<table cellspacing="0" cellpadding="6">
<tbody>
<tr>
<td colspan="2"></td>
</tr>
<tr>
<td colspan="2"><b>Battery Input Data</b></td>
</tr>
<tr>
<td>Battery Type</td>
<td>Lead-acid or Lithium-ion</td>
</tr>
<tr>
<td>Battery Voltage Range (V)</td>
<td>40&#8211;60</td>
</tr>
<tr>
<td>Max. Charging Current (A)</td>
<td>135</td>
</tr>
<tr>
<td>Max. Discharging Current (A)</td>
<td>135</td>
</tr>
<tr>
<td>Charging Strategy for Li-ion Battery</td>
<td>Self-adaption to BMS</td>
</tr>
<tr>
<td>Number of Battery Input</td>
<td>1</td>
</tr>
<tr>
<td colspan="2"></td>
</tr>
<tr>
<td colspan="2"><b>PV String Input Data</b></td>
</tr>
<tr>
<td>Max. PV Access Power (W)</td>
<td>12000</td>
</tr>
<tr>
<td>Max. PV Input Power (W)</td>
<td>9600</td>
</tr>
<tr>
<td>Max. PV Input Voltage (V)</td>
<td>500</td>
</tr>
<tr>
<td>Start-up Voltage (V)</td>
<td>125</td>
</tr>
<tr>
<td>PV Input Voltage (V)</td>
<td>125&#8211;500</td>
</tr>
<tr>
<td>MPPT Voltage Range (V)</td>
<td>150&#8211;425</td>
</tr>
<tr>
<td>Full Load MPPT Voltage Range (V)</td>
<td>300&#8211;425</td>
</tr>
<tr>
<td>Rated PV Input Voltage (V)</td>
<td>370</td>
</tr>
<tr>
<td>Max. Operating PV Input Current (A)</td>
<td>18+18</td>
</tr>
<tr>
<td>Max. Input Short-Circuit Current (A)</td>
<td>27+27</td>
</tr>
<tr>
<td>No. of MPP Trackers / No. of Strings Per Tracker</td>
<td>2 / 1+1</td>
</tr>
<tr>
<td>Max. Inverter Backfeed Current to the Array (A)</td>
<td>0</td>
</tr>
<tr>
<td colspan="2"></td>
</tr>
<tr>
<td colspan="2"><b>AC Output Data</b></td>
</tr>
<tr>
<td>Rated AC Output Power (VA/W)</td>
<td>6000</td>
</tr>
<tr>
<td>Max. AC Output Power (VA/W)</td>
<td>6000</td>
</tr>
<tr>
<td>Max. AC Output Current (A)</td>
<td>26.1</td>
</tr>
<tr>
<td>Peak Power (W)</td>
<td>2 times of rated power, 10s</td>
</tr>
<tr>
<td>Rated Output Voltage (V)</td>
<td>230</td>
</tr>
<tr>
<td>Output Type</td>
<td>L+N+PE</td>
</tr>
<tr>
<td>Rated Output Frequency</td>
<td>50Hz / 60Hz</td>
</tr>
<tr>
<td>Output Voltage Waveform</td>
<td>Pure Sine Wave</td>
</tr>
<tr>
<td>Total Current Harmonic Distortion THDi</td>
<td>&lt;3%</td>
</tr>
<tr>
<td colspan="2"></td>
</tr>
<tr>
<td colspan="2"><b>AC Input Data (Grid and Generator)</b></td>
</tr>
<tr>
<td>Max. Input Power to Battery (W)</td>
<td>6000</td>
</tr>
<tr>
<td>Rated Input Voltage (V)</td>
<td>230</td>
</tr>
<tr>
<td>Rated Input Frequency</td>
<td>50Hz / 60Hz</td>
</tr>
<tr>
<td>Grid Input Current (A)</td>
<td>35</td>
</tr>
<tr>
<td>Generator Input Current (A)</td>
<td>35</td>
</tr>
<tr>
<td colspan="2"></td>
</tr>
<tr>
<td colspan="2"><b>Efficiency</b></td>
</tr>
<tr>
<td>Max. Efficiency</td>
<td>97.60%</td>
</tr>
<tr>
<td>Euro Efficiency</td>
<td>96.50%</td>
</tr>
<tr>
<td>MPPT Efficiency</td>
<td>&gt;99%</td>
</tr>
<tr>
<td colspan="2"></td>
</tr>
<tr>
<td colspan="2"><b>Equipment Protection</b></td>
</tr>
<tr>
<td>Integrated Protection</td>
<td>AC Output Overvoltage Protection, AC Output Short Circuit Protection, DC Reverse Polarity Protection, AC Output Overcurrent Protection, DC Component Monitoring, Thermal Protection, Arc Fault Circuit Interrupter (optional), Insulation Impedance Detection, DC Switch</td>
</tr>
<tr>
<td>Surge Protection Level</td>
<td>TYPE II (DC), TYPE II (AC)</td>
</tr>
<tr>
<td colspan="2"></td>
</tr>
<tr>
<td colspan="2"><b>Interface</b></td>
</tr>
<tr>
<td>LCD/LED Display</td>
<td>LCD</td>
</tr>
<tr>
<td>Communication Interface</td>
<td>WIFI / RS485 / CAN / Bluetooth</td>
</tr>
<tr>
<td colspan="2"></td>
</tr>
<tr>
<td colspan="2"><b>General Data</b></td>
</tr>
<tr>
<td>Max. Operating Frequency (Hz)</td>
<td>200M</td>
</tr>
<tr>
<td>Operating Temperature Range (&#8451;)</td>
<td>&#8211;40 to +60&#8451;, &gt;45&#8451; Derating</td>
</tr>
<tr>
<td>Permissible Ambient Humidity</td>
<td>0&#8211;100%</td>
</tr>
<tr>
<td>Permissible Altitude</td>
<td>3000m</td>
</tr>
<tr>
<td>Noise (dB)</td>
<td>&lt;55</td>
</tr>
<tr>
<td>Ingress Protection (IP Rating)</td>
<td>IP65</td>
</tr>
<tr>
<td>Inverter Topology</td>
<td>Non-Isolated</td>
</tr>
<tr>
<td>Over Voltage Category</td>
<td>OVC II (DC), OVC III (AC)</td>
</tr>
<tr>
<td>Cabinet Size (W&#215;H&#215;D mm)</td>
<td>306&#215;427.5&#215;175.77 (Excluding Connectors and Brackets)</td>
</tr>
<tr>
<td>Weight (kg)</td>
<td>12.65</td>
</tr>
<tr>
<td>Type of Cooling</td>
<td>Intelligent Air Cooling</td>
</tr>
<tr>
<td>Warranty</td>
<td>Standard 5 years, extended warranty</td>
</tr>
<tr>
<td>Safety / EMC Standard</td>
<td>IEC62109-1/2, EN61000-6-6, EN61000-6-3, EN61000-6-4<br /><br /></td>
</tr>
</tbody>
</table>