<table style="width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); font-size: 16px;">
<tbody>
<tr style="background: #30358C; color: white;"><th style="padding: 18px 20px; text-align: left; font-weight: 600;">Parameter</th><th style="padding: 18px 20px; text-align: center; font-weight: 600;">7 Module</th><th style="padding: 18px 20px; text-align: center; font-weight: 600;">13 Module</th><th style="padding: 18px 20px; text-align: center; font-weight: 600;">21 Module</th></tr>
<tr>
<td colspan="4" style="background: #30358c; color: white; padding: 14px 20px; font-weight: bold; font-size: 17px; text-align: left;">Deye BOS-A LiFePO&#8324; Hochvolt-Batteriesystem</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px; font-weight: 600;">Zellchemie</td>
<td colspan="3" style="padding: 14px 20px; text-align: center;">LiFePO&#8324;</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Energie pro Modul</td>
<td colspan="3" style="padding: 14px 20px; text-align: center;">7,68 kWh</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Nennspannung pro Modul</td>
<td colspan="3" style="padding: 14px 20px; text-align: center;">38,4 V / 200 Ah</td>
</tr>
<tr>
<td style="padding: 14px 20px;">System-Nennspannung</td>
<td style="text-align: center;">268,8 V</td>
<td style="text-align: center;">499,2 V</td>
<td style="text-align: center;">806,4 V</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">System-Betriebsspannung</td>
<td style="text-align: center;">235,2&#8211;306,6 V</td>
<td style="text-align: center;">436,8&#8211;569,4 V</td>
<td style="text-align: center;">705,6&#8211;920,7 V</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Systemenergie</td>
<td style="text-align: center;">53,76 kWh</td>
<td style="text-align: center;">99,84 kWh</td>
<td style="text-align: center;">161,28 kWh</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Nutzenergie (90 % DoD)</td>
<td style="text-align: center;">48,38 kWh</td>
<td style="text-align: center;">89,85 kWh</td>
<td style="text-align: center;">145,15 kWh</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Lade-/Entladestrom (empf. / max.)</td>
<td colspan="3" style="padding: 14px 20px; text-align: center;">100 A / 160 A</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Betriebstemperatur</td>
<td colspan="3" style="padding: 14px 20px; text-align: center;">Laden 0 bis +55 &#176;C / Entladen &#8211;20 bis +55 &#176;C</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Schutzart</td>
<td colspan="3" style="padding: 14px 20px; text-align: center;">IP20</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Gewicht pro Modul</td>
<td colspan="3" style="padding: 14px 20px; text-align: center;">ca. 70 kg</td>
</tr>
<tr>
<td style="padding: 14px 20px;">System-Gewicht (ca.)</td>
<td style="text-align: center;">530 kg</td>
<td style="text-align: center;">985 kg</td>
<td style="text-align: center;">1590 kg</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Zyklenlebensdauer</td>
<td colspan="3" style="padding: 14px 20px; text-align: center;">&#8805;6000 (25 &#176;C, 0,5C)</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Garantie</td>
<td colspan="3" style="padding: 14px 20px; text-align: center;">10 Jahre</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Kommunikation</td>
<td colspan="3" style="padding: 14px 20px; text-align: center;">CAN2.0</td>
</tr>
</tbody>
</table>