<table style="width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;">
<tbody>
<tr style="background: #30358C; color: white;"><th style="padding: 20px; text-align: left; font-weight: 600;">Parameter</th><th style="padding: 20px; text-align: left; font-weight: 600;">Wert</th></tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px; font-size: 17px; font-weight: bold;">Dreiphasiger Hybrid-Wechselrichter SUN-6K-SG05LP3-EU-SM2</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px;">Batterie-Eingangsdaten</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Batterietyp</td>
<td style="padding: 14px 20px;">Blei-S&#228;ure oder Lithium-Ionen</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Batterie-Spannungsbereich</td>
<td style="padding: 14px 20px;">40&#8211;60 V</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. Lade-/Entladestrom</td>
<td style="padding: 14px 20px;">135 A</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Anzahl Batterie-Eing&#228;nge</td>
<td style="padding: 14px 20px;">1</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Ladestrategie</td>
<td style="padding: 14px 20px;">Selbstadaptiv an BMS</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px;">PV-String-Eingangsdaten</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. PV-Zugangsleistung</td>
<td style="padding: 14px 20px;">12 kW</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. PV-Eingangsleistung</td>
<td style="padding: 14px 20px;">9 kW</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. PV-Eingangsspannung</td>
<td style="padding: 14px 20px;">800 V</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Anlaufspannung</td>
<td style="padding: 14px 20px;">160 V</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">MPPT-Spannungsbereich</td>
<td style="padding: 14px 20px;">200&#8211;650 V</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Nenn-PV-Eingangsspannung</td>
<td style="padding: 14px 20px;">550 V</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Anzahl MPPT / Strings pro MPPT</td>
<td style="padding: 14px 20px;">2 / 1+1</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. Betriebsstrom PV</td>
<td style="padding: 14px 20px;">20 A + 20 A</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. Kurzschlussstrom PV</td>
<td style="padding: 14px 20px;">30 A + 30 A</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px;">AC-Ausgangsdaten (Netzbetrieb)</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Nenn-Ausgangsleistung</td>
<td style="padding: 14px 20px;">6.000 W</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. Scheinleistung</td>
<td style="padding: 14px 20px;">6.600 VA</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Nenn-AC-Strom (400 V / 380 V)</td>
<td style="padding: 14px 20px;">8,7 A / 9,1 A</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. AC-Strom</td>
<td style="padding: 14px 20px;">9,6 A / 10,0 A</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Spitzenleistung (Inselbetrieb)</td>
<td style="padding: 14px 20px;">2 &#215; Nennleistung, 10 s</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. Dauer-AC-Durchgang</td>
<td style="padding: 14px 20px;">45 A</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Nenn-Netzspannung</td>
<td style="padding: 14px 20px;">220/380 V, 230/400 V (3L+N+PE)</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px;">Wirkungsgrad</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. Wirkungsgrad</td>
<td style="padding: 14px 20px;">97,6 %</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Europ&#228;ischer Wirkungsgrad</td>
<td style="padding: 14px 20px;">97,0 %</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">MPPT-Wirkungsgrad</td>
<td style="padding: 14px 20px;">&gt; 99 %</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px;">Schutz &amp; Funktionen</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">100 % unsymmetrische Last</td>
<td style="padding: 14px 20px;">Ja (jede Phase bis 50 %)</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Parallelbetrieb</td>
<td style="padding: 14px 20px;">Bis 10 Ger&#228;te (Netz- &amp; Inselbetrieb)</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Dieselgenerator-Speicherung</td>
<td style="padding: 14px 20px;">Ja</td>
</tr>
<tr>
<td style="padding: 14px 20px;">&#220;berspannungsschutz</td>
<td style="padding: 14px 20px;">Typ II (DC + AC)</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px;">Allgemeine Daten</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Abmessungen (B &#215; H &#215; T)</td>
<td style="padding: 14px 20px;">386 &#215; 660 &#215; 253 mm (ohne Stecker/Halter)</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Gewicht</td>
<td style="padding: 14px 20px;">35,2 kg</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">K&#252;hlung</td>
<td style="padding: 14px 20px;">Intelligente Luftk&#252;hlung</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Ger&#228;uschpegel</td>
<td style="padding: 14px 20px;">&#8804; 55 dB</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Schutzart</td>
<td style="padding: 14px 20px;">IP65</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Betriebstemperatur</td>
<td style="padding: 14px 20px;">-40 &#176;C bis +60 &#176;C (&gt;45 &#176;C Derating)</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Kommunikation</td>
<td style="padding: 14px 20px;">RS485 / RS232 / CAN + WLAN / GPRS / Bluetooth / 4G / LAN (optional)</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Garantie</td>
<td style="padding: 14px 20px;">5 Jahre (verl&#228;ngerbar auf 10 Jahre je nach Installationsort)</td>
</tr>
</tbody>
</table>