<table style="width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;">
<tbody>
<tr style="background: #30358C; color: white;"><th style="padding: 20px; text-align: left; font-weight: 600;">Parameter</th><th style="padding: 20px; text-align: left; font-weight: 600;">Specification</th></tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px; font-size: 17px; font-weight: bold;">Single-Phase Hybrid Inverter SUN-6K-SG03LP1-EU</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px;">Battery Input Data</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Battery Type</td>
<td style="padding: 14px 20px;">Lead-acid or Lithium-ion</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Battery Voltage Range</td>
<td style="padding: 14px 20px;">40&#8211;60 V</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. Charging Current</td>
<td style="padding: 14px 20px;">135 A</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. Discharging Current</td>
<td style="padding: 14px 20px;">135 A</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Charging Strategy for Li-ion Battery</td>
<td style="padding: 14px 20px;">Self-adaption to BMS</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Number of Battery Inputs</td>
<td style="padding: 14px 20px;">1</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px;">PV String Input Data</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. PV Access Power</td>
<td style="padding: 14px 20px;">12 kW</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. PV Input Power</td>
<td style="padding: 14px 20px;">7.8 kW</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. PV Input Voltage</td>
<td style="padding: 14px 20px;">500 V</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Start-up Voltage</td>
<td style="padding: 14px 20px;">125 V</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">MPPT Voltage Range</td>
<td style="padding: 14px 20px;">150&#8211;425 V</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Rated PV Input Voltage</td>
<td style="padding: 14px 20px;">370 V</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">No. of MPP Trackers / Strings per Tracker</td>
<td style="padding: 14px 20px;">2 / 1+1</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. Operating PV Input Current</td>
<td style="padding: 14px 20px;">13 A + 13 A</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. Input Short-Circuit Current</td>
<td style="padding: 14px 20px;">17 A + 17 A</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px;">AC Input/Output Data</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Rated AC Input/Output Active Power</td>
<td style="padding: 14px 20px;">6000 W</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. AC Input/Output Apparent Power</td>
<td style="padding: 14px 20px;">6600 VA</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Peak Power (Off-grid)</td>
<td style="padding: 14px 20px;">2 &#215; rated power, 10 s</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Rated AC Input/Output Current</td>
<td style="padding: 14px 20px;">27.3 A / 26.1 A</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. AC Input/Output Current</td>
<td style="padding: 14px 20px;">30 A / 28.7 A</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. Continuous AC Passthrough</td>
<td style="padding: 14px 20px;">40 A</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Rated Voltage / Range</td>
<td style="padding: 14px 20px;">220/230 V, 0.85 Un&#8211;1.1 Un</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Grid Connection Form</td>
<td style="padding: 14px 20px;">L+N+PE</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Rated Grid Frequency / Range</td>
<td style="padding: 14px 20px;">50/60 Hz (45&#8211;55 Hz / 55&#8211;65 Hz)</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Power Factor Adjustment Range</td>
<td style="padding: 14px 20px;">0.8 leading &#8211; 0.8 lagging</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Total Harmonic Distortion (THDi)</td>
<td style="padding: 14px 20px;">&#8804; 3 % (of nominal power)</td>
</tr>
<tr>
<td style="padding: 14px 20px;">DC Injection Current</td>
<td style="padding: 14px 20px;">&#8804; 0.5 % In</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px;">Efficiency</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. Efficiency</td>
<td style="padding: 14px 20px;">97.6 %</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Euro Efficiency</td>
<td style="padding: 14px 20px;">96.5 %</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">MPPT Efficiency</td>
<td style="padding: 14px 20px;">&gt; 99 %</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px;">Protection &amp; Features</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Integrated Protections</td>
<td style="padding: 14px 20px;">DC reverse polarity, AC overcurrent, overtemperature, short circuit, ground fault, DC switch, insulation monitoring, RCD, optional arc fault, islanding detection, surge protection</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Surge Protection</td>
<td style="padding: 14px 20px;">Type II (DC + AC)</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Parallel Operation</td>
<td style="padding: 14px 20px;">Up to 16 units (on-grid &amp; off-grid)</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px;">General Data</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Operating Temperature Range</td>
<td style="padding: 14px 20px;">&#8211;40 &#176;C to +60 &#176;C (derating &gt;45 &#176;C)</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Permissible Ambient Humidity</td>
<td style="padding: 14px 20px;">0&#8211;100 %</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. Operating Altitude</td>
<td style="padding: 14px 20px;">2000 m</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Noise Emission</td>
<td style="padding: 14px 20px;">&#8804; 30 dB</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Ingress Protection</td>
<td style="padding: 14px 20px;">IP65</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Cooling</td>
<td style="padding: 14px 20px;">Intelligent air cooling</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Dimensions (W &#215; H &#215; D)</td>
<td style="padding: 14px 20px;">330 &#215; 580 &#215; 232 mm (excl. connectors/brackets)</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Weight</td>
<td style="padding: 14px 20px;">24.9 kg</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Communication</td>
<td style="padding: 14px 20px;">RS485 / RS232 / CAN</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Monitoring</td>
<td style="padding: 14px 20px;">GPRS / WIFI / Bluetooth / 4G / LAN (optional)</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Warranty</td>
<td style="padding: 14px 20px;">5 years (extendable to 10 years depending on installation location)</td>
</tr>
</tbody>
</table>