<p>The Deye&#160;SUN-80K-SG02HP3-EU-EM6 is a powerful three-phase hybrid inverter designed for high-performance solar energy systems. Equipped with 4 MPPTs and high-voltage battery support, it ensures exceptional efficiency and flexibility. This inverter supports 100% unbalanced output, allowing each phase to independently deliver up to 50% of the rated power&#8212;ideal for uneven load distribution. Thanks to its AC coupling capability, it can seamlessly retrofit into existing PV systems, enhancing performance without requiring a full overhaul. It allows for parallel operation of up to 10 units in both on-grid and off-grid modes and supports multiple batteries in parallel, offering excellent scalability. With a maximum charging and discharging current of 80A + 80A, it maintains efficient and reliable energy flow. Additionally, users can configure six charging and discharging time periods, optimizing battery use based on energy demand and tariff rates. The inverter is also compatible with diesel generators, ensuring dependable backup power in areas with unstable grid supply.</p>
<p></p>
<p><img src="https://syd-green-energy.com/files/images/syd-solar-mood-006.jpg" alt="SYD Green Energy - Solar systems and accessories from the experts" style="width: 100%;" /></p>
<p></p>
<h3>Key Features</h3>
<ul>
<li data-start="0" data-end="152">
<p data-start="2" data-end="152"><strong data-start="2" data-end="29" data-is-only-node="">100% Unbalanced Output:</strong>&#160;Each phase can operate independently with up to 50% of the rated power, ensuring flexibility for varied load conditions.</p>
</li>
<li data-start="153" data-end="296">
<p data-start="155" data-end="296"><strong data-start="155" data-end="184" data-is-only-node="">AC Coupling for Retrofit:</strong>&#160;Easily integrates into existing solar systems, enabling efficient performance upgrades without major changes.</p>
</li>
<li data-start="297" data-end="468">
<p data-start="299" data-end="468"><strong data-start="299" data-end="331" data-is-only-node="">Scalable Parallel Operation:</strong>&#160;Supports up to 10 units in parallel for both on-grid and off-grid modes, with compatibility for multiple parallel battery connections.</p>
</li>
<li data-start="469" data-end="605">
<p data-start="471" data-end="605"><strong data-start="471" data-end="516" data-is-only-node="">Max. Charging/Discharging Current of 80A + 80A:</strong>&#160;Ensures stable and efficient energy flow for both charging and discharging operations.</p>
</li>
<li data-start="606" data-end="731">
<p data-start="608" data-end="731"><strong data-start="608" data-end="641" data-is-only-node="">High Voltage Battery Support:</strong>&#160;Utilizes high-voltage batteries to increase system efficiency and reduce energy losses.</p>
</li>
<li data-start="732" data-end="899">
<p data-start="734" data-end="899"><strong data-start="734" data-end="768" data-is-only-node="">Time-based Battery Management:</strong>&#160;Allows for six configurable time periods for optimized battery charging and discharging based on energy consumption and tariffs.</p>
</li>
<li data-start="900" data-end="1059" data-is-last-node="">
<p data-start="902" data-end="1059" data-is-last-node=""><strong data-start="902" data-end="937" data-is-only-node="">Diesel Generator Compatibility:</strong>&#160;Capable of storing energy from diesel generators, offering reliable backup in areas with unstable or limited grid access.</p>
</li>
</ul>
<p></p>
<p></p>
<p><img src="https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg" alt="SYD Green Energy - Solar systems and accessories from the experts" style="width: 100%;" /></p>
<p></p>
<h3>Technical Specifications</h3>
<ul>
<li><strong data-start="283" data-end="305">Battery Input Data<br /><br /></strong>
<ul data-start="306" data-end="596">
<li data-start="306" data-end="384"><strong data-start="308" data-end="334">Battery Compatibility:</strong>&#160;Lithium-ion batteries (lead-acid not supported)</li>
<li data-start="385" data-end="424"><strong data-start="387" data-end="413">Battery Voltage Range:</strong>&#160;160&#8211;1000V</li>
<li data-start="425" data-end="471"><strong data-start="427" data-end="465">Max. Charging/Discharging Current:</strong>&#160;80A + 80A</li>
<li data-start="472" data-end="506"><strong data-start="474" data-end="492">Battery Input:</strong>&#160;Single port</li>
<li data-start="507" data-end="596"><strong data-start="509" data-end="531">BMS Communication:</strong>&#160;Self-adaptive, ensuring compatibility with various BMS protocols<br /><br /></li>
</ul>
</li>
<li><strong data-start="608" data-end="632">PV String Input Data<br /><br /></strong>
<ul data-start="633" data-end="1003">
<li data-start="633" data-end="670"><strong data-start="635" data-end="660">Max. PV Access Power:</strong>&#160;<span>160000</span>W</li>
<li data-start="671" data-end="707"><strong data-start="673" data-end="697">Max. PV Input Power:</strong>&#160;128<span>000</span>W</li>
<li data-start="708" data-end="744"><strong data-start="710" data-end="736">Max. PV Input Voltage:</strong>&#160;1000V</li>
<li data-start="745" data-end="781"><strong data-start="747" data-end="770">MPPT Voltage Range:</strong>&#160;150&#8211;850V</li>
<li data-start="782" data-end="812"><strong data-start="784" data-end="805">Start-up Voltage:</strong>&#160;180V</li>
<li data-start="813" data-end="849"><strong data-start="815" data-end="842">Rated DC Input Voltage:</strong>&#160;600V</li>
<li data-start="850" data-end="903"><strong data-start="852" data-end="891">Number of MPPTs / Strings per MPPT:</strong>&#160;6<span>&#160;/ 2+2+2+2+2+2</span></li>
<li data-start="904" data-end="954"><strong data-start="906" data-end="942">Max. Operating PV Input Current:</strong>&#160;36A + 36A + 36A + 36A + 36A + 36A</li>
<li data-start="955" data-end="1003"><strong data-start="957" data-end="991">Max. PV Short-Circuit Current:</strong>&#160;<span>54A + 54A + 54A + 54A + 54A + 54A</span><br /><br /></li>
</ul>
</li>
<li><strong data-start="1015" data-end="1041">AC Input / Output Data<br /><br /></strong>
<ul data-start="1042" data-end="1623">
<li data-start="1042" data-end="1084"><strong data-start="1044" data-end="1076">Rated AC Input/Output Power:</strong>&#160;8<span>0000</span>W</li>
<li data-start="1085" data-end="1120"><strong data-start="1087" data-end="1111">Max. Apparent Power:</strong>&#160;8800<span>0</span>A</li>
<li data-start="1121" data-end="1185"><strong data-start="1123" data-end="1149">Peak Power (Off-Grid):</strong>&#160;1.5&#215; rated power (for 10 seconds)</li>
<li data-start="1186" data-end="1238"><strong data-start="1188" data-end="1222">Rated AC Input/Output Current:</strong>&#160;<span>75.8/72.5</span></li>
<li data-start="1239" data-end="1290"><strong data-start="1241" data-end="1274">Max. AC Input/Output Current:</strong>&#160;<span>83.4/79.8</span></li>
<li data-start="1291" data-end="1349"><strong data-start="1293" data-end="1343">Max. Continuous AC Passthrough (Grid to Load):</strong>&#160;<span>200</span>A</li>
<li data-start="1350" data-end="1401"><strong data-start="1352" data-end="1370">Rated Voltage:</strong>&#160;220/380V, 230/400V (3L+N+PE)</li>
<li data-start="1402" data-end="1462"><strong data-start="1404" data-end="1429">Grid Frequency Range:</strong>&#160;50Hz (45&#8211;55Hz), 60Hz (55&#8211;65Hz)</li>
<li data-start="1463" data-end="1522"><strong data-start="1465" data-end="1493">Power Factor Adjustment:</strong>&#160;0.8 leading to 0.8 lagging</li>
<li data-start="1523" data-end="1568"><strong data-start="1525" data-end="1562">Total Harmonic Distortion (THDi):</strong>&#160;&lt;3%</li>
<li data-start="1569" data-end="1623"><strong data-start="1571" data-end="1596">DC Injection Current:</strong>&#160;&lt;0.5% of nominal current<br /><br /></li>
</ul>
</li>
<li><strong data-start="1635" data-end="1649">Efficiency<br /><br /></strong>
<ul data-start="1650" data-end="1745">
<li data-start="1650" data-end="1680"><strong data-start="1652" data-end="1672">Max. Efficiency:</strong>&#160;97.6%</li>
<li data-start="1681" data-end="1715"><strong data-start="1683" data-end="1707">European Efficiency:</strong>&#160;97.0%</li>
<li data-start="1716" data-end="1745"><strong data-start="1718" data-end="1738">MPPT Efficiency:</strong>&#160;&gt;99%<br /><br /></li>
</ul>
</li>
<li data-start="1781" data-end="2070"><strong data-start="1783" data-end="1810">Integrated Protections:<br /><br /></strong><strong data-start="2073" data-end="2094"></strong></li>
<li data-start="1781" data-end="2070"><strong data-start="2073" data-end="2094">Surge Protection:</strong>&#160;Type II (both DC &amp; AC sides)<br /><br />
<ul data-start="1815" data-end="2070">
<li data-start="1815" data-end="1838">DC reverse polarity</li>
<li data-start="1841" data-end="1866">AC output overcurrent</li>
<li data-start="1869" data-end="1887">AC overvoltage</li>
<li data-start="1890" data-end="1907">Short circuit</li>
<li data-start="1910" data-end="1932">Thermal protection</li>
<li data-start="1935" data-end="1965">Residual current detection</li>
<li data-start="1968" data-end="2004">Insulation resistance monitoring</li>
<li data-start="2007" data-end="2040">Optional arc fault protection</li>
<li data-start="2043" data-end="2070">DC component monitoring<br /><br /></li>
</ul>
</li>
<li data-start="2126" data-end="2153"><strong data-start="2128" data-end="2142">DC Switch:</strong>&#160;Included<br /><br /></li>
<li data-start="2126" data-end="2153"><strong data-start="2165" data-end="2191">Standards &amp; Compliance<br /><br /></strong>
<ul data-start="2192" data-end="2430">
<li data-start="2192" data-end="2339"><strong data-start="2194" data-end="2214">Grid Compliance:</strong><br data-start="2214" data-end="2217" />IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,<br data-start="2289" data-end="2292" />OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</li>
<li data-start="2340" data-end="2430"><strong data-start="2342" data-end="2369">Safety &amp; EMC Standards:</strong><br data-start="2369" data-end="2372" />IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2<br /><br /></li>
</ul>
</li>
<li><strong data-start="2442" data-end="2486">Environmental &amp; Physical Characteristics<br /><br /></strong>
<ul data-start="2487" data-end="2880">
<li data-start="2487" data-end="2560"><strong data-start="2489" data-end="2521">Operating Temperature Range:</strong>&#160;-40&#176;C to +60&#176;C (derating above 45&#176;C)</li>
<li data-start="2561" data-end="2585"><strong data-start="2563" data-end="2576">Humidity:</strong>&#160;0&#8211;100%</li>
<li data-start="2586" data-end="2617"><strong data-start="2588" data-end="2609">Maximum Altitude:</strong>&#160;3000m</li>
<li data-start="2618" data-end="2648"><strong data-start="2620" data-end="2636">Noise Level:</strong>&#160;&#8804;65 dB(A)</li>
<li data-start="2649" data-end="2705"><strong data-start="2651" data-end="2670">Cooling Method:</strong>&#160;<span>Intelligent Air Cooling</span></li>
<li data-start="2706" data-end="2773"><strong data-start="2708" data-end="2733">IP Protection Rating:</strong>&#160;IP65 (dust-tight and water-resistant)</li>
<li data-start="2774" data-end="2856"><strong data-start="2776" data-end="2803">Dimensions (W &#215; H &#215; D):</strong>&#160;<span>606 &#215; 927 &#215; 31</span><span>4</span> mm (excluding connectors/brackets)</li>
<li data-start="2857" data-end="2880"><strong data-start="2859" data-end="2870">Weight:</strong>&#160;105 kg<br /><br /></li>
</ul>
</li>
<li><strong data-start="2892" data-end="2921">Interface &amp; Communication<br /><br /></strong>
<ul data-start="2922" data-end="3039">
<li data-start="2922" data-end="2992"><strong data-start="2924" data-end="2947">Monitoring Options:</strong>&#160;GPRS, Wi-Fi, Bluetooth, 4G, LAN (optional)</li>
<li data-start="2993" data-end="3039"><strong data-start="2995" data-end="3019">Communication Ports:</strong>&#160;RS485, RS232, CAN</li>
</ul>
</li>
</ul>
<strong>The Deye&#160;SUN-80K-SG02HP3-EU-EM6 is a three-phase hybrid inverter designed for intelligent energy management. With quad MPPTs, high-voltage battery support, and robust protection features, it ensures efficient solar integration, seamless backup power, and long-term reliability for residential and small commercial applications.<br /></strong>