<table border="1">
<tbody>
<tr>
<td><span><strong>Modell</strong></span></td>
<td style="text-align: center;"><span><strong>SUN-25K-SG01HP3-EU</strong><b>-BM2</b></span></td>
<td style="text-align: center;" align="center"><span><strong>SUN-30K-SG01HP3-EU</strong><b>-BM3</b></span></td>
<td style="text-align: center;" align="center"><span><strong>SUN-40K-SG01HP3-EU</strong><b>-BM4</b></span></td>
<td style="text-align: center;" align="center"><span style="color: #0083c1;"><strong>SUN-50K-SG01HP3-EU</strong><b>-BM4</b></span></td>
</tr>
<tr>
<td colspan="5"><span style="font-family: helvetica, arial, sans-serif;"><strong>Batterieeingangsdaten</strong></span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Batterietyp</span></td>
<td style="text-align: center;" colspan="4"><span style="font-family: helvetica, arial, sans-serif;">Lithium-Ionen</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Batteriespannungsbereich (V)</span></td>
<td style="text-align: center;" colspan="4"><span style="font-family: helvetica, arial, sans-serif;">150 &#126; 800 V</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">max. Ladestrom (A)</span></td>
<td style="text-align: center;" colspan="4"><span style="font-family: helvetica, arial, sans-serif;">50A+50A</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">max. Entladestrom (A)</span></td>
<td style="text-align: center;" colspan="4"><span style="font-family: helvetica, arial, sans-serif;">50A+50A</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Anzahl der Batterieeing&#228;nge</span></td>
<td style="text-align: center;" colspan="4"><span style="font-family: helvetica, arial, sans-serif;">2</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Ladestrategie f&#252;r Li-Ionen-Akkus</span></td>
<td style="text-align: center;" colspan="4"><span style="font-family: helvetica, arial, sans-serif;">Selbstanpassung an BMS</span></td>
</tr>
</tbody>
</table>
<table border="1">
<tbody>
<tr>
<td colspan="5"><span style="font-family: helvetica, arial, sans-serif;"><strong>PV-String-Eingangsdaten</strong></span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">max. DC-Eingangsleistung (W)</span></td>
<td style="text-align: center;"><span style="font-family: helvetica, arial, sans-serif;">32500W</span></td>
<td style="text-align: center;" align="center"><span style="font-family: helvetica, arial, sans-serif;">39000W</span></td>
<td style="text-align: center;" align="center"><span style="font-family: helvetica, arial, sans-serif;">52000W</span></td>
<td style="text-align: center;" align="center"><span style="font-family: helvetica, arial, sans-serif;">65000W</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">max. DC-Eingangsspannung (V)</span></td>
<td style="text-align: center;" colspan="4"><span style="font-family: helvetica, arial, sans-serif;">1000 V</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Anlaufspannung (V)</span></td>
<td style="text-align: center;" colspan="4"><span style="font-family: helvetica, arial, sans-serif;">150V</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">MPPT-Bereich (V)</span></td>
<td style="text-align: center;" colspan="4"><span style="font-family: helvetica, arial, sans-serif;">200V-850V</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Volllast-DC-Spannungsbereich (V)</span></td>
<td style="text-align: center;">
<div><span style="font-family: helvetica, arial, sans-serif;">450-850</span></div>
</td>
<td style="text-align: center;">
<div><span style="font-family: helvetica, arial, sans-serif;">360-850</span></div>
</td>
<td style="text-align: center;">
<div><span style="font-family: helvetica, arial, sans-serif;">360-850</span></div>
</td>
<td style="text-align: center;">
<div><span style="font-family: helvetica, arial, sans-serif;">450-850</span></div>
</td>
</tr>
<tr>
<td>
<div><span style="font-family: helvetica, arial, sans-serif;">Nenn-DC-Eingangsspannung (V)</span></div>
</td>
<td style="text-align: center;" colspan="4">
<div><span style="font-family: helvetica, arial, sans-serif;">600</span></div>
<div></div>
</td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">PV-Eingangsstrom (A)</span></td>
<td style="text-align: center;"><span style="font-family: helvetica, arial, sans-serif;">36A+36A</span></td>
<td style="text-align: center;"><span style="font-family: helvetica, arial, sans-serif;">36A+36A+36A</span></td>
<td style="text-align: center;" colspan="2" align="center"><span style="font-family: helvetica, arial, sans-serif;">36A+36A+36A+36A</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">max. PV-ISC (A)</span></td>
<td style="text-align: center;"><span style="font-family: helvetica, arial, sans-serif;">55A+55A</span></td>
<td style="text-align: center;"><span style="font-family: helvetica, arial, sans-serif;">55A+55A+55A</span></td>
<td style="text-align: center;" colspan="2"><span style="font-family: helvetica, arial, sans-serif;">55A+55A+55A+55A</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Anzahl MPP-Tracker</span></td>
<td style="text-align: center;"><span style="font-family: helvetica, arial, sans-serif;">2</span></td>
<td style="text-align: center;"><span style="font-family: helvetica, arial, sans-serif;">3</span></td>
<td style="text-align: center;" colspan="2" align="center"><span style="font-family: helvetica, arial, sans-serif;">4</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Anzahl Strings pro MPP-Tracker</span></td>
<td style="text-align: center;" colspan="4"><span style="font-family: helvetica, arial, sans-serif;">2</span></td>
</tr>
</tbody>
</table>
<table border="1">
<tbody>
<tr>
<td colspan="5"><span style="font-family: helvetica, arial, sans-serif;"><strong>AC-Ausgangsdaten</strong></span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">AC-Nennausgang und USV-Leistung (W)</span></td>
<td style="text-align: center;"><span style="font-family: helvetica, arial, sans-serif;">25000W</span></td>
<td style="text-align: center;" align="center"><span style="font-family: helvetica, arial, sans-serif;">3000W</span></td>
<td style="text-align: center;" align="center"><span style="font-family: helvetica, arial, sans-serif;">40000W</span></td>
<td style="text-align: center;" align="center"><span style="font-family: helvetica, arial, sans-serif;">50000W</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">max. AC-Ausgangsleistung (W)</span></td>
<td style="text-align: center;"><span style="font-family: helvetica, arial, sans-serif;">27500W</span></td>
<td style="text-align: center;" align="center"><span style="font-family: helvetica, arial, sans-serif;">33000W</span></td>
<td style="text-align: center;" align="center"><span style="font-family: helvetica, arial, sans-serif;">44000W</span></td>
<td style="text-align: center;" align="center"><span style="font-family: helvetica, arial, sans-serif;">55000W</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Spitzenleistung (netzunabh&#228;ngig)</span></td>
<td style="text-align: center;" colspan="4"><span style="font-family: helvetica, arial, sans-serif;">1,5-fache Nennleistung, 10 S</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">AC-Ausgangsnennstrom (A)</span></td>
<td style="text-align: center;"><span style="font-family: helvetica, arial, sans-serif;">38</span></td>
<td style="text-align: center;" align="center"><span style="font-family: helvetica, arial, sans-serif;">45.6</span></td>
<td style="text-align: center;" align="center"><span style="font-family: helvetica, arial, sans-serif;">60.8</span></td>
<td style="text-align: center;" align="center"><span style="font-family: helvetica, arial, sans-serif;">75.8</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">max. Wechselstrom (A)</span></td>
<td style="text-align: center;"><span style="font-family: helvetica, arial, sans-serif;">50</span></td>
<td style="text-align: center;" align="center"><span style="font-family: helvetica, arial, sans-serif;">60</span></td>
<td style="text-align: center;" align="center"><span style="font-family: helvetica, arial, sans-serif;">70</span></td>
<td style="text-align: center;" align="center"><span style="font-family: helvetica, arial, sans-serif;">83.3</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">max. Kontinuierliche AC-Durchleitung (A)</span></td>
<td style="text-align: center;" colspan="4"><span style="font-family: helvetica, arial, sans-serif;">150A</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Ausgangsfrequenz und Spannung</span></td>
<td style="text-align: center;" colspan="4"><span style="font-family: helvetica, arial, sans-serif;">50/60Hz;3L/N/PE 220/380Vac, 230/400Vac</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Rastertyp</span></td>
<td style="text-align: center;" colspan="4"><span style="font-family: helvetica, arial, sans-serif;">Drei Phasen</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">DC-Injektionsstrom (mA)</span></td>
<td style="text-align: center;" colspan="4"><span style="font-family: helvetica, arial, sans-serif;">&lt;0,5% 1n</span></td>
</tr>
</tbody>
</table>
<table border="1">
<tbody>
<tr>
<td colspan="2"><span style="font-family: helvetica, arial, sans-serif;"><strong>Effizienz</strong></span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">max. Effizienz</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">97.60%</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Euro-Effizienz</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">97.00%</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">MPPT-Effizienz</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">99.90%</span></td>
</tr>
</tbody>
</table>
<table border="1">
<tbody>
<tr>
<td colspan="2"><span style="font-family: helvetica, arial, sans-serif;"><strong>Schutz</strong></span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">PV-Eingangs-Blitzschutz</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">Integriert</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Schutz vor Inselbildung</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">Integriert</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">PV-String-Eingangsverpolungsschutz</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">Integriert</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Isolationswiderstandserkennung</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">Integriert</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Fehlerstrom-&#220;berwachungseinheit</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">Integriert</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Ausgangs&#252;berstromschutz</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">Integriert</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Kurzschlussschutz am Ausgang</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">Integriert</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Ausgangs&#252;berspannungsschutz</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">Integriert</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">&#220;berspannungsschutz</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">DC-Typ II / AC-Typ II</span></td>
</tr>
</tbody>
</table>
<table border="1">
<tbody>
<tr>
<td colspan="2"><span style="font-family: helvetica, arial, sans-serif;"><strong>Zertifizierungen und Standards</strong></span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Netzregulierung</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">CEI 0-21, VDE-AR-N 4105, NRS 097, IEC 62116, IEC 61727, G99, G98, VDE 0126-1-1, RD 1699, C10-11</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Sicherheit EMV / Standard</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</span></td>
</tr>
</tbody>
</table>
<table border="1">
<tbody>
<tr>
<td colspan="2"><span style="font-family: helvetica, arial, sans-serif;"><strong>Allgemeine Daten</strong></span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Betriebstemperaturbereich (&#8451;)</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">-40&#126;60&#8451;, &gt;45&#8451; Derating</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">K&#252;hlung</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">Intelligente K&#252;hlung</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Rauschen (dB)</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">&lt;45dB</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Kommunikation mit BMS</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">RS485; KANN</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Gewicht (kg)</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">60</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Gr&#246;&#223;e (mm)</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">560,5 B &#215; 837 H &#215; 319 T</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Schutzgrad</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">IP65</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Installationsstil</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">An der Wand montiert</span></td>
</tr>
<tr>
<td><span style="color: #000000;"><span style="font-family: helvetica, arial, sans-serif;">Garantie</span></span></td>
<td align="center"><span style="color: #000000;">10 Jahre</span></td>
</tr>
</tbody>
</table>