<div style="font-family: 'Segoe UI',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.7; color: #333;">
<p style="font-size: 19px; font-weight: 300; color: #222; margin-bottom: 45px;">Das Deye AI-W5.1-B ist das moderne, stapelbare LiFePO&#8324;-Solarspeichersystem f&#252;r Wohnhaus und Gewerbe. Mit 5,12 kWh pro Modul, bis zu 6 Modulen pro Turm (30,72 kWh) und bis zu 6 T&#252;rmen parallel (184 kWh) bietet es maximale Flexibilit&#228;t. Kabellose Plug-and-Play-Installation, IP65-Schutz, Fern&#252;berwachung und kobaltfreie LFP-Zellen machen es zur sicheren und zukunftssicheren Wahl.</p>
<div style="margin: 60px 0;"><img src="https://syd-green-energy.com/files/images/syd-solar-mood-015.jpg" alt="Deye AI-W5.1-B Stapelbarer Batteriespeicher" style="width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);" /></div>
<h3 style="color: #30358c; font-size: 30px; font-weight: bold; margin: 70px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;">Wichtigste Merkmale</h3>
<div style="display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 28px; margin-bottom: 70px;">
<div style="background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;"><strong style="color: #30358c; font-size: 19px;">Modular &amp; skalierbar</strong><br />Bis 6 Module pro Turm (30,72 kWh), 6 T&#252;rme parallel &#8594; 184 kWh</div>
<div style="background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;"><strong style="color: #30358c; font-size: 19px;">Einfache Installation</strong><br />Kabellos, stapelbar, Boden- oder Wandmontage</div>
<div style="background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;"><strong style="color: #30358c; font-size: 19px;">Sicher &amp; umweltfreundlich</strong><br />Kobaltfreie LFP-Zellen, ungiftig, nicht verschmutzend</div>
<div style="background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;"><strong style="color: #30358c; font-size: 19px;">IP65 Schutz</strong><br />Innen- und Au&#223;enbereich geeignet</div>
<div style="background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;"><strong style="color: #30358c; font-size: 19px;">Breiter Temperaturbereich</strong><br />&#8211;20 &#176;C bis +55 &#176;C</div>
<div style="background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;"><strong style="color: #30358c; font-size: 19px;">Intelligentes BMS</strong><br />Fern&#252;berwachung, Firmware-Update, Auto-Networking</div>
<div style="background: #f8f9fc; padding: 28px; border-radius: 14px; border-left: 7px solid #30358C;"><strong style="color: #30358c; font-size: 19px;">10 Jahre Garantie</strong><br />&gt;6000 Zyklen</div>
</div>
<h3 style="color: #30358c; font-size: 30px; font-weight: bold; margin: 60px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;">Technische Daten</h3>
<table style="width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin-bottom: 60px; font-size: 15px;">
<thead>
<tr style="background: #30358C; color: white;"><th style="padding: 16px; text-align: left;">Parameter</th><th style="padding: 16px; text-align: center;">1 Modul</th><th style="padding: 16px; text-align: center;">2 Module</th><th style="padding: 16px; text-align: center;">3 Module</th><th style="padding: 16px; text-align: center;">4 Module</th><th style="padding: 16px; text-align: center;">5 Module</th><th style="padding: 16px; text-align: center;">6 Module</th></tr>
</thead>
<tbody>
<tr style="background: #f8f9fc;">
<td style="padding: 14px; font-weight: 600;">Zellchemie</td>
<td colspan="6" style="text-align: center; padding: 14px;">LiFePO&#8324; (LFP)</td>
</tr>
<tr>
<td style="padding: 14px;">Nennenergie</td>
<td style="text-align: center;">5,12 kWh</td>
<td style="text-align: center;">10,24 kWh</td>
<td style="text-align: center;">15,36 kWh</td>
<td style="text-align: center;">20,48 kWh</td>
<td style="text-align: center;">25,6 kWh</td>
<td style="text-align: center;">30,72 kWh</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px;">Nutzenergie (90 % DoD)</td>
<td style="text-align: center;">4,6 kWh</td>
<td style="text-align: center;">9,2 kWh</td>
<td style="text-align: center;">13,8 kWh</td>
<td style="text-align: center;">18,4 kWh</td>
<td style="text-align: center;">23 kWh</td>
<td style="text-align: center;">27,6 kWh</td>
</tr>
<tr>
<td style="padding: 14px;">Empfohlener Lade-/Entladestrom</td>
<td style="text-align: center;">50 A</td>
<td style="text-align: center;">100 A</td>
<td style="text-align: center;">150 A</td>
<td style="text-align: center;">200 A</td>
<td style="text-align: center;">250 A</td>
<td style="text-align: center;">250 A</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px;">Max. Lade-/Entladestrom</td>
<td style="text-align: center;">100 A</td>
<td style="text-align: center;">180 A</td>
<td style="text-align: center;">250 A</td>
<td style="text-align: center;">250 A</td>
<td style="text-align: center;">250 A</td>
<td style="text-align: center;">250 A</td>
</tr>
<tr>
<td style="padding: 14px;">Spitzenstrom (10 s)</td>
<td style="text-align: center;">150 A</td>
<td style="text-align: center;">270 A</td>
<td style="text-align: center;">360 A</td>
<td style="text-align: center;">360 A</td>
<td style="text-align: center;">360 A</td>
<td style="text-align: center;">360 A</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px;">Abmessungen (B&#215;T&#215;H) (mm)</td>
<td style="text-align: center;">720&#215;255&#215;569</td>
<td style="text-align: center;">720&#215;255&#215;850</td>
<td style="text-align: center;">720&#215;255&#215;1131</td>
<td style="text-align: center;">720&#215;255&#215;1412</td>
<td style="text-align: center;">720&#215;255&#215;1693</td>
<td style="text-align: center;">720&#215;255&#215;1974</td>
</tr>
<tr>
<td style="padding: 14px;">Gewicht</td>
<td style="text-align: center;">74,5 kg</td>
<td style="text-align: center;">127,5 kg</td>
<td style="text-align: center;">180,5 kg</td>
<td style="text-align: center;">233,5 kg</td>
<td style="text-align: center;">286,5 kg</td>
<td style="text-align: center;">339,5 kg</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px; font-weight: 600;">Schutzart</td>
<td colspan="6" style="text-align: center;">IP65 (nach Stapelung)</td>
</tr>
<tr>
<td style="padding: 14px;">Betriebstemperatur</td>
<td colspan="6" style="text-align: center;">Laden 0 bis +55 &#176;C / Entladen &#8211;20 bis +55 &#176;C</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px;">Zyklenlebensdauer</td>
<td colspan="6" style="text-align: center;">&#8805;6000 (90 % DoD, 70 % EOL)</td>
</tr>
<tr>
<td style="padding: 14px;">Garantie</td>
<td colspan="6" style="text-align: center;">10 Jahre</td>
</tr>
</tbody>
</table>
<div style="background: #30358C; color: white; padding: 60px 50px; border-radius: 14px; text-align: center; font-size: 26px; font-weight: 600; box-shadow: 0 15px 40px rgba(48,53,140,.5); line-height: 1.5;">
<p>Deye AI-W5.1-B &#8211; Stapelbarer LiFePO&#8324;-Speicher</p>
<p style="font-size: 22px; opacity: 0.95; margin-top: 15px;">5,12 kWh &#183; Bis 30,72 kWh pro Turm &#183; 184 kWh parallel &#183; IP65 &#183; Plug-and-Play &#183; 10 Jahre Garantie</p>
</div>
</div>