<table style="width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 40px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;">
<thead>
<tr style="background: #30358C; color: white;"><th style="padding: 18px 20px; text-align: left; font-weight: 600;">Parameter</th><th style="padding: 18px 20px; text-align: center;">SUN-3.6K<br />SG05LP1-EU</th><th style="padding: 18px 20px; text-align: center;">SUN-5K<br />SG05LP1-EU</th><th style="padding: 18px 20px; text-align: center;">SUN-6K<br />SG05LP1-EU<br /><small>(AM2-P)</small></th><th style="padding: 18px 20px; text-align: center;">SUN-7K<br />SG05LP1-EU</th><th style="padding: 18px 20px; text-align: center;">SUN-7.6K<br />SG05LP1-EU</th><th style="padding: 18px 20px; text-align: center;">SUN-8K<br />SG05LP1-EU</th><th style="padding: 18px 20px; text-align: center;">SUN-10K<br />SG05LP1-EU</th></tr>
</thead>
<tbody><!-- Batterie -->
<tr style="background: #30358C; color: white;">
<td colspan="8" style="padding: 16px 20px; font-weight: bold;">Batterie-Eingangsdaten</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Batterietyp</td>
<td colspan="7" style="padding: 14px 20px; text-align: center;">Blei-S&#228;ure oder Lithium-Ionen</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Batterie-Spannungsbereich</td>
<td colspan="7" style="padding: 14px 20px; text-align: center;">40&#8211;60 V</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. Lade-/Entladestrom</td>
<td style="text-align: center;">90 A</td>
<td style="text-align: center;">120 A</td>
<td style="text-align: center;">135 A</td>
<td style="text-align: center;">175 A</td>
<td style="text-align: center;">190 A</td>
<td style="text-align: center;">190 A</td>
<td style="text-align: center;">210 A</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Ladestrategie Li-Ionen</td>
<td colspan="7" style="padding: 14px 20px; text-align: center;">Selbstadaptiv an BMS</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Anzahl Batterie-Eing&#228;nge</td>
<td colspan="7" style="padding: 14px 20px; text-align: center;">1</td>
</tr>
<!-- PV -->
<tr style="background: #30358C; color: white;">
<td colspan="8" style="padding: 16px 20px;">PV-String-Eingangsdaten</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. PV-Zugangsleistung</td>
<td style="text-align: center;">7,2 kW</td>
<td style="text-align: center;">10 kW</td>
<td style="text-align: center;">12 kW</td>
<td style="text-align: center;">14 kW</td>
<td style="text-align: center;">15,2 kW</td>
<td style="text-align: center;">16 kW</td>
<td style="text-align: center;">20 kW</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. PV-Eingangsleistung</td>
<td style="text-align: center;">5,76 kW</td>
<td style="text-align: center;">8 kW</td>
<td style="text-align: center;">9,6 kW</td>
<td style="text-align: center;">11,2 kW</td>
<td style="text-align: center;">12,16 kW</td>
<td style="text-align: center;">12,8 kW</td>
<td style="text-align: center;">16 kW</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. PV-Eingangsspannung</td>
<td colspan="7" style="text-align: center;">500 V</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Anlauf- / MPPT-Bereich</td>
<td colspan="7" style="text-align: center;">125 V / 150&#8211;425 V</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. Betriebsstrom PV</td>
<td colspan="5" style="text-align: center;">13+13 A</td>
<td colspan="2" style="text-align: center;">26+26 A</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. Kurzschlussstrom PV</td>
<td colspan="5" style="text-align: center;">17+17 A</td>
<td colspan="2" style="text-align: center;">34+34 A</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Anzahl MPPT / Strings</td>
<td colspan="5" style="text-align: center;">2 / 1+1</td>
<td colspan="2" style="text-align: center;">2 / 2+2</td>
</tr>
<!-- AC -->
<tr style="background: #30358C; color: white;">
<td colspan="8" style="padding: 16px 20px;">AC-Ein-/Ausgangsdaten</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Nenn-Wirkleistung</td>
<td style="text-align: center;">3600 W</td>
<td style="text-align: center;">5000 W</td>
<td style="text-align: center;">6000 W</td>
<td style="text-align: center;">7000 W</td>
<td style="text-align: center;">7600 W</td>
<td style="text-align: center;">8000 W</td>
<td style="text-align: center;">10000 W</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. Scheinleistung</td>
<td style="text-align: center;">3960 VA</td>
<td style="text-align: center;">5500 VA</td>
<td style="text-align: center;">6600 VA</td>
<td style="text-align: center;">7700 VA</td>
<td style="text-align: center;">8360 VA</td>
<td style="text-align: center;">8800 VA</td>
<td style="text-align: center;">11000 VA</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Nennstrom (Ein/Aus)</td>
<td style="text-align: center;">16,4/15,7 A</td>
<td style="text-align: center;">22,7/21,7 A</td>
<td style="text-align: center;">27,3/26,1 A</td>
<td style="text-align: center;">31,9/30,5 A</td>
<td style="text-align: center;">34,5/33 A</td>
<td style="text-align: center;">36,4/34,8 A</td>
<td style="text-align: center;">45,5/43,5 A</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. Strom (Ein/Aus)</td>
<td style="text-align: center;">18/17,2 A</td>
<td style="text-align: center;">25/23,9 A</td>
<td style="text-align: center;">30/28,7 A</td>
<td style="text-align: center;">35/33,5 A</td>
<td style="text-align: center;">38/36,3 A</td>
<td style="text-align: center;">40/38,3 A</td>
<td style="text-align: center;">50/47,9 A</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. AC-Durchgang (Netz &#8594; Last)</td>
<td colspan="2" style="text-align: center;">35 A</td>
<td colspan="3" style="text-align: center;">40 A</td>
<td colspan="2" style="text-align: center;">50 A</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Spitzenleistung (Insel)</td>
<td colspan="7" style="text-align: center;">2 &#215; Nennleistung, 10 s</td>
</tr>
<!-- Wirkungsgrad & Schutz -->
<tr style="background: #30358C; color: white;">
<td colspan="8" style="padding: 16px 20px;">Wirkungsgrad &amp; Schutz</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. Wirkungsgrad</td>
<td colspan="7" style="text-align: center;">97,6 %</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Euro-Wirkungsgrad</td>
<td colspan="7" style="text-align: center;">96,5 %</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">MPPT-Wirkungsgrad</td>
<td colspan="7" style="text-align: center;">&gt; 99 %</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Schutzart</td>
<td colspan="7" style="text-align: center;">IP65</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Ger&#228;uschpegel</td>
<td colspan="7" style="text-align: center;">&#8804; 30 dB</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Parallelbetrieb</td>
<td colspan="7" style="text-align: center;">Bis 16 Ger&#228;te (On-Grid + Off-Grid)</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Zeitgesteuerte Lade-/Entladezeitr&#228;ume</td>
<td colspan="7" style="text-align: center;">6 individuell programmierbar</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Dieselgenerator-Speicherung</td>
<td colspan="7" style="text-align: center;">Ja</td>
</tr>
</tbody>
</table>