<table style="width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;">
<tbody>
<tr style="background: #30358C; color: white;"><th style="padding: 20px; text-align: left; font-weight: 600;">Parameter</th><th style="padding: 20px; text-align: left; font-weight: 600;">Wert</th></tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px; font-size: 17px; font-weight: bold;">Stringwechselrichter Modell SUN-12K-G06P3-EU-AM2-P1</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px; font-size: 17px; font-weight: bold;">PV-Eingangsdaten</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. PV-Eingangsleistung</td>
<td style="padding: 14px 20px;">18 kW</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. PV-Eingangsspannung</td>
<td style="padding: 14px 20px;">1100 V</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Anlaufspannung</td>
<td style="padding: 14px 20px;">140 V</td>
</tr>
<tr>
<td style="padding: 14px 20px;">MPPT-Spannungsbereich</td>
<td style="padding: 14px 20px;">120&#8211;1000 V</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Nenn-PV-Eingangsspannung</td>
<td style="padding: 14px 20px;">600 V</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. Betriebsstrom PV-Eingang</td>
<td style="padding: 14px 20px;">20 + 20 A</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. Kurzschlussstrom PV-Eingang</td>
<td style="padding: 14px 20px;">30 + 30 A</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Anzahl MPP-Tracker / Strings pro Tracker</td>
<td style="padding: 14px 20px;">2 / 1+1</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px; font-size: 17px; font-weight: bold;">AC-Ausgangsdaten</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Nenn-AC-Ausgangsleistung</td>
<td style="padding: 14px 20px;">12 kW</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. AC-Scheinleistung</td>
<td style="padding: 14px 20px;">13,2 kVA</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Nenn-AC-Ausgangsstrom (400 V / 380 V)</td>
<td style="padding: 14px 20px;">17,4 / 18,2 A</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. AC-Ausgangsstrom (400 V / 380 V)</td>
<td style="padding: 14px 20px;">19,2 / 20 A</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Nennspannung / Bereich</td>
<td style="padding: 14px 20px;">220/380 V, 230/400 V (0,85&#8211;1,1 Un)</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Netzanschlussform</td>
<td style="padding: 14px 20px;">3L/N/PE</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Nenn-Netzfrequenz / Bereich</td>
<td style="padding: 14px 20px;">50/60 Hz (45&#8211;55 / 55&#8211;65 Hz)</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Leistungsfaktor-Bereich</td>
<td style="padding: 14px 20px;">0,8 vor- bis 0,8 nacheilend</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Klirrfaktor THDi</td>
<td style="padding: 14px 20px;">&lt; 3 %</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Gleichstrom-Einspeisung</td>
<td style="padding: 14px 20px;">&lt; 0,5 % In</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px; font-size: 17px; font-weight: bold;">Wirkungsgrad</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. Wirkungsgrad</td>
<td style="padding: 14px 20px;">98,3 %</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Europ&#228;ischer Wirkungsgrad</td>
<td style="padding: 14px 20px;">97,8 %</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">MPPT-Wirkungsgrad</td>
<td style="padding: 14px 20px;">&gt; 99 %</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px; font-size: 17px; font-weight: bold;">Schutzeinrichtungen</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Verpolschutz DC</td>
<td style="padding: 14px 20px;">Ja</td>
</tr>
<tr>
<td style="padding: 14px 20px;">AC-&#220;berstromschutz</td>
<td style="padding: 14px 20px;">Ja</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">AC-&#220;berspannungsschutz</td>
<td style="padding: 14px 20px;">Ja</td>
</tr>
<tr>
<td style="padding: 14px 20px;">AC-Kurzschlussschutz</td>
<td style="padding: 14px 20px;">Ja</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Thermische Schutzfunktion</td>
<td style="padding: 14px 20px;">Ja</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Isolations&#252;berwachung DC-Klemmen</td>
<td style="padding: 14px 20px;">Ja</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Gleichstromkomponente-&#220;berwachung</td>
<td style="padding: 14px 20px;">Ja</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Lichtbogen-Erkennung (AFCI)</td>
<td style="padding: 14px 20px;">Optional</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Fehlerstrom&#252;berwachung</td>
<td style="padding: 14px 20px;">Ja</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Netz&#252;berwachung</td>
<td style="padding: 14px 20px;">Ja</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Inselnetzerkennung</td>
<td style="padding: 14px 20px;">Ja</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Erdschluss-Erkennung</td>
<td style="padding: 14px 20px;">Ja</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">&#220;berlast-Abschaltung bei &#220;berspannung</td>
<td style="padding: 14px 20px;">Ja</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Reststrom&#252;berwachung (RCD)</td>
<td style="padding: 14px 20px;">Ja</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">&#220;berspannungsschutz</td>
<td style="padding: 14px 20px;">Typ II (DC), Typ II (AC)</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px; font-size: 17px; font-weight: bold;">Schnittstellen</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Kommunikationsschnittstelle</td>
<td style="padding: 14px 20px;">RS485 / RS232</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Monitoring</td>
<td style="padding: 14px 20px;">GPRS / WLAN / Bluetooth / 4G / LAN (optional)</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px; font-size: 17px; font-weight: bold;">Allgemeine Daten</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Betriebstemperaturbereich</td>
<td style="padding: 14px 20px;">-25 &#176;C bis +60 &#176;C (&gt;45 &#176;C Derating)</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Zul&#228;ssige Luftfeuchtigkeit</td>
<td style="padding: 14px 20px;">0&#8211;100 %</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Zul&#228;ssige H&#246;he</td>
<td style="padding: 14px 20px;">4000 m</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Ger&#228;uschentwicklung</td>
<td style="padding: 14px 20px;">&lt; 45 dB</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Schutzart</td>
<td style="padding: 14px 20px;">IP65</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Wechselrichtertopologie</td>
<td style="padding: 14px 20px;">Nicht isoliert</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">&#220;berspannungskategorie</td>
<td style="padding: 14px 20px;">OVC II (DC), OVC III (AC)</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Geh&#228;useabmessungen (B &#215; H &#215; T)</td>
<td style="padding: 14px 20px;">283 &#215; 463 &#215; 178 mm (ohne Stecker und Halter)</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Gewicht</td>
<td style="padding: 14px 20px;">11 kg</td>
</tr>
<tr>
<td style="padding: 14px 20px;">K&#252;hlung</td>
<td style="padding: 14px 20px;">Nat&#252;rliche K&#252;hlung</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Garantie</td>
<td style="padding: 14px 20px;">5 Jahre</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Netzvorschriften</td>
<td style="padding: 14px 20px;">IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002, OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Sicherheit / EMV / Norm</td>
<td style="padding: 14px 20px;">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1/2</td>
</tr>
</tbody>
</table>