20px;\">39 kg</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">5 years</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Cooling</td>\n<td style=\"padding: 14px 20px;\">Intelligent air cooling</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Regulation</td>\n<td style=\"padding: 14px 20px;\">IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002, OVE-Richtlinie R25, G99, VDE-AR-N 4105</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Safety / EMC</td>\n<td style=\"padding: 14px 20px;\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</td>\n</tr>\n</tbody>\n</table>', 3, 'SUN-40K-G04 | Three Phase String Inverter | 3 MPPT', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye SUN-40K-G04 is a state-of-the-art 40 kW three-phase string inverter engineered for medium to large commercial and industrial solar projects. Delivering an outstanding 98.7 % maximum efficiency and 98.1 % European efficiency, it sets the benchmark in energy conversion. With support for zero export and VSG applications, a wide 200&#8211;1000 V MPPT range, and optional intelligent string monitoring, it offers unmatched flexibility and precision diagnostics. A comprehensive protection suite, optional anti-PID function, and intelligent air cooling ensure maximum safety and longevity. Featuring IP65 protection, operation from -25 &#176;C to +60 &#176;C, and extensive connectivity (Wi-Fi, GPRS, LAN, etc.), this inverter excels in any environment. Fully compliant with global standards, it guarantees safe, efficient, and future-proof integration worldwide.</p>\n<div style=\"margin: 60px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-011.jpg\" alt=\"Deye SUN-40K-G04 40kW String Inverter\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Advantages</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Top Efficiency</strong><br />98.7 % peak and 98.1 % European efficiency &#8211; minimal losses, maximum performance in all conditions.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Versatile Applications</strong><br />Zero export &amp; VSG capable &#8211; perfectly adapts to diverse grid codes and requirements.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Intelligent String Monitoring</strong><br />Optional per-string monitoring for precise fault detection and optimal maintenance.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Wide MPPT Range</strong><br />200&#8211;1000 V enables flexible system design and maximum yield in varying light conditions.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Full Protection Suite</strong><br />DC reverse polarity, AC overcurrent/overvoltage/short-circuit, anti-islanding, RCMU, etc.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Optional Anti-PID</strong><br />Prevents long-term module degradation &#8211; ensures sustained high performance.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Rugged IP65 Design</strong><br />Dust- and waterproof, -25 &#176;C to +60 &#176;C operation &#8211; built for outdoor use.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Smart Air Cooling</strong><br />Efficient thermal management for reliability even in extreme heat.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Full Connectivity</strong><br />RS485/RS232 standard, Wi-Fi/GPRS/4G/LAN optional &#8211; seamless remote monitoring.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Global Certification</strong><br />VDE-AR-N 4105, G99, CEI 0-21, EN 50549, IEC 61727 etc. &#8211; ready for worldwide deployment.</div>\n</div>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5; margin: 70px 0;\">\n<p>Deye SUN-40K-G04 &#8211; The Professional 40 kW String Inverter for Commercial Solar Systems</p>\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">98.7 % Efficiency &#183; 3 MPPT &#183; IP65 &#183; Smart Cooling &#183; Global Standards</p>\n</div>\n</div>', 'Deye SUN-40K-G04 40kW Three-Phase String Inverter (EU)<br /><br />High-performance 40 kW inverter with 98.7 % peak efficiency and three independent MPPTs (200&#8211;1000 V). Supports zero export and VSG, optional string monitoring and anti-PID function. IP65-rated, intelligent air cooling, comprehensive protection features, and certified to global standards (VDE-AR-N 4105, G99, CEI 0-21, EN 50549, etc.). Perfect for medium to large commercial and industrial solar installations.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(1039, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin-bottom: 60px; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Parameter</th><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Value</th></tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">String Inverter Model SUN-50K-G04</td>\n</tr>\n<!-- PV String Input Data -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">PV String Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Input Power</td>\n<td style=\"padding: 14px 20px;\">65 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">1100 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Start-up Voltage</td>\n<td style=\"padding: 14px 20px;\">250 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range</td>\n<td style=\"padding: 14px 20px;\">200&#8211;1000 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">600 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current</td>\n<td style=\"padding: 14px 20px;\">40 + 40 + 40 + 40 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Input Short Circuit Current</td>\n<td style=\"padding: 14px 20px;\">60 + 60 + 60 + 60 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">No. of MPP Trackers / Strings per Tracker</td>\n<td style=\"padding: 14px 20px;\">4 / 3+3+3+3</td>\n</tr>\n<!-- AC Output Side -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">AC Output Side</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Active Power</td>\n<td style=\"padding: 14px 20px;\">50 kW</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Apparent Power</td>\n<td style=\"padding: 14px 20px;\">55 kVA</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Current</td>\n<td style=\"padding: 14px 20px;\">75.8 A / 72.5 A (220 V / 230 V)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Current</td>\n<td style=\"padding: 14px 20px;\">83.3 A / 79.7 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Output Voltage / Range</td>\n<td style=\"padding: 14px 20px;\">220/380 V, 230/400 V (0.85 Un &#8211; 1.1 Un)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Connection Form</td>\n<td style=\"padding: 14px 20px;\">3L/N/PE</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Grid Frequency / Range</td>\n<td style=\"padding: 14px 20px;\">50/60 Hz (45&#8211;55 Hz / 55&#8211;65 Hz)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Power Factor Adjustment Range</td>\n<td style=\"padding: 14px 20px;\">0.8 leading &#8211; 0.8 lagging</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Total Harmonic Distortion (THDi)</td>\n<td style=\"padding: 14px 20px;\">&lt; 3 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">DC Injection Current</td>\n<td style=\"padding: 14px 20px;\">&lt; 0.5 % In</td>\n</tr>\n<!-- Efficiency -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Efficiency</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Efficiency</td>\n<td style=\"padding: 14px 20px;\">98.7 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Euro Efficiency</td>\n<td style=\"padding: 14px 20px;\">98.1 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Efficiency</td>\n<td style=\"padding: 14px 20px;\">&gt; 99 %</td>\n</tr>\n<!-- Equipment Protection -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Equipment Protection</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Reverse Polarity Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Output Overcurrent / Overvoltage / Short Circuit Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Thermal Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Insulation Impedance / Residual Current Detection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Anti-Islanding Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Surge Protection</td>\n<td style=\"padding: 14px 20px;\">Type II (DC), Type II (AC)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Switch</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Arc Fault Circuit Interrupter (AFCI)</td>\n<td style=\"padding: 14px 20px;\">Optional</td>\n</tr>\n<!-- Interface -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Interface</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Communication Interface</td>\n<td style=\"padding: 14px 20px;\">RS485/RS232</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Monitoring Modes</td>\n<td style=\"padding: 14px 20px;\">GPRS/Wi-Fi/Bluetooth/4G/LAN (optional)</td>\n</tr>\n<!-- General Data -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">General Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Operating Temperature Range</td>\n<td style=\"padding: 14px 20px;\">-25 &#176;C to +60 &#176;C (&gt;45 &#176;C derating)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Permissible Ambient Humidity</td>\n<td style=\"padding: 14px 20px;\">0&#8211;100 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Permissible Altitude</td>\n<td style=\"padding: 14px 20px;\">4000 m</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Noise Emission</td>\n<td style=\"padding: 14px 20px;\">&lt; 65 dB</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Ingress Protection Rating</td>\n<td style=\"padding: 14px 20px;\">IP65</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Inverter Topology</td>\n<td style=\"padding: 14px 20px;\">Non-isolated</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Over Voltage Category</td>\n<td style=\"padding: 14px 20px;\">OVC II (DC), OVC III (AC)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Dimensions (W &#215; H &#215; D)</td>\n<td style=\"padding: 14px 20px;\">434 &#215; 570 &#215; 243 mm (excl. connectors)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Weight</td>\n<td style=\"padding: 14px 20px;\">39 kg</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">5 years</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Cooling</td>\n<td style=\"padding: 14px 20px;\">Intelligent air cooling</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Regulation</td>\n<td style=\"padding: 14px 20px;\">IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002, OVE-Richtlinie R25, G99, VDE-AR-N 4105</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Safety / EMC</td>\n<td style=\"padding: 14px 20px;\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</td>\n</tr>\n</tbody>\n</table>', 3, 'SUN-50K-G04 | Three Phase String Inverter | 4 MPPT', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye SUN-50K-G04 is a state-of-the-art 50 kW three-phase string inverter engineered for demanding commercial and industrial solar installations. Boasting an exceptional 98.7 % maximum efficiency and a 98.1 % European efficiency, it delivers unparalleled energy conversion performance. Designed for versatility, it supports zero export and Virtual Synchronous Generator (VSG) applications, features a wide MPPT voltage range (200&#8211;1000 V) for flexible system design, and offers optional intelligent string monitoring for precise diagnostics. A comprehensive protection suite, optional anti-PID function, and advanced intelligent air cooling ensure maximum safety and durability. With IP65 protection, a broad operating temperature range (-25 &#176;C to +60 &#176;C), and extensive communication interfaces (Wi-Fi, GPRS, LAN, etc.), this inverter is built to excel in diverse environments. Compliant with major international standards, it guarantees seamless and secure integration into global solar systems &#8211; the ultimate choice for high-performance solar projects.</p>\n<div style=\"margin: 60px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-011.jpg\" alt=\"Deye SUN-50K-G04 50kW String Inverter\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Features</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Unmatched Efficiency</strong><br />Achieves a maximum efficiency of 98.7 % and a European efficiency of 98.1 %, minimizing energy losses and ensuring consistent, high-performance output across various conditions.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Versatile Applications</strong><br />Supports zero export and VSG applications, making it adaptable to diverse grid requirements and regulations &#8211; perfect for flexible commercial installations.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Intelligent String Monitoring</strong><br />Optional intelligent string monitoring provides granular insights into each solar string&#8217;s performance, enabling precise diagnostics and enhanced system maintenance.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Wide Voltage Range</strong><br />Features a 200&#8211;1000 V MPPT voltage range, allowing flexible system design and maximizing energy yield under varying sunlight conditions.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Comprehensive Protection Suite</strong><br />Includes DC reverse polarity protection, AC overcurrent, overvoltage, and short-circuit protection, plus thermal shutdown, anti-islanding, and ground fault monitoring for ultimate safety.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Optional Anti-PID Function</strong><br />The anti-PID function prevents long-term performance degradation in solar panels, ensuring sustained efficiency throughout the system&#8217;s lifespan.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Robust Design</strong><br />IP65-rated for dust and water resistance, with a -25 &#176;C to +60 &#176;C operating range, making it ideal for outdoor installations in challenging environments.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Intelligent Air Cooling</strong><br />Advanced air cooling technology ensures efficient thermal management, enhancing durability and stability even in high-temperature conditions.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Extensive Communication</strong><br />Supports GPRS, Wi-Fi, Bluetooth, 4G, and LAN (optional), plus standard RS485/RS232, for seamless integration and easy system monitoring.</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Global Standards Compliance</strong><br />Meets IEC 61727, EN 50549, VDE-AR-N 4105, and other standards, ensuring safe and efficient integration into solar systems worldwide.</div>\n</div>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5; margin: 70px 0;\">\n<p>Deye SUN-50K-G04 &#8211; The High-Performance 50 kW String Inverter for Commercial Solar Projects</p>\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">98.7 % Efficiency &#183; Wide MPPT Range &#183; IP65 &#183; Intelligent Cooling &#183; Global Standards</p>\n</div>\n</div>', 'Deye SUN-50K-G04 50kW Three-Phase String Inverter (EU)<br /><br />The Deye SUN-50K-G04 is a high-performance 50 kW inverter designed for large-scale commercial and industrial solar systems. With a peak efficiency of 98.7 %, a wide 200&#8211;1000 V MPPT range, and support for zero export and VSG applications, it delivers unmatched flexibility and efficiency. Optional intelligent string monitoring, a robust protection suite, and an anti-PID function ensure long-term reliability. Featuring IP65 protection, intelligent air cooling, and extensive communication options (Wi-Fi, GPRS, LAN), it thrives in demanding environments. Certified to IEC 61727, VDE-AR-N 4105, and more, it guarantees global compatibility and safety.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', '');
INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(1040, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin-bottom: 60px; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Parameter</th><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Value</th></tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Microinverter Model SUN-M80G4-EU-Q0</td>\n</tr>\n<!-- PV String Input Data -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">PV String Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Input Power</td>\n<td style=\"padding: 14px 20px;\">210&#8211;560 W (2 pieces)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">60 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Start-up Voltage</td>\n<td style=\"padding: 14px 20px;\">20 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range</td>\n<td style=\"padding: 14px 20px;\">25&#8211;55 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">42.5 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current</td>\n<td style=\"padding: 14px 20px;\">13 + 13 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Input Short Circuit Current</td>\n<td style=\"padding: 14px 20px;\">19.5 + 19.5 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">No. of MPP Trackers / Strings per Tracker</td>\n<td style=\"padding: 14px 20px;\">2 / 1</td>\n</tr>\n<!-- AC Output Side -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">AC Output Side</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Active Power</td>\n<td style=\"padding: 14px 20px;\">800 W</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Apparent Power</td>\n<td style=\"padding: 14px 20px;\">800 VA</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Current</td>\n<td style=\"padding: 14px 20px;\">3.7 A / 3.5 A (230 V / 220 V)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Current</td>\n<td style=\"padding: 14px 20px;\">3.7 A / 3.5 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Output Voltage / Range</td>\n<td style=\"padding: 14px 20px;\">220/230 V (0.85 Un &#8211; neuen1.1 Un)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Connection Form</td>\n<td style=\"padding: 14px 20px;\">L/N/PE</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Grid Frequency / Range</td>\n<td style=\"padding: 14px 20px;\">50/60 Hz (45&#8211;55 Hz / 55&#8211;65 Hz)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Units per Branch</td>\n<td style=\"padding: 14px 20px;\">6</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Power Factor Adjustment Range</td>\n<td style=\"padding: 14px 20px;\">0.9 leading &#8211; 0.9 lagging</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Total Harmonic Distortion (THDi)</td>\n<td style=\"padding: 14px 20px;\">&lt; 3 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Injection Current</td>\n<td style=\"padding: 14px 20px;\">&lt; 0.5 % In</td>\n</tr>\n<!-- Efficiency -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Efficiency</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Efficiency</td>\n<td style=\"padding: 14px 20px;\">96.5 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Euro Efficiency</td>\n<td style=\"padding: 14px 20px;\">96.0 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Efficiency</td>\n<td style=\"padding: 14px 20px;\">&gt; 99 %</td>\n</tr>\n<!-- Equipment Protection -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Equipment Protection</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Reverse Polarity Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Output Overcurrent / Overvoltage / Short Circuit Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Thermal Protection / Anti-Islanding / Surge Protection</td>\n<td style=\"padding: 14px 20px;\">Yes / Yes / Type II (AC)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Insulation Impedance Detection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<!-- General Data -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">General Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Communication Interface</td>\n<td style=\"padding: 14px 20px;\">Wi-Fi (module-level monitoring)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Operating Temperature Range</td>\n<td style=\"padding: 14px 20px;\">&#8211;40 &#176;C to +65 &#176;C (&gt;45 &#176;C derating)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Permissible Ambient Humidity</td>\n<td style=\"padding: 14px 20px;\">0 &#8211; 100 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Permissible Altitude</td>\n<td style=\"padding: 14px 20px;\">2000 m</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Noise Emission</td>\n<td style=\"padding: 14px 20px;\">&#8804; 25 dB</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Ingress Protection Rating</td>\n<td style=\"padding: 14px 20px;\">IP67</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Cooling</td>\n<td style=\"padding: 14px 20px;\">Natural cooling</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Dimensions (W &#215; H &#215; D)</td>\n<td style=\"padding: 14px 20px;\">280.5 &#215; 190 &#215; 40 mm (excl. connectors)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Weight</td>\n<td style=\"padding: 14px 20px;\">3 kg</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">15 years</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Design Lifetime</td>\n<td style=\"padding: 14px 20px;\">25 years</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Regulation</td>\n<td style=\"padding: 14px 20px;\">VDE-AR-N 4105, G98/G99, CEI 0-21, EN 50549, IEC 61727 etc.</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Safety / EMC</td>\n<td style=\"padding: 14px 20px;\">IEC/EN 62109-1/-2, IEC/EN 61000-6-1/2/3/4</td>\n</tr>\n</tbody>\n</table>', 3, 'SUN-M80G4-EU-Q0 | Micro Inverter | 2 MPPT', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye SUN-M80G4-EU-Q0 is the most popular 800 W microinverter with true Dual MPPT technology. Perfectly suited for balcony power plants up to 800 W (VDE-compliant in Germany), it features rapid shutdown &lt; 100 ms, full IP67 sealing, integrated Wi-Fi, and an outstanding 15-year warranty with a 25-year design life.</p>\n<div style=\"margin: 60px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-012.jpg\" alt=\"Deye SUN-M80G4-EU-Q0 800W Microinverter\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Advantages</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">True Dual MPPT</strong><br />2 independent trackers &#8211; maximum yield even with partial shading</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">800 W Output</strong><br />Ideal for 2 &#215; 400&#8211;500 W+ modules</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Rapid Shutdown &lt; 100 ms</strong><br />Compliant with DIN VDE V 0126-95</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">IP67 Waterproof</strong><br />Fully sealed &#8211; perfect for balconies &amp; roofs</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Built-in Wi-Fi</strong><br />Module-level monitoring via app</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Only 3 kg</strong><br />Extremely lightweight and compact</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">15-Year Warranty</strong><br />25-year design life &#8211; maximum reliability</div>\n</div>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5; margin: 70px 0;\">\n<p>Deye SUN-M80G4-EU-Q0 &#8211; The #1 800 W Microinverter for Balcony Solar Systems</p>\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">Dual MPPT &#183; Rapid Shutdown &#183; IP67 &#183; 15-Year Warranty &#183; 25-Year Lifetime</p>\n</div>\n</div>', 'Deye SUN-M80G4-EU-Q0 800W Microinverter (EU)<br /><br />&#8226; True Dual MPPT &#8211; 2 independent trackers<br />&#8226; 800 W rated output &#8211; perfect for 2 &#215; 400&#8211;500 W+ modules<br />&#8226; Rapid shutdown &lt; 100 ms (DIN VDE V 0126-95 compliant)<br />&#8226; IP67 fully waterproof &amp; dustproof<br />&#8226; Integrated Wi-Fi with module-level monitoring<br />&#8226; Ultra-compact &amp; lightweight &#8211; only 3 kg<br />&#8226; 15-year warranty + 25-year design life<br />&#8226; Certified: VDE-AR-N 4105, G98/G99, CEI 0-21 etc.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(1041, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin-bottom: 60px; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Parameter</th><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Value</th></tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Microinverter Model SUN-M100G4-EU-Q0</td>\n</tr>\n<!-- PV String Input Data -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">PV String Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Input Power</td>\n<td style=\"padding: 14px 20px;\">210&#8211;700 W (2 pieces)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">60 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Start-up Voltage</td>\n<td style=\"padding: 14px 20px;\">20 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range</td>\n<td style=\"padding: 14px 20px;\">25&#8211;55 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">42.5 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current</td>\n<td style=\"padding: 14px 20px;\">13 + 13 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Input Short Circuit Current</td>\n<td style=\"padding: 14px 20px;\">19.5 + 19.5 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">No. of MPP Trackers / Strings per Tracker</td>\n<td style=\"padding: 14px 20px;\">2 / 1</td>\n</tr>\n<!-- AC Output Side -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">AC Output Side</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Active Power</td>\n<td style=\"padding: 14px 20px;\">1000 W</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Apparent Power</td>\n<td style=\"padding: 14px 20px;\">1000 VA</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Current</td>\n<td style=\"padding: 14px 20px;\">4.6 A / 4.4 A (230 V / 220 V)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Current</td>\n<td style=\"padding: 14px 20px;\">4.6 A / 4.4 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Output Voltage / Range</td>\n<td style=\"padding: 14px 20px;\">220/230 V (0.85 Un &#8211; 1.1 Un)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Connection Form</td>\n<td style=\"padding: 14px 20px;\">L/N/PE</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Grid Frequency / Range</td>\n<td style=\"padding: 14px 20px;\">50/60 Hz (45&#8211;55 Hz / 55&#8211;65 Hz)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Units per Branch</td>\n<td style=\"padding: 14px 20px;\">5</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Power Factor Adjustment Range</td>\n<td style=\"padding: 14px 20px;\">0.9 leading &#8211; 0.9 lagging</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Total Harmonic Distortion (THDi)</td>\n<td style=\"padding: 14px 20px;\">&lt; 3 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Injection Current</td>\n<td style=\"padding: 14px 20px;\">&lt; 0.5 % In</td>\n</tr>\n<!-- Efficiency -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Efficiency</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Efficiency</td>\n<td style=\"padding: 14px 20px;\">96.5 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Euro Efficiency</td>\n<td style=\"padding: 14px 20px;\">96.0 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Efficiency</td>\n<td style=\"padding: 14px 20px;\">&gt; 99 %</td>\n</tr>\n<!-- Equipment Protection -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Equipment Protection</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Reverse Polarity Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Output Overcurrent / Overvoltage / Short Circuit Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Thermal Protection / Anti-Islanding / Surge Protection</td>\n<td style=\"padding: 14px 20px;\">Yes / Yes / Type II (AC)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Insulation Impedance Detection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<!-- General Data -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">General Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Communication Interface</td>\n<td style=\"padding: 14px 20px;\">Wi-Fi (module-level monitoring)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Operating Temperature Range</td>\n<td style=\"padding: 14px 20px;\">&#8211;40 &#176;C to +65 &#176;C (&gt;45 &#176;C derating)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Permissible Ambient Humidity</td>\n<td style=\"padding: 14px 20px;\">0 &#8211; 100 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Permissible Altitude</td>\n<td style=\"padding: 14px 20px;\">2000 m</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Noise Emission</td>\n<td style=\"padding: 14px 20px;\">&#8804; 25 dB</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Ingress Protection Rating</td>\n<td style=\"padding: 14px 20px;\">IP67</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Cooling</td>\n<td style=\"padding: 14px 20px;\">Natural cooling</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Dimensions (W &#215; H &#215; D)</td>\n<td style=\"padding: 14px 20px;\">280.5 &#215; 190 &#215; 40 mm (excl. connectors)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Weight</td>\n<td style=\"padding: 14px 20px;\">3 kg</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">15 years</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Design Lifetime</td>\n<td style=\"padding: 14px 20px;\">25 years</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Regulation</td>\n<td style=\"padding: 14px 20px;\">VDE-AR-N 4105, G98/G99, CEI 0-21, EN 50549, IEC 61727 etc.</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Safety / EMC</td>\n<td style=\"padding: 14px 20px;\">IEC/EN 62109-1/-2, IEC/EN 61000-6-1/2/3/4</td>\n</tr>\n</tbody>\n</table>', 3, 'SUN-M100G4-EU-Q0 | Micro Inverter | 2 MPPT', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye SUN-M100G4-EU-Q0 is a premium 1000 W microinverter with true Dual MPPT technology, specially developed for balcony power plants and small roof systems. With its compact design, extremely long 15-year warranty (25-year design life), rapid shutdown function and IP67 protection, it sets new standards in safety, reliability and ease of installation.</p>\n<div style=\"margin: 60px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-012.jpg\" alt=\"Deye SUN-M100G4-EU-Q0 1000W Mikrowechselrichter\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Advantages</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">True Dual MPPT</strong><br />2 independent trackers &#8211; maximum yield even with shading</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">1000 W Output</strong><br />Perfect for 2 &#215; 450&#8211;600 W+ modules</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Rapid Shutdown &lt;100 ms</strong><br />Compliant with DIN VDE V 0126-95</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">IP67 Waterproof</strong><br />Fully sealed &#8211; ideal for balconies &amp; roofs</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Built-in Wi-Fi</strong><br />Module-level monitoring via app</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Only 3 kg</strong><br />Extremely light and compact</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">15-Year Warranty</strong><br />25-year design life &#8211; maximum reliability</div>\n</div>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5; margin: 70px 0;\">\n<p>Deye SUN-M100G4-EU-Q0 &#8211; The Ultimate 1000 W Dual-MPPT Microinverter</p>\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">Rapid Shutdown &#183; IP67 &#183; 15-Year Warranty &#183; 25-Year Lifetime</p>\n</div>\n</div>', 'Deye SUN-M100G4-EU-Q0 1000W Microinverter (EU)<br /><br />&#8226; True Dual MPPT &#8211; 2 independent trackers<br />&#8226; 1000 W rated output &#8211; ideal for 2 high-performance modules<br />&#8226; Rapid shutdown &lt;100 ms (DIN VDE V 0126-95 compliant)<br />&#8226; IP67 fully waterproof &amp; dustproof<br />&#8226; Integrated Wi-Fi with module-level monitoring<br />&#8226; Extremely compact &amp; lightweight (only 3 kg)<br />&#8226; 15-year warranty + 25-year design life<br />&#8226; Certified: VDE-AR-N 4105, G98/G99, CEI 0-21 etc.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(1042, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin-bottom: 60px; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Parameter</th><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Value</th></tr>\n<tr style=\"background: #30358C; color: white;\"><th colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold; text-align: left;\">Deye SUN-M160G4-EU-Q0 (1600 W Quad MPPT Microinverter)</th></tr>\n<!-- PV String Input Data -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">PV String Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Input Power</td>\n<td style=\"padding: 14px 20px;\">210&#8211;560 W (4 pieces)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">60 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Start-up Voltage</td>\n<td style=\"padding: 14px 20px;\">20 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range</td>\n<td style=\"padding: 14px 20px;\">25&#8211;55 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">42.5 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current</td>\n<td style=\"padding: 14px 20px;\">15 + 15 + 15 + 15 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Input Short Circuit Current</td>\n<td style=\"padding: 14px 20px;\">22.5 + 22.5 + 22.5 + 22.5 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">No. of MPP Trackers / Strings per Tracker</td>\n<td style=\"padding: 14px 20px;\">4 / 1</td>\n</tr>\n<!-- AC Output Side -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">AC Output Side</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Active Power</td>\n<td style=\"padding: 14px 20px;\">1600 W</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Apparent Power</td>\n<td style=\"padding: 14px 20px;\">1600 VA</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Current</td>\n<td style=\"padding: 14px 20px;\">7.3 A / 7 A (230 V / 220 V)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Current</td>\n<td style=\"padding: 14px 20px;\">7.3 A / 7 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Output Voltage / Range</td>\n<td style=\"padding: 14px 20px;\">220/230 V (0.85 Un &#8211; 1.1 Un)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Connection Form</td>\n<td style=\"padding: 14px 20px;\">L/N/PE</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Grid Frequency / Range</td>\n<td style=\"padding: 14px 20px;\">50/60 Hz (45&#8211;55 Hz / 55&#8211;65 Hz)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Units per Branch</td>\n<td style=\"padding: 14px 20px;\">4</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Power Factor Adjustment Range</td>\n<td style=\"padding: 14px 20px;\">0.9 leading &#8211; 0.9 lagging</td>\n</tr>\n<tr>\n<td style=\"padding: 14&#1089;&#1110;&#1074;px 20px;\">Total Harmonic Distortion (THDi)</td>\n<td style=\"padding: 14px 20px;\">&lt; 3 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Injection Current</td>\n<td style=\"padding: 14px 20px;\">&lt; 0.5 % In</td>\n</tr>\n<!-- Efficiency -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Efficiency</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Efficiency</td>\n<td style=\"padding: 14px 20px;\">96.50 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Euro Efficiency</td>\n<td style=\"padding: 14px 20px;\">96.0 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Efficiency</td>\n<td style=\"padding: 14px 20px;\">&gt; 99 %</td>\n</tr>\n<!-- Equipment Protection -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Equipment Protection</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Reverse Polarity Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Output Overcurrent / Overvoltage / Short Circuit Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Thermal Protection / Anti-Islanding / Surge Protection</td>\n<td style=\"padding: 14px 20px;\">Yes / Yes / Type II (AC)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Insulation Impedance Detection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<!-- Interface & General Data -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">General Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Communication Interface</td>\n<td style=\"padding: 14px 20px;\">Wi-Fi</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Operating Temperature Range</td>\n<td style=\"padding: 14px 20px;\">&#8211;40 &#176;C to +65 &#176;C (&gt;45 &#176;C derating)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Permissible Ambient Humidity</td>\n<td style=\"padding: 14px 20px;\">0 &#8211; 100 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Permissible Altitude</td>\n<td style=\"padding: 14px 20px;\">2000 m</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Noise Emission</td>\n<td style=\"padding: 14px 20px;\">&#8804; 25 dB</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Ingress Protection Rating</td>\n<td style=\"padding: 14px 20px;\">IP67</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Cooling</td>\n<td style=\"padding: 14px 20px;\">Natural cooling</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Dimensions (W &#215; H &#215; D)</td>\n<td style=\"padding: 14px 20px;\">311 &#215; 250.5 &#215; 36.5 mm (excl. connectors)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Weight</td>\n<td style=\"padding: 14px 20px;\">5.1 kg</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">10 years (extendable to 15 years in Germany &amp; Austria)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Grid Regulation</td>\n<td style=\"padding: 14px 20px;\">VDE-AR-N 4105, G99, CEI 0-21, EN 50549, IEC 61727 etc.</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Safety / EMC</td>\n<td style=\"padding: 14px 20px;\">IEC/EN 62109-1/-2, IEC/EN 61000-6-1/2/3/4</td>\n</tr>\n</tbody>\n</table>', 3, 'SUN-M160G4-EU-Q0 | Micro Inverter | 4 MPPT', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye SUN-M160G4-EU-Q0 is a powerful 1600 W 4-in-1 microinverter with true Quad MPPT technology. Supporting up to 18 A per channel, it is fully compatible with the latest high-performance modules up to 560 W+ and perfect for balcony power plants and roof installations.</p>\n<div style=\"margin: 60px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-013.jpg\" alt=\"Deye SUN-M160G4-EU-Q0 1600W Microinverter\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Advantages</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">True Quad MPPT</strong><br />4 independent MPP trackers &#8211; maximum yield even with shading</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">1600 W Output</strong><br />Ideal for 4 &#215; 400&#8211;560 W modules</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">18 A per Channel</strong><br />Future-proof for high-current panels</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">IP67 Waterproof</strong><br />Fully sealed &#8211; perfect for balconies and roofs</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Built-in Wi-Fi</strong><br />Module-level monitoring via app</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Plug &amp; Play</strong><br />Quick-connector system &#8211; often no electrician required</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">15-Year Warranty (DE/AT)</strong><br />10 years standard &#8211; extendable to 15 years</div>\n</div>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5; margin: 70px 0;\">\n<p>Deye SUN-M160G4-EU-Q0 &#8211; 1600 W 4-in-1 Microinverter</p>\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">Quad MPPT &#183; 18 A per channel &#183; IP67 &#183; Wi-Fi &#183; 15-Year Warranty Option</p>\n</div>\n</div>', 'Deye SUN-M160G4-EU-Q0 1600W Microinverter (EU)<br /><br />&#8226; True 4-in-1 Quad MPPT &#8211; 4 independent MPP trackers<br />&#8226; 1600 W rated output &#8211; perfect for 4 &#215; 400&#8211;560 W+ modules<br />&#8226; 18 A per channel &#8211; ready for the latest high-current panels<br />&#8226; IP67 completely waterproof &amp; dustproof<br />&#8226; Integrated Wi-Fi with module-level monitoring<br />&#8226; Plug &amp; Play quick-connector system<br />&#8226; Extremely quiet &#8804;25 dB, natural cooling<br />&#8226; 10-year warranty (extendable to 15 years in Germany/Austria)<br />&#8226; Certified: VDE-AR-N 4105, G99, CEI 0-21 etc.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', '');
INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(1043, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin-bottom: 60px; font-size: 15px;\">\n<tbody><!-- Header Row -->\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\"><span style=\"font-weight: 600;\">Parameter</span></th><th style=\"padding: 20px; text-align: left; font-weight: 600;\"><span style=\"font-weight: 600;\">Value</span></th></tr>\n<tr style=\"background: #30358C; color: white;\"><th colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold; text-align: left;\">Deye SUN-M200G4-EU-Q0 (2000 W Quad MPPT Microinverter)</th></tr>\n<!-- PV String Input Data -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">PV String Input Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Input Power</td>\n<td style=\"padding: 14px 20px;\">210&#8211;700 W (4 pieces)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">60 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Start-up Voltage</td>\n<td style=\"padding: 14px 20px;\">20 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range</td>\n<td style=\"padding: 14px 20px;\">25&#8211;55 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">42.5 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current</td>\n<td style=\"padding: 14px 20px;\">15 + 15 + 15 + 15 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Input Short Circuit Current</td>\n<td style=\"padding: 14px 20px;\">22.5 + 22.5 + 22.5 + 22.5 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">No. of MPP trackers / Strings per MPP Tracker</td>\n<td style=\"padding: 14px 20px;\">4 / 1</td>\n</tr>\n<!-- AC Output Side -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">AC Output Side</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Active Power</td>\n<td style=\"padding: 14px 20px;\">2000 W</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Apparent Power</td>\n<td style=\"padding: 14px 20px;\">2000 VA</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated AC Output Current</td>\n<td style=\"padding: 14px 20px;\">9.1 A / 8.7 A (at 220 V / 230 V)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. AC Output Current</td>\n<td style=\"padding: 14px 20px;\">9.1 A / 8.7 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Output Voltage / Range</td>\n<td style=\"padding: 14px 20px;\">220/230 V (0.85 Un &#8211; 1.1 Un)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Connection Form</td>\n<td style=\"padding: 14px 20px;\">L/N/PE</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated Output Grid Frequency / Range</td>\n<td style=\"padding: 14px 20px;\">50/60 Hz (45&#8211;55 Hz / 55&#8211;65 Hz)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Units per Branch</td>\n<td style=\"padding: 14px 20px;\">3</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Power Factor Adjustment Range</td>\n<td style=\"padding: 14px 20px;\">0.9 leading to 0.9 lagging</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Total Current Harmonic Distortion THDi</td>\n<td style=\"padding: 14px 20px;\">&lt; 3 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Injection Current</td>\n<td style=\"padding: 14px 20px;\">&lt; 0.5 % In</td>\n</tr>\n<!-- Efficiency -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Efficiency</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Efficiency</td>\n<td style=\"padding: 14px 20px;\">96.50 %</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Euro Efficiency</td>\n<td style=\"padding: 14px 20px;\">96.0 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Efficiency</td>\n<td style=\"padding: 14px 20px;\">&gt; 99 %</td>\n</tr>\n<!-- Equipment Protection -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Equipment&#160;Protection</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">DC Reverse Polarity Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Output Overcurrent Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">AC Output Overvoltage Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Output Short Circuit Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Thermal Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Insulation Impedance Detection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Anti-Islanding Protection</td>\n<td style=\"padding: 14px 20px;\">Yes</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Surge Protection Level</td>\n<td style=\"padding: 14px 20px;\">Type II (AC)</td>\n</tr>\n<!-- Interface -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Interface</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Communication Interface</td>\n<td style=\"padding: 14px 20px;\">Wi-Fi</td>\n</tr>\n<!-- General Data -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">General Data</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Operating Temperature Range</td>\n<td style=\"padding: 14px 20px;\">&#8211;40 &#176;C to +65 &#176;C (&gt;45 &#176;C derating)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Permissible Ambient Humidity</td>\n<td style=\"padding: 14px 20px;\">0 &#8211; 100 %</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Permissible Altitude</td>\n<td style=\"padding: 14px 20px;\">2000 m</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Noise</td>\n<td style=\"padding: 14px 20px;\">&#8804; 25 dB</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Ingress Protection Rating</td>\n<td style=\"padding: 14px 20px;\">IP67</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Inverter Topology</td>\n<td style=\"padding: 14px 20px;\">Isolated</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Over Voltage Category</td>\n<td style=\"padding: 14px 20px;\">OVC II (DC), OVC III (AC)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Dimensions (W &#215; H &#215; D)</td>\n<td style=\"padding: 14px 20px;\">311 &#215; 250.5 &#215; 36.5 mm (excl. connectors)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Weight</td>\n<td style=\"padding: 14px 20px;\">5.1 kg</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Type of Cooling</td>\n<td style=\"padding: 14px 20px;\">Natural cooling</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">10 years (extendable to 15 years in Germany &amp; Austria)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Grid Regulation</td>\n<td style=\"padding: 14px 20px;\">IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002, OVE-Richtlinie R25, G99, VDE-AR-N 4105</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Safety EMC / Standard</td>\n<td style=\"padding: 14px 20px;\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1/-2</td>\n</tr>\n</tbody>\n</table>', 3, 'SUN-M200G4-EU-Q0 | Micro Inverter | 4 MPPT', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye SUN-M200G4-EU-Q0 is the most powerful 4-in-1 microinverter on the market with 2000 W rated output and true Quad MPPT technology. Supporting up to 18 A per channel, it is perfectly suited for the latest high-performance modules up to 560 W+ and ideal for balcony power plants, roof systems and commercial installations.</p>\n<div style=\"margin: 60px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-013.jpg\" alt=\"Deye SUN-M200G4-EU-Q0 2000W Microinverter\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Advantages</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">True Quad MPPT</strong><br />4 independent MPP trackers &#8211; maximum yield even with shading</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">2000 W Output</strong><br />Perfect for 4 &#215; 500&#8211;560 W+ modules</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">18 A per Channel</strong><br />Future-proof for the newest high-current panels</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">IP67 Waterproof</strong><br />Fully sealed &#8211; works perfectly on balconies and roofs</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Built-in Wi-Fi</strong><br />Module-level monitoring via app</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Plug &amp; Play</strong><br />Quick-connector system &#8211; no electrician needed for many installations</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">15-Year Warranty (DE/AT)</strong><br />10 years standard &#8211; extendable to 15 years</div>\n</div>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5; margin: 70px 0;\">\n<p>Deye SUN-M200G4-EU-Q0 &#8211; The Ultimate 2000 W 4-in-1 Microinverter</p>\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">Quad MPPT &#183; 18 A per channel &#183; IP67 &#183; Wi-Fi &#183; 15-Year Warranty Option</p>\n</div>\n</div>', 'Deye SUN-M200G4-EU-Q0 2000W Microinverter (EU)<br /><br />&#8226; True 4-in-1 Quad MPPT &#8211; 4 independent MPP trackers<br />&#8226; 2000 W rated output &#8211; ideal for 4 &#215; 500&#8211;560 W+ modules<br />&#8226; 18 A per channel &#8211; future-proof for high-current panels<br />&#8226; IP67 fully waterproof &amp; dustproof<br />&#8226; Integrated Wi-Fi with module-level monitoring<br />&#8226; Plug &amp; Play quick-connector system<br />&#8226; Ultra-quiet &#8804;25 dB, natural cooling<br />&#8226; 10-year warranty (extendable to 15 years in Germany/Austria)<br />&#8226; Certified: VDE-AR-N 4105, G99, CEI 0-21 etc.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(1044, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin-bottom: 60px; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Parameter</th><th style=\"padding: 20px; text-align: left; font-weight: 600;\">Value</th></tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Battery Model AE-F2.0</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Battery Chemistry</td>\n<td style=\"padding: 14px 20px;\">LiFePO&#8324;</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Battery Nominal Voltage</td>\n<td style=\"padding: 14px 20px;\">51.2 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Battery Nominal Energy</td>\n<td style=\"padding: 14px 20px;\">2000 Wh</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Charging / Discharging Current</td>\n<td style=\"padding: 14px 20px;\">50 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Battery Operating Voltage</td>\n<td style=\"padding: 14px 20px;\">44.8 &#8211; 57.6 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Battery Cycle Life</td>\n<td style=\"padding: 14px 20px;\">&#8805;6000 (@25&#176;C &#177;2&#176;C, 0.5C/0.5C, 70% EOL)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Parallel Capability</td>\n<td style=\"padding: 14px 20px;\">Up to 5 units (max. 10 kWh)</td>\n</tr>\n<!-- Other Technical Specification -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Other Technical Specification</td>\n</tr>\n<tr style=\"background: f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Display</td>\n<td style=\"padding: 14px 20px;\">LED (SOC, Alarm)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Communication Interfaces</td>\n<td style=\"padding: 14px 20px;\">CAN2.0, LoRa</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Dimensions (W &#215; D &#215; H)</td>\n<td style=\"padding: 14px 20px;\">450 &#215; 210 &#215; 244 mm</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Weight (Approx.)</td>\n<td style=\"padding: 14px 20px;\">20 kg</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Operating Temperature Range</td>\n<td style=\"padding: 14px 20px;\">&#8211;10 &#176;C to +50 &#176;C</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating Altitude</td>\n<td style=\"padding: 14px 20px;\">3000 m</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Relative Humidity</td>\n<td style=\"padding: 14px 20px;\">15 &#8211; 85 % (non-condensing)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Certification</td>\n<td style=\"padding: 14px 20px;\">UN38.3, IEC 62619, CE</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Installation Style</td>\n<td style=\"padding: 14px 20px;\">Floor-Mounted</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">10 Years</td>\n</tr>\n</tbody>\n</table>', 3, 'AE-F2.0 (EU) Battery Pack Module | ESS', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye AE-F2.0 is the official 2 kWh expansion battery for the AE-F(S) 2.0-2H2 all-in-one system as well as balcony power plants and home storage applications. Featuring ultra-safe LiFePO&#8324; technology, &#8805;6000 cycles and parallel connection of up to 5 units (10 kWh total) &#8211; all in a compact 20 kg floor-standing module.</p>\n<div style=\"margin: 60px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-014.jpg\" alt=\"Deye AE-F2.0 Expansion Battery\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Features</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Safe LiFePO&#8324; Cells</strong><br />Maximum safety &amp; thermal stability</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">2 kWh Capacity</strong><br />51.2 V &#183; 2000 Wh</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Expandable to 10 kWh</strong><br />Max. 5 modules in parallel</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">&#8805;6000 Cycles</strong><br />At 70 % remaining capacity</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Compact &amp; Lightweight</strong><br />450&#215;210&#215;244 mm &#183; only 20 kg</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">LED Status Display</strong><br />SOC + alarm at a glance</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">10-Year Warranty</strong><br />Full manufacturer coverage</div>\n</div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 60px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Technical Specifications</h3>\n<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin-bottom: 60px; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 18px; text-align: left;\">Parameter</th><th style=\"padding: 18px; text-align: left;\">Value</th></tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px;\">Battery Chemistry</td>\n<td style=\"padding: 14px;\">LiFePO&#8324;</td>\n</tr>\n<tr>\n<td style=\"padding: 14px;\">Nominal Voltage</td>\n<td style=\"padding: 14px;\">51.2 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px;\">Nominal Capacity</td>\n<td style=\"padding: 14px;\">2000 Wh (2 kWh)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px;\">Max. Charge/Discharge Current</td>\n<td style=\"padding: 14px;\">50 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px;\">Operating Voltage</td>\n<td style=\"padding: 14px;\">44.8 &#8211; 57.6 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px;\">Cycle Life</td>\n<td style=\"padding: 14px;\">&#8805;6000 (0.5C, 70 % EOL)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px;\">Parallel Capability</td>\n<td style=\"padding: 14px;\">Max. 5 units &#8594; 10 kWh</td>\n</tr>\n<tr>\n<td style=\"padding: 14px;\">Communication</td>\n<td style=\"padding: 14px;\">CAN 2.0 + LoRa</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px;\">Dimensions (W&#215;D&#215;H)</td>\n<td style=\"padding: 14px;\">450 &#215; 210 &#215; 244 mm</td>\n</tr>\n<tr>\n<td style=\"padding: 14px;\">Weight</td>\n<td style=\"padding: 14px;\">approx. 20 kg</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px;\">Operating Temperature</td>\n<td style=\"padding: 14px;\">&#8211;10 &#176;C to +50 &#176;C</td>\n</tr>\n<tr>\n<td style=\"padding: 14px;\">Certification</td>\n<td style=\"padding: 14px;\">UN38.3, IEC 62619, CE</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px;\">Warranty</td>\n<td style=\"padding: 14px;\">10 Years</td>\n</tr>\n</tbody>\n</table>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Why Choose Deye AE-F2.0 for Your Home ESS?</h3>\n<ol style=\"font-size: 18px; line-height: 1.9; margin-bottom: 50px; padding-left: 28px; color: #333;\">\n<li><strong>User-Friendly:</strong> Intuitive LED display keeps you informed about your energy levels at all times.</li>\n<li><strong>Reliable Durability:</strong> Built for demanding environments, from extreme temperatures to high altitudes.</li>\n<li><strong>Safe and Certified:</strong> Fully compliant with international safety standards, giving you peace of mind.</li>\n<li><strong>Generous Warranty:</strong> Backed by a <strong>10-year warranty</strong>, ensuring your investment is protected.</li>\n</ol>\n<p style=\"font-size: 18px; line-height: 1.8; margin-bottom: 50px; color: #333;\">Whether you&#8217;re looking to maximize solar energy usage, prepare for outages, or increase your home&#8217;s energy independence, the <strong>Deye AE-F2.0 Battery Pack Module</strong> delivers dependable storage and exceptional performance. Its scalability, robust features, and sustainable battery technology make it a top-tier choice for modern homes. Upgrade your home ESS today with the Deye AE-F2.0 and experience the future of energy storage.</p>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5;\">\n<p>Deye AE-F2.0 Expansion Battery</p>\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">2 kWh LiFePO&#8324; &#183; &#8805;6000 Cycles &#183; Up to 10 kWh &#183; 10-Year Warranty</p>\n</div>\n</div>', 'Deye AE-F2.0 Expansion Battery Pack (EU)<br /><br />&#8226; 2 kWh LiFePO&#8324; storage (51.2 V)<br />&#8226; &#8805;6000 cycles at 70 % remaining capacity<br />&#8226; Up to 5 units in parallel &#8594; 10 kWh total<br />&#8226; 50 A max. charge/discharge current<br />&#8226; Compact &amp; lightweight: 450&#215;210&#215;244 mm, only 20 kg<br />&#8226; LED display (SOC + alarm)<br />&#8226; Operating range &#8211;10 &#176;C to +50 &#176;C<br />&#8226; 10-year warranty &#183; UN38.3, IEC 62619, CE certified', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(1045, '<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin-bottom: 40px; font-size: 15px;\">\n<tbody><!-- System-Model -->\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-size: 18px;\">System Model</th><th style=\"padding: 20px; text-align: left; font-size: 18px;\">AE-F(S) 2.0-2H2</th></tr>\n<!-- AC Technical Specifications -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">AC Technical Specifications</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Nominal Input / Output Power / UPS Power</td>\n<td style=\"padding: 14px 20px;\">1000 / 1000 W</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">AC Input / Output Frequency and Voltage</td>\n<td style=\"padding: 14px 20px;\">50 Hz (45&#8211;55 Hz), 60 Hz (55&#8211;65 Hz), L/N/PE, 220/230 Vac</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Grid Type</td>\n<td style=\"padding: 14px 20px;\">Single Phase</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Rated Grid Input / Output Current</td>\n<td style=\"padding: 14px 20px;\">4.6 A / 4.4 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Grid Input / Output Current</td>\n<td style=\"padding: 14px 20px;\">5.0 A / 4.8 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Peak Power (off-grid)</td>\n<td style=\"padding: 14px 20px;\">2 &#215; rated power, 10 s</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Power Factor Adjustment Range</td>\n<td style=\"padding: 14px 20px;\">0.8 leading to 0.8 lagging</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Bypass Grid to Load</td>\n<td style=\"padding: 14px 20px;\">10 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">THD / DC Injection Current</td>\n<td style=\"padding: 14px 20px;\">&lt; 3 % (linear load &lt; 1.5 %)</td>\n</tr>\n<!-- DC Technical Specifications (PV) -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">DC Technical Specifications (PV)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Access Power</td>\n<td style=\"padding: 14px 20px;\">2200 W</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. PV Input Power</td>\n<td style=\"padding: 14px 20px;\">1600 W</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">60 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Start-up Voltage</td>\n<td style=\"padding: 14px 20px;\">25 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">MPPT Voltage Range</td>\n<td style=\"padding: 14px 20px;\">20 &#8211; 55 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Full Load MPPT Voltage Range</td>\n<td style=\"padding: 14px 20px;\">30 &#8211; 55 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Rated PV Input Voltage</td>\n<td style=\"padding: 14px 20px;\">42.5 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Input Short-Circuit Current</td>\n<td style=\"padding: 14px 20px;\">27 + 27 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Operating PV Input Current</td>\n<td style=\"padding: 14px 20px;\">18 + 18 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">No. of MPP Trackers / Strings per Tracker</td>\n<td style=\"padding: 14px 20px;\">2 / 1</td>\n</tr>\n<!-- Battery Technical Specification (integrated) -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Battery Technical Specification (Integrated)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Battery Chemistry</td>\n<td style=\"padding: 14px 20px;\">LiFePO&#8324;</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Battery Nominal Voltage</td>\n<td style=\"padding: 14px 20px;\">51.2 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Battery Nominal Energy</td>\n<td style=\"padding: 14px 20px;\">2000 Wh</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Charging / Discharging Current</td>\n<td style=\"padding: 14px 20px;\">25 A</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Battery Operating Voltage</td>\n<td style=\"padding: 14px 20px;\">44.8 &#8211; 57.6 V</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Battery Cycle Life</td>\n<td style=\"padding: 14px 20px;\">&#8805;6000 (@25&#176;C &#177;2&#176;C, 0.5C/0.5C, 70% EOL)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Parallel Capability</td>\n<td style=\"padding: 14px 20px;\">Supports up to 4 &#215; AE-F2.0 extra batteries (max. 10 kWh)</td>\n</tr>\n<!-- USB Port Technical Specifications -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">USB Port Technical Specifications</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">USB-A Output</td>\n<td style=\"padding: 14px 20px;\">2 ports, 5 V, 2.4 A, 12 W max per port</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">USB-C Output</td>\n<td style=\"padding: 14px 20px;\">2 ports, 5 V, 3.0 A, 15 W max per port</td>\n</tr>\n<!-- Other Technical Specification -->\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Other Technical Specifications</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Display</td>\n<td style=\"padding: 14px 20px;\">Colorful Touch LCD + App + Battery LED (SOC, Alarm)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Communication Interfaces</td>\n<td style=\"padding: 14px 20px;\">Wi-Fi, Bluetooth</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Dimensions (W &#215; D &#215; H)</td>\n<td style=\"padding: 14px 20px;\">450 &#215; 210 &#215; 312 mm</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Weight (Approx.)</td>\n<td style=\"padding: 14px 20px;\">26 kg</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Operating Temperature Range</td>\n<td style=\"padding: 14px 20px;\">&#8211;10 &#176;C to +50 &#176;C</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating Altitude</td>\n<td style=\"padding: 14px 20px;\">2000 m</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Relative Humidity</td>\n<td style=\"padding: 14px 20px;\">0 &#8211; 95 % (non-condensing)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Safety / EMC Standards</td>\n<td style=\"padding: 14px 20px;\">IEC62619, UN38.3, IEC/EN62109-1/2, IEC/EN61000-6-1/2/3/4</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Grid Regulation</td>\n<td style=\"padding: 14px 20px;\">VDE4105, IEC61727/62116, CEI0-21, EN50549-1, G98, G99, etc.</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Battery Certification</td>\n<td style=\"padding: 14px 20px;\">UN38.3, IEC 62619</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Installation Style</td>\n<td style=\"padding: 14px 20px;\">Floor-Mounted</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">10 years (battery) / 5 years (system)</td>\n</tr>\n</tbody>\n</table>\n<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 20px; text-align: left; font-size: 18px;\">Battery Model</th><th style=\"padding: 20px; text-align: left; font-size: 18px;\">AE-F2.0</th></tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Battery Technical Specification</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Battery Chemistry</td>\n<td style=\"padding: 14px 20px;\">LiFePO&#8324;</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Battery Nominal Voltage / Energy</td>\n<td style=\"padding: 14px 20px;\">51.2 V / 2000 Wh</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Max. Charging / Discharging Current</td>\n<td style=\"padding: 14px 20px;\">50 A</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Battery Operating Voltage</td>\n<td style=\"padding: 14px 20px;\">44.8 &#8211; 57.6 V</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Battery Cycle Life</td>\n<td style=\"padding: 14px 20px;\">&#8805;6000 (@25&#176;C &#177;2&#176;C, 0.5C/0.5C, 70% EOL)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Parallel Capability</td>\n<td style=\"padding: 14px 20px;\">Up to 5 units</td>\n</tr>\n<tr style=\"background: #30358C; color: white;\">\n<td colspan=\"2\" style=\"padding: 16px 20px; font-size: 17px; font-weight: bold;\">Other Technical Specification</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Display</td>\n<td style=\"padding: 14px 20px;\">LED (SOC, Alarm)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Communication Interfaces</td>\n<td style=\"padding: 14px 20px;\">CAN2.0, LoRa</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Dimensions (W &#215; D &#215; H)</td>\n<td style=\"padding: 14px 20px;\">450 &#215; 210 &#215; 244 mm</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Weight (Approx.)</td>\n<td style=\"padding: 14px 20px;\">20 kg</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Operating Temperature Range</td>\n<td style=\"padding: 14px 20px;\">&#8211;10 &#176;C to +50 &#176;C</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Max. Operating Altitude</td>\n<td style=\"padding: 14px 20px;\">3000 m</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Relative Humidity</td>\n<td style=\"padding: 14px 20px;\">15 &#8211; 85 % (non-condensing)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Certification</td>\n<td style=\"padding: 14px 20px;\">UN38.3, IEC 62619, CE</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px 20px;\">Installation Style</td>\n<td style=\"padding: 14px 20px;\">Floor-Mounted</td>\n</tr>\n<tr>\n<td style=\"padding: 14px 20px;\">Warranty</td>\n<td style=\"padding: 14px 20px;\">10 Years</td>\n</tr>\n</tbody>\n</table>', 3, 'AE-FS2.0-2H2 (EU) Home Solar Battery System | ESS', '<div style=\"font-family: \'Segoe UI\',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;\">\n<p style=\"font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;\">The Deye AE-F(S) 2.0-2H2 is the revolutionary all-in-one home and portable solar storage system with an integrated 2 kWh LiFePO&#8324; battery, 1000 W PV input, 800 W inverter and an ultra-fast 4 ms UPS switch-over. IP65-rated, app-controlled via Wi-Fi/Bluetooth, compact, mobile and expandable up to 10 kWh &#8211; the perfect solution for home backup, camping or commercial use.</p>\n<div style=\"margin: 60px 0;\"><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-014.jpg\" alt=\"Deye AE-F(S) 2.0-2H2 All-in-One Solar Storage\" style=\"width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);\" /></div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Key Features</h3>\n<div style=\"display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;\">\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Robust &amp; Safe</strong><br />IP65, 10-year warranty, &#8805;6000 cycles, UN38.3 &amp; IEC62619</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Powerful Performance</strong><br />1000 W PV input, 800 W AC/DC output, 4 ms UPS</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Smart &amp; Connected</strong><br />Wi-Fi + Bluetooth + app control</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Compact &amp; Portable</strong><br />450&#215;210&#215;321 mm, only &#126;26 kg</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Expandable</strong><br />Up to 4&#215; AE-F2.0 extra batteries &#8594; 10 kWh</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">All-Weather Ready</strong><br />&#8211;10 &#176;C to +50 &#176;C, up to 3000 m altitude</div>\n<div style=\"background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;\"><strong style=\"color: #30358c; font-size: 19px;\">Easy Operation</strong><br />Colour touch LCD + app</div>\n</div>\n<h3 style=\"color: #30358c; font-size: 30px; font-weight: bold; margin: 60px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;\">Technical Specifications</h3>\n<table style=\"width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin-bottom: 60px; font-size: 15px;\">\n<tbody>\n<tr style=\"background: #30358C; color: white;\"><th style=\"padding: 18px; text-align: left;\">Parameter</th><th style=\"padding: 18px; text-align: left;\">Value</th></tr>\n<tr style=\"background: #f8f9fc; font-weight: 600;\"></tr>\n<tr>\n<td style=\"padding: 14px;\">Battery Chemistry</td>\n<td style=\"padding: 14px;\">LiFePO&#8324;</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px;\">Nominal Capacity</td>\n<td style=\"padding: 14px;\">2 kWh (expandable to 10 kWh)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px;\">PV Input (max.)</td>\n<td style=\"padding: 14px;\">1000 W (2&#215; MPPT)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px;\">AC Output</td>\n<td style=\"padding: 14px;\">800 W continuous / 1600 W peak (10 s)</td>\n</tr>\n<tr>\n<td style=\"padding: 14px;\">UPS Switching Time</td>\n<td style=\"padding: 14px;\">&#8804;4 ms</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px;\">Protection Rating</td>\n<td style=\"padding: 14px;\">IP65</td>\n</tr>\n<tr>\n<td style=\"padding: 14px;\">Operating Temperature</td>\n<td style=\"padding: 14px;\">&#8211;10 &#176;C to +50 &#176;C</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px;\">Dimensions (W&#215;D&#215;H)</td>\n<td style=\"padding: 14px;\">450 &#215; 210 &#215; 321 mm</td>\n</tr>\n<tr>\n<td style=\"padding: 14px;\">Weight</td>\n<td style=\"padding: 14px;\">approx. 26 kg</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px;\">Cycle Life</td>\n<td style=\"padding: 14px;\">&#8805;6000 cycles</td>\n</tr>\n<tr>\n<td style=\"padding: 14px;\">Warranty</td>\n<td style=\"padding: 14px;\">10 years (battery), 5 years (system)</td>\n</tr>\n<tr style=\"background: #f8f9fc;\">\n<td style=\"padding: 14px;\">Connectivity</td>\n<td style=\"padding: 14px;\">Wi-Fi, Bluetooth, app</td>\n</tr>\n</tbody>\n</table>\n<div style=\"background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5;\">\n<p>Deye AE-F(S) 2.0-2H2 &#8211; All-in-One Solar Storage</p>\n<p style=\"font-size: 22px; opacity: 0.95; margin-top: 15px;\">2 kWh &#183; 1000 W PV &#183; 800 W Output &#183; 4 ms UPS &#183; IP65 &#183; App Control &#183; Expandable to 10 kWh</p>\n</div>\n</div>', '<p>Deye AE-F(S) 2.0-2H2 (EU) &#8211; All-in-One Solar Power Station<br /><br />&#8226; 2 kWh LiFePO&#8324; (expandable to 10 kWh)<br />&#8226; 1000 W dual MPPT solar input<br />&#8226; 800 W continuous AC/DC output, 1600 W peak<br />&#8226; Ultra-fast 4 ms UPS switching<br />&#8226; IP65 waterproof &#8211; indoor &amp; outdoor<br />&#8226; Wi-Fi + Bluetooth + touch LCD + app control<br />&#8226; 2&#215; USB-A + 2&#215; USB-C fast charging ports<br />&#8226; &#8805;6000 cycles, 10-year battery warranty</p>\n<p>Perfect for home backup, off-grid, camping and mobile use.</p>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\n\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\n\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\n\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\n\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\n\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\n\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', '');
