<table border="1">
<tbody>
<tr style="height: 62px;">
<td style="height: 62px;"><span style="font-family: helvetica, arial, sans-serif;"><strong>Modell</strong></span></td>
<td style="height: 62px;" align="center"><span style="font-family: helvetica, arial, sans-serif; color: #0083c1;"><strong>SUN1200G-230-EU</strong></span></td>
<td style="height: 62px;" align="center"><span style="font-family: helvetica, arial, sans-serif;"><strong>SUN1300G2-US-208/240</strong></span></td>
<td style="height: 62px;" align="center"><span style="font-family: helvetica, arial, sans-serif;"><strong>SUN1300G</strong></span></td>
</tr>
<tr style="height: 62px;">
<td style="height: 62px;" colspan="4"><span style="font-family: helvetica, arial, sans-serif;"><strong>Eingangsdaten (DC)</strong></span></td>
</tr>
<tr style="height: 62px;">
<td style="height: 62px;"><span style="font-family: helvetica, arial, sans-serif;">Empfohlene Eingangsleistung (STC)</span></td>
<td style="text-align: center; height: 62px;" colspan="3" align="center"><span style="font-family: helvetica, arial, sans-serif;">210&#126;400W (4 St&#252;ck)</span></td>
</tr>
<tr style="height: 62px;">
<td style="height: 62px;"><span style="font-family: helvetica, arial, sans-serif;">Maximale DC-Eingangsspannung</span></td>
<td style="text-align: center; height: 62px;" colspan="3" align="center"><span style="font-family: helvetica, arial, sans-serif;">60V</span></td>
</tr>
<tr style="height: 62px;">
<td style="height: 62px;"><span style="font-family: helvetica, arial, sans-serif;">MPPT-Spannungsbereich</span></td>
<td style="text-align: center; height: 62px;" colspan="3" align="center"><span style="font-family: helvetica, arial, sans-serif;">25&#126;55V</span></td>
</tr>
<tr style="height: 62px;">
<td style="height: 62px;"><span style="font-family: helvetica, arial, sans-serif;">DC-Betriebsspannungsbereich</span></td>
<td style="text-align: center; height: 62px;" colspan="3" align="center"><span style="font-family: helvetica, arial, sans-serif;">20&#126;60V</span></td>
</tr>
<tr style="height: 62px;">
<td style="height: 62px;"><span style="font-family: helvetica, arial, sans-serif;">max. DC-Kurzschlussstrom</span></td>
<td style="text-align: center; height: 62px;" align="center"><span style="font-family: helvetica, arial, sans-serif;">13A</span></td>
<td style="text-align: center; height: 62px;" align="center"><span style="font-family: helvetica, arial, sans-serif;">13A</span></td>
<td style="text-align: center; height: 62px;" align="center"><span style="font-family: helvetica, arial, sans-serif;">14A</span></td>
</tr>
<tr style="height: 62px;">
<td style="height: 62px;"><span style="font-family: helvetica, arial, sans-serif;">max. Eingangsstrom</span></td>
<td style="text-align: center; height: 62px;" colspan="3" align="center"><span style="font-family: helvetica, arial, sans-serif;">10,4A&#215;4</span></td>
</tr>
</tbody>
</table>
<table border="1">
<tbody>
<tr>
<td colspan="4"><span style="font-family: helvetica, arial, sans-serif;"><strong>Ausgangsdaten (AC)</strong></span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Nennleistung</span></td>
<td colspan="3" align="center"><span style="font-family: helvetica, arial, sans-serif;">1300W</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Maximale Ausgangsleistung</span></td>
<td colspan="3" align="center"><span style="font-family: helvetica, arial, sans-serif;">1300W</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Maximaler Ausgangsstrom</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">4.3A</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">6,3A / 5,4A</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">5,9A</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Nennspannung / Bereich</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">184&#126;265V</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">208V / 183&#126;229V</span><br /> <span style="font-family: helvetica, arial, sans-serif;">240V / 211&#126;264V</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">176&#126;242V</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Nennfrequenz / Bereich</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">50,0 / 47,5 &#126; 51,5 Hz</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">60,0 / 59,3 &#126; 60,5 Hz</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">60,0 / 59,3 &#126; 60,5 Hz</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Erweiterte Frequenz/Bereich</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">50,0 / 45 &#126; 55 Hz</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">60,0 / 55&#126;65Hz</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">60,0 / 55&#126;65Hz</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Leistungsfaktor</span></td>
<td colspan="3" align="center"><span style="font-family: helvetica, arial, sans-serif;">&gt;0,99</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Maximale Einheiten pro Filiale</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">5</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">4</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">4</span></td>
</tr>
</tbody>
</table>
<table border="1">
<tbody>
<tr>
<td colspan="2"><span style="font-family: helvetica, arial, sans-serif;"><strong>Effizienz</strong></span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">CEC-gewichteter Wirkungsgrad</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">95%</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Spitzenwirkungsgrad des Wechselrichters</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">96,5 %</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Statischer MPPT-Wirkungsgrad</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">99%</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Stromverbrauch bei Nacht</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">50mW</span></td>
</tr>
</tbody>
</table>
<table border="1">
<tbody>
<tr>
<td colspan="2"><span style="font-family: helvetica, arial, sans-serif;"><strong>Mechanische Daten</strong></span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Umgebungstemperaturbereich</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">-40&#126;65&#8451;</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Gr&#246;&#223;e (mm)</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">298,5 B &#215; 287 H &#215; 36 T (ohne Montagehalterung und Kabel)</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Gewicht (kg)</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">6.3</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">K&#252;hlung</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">Nat&#252;rliche K&#252;hlung</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Umwelteinstufung des Geh&#228;uses</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">IP67</span></td>
</tr>
</tbody>
</table>
<table border="1">
<tbody>
<tr>
<td colspan="2"><span style="font-family: helvetica, arial, sans-serif;"><strong>Merkmale</strong></span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Kompatibilit&#228;t</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">Kompatibel mit PV-Modulen mit 60 bis 72 Zellen</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Kommunikation</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">Stromleitung / WIFI / Zigbee</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Beachtung</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">UL1741, VDE0126, VDE4105, IEC62109, CE, INMETRO</span></td>
</tr>
<tr>
<td><span style="font-family: helvetica, arial, sans-serif;">Garantie</span></td>
<td align="center"><span style="font-family: helvetica, arial, sans-serif;">10 Jahre</span></td>
</tr>
</tbody>
</table>