INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(538, '<table selecttype=\"cells\">\r\n<tbody>\r\n<tr height=\"35\">\r\n<td colspan=\"2\" width=\"912\"><strong>Battery Input Data</strong></td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Battery Type</td>\r\n<td width=\"650\">Lead-acid or Lithium-ion</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Battery Voltage Range (V)</td>\r\n<td width=\"650\">40-60</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. Charging Current (A)</td>\r\n<td width=\"130\">280</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. Discharging Current (A)</td>\r\n<td width=\"130\">280</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Charging Strategy forLi-ion Battery</td>\r\n<td width=\"650\">Self-adaption to BMS</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Number of Battery Input</td>\r\n<td width=\"650\">1</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td colspan=\"2\" width=\"912\">\r\n<p></p>\r\n<p><strong>PV String Input Data</strong></p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<div><span>Max. PV Access Power (W)</span></div>\r\n</td>\r\n<td>30000</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. DC Input Power (W)</td>\r\n<td width=\"130\">24000</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. DC Input Voltage (V)</td>\r\n<td width=\"650\">800</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Start-up Voltage (V)</td>\r\n<td width=\"650\">160</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">MPPT Voltage Range (V)</td>\r\n<td width=\"650\">160-650</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Rated DC Input Voltage (V)</td>\r\n<td width=\"650\">550</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. Operating PV Input Current (A)</td>\r\n<td width=\"650\">36+36</td>\r\n</tr>\r\n<tr height=\"31\">\r\n<td width=\"262\">Max. Input Short-Circuit Current (A)</td>\r\n<td width=\"650\">54+54</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">No.of MPPT Trackers/<br />No.of String PerMPPT Tracker</td>\r\n<td width=\"650\">2/2+2</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">\r\n<p></p>\r\n<p><strong>AC Input/Output Data</strong></p>\r\n</td>\r\n<td width=\"650\"></td>\r\n</tr>\r\n<tr height=\"33\">\r\n<td width=\"262\">Rated AC Input/Output Active Power (W)</td>\r\n<td width=\"130\">15000</td>\r\n</tr>\r\n<tr height=\"31\">\r\n<td width=\"262\">Max. AC Input/Output Apparent Power (VA)</td>\r\n<td width=\"130\">16500</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Rated AC Input/Output Current (A)</td>\r\n<td width=\"130\">22.8/21.8</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. AC Input/Output Current (A)</td>\r\n<td width=\"130\">25/24</td>\r\n</tr>\r\n<tr height=\"29\">\r\n<td width=\"262\">Max. Continuous AC Passthrough (grid to load) (A)</td>\r\n<td width=\"650\">70</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Peak Power (off-grid) (W)</td>\r\n<td width=\"650\">2 times of rated power, 10s</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Power Factor Adjustment Range</td>\r\n<td width=\"650\">0.8 leading to 0.8 lagging</td>\r\n</tr>\r\n<tr height=\"34\">\r\n<td width=\"262\">Rated Input/Output Voltage/Range (V)</td>\r\n<td width=\"650\">220/380V, 230/400V&#160; 0.85Un-1.1Un</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Rated Input/Output Grid Frequency/Range(Hz)</td>\r\n<td width=\"650\">50/45-55, 60/55-65</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Grid Connection Form</td>\r\n<td width=\"650\">3L+N+PE</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Total Current Harmonic Distortion THDi</td>\r\n<td width=\"650\">&lt;3% (of nominal power)</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">DC Component of Grid</td>\r\n<td width=\"650\">&lt;0.5% In</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">\r\n<p></p>\r\n<p><strong>E&#64259;ciency</strong></p>\r\n</td>\r\n<td width=\"650\"></td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. Ef&#64257;ciency</td>\r\n<td width=\"650\">97.6%</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Euro Ef&#64257;ciency</td>\r\n<td width=\"650\">97.0%</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">MPPTEf&#64257;ciency</td>\r\n<td width=\"650\">&gt;99%</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">\r\n<p></p>\r\n<p><strong>Equipment Protection</strong></p>\r\n</td>\r\n<td width=\"650\"></td>\r\n</tr>\r\n<tr height=\"136\">\r\n<td width=\"262\">Integrated</td>\r\n<td width=\"650\">\r\n<div><span>DC Polarity Reverse Connection Protection, AC Output Overcurrent Protection, Thermal Protection,</span></div>\r\n<div><span>AC Output Overvoltage Protection, AC Output Short Circuit Protection, DC Component Monitoring,</span></div>\r\n<div><span>Overvoltage Load Drop Protection, Ground Fault Current Monitoring, Arc Fault Circuit Interrupter (optional),</span></div>\r\n<div><span>Power Network Monitoring, Island Protection Monitoring, Earth Fault Detection, DC Input Switch,</span></div>\r\n<div><span>DC Terminal Insulation Impedance Monitoring, Residual Current (RCD) Detection, Surge protection level</span></div>\r\n</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Surge Protection Level</td>\r\n<td width=\"650\">TYPE II(DC),TYPE II(AC)</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">\r\n<p></p>\r\n<p><strong>Interface</strong></p>\r\n</td>\r\n<td width=\"650\"></td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Communication Interface</td>\r\n<td width=\"650\">RS485/RS232/CAN</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<div><span>Monitor Mode</span></div>\r\n</td>\r\n<td>\r\n<div><span>GPRS/WIFI/Bluetooth/4G/LAN(optional)</span></div>\r\n</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">\r\n<p></p>\r\n<p><strong>General Data</strong></p>\r\n</td>\r\n<td width=\"650\"></td>\r\n</tr>\r\n<tr height=\"39\">\r\n<td width=\"262\"><span>Operating Temperature Range (</span><span>&#8451;</span><span>)</span></td>\r\n<td width=\"650\"><span>-40 to +60</span><span>&#8451;</span><span>, &gt;45</span><span>&#8451;&#160;</span><span>Derating</span></td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Permissible Ambient Humidity</td>\r\n<td width=\"650\">0-100%</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Permissible Altitude</td>\r\n<td width=\"650\">3000m</td>\r\n</tr>\r\n<tr height=\"29\">\r\n<td width=\"262\">Noise</td>\r\n<td width=\"650\">&#8804;60</td>\r\n</tr>\r\n<tr height=\"31\">\r\n<td width=\"262\">Ingress Protection(IP) Rating</td>\r\n<td width=\"650\">IP 65</td>\r\n</tr>\r\n<tr height=\"32\">\r\n<td width=\"262\">Inverter Topology</td>\r\n<td width=\"650\">Non-Isolated</td>\r\n</tr>\r\n<tr height=\"40\">\r\n<td width=\"262\">Over Voltage Category</td>\r\n<td width=\"650\">OVC II(DC), OVC III(AC)</td>\r\n</tr>\r\n<tr height=\"36\">\r\n<td width=\"262\">Cabinet Size (WxHxD mm)</td>\r\n<td width=\"650\">456&#215;750&#215;268.5 (Excluding Connectors and Brackets)</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Weight (kg)</td>\r\n<td width=\"650\">51.9</td>\r\n</tr>\r\n<tr height=\"36\">\r\n<td width=\"262\">Type of Cooling</td>\r\n<td width=\"650\">Intelligent Air Cooling</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"262\">Warranty</td>\r\n<td width=\"650\">5 Years/10 Years<br />the Warranty Period Depends the Final Installation Site of Inverter, More Info Please Refer to Warranty Policy</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"262\">Grid Regulation</td>\r\n<td width=\"650\">IEC 61727, IEC 62116,CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,<br />OVE-Richtlinie R25, G99,VDE-AR-N 4105</td>\r\n</tr>\r\n<tr height=\"31\">\r\n<td width=\"262\">Safety / EMC Standard</td>\r\n<td width=\"650\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</td>\r\n</tr>\r\n</tbody>\r\n</table>', 2, 'SUN-15K-SG05LP3-EU-SM2 | Three-Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', '<p>The&#160;SUN-15K-SG05LP3-EU-SM2 is a powerful and flexible hybrid inverter designed for residential and small commercial solar applications. It supports a maximum charging and discharging current of 280A, enabling rapid and responsive energy storage. The inverter is compatible with diesel generators, allowing energy storage from these sources for added backup power. It supports parallel operation of up to 10 units in both on-grid and off-grid modes, providing scalability for expanding energy systems. AC coupling enables easy integration into existing solar installations for cost-effective upgrades. The inverter features time-based battery management with six configurable periods to optimize charging and discharging based on consumption patterns and electricity tariffs. Operating with a low voltage 48V battery and transformer isolation, it ensures safe and efficient energy storage. Additionally, it can handle 100% unbalanced output, with each phase capable of delivering up to 50% of the rated power, allowing flexible load management without loss of efficiency.</p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-004.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" /></p>\r\n<p></p>\r\n<h3>Key Features</h3>\r\n<ul>\r\n<li><strong>High Charging/Discharging Current:</strong>&#160;The Deye&#160;SUN 15K-SG05LP3-EU-SM2 supports a maximum charging and discharging current of 280A. This high current capacity ensures rapid energy storage and retrieval, making the system highly responsive to energy demand peaks.<br /><br /></li>\r\n<li><strong>Compatibility with Diesel Generators:&#160;</strong>These inverters support the storage of energy from diesel generators, providing versatility and additional backup power capabilities, especially useful in areas with unreliable grid supply.<br /><br /></li>\r\n<li><strong>Scalable Parallel Operation:</strong>&#160;Up to 10 units can operate in parallel both in on-grid and off-grid modes. This scalability allows for both small-scale and large-scale energy requirements to be met efficiently, making it ideal for expanding energy systems.<br /><br /></li>\r\n<li><strong>AC Coupling for Retrofit:</strong>&#160;The inverters can easily integrate into existing solar systems through AC coupling, offering a cost-effective route to upgrade current installations for enhanced performance and energy storage.<br /><br /></li>\r\n<li><strong>Time-based Battery Management:</strong>&#160;Supports six time periods for battery charging and discharging, allowing users to optimize energy storage based on consumption patterns and electricity tariffs. This feature significantly enhances the cost-effectiveness of the energy system.<br /><br /></li>\r\n<li><strong>Low Voltage Battery with Isolation:</strong>&#160;Operating with a 48V low voltage battery and transformer isolation design, the inverter ensures safe and efficient energy storage, reducing the risk of electrical hazards.<br /><br /></li>\r\n<li><strong>Unbalanced Output Capability:</strong>&#160;Each phase can handle a 100% unbalanced output with a maximum output of up to 50% of the rated power for each phase. This flexibility supports varied load requirements without efficiency loss.</li>\r\n</ul>\r\n<p></p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" /></p>\r\n<p></p>\r\n<h3>Technical Specifications</h3>\r\n<ul>\r\n<li><strong>Battery Input:</strong>\r\n<ul>\r\n<li>Compatible with lead-acid and lithium-ion batteries</li>\r\n<li>Voltage range: 40-60V</li>\r\n<li>Single battery input with self-adaptive BMS<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong>PV Input:</strong>\r\n<ul>\r\n<li>Maximum input power ranges up to 24000W</li>\r\n<li>Maximum PV input voltage: 550V</li>\r\n<li>MPPT voltage range: 200-650V<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong>AC Input/Output:</strong>\r\n<ul>\r\n<li>Rated power ranges up to 15000W</li>\r\n<li>Rated AC Input/Output Current:&#160;22.8/21.8&#160;per phase</li>\r\n<li>Maximum Continuous AC Passthrough (grid to load): 45A<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong>Efficiency and Protection:</strong>\r\n<ul>\r\n<li>Maximum efficiency: 97.6%</li>\r\n<li>European efficiency: 97.0%</li>\r\n<li>MPPT efficiency greater than 99%</li>\r\n<li>Features comprehensive protection mechanisms, including reverse polarity, overcurrent, overvoltage, thermal protection, and more.<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong>Standards and Compliance:</strong>\r\n<ul>\r\n<li>Meets grid regulations including IEC 61727, IEC 62116, and several national standards</li>\r\n<li>Safety standards: IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1/2<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong>Environmental and Physical:</strong>\r\n<ul>\r\n<li>Operating temperature: -40 to +60 &#8451;</li>\r\n<li>Permissible humidity: up to 100%</li>\r\n<li>Maximum altitude: 3000m</li>\r\n<li>Noise level: &#8804;60dB</li>\r\n<li>IP65 rated for dust and water protection</li>\r\n<li>Intelligent air cooling system</li>\r\n<li>Weight: 51.9 kg</li>\r\n<li>Dimensions:&#160;456&#215;750&#215;268.5&#160;mm (excluding connectors and brackets)</li>\r\n</ul>\r\n</li>\r\n</ul>\r\n<p><strong>The Deye SUN-15K-SG05LP3-EU-SM2 series inverters are designed to deliver high performance, reliability, and flexibility. They provide a comprehensive energy solution by combining photovoltaic and battery storage capabilities with sophisticated energy management, making them ideal for a wide range of applications.</strong></p>', '<span>The Deye SUN-15K-SG05LP3-EU-SM2 series comprises sophisticated three-phase hybrid inverters designed to meet the energy needs of residential and commercial establishments. These units are engineered to seamlessly integrate solar, battery storage, and grid electricity to provide a reliable and efficient energy management system. Whether for new installations or retrofitting existing solar setups, these hybrid inverters offer a robust solution that maximizes energy utilization and enhances system resilience.</span>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\r\n\r\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\r\n\r\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\r\n\r\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\r\n\r\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\r\n\r\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\r\n\r\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(538, '<table selecttype=\"cells\">\r\n<tbody>\r\n<tr height=\"35\">\r\n<td colspan=\"2\" width=\"912\"><strong>Battery Input Data</strong></td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Battery Type</td>\r\n<td width=\"650\">Lead-acid or Lithium-ion</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Battery Voltage Range (V)</td>\r\n<td width=\"650\">40-60</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. Charging Current (A)</td>\r\n<td width=\"130\">280</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. Discharging Current (A)</td>\r\n<td width=\"130\">280</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Charging Strategy forLi-ion Battery</td>\r\n<td width=\"650\">Self-adaption to BMS</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Number of Battery Input</td>\r\n<td width=\"650\">1</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td colspan=\"2\" width=\"912\">\r\n<p></p>\r\n<p><strong>PV String Input Data</strong></p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>Max. PV Access Power (W)</td>\r\n<td>30000</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. DC Input Power (W)</td>\r\n<td width=\"130\">24000</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. DC Input Voltage (V)</td>\r\n<td width=\"650\">800</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Start-up Voltage (V)</td>\r\n<td width=\"650\">160</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">MPPT Voltage Range (V)</td>\r\n<td width=\"650\">160-650</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Rated DC Input Voltage (V)</td>\r\n<td width=\"650\">550</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. Operating PV Input Current (A)</td>\r\n<td width=\"650\">36+36</td>\r\n</tr>\r\n<tr height=\"31\">\r\n<td width=\"262\">Max. Input Short-Circuit Current (A)</td>\r\n<td width=\"650\">54+54</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">No.of MPPT Trackers/<br />No.of String PerMPPT Tracker</td>\r\n<td width=\"650\">2/2+2</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">\r\n<p></p>\r\n<p><strong>AC Input/Output Data</strong></p>\r\n</td>\r\n<td width=\"650\"></td>\r\n</tr>\r\n<tr height=\"33\">\r\n<td width=\"262\">Rated AC Input/Output Active Power (W)</td>\r\n<td width=\"130\">15000</td>\r\n</tr>\r\n<tr height=\"31\">\r\n<td width=\"262\">Max. AC Input/Output Apparent Power (VA)</td>\r\n<td width=\"130\">16500</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Rated AC Input/Output Current (A)</td>\r\n<td width=\"130\">22.8/21.8</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. AC Input/Output Current (A)</td>\r\n<td width=\"130\">25/24</td>\r\n</tr>\r\n<tr height=\"29\">\r\n<td width=\"262\">Max. Continuous AC Passthrough (grid to load) (A)</td>\r\n<td width=\"650\">70</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Peak Power (off-grid) (W)</td>\r\n<td width=\"650\">2 times of rated power, 10s</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Power Factor Adjustment Range</td>\r\n<td width=\"650\">0.8 leading to 0.8 lagging</td>\r\n</tr>\r\n<tr height=\"34\">\r\n<td width=\"262\">Rated Input/Output Voltage/Range (V)</td>\r\n<td width=\"650\">220/380V, 230/400V&#160; 0.85Un-1.1Un</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Rated Input/Output Grid Frequency/Range(Hz)</td>\r\n<td width=\"650\">50/45-55, 60/55-65</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Grid Connection Form</td>\r\n<td width=\"650\">3L+N+PE</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Total Current Harmonic Distortion THDi</td>\r\n<td width=\"650\">&lt;3% (of nominal power)</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">DC Component of Grid</td>\r\n<td width=\"650\">&lt;0.5% In</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">\r\n<p></p>\r\n<p><strong>E&#64259;ciency</strong></p>\r\n</td>\r\n<td width=\"650\"></td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. Ef&#64257;ciency</td>\r\n<td width=\"650\">97.6%</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Euro Ef&#64257;ciency</td>\r\n<td width=\"650\">97.0%</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">MPPTEf&#64257;ciency</td>\r\n<td width=\"650\">&gt;99%</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">\r\n<p></p>\r\n<p><strong>Equipment Protection</strong></p>\r\n</td>\r\n<td width=\"650\"></td>\r\n</tr>\r\n<tr height=\"136\">\r\n<td width=\"262\">Integrated</td>\r\n<td width=\"650\">\r\n<div>DC Polarity Reverse Connection Protection, AC Output Overcurrent Protection, Thermal Protection,</div>\r\n<div>AC Output Overvoltage Protection, AC Output Short Circuit Protection, DC Component Monitoring,</div>\r\n<div>Overvoltage Load Drop Protection, Ground Fault Current Monitoring, Arc Fault Circuit Interrupter (optional),</div>\r\n<div>Power Network Monitoring, Island Protection Monitoring, Earth Fault Detection, DC Input Switch,</div>\r\n<div>DC Terminal Insulation Impedance Monitoring, Residual Current (RCD) Detection, Surge protection level</div>\r\n</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Surge Protection Level</td>\r\n<td width=\"650\">TYPE II(DC),TYPE II(AC)</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">\r\n<p></p>\r\n<p><strong>Interface</strong></p>\r\n</td>\r\n<td width=\"650\"></td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Communication Interface</td>\r\n<td width=\"650\">RS485/RS232/CAN</td>\r\n</tr>\r\n<tr>\r\n<td>Monitor Mode</td>\r\n<td>GPRS/WIFI/Bluetooth/4G/LAN(optional)</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">\r\n<p></p>\r\n<p><strong>General Data</strong></p>\r\n</td>\r\n<td width=\"650\"></td>\r\n</tr>\r\n<tr height=\"39\">\r\n<td width=\"262\">Operating Temperature Range (&#8451;)</td>\r\n<td width=\"650\">-40 to +60&#8451;, &gt;45&#8451;&#160;Derating</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Permissible Ambient Humidity</td>\r\n<td width=\"650\">0-100%</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Permissible Altitude</td>\r\n<td width=\"650\">3000m</td>\r\n</tr>\r\n<tr height=\"29\">\r\n<td width=\"262\">Noise</td>\r\n<td width=\"650\">&#8804;60</td>\r\n</tr>\r\n<tr height=\"31\">\r\n<td width=\"262\">Ingress Protection(IP) Rating</td>\r\n<td width=\"650\">IP 65</td>\r\n</tr>\r\n<tr height=\"32\">\r\n<td width=\"262\">Inverter Topology</td>\r\n<td width=\"650\">Non-Isolated</td>\r\n</tr>\r\n<tr height=\"40\">\r\n<td width=\"262\">Over Voltage Category</td>\r\n<td width=\"650\">OVC II(DC), OVC III(AC)</td>\r\n</tr>\r\n<tr height=\"36\">\r\n<td width=\"262\">Cabinet Size (WxHxD mm)</td>\r\n<td width=\"650\">456&#215;750&#215;268.5 (Excluding Connectors and Brackets)</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Weight (kg)</td>\r\n<td width=\"650\">51.9</td>\r\n</tr>\r\n<tr height=\"36\">\r\n<td width=\"262\">Type of Cooling</td>\r\n<td width=\"650\">Intelligent Air Cooling</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"262\">Warranty</td>\r\n<td width=\"650\">5 Years/10 Years<br />the Warranty Period Depends the Final Installation Site of Inverter, More Info Please Refer to Warranty Policy</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"262\">Grid Regulation</td>\r\n<td width=\"650\">IEC 61727, IEC 62116,CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,<br />OVE-Richtlinie R25, G99,VDE-AR-N 4105</td>\r\n</tr>\r\n<tr height=\"31\">\r\n<td width=\"262\">Safety / EMC Standard</td>\r\n<td width=\"650\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2<br /><br /></td>\r\n</tr>\r\n</tbody>\r\n</table>', 3, 'SUN-15K-SG05LP3-EU-SM2 | Three-Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', '<p>The&#160;SUN-15K-SG05LP3-EU-SM2 is a powerful and flexible hybrid inverter designed for residential and small commercial solar applications. It supports a maximum charging and discharging current of 280A, enabling rapid and responsive energy storage. The inverter is compatible with diesel generators, allowing energy storage from these sources for added backup power. It supports parallel operation of up to 10 units in both on-grid and off-grid modes, providing scalability for expanding energy systems. AC coupling enables easy integration into existing solar installations for cost-effective upgrades. The inverter features time-based battery management with six configurable periods to optimize charging and discharging based on consumption patterns and electricity tariffs. Operating with a low voltage 48V battery and transformer isolation, it ensures safe and efficient energy storage. Additionally, it can handle 100% unbalanced output, with each phase capable of delivering up to 50% of the rated power, allowing flexible load management without loss of efficiency.</p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-004.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" /></p>\r\n<p></p>\r\n<h3>Key Features</h3>\r\n<ul>\r\n<li><strong>High Charging/Discharging Current:</strong>&#160;The Deye&#160;SUN 15K-SG05LP3-EU-SM2 supports a maximum charging and discharging current of 280A. This high current capacity ensures rapid energy storage and retrieval, making the system highly responsive to energy demand peaks.<br /><br /></li>\r\n<li><strong>Compatibility with Diesel Generators:&#160;</strong>These inverters support the storage of energy from diesel generators, providing versatility and additional backup power capabilities, especially useful in areas with unreliable grid supply.<br /><br /></li>\r\n<li><strong>Scalable Parallel Operation:</strong>&#160;Up to 10 units can operate in parallel both in on-grid and off-grid modes. This scalability allows for both small-scale and large-scale energy requirements to be met efficiently, making it ideal for expanding energy systems.<br /><br /></li>\r\n<li><strong>AC Coupling for Retrofit:</strong>&#160;The inverters can easily integrate into existing solar systems through AC coupling, offering a cost-effective route to upgrade current installations for enhanced performance and energy storage.<br /><br /></li>\r\n<li><strong>Time-based Battery Management:</strong>&#160;Supports six time periods for battery charging and discharging, allowing users to optimize energy storage based on consumption patterns and electricity tariffs. This feature significantly enhances the cost-effectiveness of the energy system.<br /><br /></li>\r\n<li><strong>Low Voltage Battery with Isolation:</strong>&#160;Operating with a 48V low voltage battery and transformer isolation design, the inverter ensures safe and efficient energy storage, reducing the risk of electrical hazards.<br /><br /></li>\r\n<li><strong>Unbalanced Output Capability:</strong>&#160;Each phase can handle a 100% unbalanced output with a maximum output of up to 50% of the rated power for each phase. This flexibility supports varied load requirements without efficiency loss.</li>\r\n</ul>\r\n<p></p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" /></p>\r\n<p></p>\r\n<h3>Technical Specifications</h3>\r\n<ul>\r\n<li><strong>Battery Input:</strong>\r\n<ul>\r\n<li>Compatible with lead-acid and lithium-ion batteries</li>\r\n<li>Voltage range: 40-60V</li>\r\n<li>Single battery input with self-adaptive BMS<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong>PV Input:</strong>\r\n<ul>\r\n<li>Maximum input power ranges up to 24000W</li>\r\n<li>Maximum PV input voltage: 550V</li>\r\n<li>MPPT voltage range: 200-650V<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong>AC Input/Output:</strong>\r\n<ul>\r\n<li>Rated power ranges up to 15000W</li>\r\n<li>Rated AC Input/Output Current:&#160;22.8/21.8&#160;per phase</li>\r\n<li>Maximum Continuous AC Passthrough (grid to load): 45A<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong>Efficiency and Protection:</strong>\r\n<ul>\r\n<li>Maximum efficiency: 97.6%</li>\r\n<li>European efficiency: 97.0%</li>\r\n<li>MPPT efficiency greater than 99%</li>\r\n<li>Features comprehensive protection mechanisms, including reverse polarity, overcurrent, overvoltage, thermal protection, and more.<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong>Standards and Compliance:</strong>\r\n<ul>\r\n<li>Meets grid regulations including IEC 61727, IEC 62116, and several national standards</li>\r\n<li>Safety standards: IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1/2<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong>Environmental and Physical:</strong>\r\n<ul>\r\n<li>Operating temperature: -40 to +60 &#8451;</li>\r\n<li>Permissible humidity: up to 100%</li>\r\n<li>Maximum altitude: 3000m</li>\r\n<li>Noise level: &#8804;60dB</li>\r\n<li>IP65 rated for dust and water protection</li>\r\n<li>Intelligent air cooling system</li>\r\n<li>Weight: 51.9 kg</li>\r\n<li>Dimensions:&#160;456&#215;750&#215;268.5&#160;mm (excluding connectors and brackets)</li>\r\n</ul>\r\n</li>\r\n</ul>\r\n<p><strong>The Deye SUN-15K-SG05LP3-EU-SM2 series inverters are designed to deliver high performance, reliability, and flexibility. They provide a comprehensive energy solution by combining photovoltaic and battery storage capabilities with sophisticated energy management, making them ideal for a wide range of applications.</strong></p>', 'The Deye SUN-15K-SG05LP3-EU-SM2 series comprises sophisticated three-phase hybrid inverters designed to meet the energy needs of residential and commercial establishments. These units are engineered to seamlessly integrate solar, battery storage, and grid electricity to provide a reliable and efficient energy management system. Whether for new installations or retrofitting existing solar setups, these hybrid inverters offer a robust solution that maximizes energy utilization and enhances system resilience.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\r\n\r\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\r\n\r\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\r\n\r\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\r\n\r\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\r\n\r\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\r\n\r\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(539, '<table selecttype=\"cells\">\r\n<tbody>\r\n<tr height=\"35\">\r\n<td colspan=\"2\" width=\"912\"><strong>Battery Input Data</strong></td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Battery Type</td>\r\n<td width=\"650\">Lead-acid or Lithium-ion</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Battery Voltage Range (V)</td>\r\n<td width=\"650\">40-60</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. Charging Current (A)</td>\r\n<td width=\"130\">350</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. Discharging Current (A)</td>\r\n<td width=\"130\">350</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Charging Strategy forLi-ion Battery</td>\r\n<td width=\"650\">Self-adaption to BMS</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Number of Battery Input</td>\r\n<td width=\"650\">1</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td colspan=\"2\" width=\"912\">\r\n<p></p>\r\n<p><strong>PV String Input Data</strong></p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<div><span>Max. PV Access Power (W)</span></div>\r\n</td>\r\n<td>40000</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. DC Input Power (W)</td>\r\n<td width=\"130\">32000</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. DC Input Voltage (V)</td>\r\n<td width=\"650\">800</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Start-up Voltage (V)</td>\r\n<td width=\"650\">160</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">MPPT Voltage Range (V)</td>\r\n<td width=\"650\">160-650</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Rated DC Input Voltage (V)</td>\r\n<td width=\"650\">550</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. Operating PV Input Current (A)</td>\r\n<td width=\"650\">36+36</td>\r\n</tr>\r\n<tr height=\"31\">\r\n<td width=\"262\">Max. Input Short-Circuit Current (A)</td>\r\n<td width=\"650\">54+54</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">No.of MPPT Trackers/<br />No.of String PerMPPT Tracker</td>\r\n<td width=\"650\">2/2+2</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">\r\n<p></p>\r\n<p><strong>AC Input/Output Data</strong></p>\r\n</td>\r\n<td width=\"650\"></td>\r\n</tr>\r\n<tr height=\"33\">\r\n<td width=\"262\">Rated AC Input/Output Active Power (W)</td>\r\n<td width=\"130\">20000</td>\r\n</tr>\r\n<tr height=\"31\">\r\n<td width=\"262\">Max. AC Input/Output Apparent Power (VA)</td>\r\n<td width=\"130\">22000</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Rated AC Input/Output Current (A)</td>\r\n<td width=\"130\">30.4/29</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. AC Input/Output Current (A)</td>\r\n<td width=\"130\">33.4/31.9</td>\r\n</tr>\r\n<tr height=\"29\">\r\n<td width=\"262\">Max. Continuous AC Passthrough (grid to load) (A)</td>\r\n<td width=\"650\">70</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Peak Power (off-grid) (W)</td>\r\n<td width=\"650\">2 times of rated power, 10s</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Power Factor Adjustment Range</td>\r\n<td width=\"650\">0.8 leading to 0.8 lagging</td>\r\n</tr>\r\n<tr height=\"34\">\r\n<td width=\"262\">Rated Input/Output Voltage/Range (V)</td>\r\n<td width=\"650\">220/380V, 230/400V&#160; 0.85Un-1.1Un</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Rated Input/Output Grid Frequency/Range(Hz)</td>\r\n<td width=\"650\">50/45-55, 60/55-65</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Grid Connection Form</td>\r\n<td width=\"650\">3L+N+PE</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Total Current Harmonic Distortion THDi</td>\r\n<td width=\"650\">&lt;3% (of nominal power)</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">DC Component of Grid</td>\r\n<td width=\"650\">&lt;0.5% In</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">\r\n<p></p>\r\n<p><strong>E&#64259;ciency</strong></p>\r\n</td>\r\n<td width=\"650\"></td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. Ef&#64257;ciency</td>\r\n<td width=\"650\">97.6%</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Euro Ef&#64257;ciency</td>\r\n<td width=\"650\">97.0%</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">MPPTEf&#64257;ciency</td>\r\n<td width=\"650\">&gt;99%</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">\r\n<p></p>\r\n<p><strong>Equipment Protection</strong></p>\r\n</td>\r\n<td width=\"650\"></td>\r\n</tr>\r\n<tr height=\"136\">\r\n<td width=\"262\">Integrated</td>\r\n<td width=\"650\">\r\n<div><span>DC Polarity Reverse Connection Protection, AC Output Overcurrent Protection, Thermal Protection,</span></div>\r\n<div><span>AC Output Overvoltage Protection, AC Output Short Circuit Protection, DC Component Monitoring,</span></div>\r\n<div><span>Overvoltage Load Drop Protection, Ground Fault Current Monitoring, Arc Fault Circuit Interrupter (optional),</span></div>\r\n<div><span>Power Network Monitoring, Island Protection Monitoring, Earth Fault Detection, DC Input Switch,</span></div>\r\n<div><span>DC Terminal Insulation Impedance Monitoring, Residual Current (RCD) Detection, Surge protection level</span></div>\r\n</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Surge Protection Level</td>\r\n<td width=\"650\">TYPE II(DC),TYPE II(AC)</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">\r\n<p></p>\r\n<p><strong>Interface</strong></p>\r\n</td>\r\n<td width=\"650\"></td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Communication Interface</td>\r\n<td width=\"650\">RS485/RS232/CAN</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<div><span>Monitor Mode</span></div>\r\n</td>\r\n<td>\r\n<div><span>GPRS/WIFI/Bluetooth/4G/LAN(optional)</span></div>\r\n</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">\r\n<p></p>\r\n<p><strong>General Data</strong></p>\r\n</td>\r\n<td width=\"650\"></td>\r\n</tr>\r\n<tr height=\"39\">\r\n<td width=\"262\"><span>Operating Temperature Range (</span><span>&#8451;</span><span>)</span></td>\r\n<td width=\"650\"><span>-40 to +60</span><span>&#8451;</span><span>, &gt;45</span><span>&#8451;&#160;</span><span>Derating</span></td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Permissible Ambient Humidity</td>\r\n<td width=\"650\">0-100%</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Permissible Altitude</td>\r\n<td width=\"650\">3000m</td>\r\n</tr>\r\n<tr height=\"29\">\r\n<td width=\"262\">Noise</td>\r\n<td width=\"650\">&#8804;60</td>\r\n</tr>\r\n<tr height=\"31\">\r\n<td width=\"262\">Ingress Protection(IP) Rating</td>\r\n<td width=\"650\">IP 65</td>\r\n</tr>\r\n<tr height=\"32\">\r\n<td width=\"262\">Inverter Topology</td>\r\n<td width=\"650\">Non-Isolated</td>\r\n</tr>\r\n<tr height=\"40\">\r\n<td width=\"262\">Over Voltage Category</td>\r\n<td width=\"650\">OVC II(DC), OVC III(AC)</td>\r\n</tr>\r\n<tr height=\"36\">\r\n<td width=\"262\">Cabinet Size (WxHxD mm)</td>\r\n<td width=\"650\">456&#215;750&#215;268.5 (Excluding Connectors and Brackets)</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Weight (kg)</td>\r\n<td width=\"650\">51.9</td>\r\n</tr>\r\n<tr height=\"36\">\r\n<td width=\"262\">Type of Cooling</td>\r\n<td width=\"650\">Intelligent Air Cooling</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"262\">Warranty</td>\r\n<td width=\"650\">5 Years/10 Years<br />the Warranty Period Depends the Final Installation Site of Inverter, More Info Please Refer to Warranty Policy</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"262\">Grid Regulation</td>\r\n<td width=\"650\">IEC 61727, IEC 62116,CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,<br />OVE-Richtlinie R25, G99,VDE-AR-N 4105</td>\r\n</tr>\r\n<tr height=\"31\">\r\n<td width=\"262\">Safety / EMC Standard</td>\r\n<td width=\"650\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</td>\r\n</tr>\r\n</tbody>\r\n</table>', 2, 'SUN-20K-SG05LP3-EU-SM2 | Three-Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', '<p>The&#160;SUN-20K-SG05LP3-EU-SM2 is a powerful and flexible hybrid inverter designed for residential and small commercial solar applications. It supports a maximum charging and discharging current of 350A, enabling rapid and responsive energy storage. The inverter is compatible with diesel generators, allowing energy storage from these sources for added backup power. It supports parallel operation of up to 10 units in both on-grid and off-grid modes, providing scalability for expanding energy systems. AC coupling enables easy integration into existing solar installations for cost-effective upgrades. The inverter features time-based battery management with six configurable periods to optimize charging and discharging based on consumption patterns and electricity tariffs. Operating with a low voltage 48V battery and transformer isolation, it ensures safe and efficient energy storage. Additionally, it can handle 100% unbalanced output, with each phase capable of delivering up to 50% of the rated power, allowing flexible load management without loss of efficiency.</p>\r\n<p></p>\r\n<img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-004.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" />\r\n<p></p>\r\n<h3>Key Features</h3>\r\n<ul>\r\n<li><span><strong>High Charging/Discharging Current:</strong>&#160;</span>The Deye&#160;SUN 20K-SG05LP3-EU-SM2 supports a maximum charging and discharging current of 350A. This high current capacity ensures rapid energy storage and retrieval, making the system highly responsive to energy demand peaks.<br /><br /></li>\r\n<li><strong>Compatibility with Diesel Generators:&#160;</strong>These inverters support the storage of energy from diesel generators, providing versatility and additional backup power capabilities, especially useful in areas with unreliable grid supply.<br /><br /></li>\r\n<li><span><strong>Scalable Parallel Operation:</strong>&#160;</span>Up to 10 units can operate in parallel both in on-grid and off-grid modes. This scalability allows for both small-scale and large-scale energy requirements to be met efficiently, making it ideal for expanding energy systems.<br /><br /></li>\r\n<li><span><strong>AC Coupling for Retrofit:</strong>&#160;</span>The inverters can easily integrate into existing solar systems through AC coupling, offering a cost-effective route to upgrade current installations for enhanced performance and energy storage.<br /><br /></li>\r\n<li><span><strong>Time-based Battery Management:</strong>&#160;</span>Supports six time periods for battery charging and discharging, allowing users to optimize energy storage based on consumption patterns and electricity tariffs. This feature significantly enhances the cost-effectiveness of the energy system.<br /><br /></li>\r\n<li><span><strong>Low Voltage Battery with Isolation:</strong>&#160;</span>Operating with a 48V low voltage battery and transformer isolation design, the inverter ensures safe and efficient energy storage, reducing the risk of electrical hazards.<br /><br /></li>\r\n<li><span><strong>Unbalanced Output Capability:</strong>&#160;</span>Each phase can handle a 100% unbalanced output with a maximum output of up to 50% of the rated power for each phase. This flexibility supports varied load requirements without efficiency loss.</li>\r\n</ul>\r\n<br />\r\n<p></p>\r\n<img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" />\r\n<p></p>\r\n<h3>Technical Specifications</h3>\r\n<ul>\r\n<li><strong>Battery Input:</strong>\r\n<ul>\r\n<li>Compatible with lead-acid and lithium-ion batteries</li>\r\n<li>Voltage range: 40-60V</li>\r\n<li>Single battery input with self-adaptive BMS<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong>PV Input:</strong>\r\n<ul>\r\n<li>Maximum input power ranges up to 32000W</li>\r\n<li>Maximum PV input voltage: 550V</li>\r\n<li>MPPT voltage range: 200-650V<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong>AC Input/Output:</strong>\r\n<ul>\r\n<li>Rated power ranges up to 20000W</li>\r\n<li>Rated AC Input/Output Current:&#160;<span>30.4/29</span><span>&#160;per phase</span></li>\r\n<li>Maximum Continuous AC Passthrough (grid to load): 45A<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong>Efficiency and Protection:</strong>\r\n<ul>\r\n<li>Maximum efficiency: 97.6%</li>\r\n<li>European efficiency: 97.0%</li>\r\n<li>MPPT efficiency greater than 99%</li>\r\n<li>Features comprehensive protection mechanisms, including reverse polarity, overcurrent, overvoltage, thermal protection, and more.<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong>Standards and Compliance:</strong>\r\n<ul>\r\n<li>Meets grid regulations including IEC 61727, IEC 62116, and several national standards</li>\r\n<li>Safety standards: IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1/2<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong>Environmental and Physical:</strong>\r\n<ul>\r\n<li>Operating temperature: -40 to +60 &#8451;</li>\r\n<li>Permissible humidity: up to 100%</li>\r\n<li>Maximum altitude: 3000m</li>\r\n<li>Noise level: &#8804;60dB</li>\r\n<li>IP65 rated for dust and water protection</li>\r\n<li>Intelligent air cooling system</li>\r\n<li>Weight: 51.9 kg</li>\r\n<li>Dimensions: <span>456&#215;750&#215;268.5</span>&#160;mm (excluding connectors and brackets)</li>\r\n</ul>\r\n</li>\r\n</ul>\r\n<p><strong>The Deye SUN-20K-SG05LP3-EU-SM2 series inverters are designed to deliver high performance, reliability, and flexibility. They provide a comprehensive energy solution by combining photovoltaic and battery storage capabilities with sophisticated energy management, making them ideal for a wide range of applications.</strong></p>', '<span>The Deye SUN-20K-SG05LP3-EU-SM2 series comprises sophisticated three-phase hybrid inverters designed to meet the energy needs of residential and commercial establishments. These units are engineered to seamlessly integrate solar, battery storage, and grid electricity to provide a reliable and efficient energy management system. Whether for new installations or retrofitting existing solar setups, these hybrid inverters offer a robust solution that maximizes energy utilization and enhances system resilience.</span>', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\r\n\r\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\r\n\r\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\r\n\r\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\r\n\r\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\r\n\r\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\r\n\r\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', '');
INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(540, '<table selecttype=\"cells\">\r\n<tbody>\r\n<tr height=\"24\">\r\n<td width=\"273\"><strong>Battery Input Data</strong></td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Battery Type</td>\r\n<td width=\"800\">Lithium-ion</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Battery Voltage Range(V)</td>\r\n<td width=\"800\">160-700</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max.Charging Current(A)</td>\r\n<td width=\"500\">37</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max.Discharging Current(A)</td>\r\n<td width=\"500\">37</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Charging Strategy for Li-ion Battery</td>\r\n<td width=\"800\">Self-adaption to BMS</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Number of battery input</td>\r\n<td width=\"800\">1</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>PV String Input Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr>\r\n<td>Max. PV Access Power (W)</td>\r\n<td>16000</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max. PV Input Power (W)</td>\r\n<td width=\"100\">12800</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max. PV Input Voltage (V)</td>\r\n<td width=\"800\">1000</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Start-up Voltage&#65288;V&#65289;</td>\r\n<td width=\"800\">180</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">MPPT Voltage Range&#65288;V&#65289;</td>\r\n<td width=\"800\">150-850</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated DC Input Voltage(V)</td>\r\n<td width=\"700\">600</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max Input Short-Circuit Current&#65288;A&#65289;</td>\r\n<td width=\"400\">30+30</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max Operating PV Input Current&#65288;A&#65289;</td>\r\n<td width=\"400\">20+20</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">No.of MPP Trackers/No.of String Per MPP Tracker</td>\r\n<td width=\"400\">2/1+1</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>AC Input/Output Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated AC Input/Output Active Power&#65288;W&#65289;</td>\r\n<td width=\"100\">8000</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max AC Input/Output Apparent Power &#65288;VA&#65289;</td>\r\n<td width=\"100\">8800</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Peak Power (off-grid)&#65288;W&#65289;</td>\r\n<td width=\"800\">1.5 times of rated power,10s</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated AC Input/Output Current&#65288;A&#65289;</td>\r\n<td width=\"100\">12.2/11.6</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max AC Input/Output Current&#65288;A&#65289;</td>\r\n<td width=\"100\">13.4/12.8</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max Continuous AC Passthrough (grid to load)&#65288;A&#65289;</td>\r\n<td width=\"400\">40</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated Input/Output Voltage/Range(V)</td>\r\n<td width=\"800\">220/380V&#65292;230/400V 0.85Un-1.1Un</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Grid Connection Form</td>\r\n<td width=\"800\">3L+N+PE</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated Input/Output Grid Frequency/Range</td>\r\n<td width=\"800\">50Hz/45Hz-55Hz&#160; 60Hz/55Hz-65Hz</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Power Factor Adjustment Range</td>\r\n<td width=\"800\">0.8 leading to 0.8 lagging</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Total Current Harmonic Distortion THDi</td>\r\n<td width=\"800\">&lt;3% (of nominal power)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">DC Injection Current</td>\r\n<td width=\"800\">&lt;0.5%ln</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Efficiency</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max Efficiency</td>\r\n<td width=\"800\">97.6%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Euro Efficiency</td>\r\n<td width=\"800\">97.0%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">MPPT Efficiency</td>\r\n<td width=\"800\">&#65310;99%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Equipment Protection</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Integrated</td>\r\n<td width=\"800\">\r\n<div>DC Reverse Polarity Protection, AC Output Overcurrent Protection, Thermal Protection, AC Output Overvoltage</div>\r\n<div>Protection,&#160;AC Output Short Circuit Protection, DC Component Monitoring, Arc Fault Circuit Interrupter (optional),</div>\r\n<div>Anti-islanding Protection, DC Switch,&#160;Insulation Impedance Detection, Residual Current Detection</div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Surge Protection Level</td>\r\n<td width=\"800\">TYPE II(DC),TYPE II(AC)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Interface</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Communication Interface</td>\r\n<td width=\"800\">RS485/RS232/CAN</td>\r\n</tr>\r\n<tr>\r\n<td>Monitor Mode</td>\r\n<td>GPRS/WIFI/Bluetooth/4G/LAN(optional)</td>\r\n</tr>\r\n<tr>\r\n<td>LCD/LED Display</td>\r\n<td>LCD</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>General Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Operating Temperature Range</td>\r\n<td width=\"800\">-40 to +60&#8451;, &gt;45&#8451; Derating</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Permissible Ambient Humidity</td>\r\n<td width=\"800\">0-100%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Permissible Altitude</td>\r\n<td width=\"800\">2000m</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Noise</td>\r\n<td width=\"800\">&#8804; 55 dB(A)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Ingress Protection(IP) Rating</td>\r\n<td width=\"800\">IP 65</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Inverter Topology</td>\r\n<td width=\"800\">Non-Isolated</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Over Voltage Category</td>\r\n<td width=\"800\">OVC II(DC),OVC III(AC)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Cabinet size&#65288;W*H*D&#65289;[mm]</td>\r\n<td width=\"800\">408*638*237&#65288;Excluding connectors and brackets&#65289;</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Weight[kg]</td>\r\n<td width=\"800\">30.5</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Warranty</td>\r\n<td width=\"800\">\r\n<div>5 Years/10 Years</div>\r\n<div>the Warranty Period Depends the Final Installation Site of Inverter, More Info Please Refer to Warranty Policy</div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Type Of Cooling</td>\r\n<td width=\"600\">Intelligent air cooling</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Grid Regulation</td>\r\n<td width=\"800\">\r\n<p>IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</p>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Safety EMC/Standard</td>\r\n<td width=\"800\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</td>\r\n</tr>\r\n</tbody>\r\n</table>', 3, 'SUN-8K-SG01HP3-EU | Three-Phase Hybrid Inverter | 2 MPPT | HV Battery Supported', '<p>The Deye SUN-8K-SG01HP3-EU is a powerful three-phase hybrid inverter designed for high-performance solar energy systems. Equipped with 2 MPPTs and high-voltage battery support, it ensures exceptional efficiency and flexibility. This inverter supports 100% unbalanced output, allowing each phase to independently deliver up to 50% of the rated power&#8212;ideal for uneven load distribution. Thanks to its AC coupling capability, it can seamlessly retrofit into existing PV systems, enhancing performance without requiring a full overhaul. It allows for parallel operation of up to 10 units in both on-grid and off-grid modes and supports multiple batteries in parallel, offering excellent scalability. With a maximum charging and discharging current of 37A, it maintains efficient and reliable energy flow. Additionally, users can configure six charging and discharging time periods, optimizing battery use based on energy demand and tariff rates. The inverter is also compatible with diesel generators, ensuring dependable backup power in areas with unstable grid supply.</p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-005.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\r\n<p></p>\r\n<h3>Key Features</h3>\r\n<ul>\r\n<li data-start=\"0\" data-end=\"152\">\r\n<p data-start=\"2\" data-end=\"152\"><strong data-start=\"2\" data-end=\"29\" data-is-only-node=\"\">100% Unbalanced Output:</strong>&#160;Each phase can operate independently with up to 50% of the rated power, ensuring flexibility for varied load conditions.</p>\r\n</li>\r\n<li data-start=\"153\" data-end=\"296\">\r\n<p data-start=\"155\" data-end=\"296\"><strong data-start=\"155\" data-end=\"184\" data-is-only-node=\"\">AC Coupling for Retrofit:</strong>&#160;Easily integrates into existing solar systems, enabling efficient performance upgrades without major changes.</p>\r\n</li>\r\n<li data-start=\"297\" data-end=\"468\">\r\n<p data-start=\"299\" data-end=\"468\"><strong data-start=\"299\" data-end=\"331\" data-is-only-node=\"\">Scalable Parallel Operation:</strong>&#160;Supports up to 10 units in parallel for both on-grid and off-grid modes, with compatibility for multiple parallel battery connections.</p>\r\n</li>\r\n<li data-start=\"469\" data-end=\"605\">\r\n<p data-start=\"471\" data-end=\"605\"><strong data-start=\"471\" data-end=\"516\" data-is-only-node=\"\">Max. Charging/Discharging Current of 37A:</strong>&#160;Ensures stable and efficient energy flow for both charging and discharging operations.</p>\r\n</li>\r\n<li data-start=\"606\" data-end=\"731\">\r\n<p data-start=\"608\" data-end=\"731\"><strong data-start=\"608\" data-end=\"641\" data-is-only-node=\"\">High Voltage Battery Support:</strong>&#160;Utilizes high-voltage batteries to increase system efficiency and reduce energy losses.</p>\r\n</li>\r\n<li data-start=\"732\" data-end=\"899\">\r\n<p data-start=\"734\" data-end=\"899\"><strong data-start=\"734\" data-end=\"768\" data-is-only-node=\"\">Time-based Battery Management:</strong>&#160;Allows for six configurable time periods for optimized battery charging and discharging based on energy consumption and tariffs.</p>\r\n</li>\r\n<li data-start=\"900\" data-end=\"1059\" data-is-last-node=\"\">\r\n<p data-start=\"902\" data-end=\"1059\" data-is-last-node=\"\"><strong data-start=\"902\" data-end=\"937\" data-is-only-node=\"\">Diesel Generator Compatibility:</strong>&#160;Capable of storing energy from diesel generators, offering reliable backup in areas with unstable or limited grid access.</p>\r\n</li>\r\n</ul>\r\n<p></p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\r\n<p></p>\r\n<h3>Technical Specifications</h3>\r\n<ul>\r\n<li><strong data-start=\"283\" data-end=\"305\">Battery Input Data<br /><br /></strong>\r\n<ul data-start=\"306\" data-end=\"596\">\r\n<li data-start=\"306\" data-end=\"384\"><strong data-start=\"308\" data-end=\"334\">Battery Compatibility:</strong>&#160;Lithium-ion batteries (lead-acid not supported)</li>\r\n<li data-start=\"385\" data-end=\"424\"><strong data-start=\"387\" data-end=\"413\">Battery Voltage Range:</strong>&#160;160&#8211;700V</li>\r\n<li data-start=\"425\" data-end=\"471\"><strong data-start=\"427\" data-end=\"465\">Max. Charging/Discharging Current:</strong>&#160;37A</li>\r\n<li data-start=\"472\" data-end=\"506\"><strong data-start=\"474\" data-end=\"492\">Battery Input:</strong>&#160;Single port</li>\r\n<li data-start=\"507\" data-end=\"596\"><strong data-start=\"509\" data-end=\"531\">BMS Communication:</strong>&#160;Self-adaptive, ensuring compatibility with various BMS protocols<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"608\" data-end=\"632\">PV String Input Data<br /><br /></strong>\r\n<ul data-start=\"633\" data-end=\"1003\">\r\n<li data-start=\"633\" data-end=\"670\"><strong data-start=\"635\" data-end=\"660\">Max. PV Access Power:</strong>&#160;16000W</li>\r\n<li data-start=\"671\" data-end=\"707\"><strong data-start=\"673\" data-end=\"697\">Max. PV Input Power:</strong>&#160;12800W</li>\r\n<li data-start=\"708\" data-end=\"744\"><strong data-start=\"710\" data-end=\"736\">Max. PV Input Voltage:</strong>&#160;1000V</li>\r\n<li data-start=\"745\" data-end=\"781\"><strong data-start=\"747\" data-end=\"770\">MPPT Voltage Range:</strong>&#160;150&#8211;850V</li>\r\n<li data-start=\"782\" data-end=\"812\"><strong data-start=\"784\" data-end=\"805\">Start-up Voltage:</strong>&#160;180V</li>\r\n<li data-start=\"813\" data-end=\"849\"><strong data-start=\"815\" data-end=\"842\">Rated DC Input Voltage:</strong>&#160;600V</li>\r\n<li data-start=\"850\" data-end=\"903\"><strong data-start=\"852\" data-end=\"891\">Number of MPPTs / Strings per MPPT:</strong>&#160;2 / (1+1)</li>\r\n<li data-start=\"904\" data-end=\"954\"><strong data-start=\"906\" data-end=\"942\">Max. Operating PV Input Current:</strong>&#160;20A + 20A</li>\r\n<li data-start=\"955\" data-end=\"1003\"><strong data-start=\"957\" data-end=\"991\">Max. PV Short-Circuit Current:</strong>&#160;30A + 30A<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1015\" data-end=\"1041\">AC Input / Output Data<br /><br /></strong>\r\n<ul data-start=\"1042\" data-end=\"1623\">\r\n<li data-start=\"1042\" data-end=\"1084\"><strong data-start=\"1044\" data-end=\"1076\">Rated AC Input/Output Power:</strong>&#160;8000W</li>\r\n<li data-start=\"1085\" data-end=\"1120\"><strong data-start=\"1087\" data-end=\"1111\">Max. Apparent Power:</strong>&#160;8800A</li>\r\n<li data-start=\"1121\" data-end=\"1185\"><strong data-start=\"1123\" data-end=\"1149\">Peak Power (Off-Grid):</strong>&#160;1.5&#215; rated power (for 10 seconds)</li>\r\n<li data-start=\"1186\" data-end=\"1238\"><strong data-start=\"1188\" data-end=\"1222\">Rated AC Input/Output Current:</strong>&#160;12.2A / 11.6A</li>\r\n<li data-start=\"1239\" data-end=\"1290\"><strong data-start=\"1241\" data-end=\"1274\">Max. AC Input/Output Current:</strong>&#160;13.4A / 12.8A</li>\r\n<li data-start=\"1291\" data-end=\"1349\"><strong data-start=\"1293\" data-end=\"1343\">Max. Continuous AC Passthrough (Grid to Load):</strong>&#160;40A</li>\r\n<li data-start=\"1350\" data-end=\"1401\"><strong data-start=\"1352\" data-end=\"1370\">Rated Voltage:</strong>&#160;220/380V, 230/400V (3L+N+PE)</li>\r\n<li data-start=\"1402\" data-end=\"1462\"><strong data-start=\"1404\" data-end=\"1429\">Grid Frequency Range:</strong>&#160;50Hz (45&#8211;55Hz), 60Hz (55&#8211;65Hz)</li>\r\n<li data-start=\"1463\" data-end=\"1522\"><strong data-start=\"1465\" data-end=\"1493\">Power Factor Adjustment:</strong>&#160;0.8 leading to 0.8 lagging</li>\r\n<li data-start=\"1523\" data-end=\"1568\"><strong data-start=\"1525\" data-end=\"1562\">Total Harmonic Distortion (THDi):</strong>&#160;&lt;3%</li>\r\n<li data-start=\"1569\" data-end=\"1623\"><strong data-start=\"1571\" data-end=\"1596\">DC Injection Current:</strong>&#160;&lt;0.5% of nominal current<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1635\" data-end=\"1649\">Efficiency<br /><br /></strong>\r\n<ul data-start=\"1650\" data-end=\"1745\">\r\n<li data-start=\"1650\" data-end=\"1680\"><strong data-start=\"1652\" data-end=\"1672\">Max. Efficiency:</strong>&#160;97.6%</li>\r\n<li data-start=\"1681\" data-end=\"1715\"><strong data-start=\"1683\" data-end=\"1707\">European Efficiency:</strong>&#160;97.0%</li>\r\n<li data-start=\"1716\" data-end=\"1745\"><strong data-start=\"1718\" data-end=\"1738\">MPPT Efficiency:</strong>&#160;&gt;99%<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"1783\" data-end=\"1810\">Integrated Protections:<br /><br /></strong><strong data-start=\"2073\" data-end=\"2094\"></strong></li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"2073\" data-end=\"2094\">Surge Protection:</strong>&#160;Type II (both DC &amp; AC sides)<br /><br />\r\n<ul data-start=\"1815\" data-end=\"2070\">\r\n<li data-start=\"1815\" data-end=\"1838\">DC reverse polarity</li>\r\n<li data-start=\"1841\" data-end=\"1866\">AC output overcurrent</li>\r\n<li data-start=\"1869\" data-end=\"1887\">AC overvoltage</li>\r\n<li data-start=\"1890\" data-end=\"1907\">Short circuit</li>\r\n<li data-start=\"1910\" data-end=\"1932\">Thermal protection</li>\r\n<li data-start=\"1935\" data-end=\"1965\">Residual current detection</li>\r\n<li data-start=\"1968\" data-end=\"2004\">Insulation resistance monitoring</li>\r\n<li data-start=\"2007\" data-end=\"2040\">Optional arc fault protection</li>\r\n<li data-start=\"2043\" data-end=\"2070\">DC component monitoring<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2128\" data-end=\"2142\">DC Switch:</strong>&#160;Included<br /><br /></li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2165\" data-end=\"2191\">Standards &amp; Compliance<br /><br /></strong>\r\n<ul data-start=\"2192\" data-end=\"2430\">\r\n<li data-start=\"2192\" data-end=\"2339\"><strong data-start=\"2194\" data-end=\"2214\">Grid Compliance:</strong><br data-start=\"2214\" data-end=\"2217\" />IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,<br data-start=\"2289\" data-end=\"2292\" />OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</li>\r\n<li data-start=\"2340\" data-end=\"2430\"><strong data-start=\"2342\" data-end=\"2369\">Safety &amp; EMC Standards:</strong><br data-start=\"2369\" data-end=\"2372\" />IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2442\" data-end=\"2486\">Environmental &amp; Physical Characteristics<br /><br /></strong>\r\n<ul data-start=\"2487\" data-end=\"2880\">\r\n<li data-start=\"2487\" data-end=\"2560\"><strong data-start=\"2489\" data-end=\"2521\">Operating Temperature Range:</strong>&#160;-40&#176;C to +60&#176;C (derating above 45&#176;C)</li>\r\n<li data-start=\"2561\" data-end=\"2585\"><strong data-start=\"2563\" data-end=\"2576\">Humidity:</strong>&#160;0&#8211;100%</li>\r\n<li data-start=\"2586\" data-end=\"2617\"><strong data-start=\"2588\" data-end=\"2609\">Maximum Altitude:</strong>&#160;2000m</li>\r\n<li data-start=\"2618\" data-end=\"2648\"><strong data-start=\"2620\" data-end=\"2636\">Noise Level:</strong>&#160;&#8804;55 dB(A)</li>\r\n<li data-start=\"2649\" data-end=\"2705\"><strong data-start=\"2651\" data-end=\"2670\">Cooling Method:</strong>&#160;Inteligent Air Cooling</li>\r\n<li data-start=\"2706\" data-end=\"2773\"><strong data-start=\"2708\" data-end=\"2733\">IP Protection Rating:</strong>&#160;IP65 (dust-tight and water-resistant)</li>\r\n<li data-start=\"2774\" data-end=\"2856\"><strong data-start=\"2776\" data-end=\"2803\">Dimensions (W &#215; H &#215; D):</strong>&#160;408 &#215; 638 &#215; 237 mm (excluding connectors/brackets)</li>\r\n<li data-start=\"2857\" data-end=\"2880\"><strong data-start=\"2859\" data-end=\"2870\">Weight:</strong>&#160;30.5 kg<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2892\" data-end=\"2921\">Interface &amp; Communication<br /><br /></strong>\r\n<ul data-start=\"2922\" data-end=\"3039\">\r\n<li data-start=\"2922\" data-end=\"2992\"><strong data-start=\"2924\" data-end=\"2947\">Monitoring Options:</strong>&#160;GPRS, Wi-Fi, Bluetooth, 4G, LAN (optional)</li>\r\n<li data-start=\"2993\" data-end=\"3039\"><strong data-start=\"2995\" data-end=\"3019\">Communication Ports:</strong>&#160;RS485, RS232, CAN</li>\r\n</ul>\r\n</li>\r\n</ul>\r\n<strong>The Deye SUN-5K-SG01HP3-EU is a three-phase hybrid inverter designed for intelligent energy management. With dual MPPTs, high-voltage battery support, and robust protection features, it ensures efficient solar integration, seamless backup power, and long-term reliability for residential and small commercial applications.</strong>', 'The Deye SUN-8K-SG01HP3-EU-AM2 is a high-performance three-phase hybrid inverter tailored for residential and light commercial applications. Designed to seamlessly integrate solar energy, high-voltage lithium-ion battery storage, and grid power, this inverter enables smart and efficient energy management. With dual MPPTs, a wide PV voltage range of 150&#8211;850V, and support for up to 8000W of PV input, it maximizes solar harvest and system flexibility. Its advanced protection features, natural cooling system, and IP65-rated housing ensure reliable operation under various environmental conditions. Whether for new installations or retrofitting existing systems, the SUN-8K-SG01HP3-EU-AM2 offers a compact, robust, and future-ready energy solution.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\r\n\r\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\r\n\r\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\r\n\r\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\r\n\r\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\r\n\r\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\r\n\r\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(539, '<table selecttype=\"cells\">\r\n<tbody>\r\n<tr height=\"35\">\r\n<td colspan=\"2\" width=\"912\"><strong>Battery Input Data</strong></td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Battery Type</td>\r\n<td width=\"650\">Lead-acid or Lithium-ion</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Battery Voltage Range (V)</td>\r\n<td width=\"650\">40-60</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. Charging Current (A)</td>\r\n<td width=\"130\">350</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. Discharging Current (A)</td>\r\n<td width=\"130\">350</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Charging Strategy forLi-ion Battery</td>\r\n<td width=\"650\">Self-adaption to BMS</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Number of Battery Input</td>\r\n<td width=\"650\">1</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td colspan=\"2\" width=\"912\">\r\n<p></p>\r\n<p><strong>PV String Input Data</strong></p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>Max. PV Access Power (W)</td>\r\n<td>40000</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. DC Input Power (W)</td>\r\n<td width=\"130\">32000</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. DC Input Voltage (V)</td>\r\n<td width=\"650\">800</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Start-up Voltage (V)</td>\r\n<td width=\"650\">160</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">MPPT Voltage Range (V)</td>\r\n<td width=\"650\">160-650</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Rated DC Input Voltage (V)</td>\r\n<td width=\"650\">550</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. Operating PV Input Current (A)</td>\r\n<td width=\"650\">36+36</td>\r\n</tr>\r\n<tr height=\"31\">\r\n<td width=\"262\">Max. Input Short-Circuit Current (A)</td>\r\n<td width=\"650\">54+54</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">No.of MPPT Trackers/<br />No.of String PerMPPT Tracker</td>\r\n<td width=\"650\">2/2+2</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">\r\n<p></p>\r\n<p><strong>AC Input/Output Data</strong></p>\r\n</td>\r\n<td width=\"650\"></td>\r\n</tr>\r\n<tr height=\"33\">\r\n<td width=\"262\">Rated AC Input/Output Active Power (W)</td>\r\n<td width=\"130\">20000</td>\r\n</tr>\r\n<tr height=\"31\">\r\n<td width=\"262\">Max. AC Input/Output Apparent Power (VA)</td>\r\n<td width=\"130\">22000</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Rated AC Input/Output Current (A)</td>\r\n<td width=\"130\">30.4/29</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. AC Input/Output Current (A)</td>\r\n<td width=\"130\">33.4/31.9</td>\r\n</tr>\r\n<tr height=\"29\">\r\n<td width=\"262\">Max. Continuous AC Passthrough (grid to load) (A)</td>\r\n<td width=\"650\">70</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Peak Power (off-grid) (W)</td>\r\n<td width=\"650\">2 times of rated power, 10s</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Power Factor Adjustment Range</td>\r\n<td width=\"650\">0.8 leading to 0.8 lagging</td>\r\n</tr>\r\n<tr height=\"34\">\r\n<td width=\"262\">Rated Input/Output Voltage/Range (V)</td>\r\n<td width=\"650\">220/380V, 230/400V&#160; 0.85Un-1.1Un</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Rated Input/Output Grid Frequency/Range(Hz)</td>\r\n<td width=\"650\">50/45-55, 60/55-65</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Grid Connection Form</td>\r\n<td width=\"650\">3L+N+PE</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Total Current Harmonic Distortion THDi</td>\r\n<td width=\"650\">&lt;3% (of nominal power)</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">DC Component of Grid</td>\r\n<td width=\"650\">&lt;0.5% In</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">\r\n<p></p>\r\n<p><strong>E&#64259;ciency</strong></p>\r\n</td>\r\n<td width=\"650\"></td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Max. Ef&#64257;ciency</td>\r\n<td width=\"650\">97.6%</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Euro Ef&#64257;ciency</td>\r\n<td width=\"650\">97.0%</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">MPPTEf&#64257;ciency</td>\r\n<td width=\"650\">&gt;99%</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">\r\n<p></p>\r\n<p><strong>Equipment Protection</strong></p>\r\n</td>\r\n<td width=\"650\"></td>\r\n</tr>\r\n<tr height=\"136\">\r\n<td width=\"262\">Integrated</td>\r\n<td width=\"650\">\r\n<div>DC Polarity Reverse Connection Protection, AC Output Overcurrent Protection, Thermal Protection,</div>\r\n<div>AC Output Overvoltage Protection, AC Output Short Circuit Protection, DC Component Monitoring,</div>\r\n<div>Overvoltage Load Drop Protection, Ground Fault Current Monitoring, Arc Fault Circuit Interrupter (optional),</div>\r\n<div>Power Network Monitoring, Island Protection Monitoring, Earth Fault Detection, DC Input Switch,</div>\r\n<div>DC Terminal Insulation Impedance Monitoring, Residual Current (RCD) Detection, Surge protection level</div>\r\n</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Surge Protection Level</td>\r\n<td width=\"650\">TYPE II(DC),TYPE II(AC)</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">\r\n<p></p>\r\n<p><strong>Interface</strong></p>\r\n</td>\r\n<td width=\"650\"></td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Communication Interface</td>\r\n<td width=\"650\">RS485/RS232/CAN</td>\r\n</tr>\r\n<tr>\r\n<td>Monitor Mode</td>\r\n<td>GPRS/WIFI/Bluetooth/4G/LAN(optional)</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">\r\n<p></p>\r\n<p><strong>General Data</strong></p>\r\n</td>\r\n<td width=\"650\"></td>\r\n</tr>\r\n<tr height=\"39\">\r\n<td width=\"262\">Operating Temperature Range (&#8451;)</td>\r\n<td width=\"650\">-40 to +60&#8451;, &gt;45&#8451;&#160;Derating</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Permissible Ambient Humidity</td>\r\n<td width=\"650\">0-100%</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Permissible Altitude</td>\r\n<td width=\"650\">3000m</td>\r\n</tr>\r\n<tr height=\"29\">\r\n<td width=\"262\">Noise</td>\r\n<td width=\"650\">&#8804;60</td>\r\n</tr>\r\n<tr height=\"31\">\r\n<td width=\"262\">Ingress Protection(IP) Rating</td>\r\n<td width=\"650\">IP 65</td>\r\n</tr>\r\n<tr height=\"32\">\r\n<td width=\"262\">Inverter Topology</td>\r\n<td width=\"650\">Non-Isolated</td>\r\n</tr>\r\n<tr height=\"40\">\r\n<td width=\"262\">Over Voltage Category</td>\r\n<td width=\"650\">OVC II(DC), OVC III(AC)</td>\r\n</tr>\r\n<tr height=\"36\">\r\n<td width=\"262\">Cabinet Size (WxHxD mm)</td>\r\n<td width=\"650\">456&#215;750&#215;268.5 (Excluding Connectors and Brackets)</td>\r\n</tr>\r\n<tr height=\"35\">\r\n<td width=\"262\">Weight (kg)</td>\r\n<td width=\"650\">51.9</td>\r\n</tr>\r\n<tr height=\"36\">\r\n<td width=\"262\">Type of Cooling</td>\r\n<td width=\"650\">Intelligent Air Cooling</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"262\">Warranty</td>\r\n<td width=\"650\">5 Years/10 Years<br />the Warranty Period Depends the Final Installation Site of Inverter, More Info Please Refer to Warranty Policy</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"262\">Grid Regulation</td>\r\n<td width=\"650\">IEC 61727, IEC 62116,CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,<br />OVE-Richtlinie R25, G99,VDE-AR-N 4105</td>\r\n</tr>\r\n<tr height=\"31\">\r\n<td width=\"262\">Safety / EMC Standard</td>\r\n<td width=\"650\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</td>\r\n</tr>\r\n</tbody>\r\n</table>', 3, 'SUN-20K-SG05LP3-EU-SM2 | Three-Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', '<p>The&#160;SUN-20K-SG05LP3-EU-SM2 is a powerful and flexible hybrid inverter designed for residential and small commercial solar applications. It supports a maximum charging and discharging current of 350A, enabling rapid and responsive energy storage. The inverter is compatible with diesel generators, allowing energy storage from these sources for added backup power. It supports parallel operation of up to 10 units in both on-grid and off-grid modes, providing scalability for expanding energy systems. AC coupling enables easy integration into existing solar installations for cost-effective upgrades. The inverter features time-based battery management with six configurable periods to optimize charging and discharging based on consumption patterns and electricity tariffs. Operating with a low voltage 48V battery and transformer isolation, it ensures safe and efficient energy storage. Additionally, it can handle 100% unbalanced output, with each phase capable of delivering up to 50% of the rated power, allowing flexible load management without loss of efficiency.</p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-004.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" /></p>\r\n<p></p>\r\n<h3>Key Features</h3>\r\n<ul>\r\n<li><strong>High Charging/Discharging Current:</strong>&#160;The Deye&#160;SUN 20K-SG05LP3-EU-SM2 supports a maximum charging and discharging current of 350A. This high current capacity ensures rapid energy storage and retrieval, making the system highly responsive to energy demand peaks.<br /><br /></li>\r\n<li><strong>Compatibility with Diesel Generators:&#160;</strong>These inverters support the storage of energy from diesel generators, providing versatility and additional backup power capabilities, especially useful in areas with unreliable grid supply.<br /><br /></li>\r\n<li><strong>Scalable Parallel Operation:</strong>&#160;Up to 10 units can operate in parallel both in on-grid and off-grid modes. This scalability allows for both small-scale and large-scale energy requirements to be met efficiently, making it ideal for expanding energy systems.<br /><br /></li>\r\n<li><strong>AC Coupling for Retrofit:</strong>&#160;The inverters can easily integrate into existing solar systems through AC coupling, offering a cost-effective route to upgrade current installations for enhanced performance and energy storage.<br /><br /></li>\r\n<li><strong>Time-based Battery Management:</strong>&#160;Supports six time periods for battery charging and discharging, allowing users to optimize energy storage based on consumption patterns and electricity tariffs. This feature significantly enhances the cost-effectiveness of the energy system.<br /><br /></li>\r\n<li><strong>Low Voltage Battery with Isolation:</strong>&#160;Operating with a 48V low voltage battery and transformer isolation design, the inverter ensures safe and efficient energy storage, reducing the risk of electrical hazards.<br /><br /></li>\r\n<li><strong>Unbalanced Output Capability:</strong>&#160;Each phase can handle a 100% unbalanced output with a maximum output of up to 50% of the rated power for each phase. This flexibility supports varied load requirements without efficiency loss.</li>\r\n</ul>\r\n<p></p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" /></p>\r\n<p></p>\r\n<h3>Technical Specifications</h3>\r\n<ul>\r\n<li><strong>Battery Input:</strong>\r\n<ul>\r\n<li>Compatible with lead-acid and lithium-ion batteries</li>\r\n<li>Voltage range: 40-60V</li>\r\n<li>Single battery input with self-adaptive BMS<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong>PV Input:</strong>\r\n<ul>\r\n<li>Maximum input power ranges up to 32000W</li>\r\n<li>Maximum PV input voltage: 550V</li>\r\n<li>MPPT voltage range: 200-650V<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong>AC Input/Output:</strong>\r\n<ul>\r\n<li>Rated power ranges up to 20000W</li>\r\n<li>Rated AC Input/Output Current:&#160;30.4/29&#160;per phase</li>\r\n<li>Maximum Continuous AC Passthrough (grid to load): 45A<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong>Efficiency and Protection:</strong>\r\n<ul>\r\n<li>Maximum efficiency: 97.6%</li>\r\n<li>European efficiency: 97.0%</li>\r\n<li>MPPT efficiency greater than 99%</li>\r\n<li>Features comprehensive protection mechanisms, including reverse polarity, overcurrent, overvoltage, thermal protection, and more.<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong>Standards and Compliance:</strong>\r\n<ul>\r\n<li>Meets grid regulations including IEC 61727, IEC 62116, and several national standards</li>\r\n<li>Safety standards: IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1/2<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong>Environmental and Physical:</strong>\r\n<ul>\r\n<li>Operating temperature: -40 to +60 &#8451;</li>\r\n<li>Permissible humidity: up to 100%</li>\r\n<li>Maximum altitude: 3000m</li>\r\n<li>Noise level: &#8804;60dB</li>\r\n<li>IP65 rated for dust and water protection</li>\r\n<li>Intelligent air cooling system</li>\r\n<li>Weight: 51.9 kg</li>\r\n<li>Dimensions:&#160;456&#215;750&#215;268.5&#160;mm (excluding connectors and brackets)</li>\r\n</ul>\r\n</li>\r\n</ul>\r\n<p><strong>The Deye SUN-20K-SG05LP3-EU-SM2 series inverters are designed to deliver high performance, reliability, and flexibility. They provide a comprehensive energy solution by combining photovoltaic and battery storage capabilities with sophisticated energy management, making them ideal for a wide range of applications.</strong></p>', 'The Deye SUN-20K-SG05LP3-EU-SM2 series comprises sophisticated three-phase hybrid inverters designed to meet the energy needs of residential and commercial establishments. These units are engineered to seamlessly integrate solar, battery storage, and grid electricity to provide a reliable and efficient energy management system. Whether for new installations or retrofitting existing solar setups, these hybrid inverters offer a robust solution that maximizes energy utilization and enhances system resilience.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\r\n\r\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\r\n\r\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\r\n\r\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\r\n\r\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\r\n\r\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\r\n\r\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', '');
INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(541, '<table selecttype=\"cells\">\r\n<tbody>\r\n<tr height=\"24\">\r\n<td width=\"273\"><strong>Battery Input Data</strong></td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Battery Type</span></td>\r\n<td width=\"800\"><span>Lithium-ion</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Battery Voltage Range(V)</span></td>\r\n<td width=\"800\"><span>160-700</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max.Charging Current(A)</span></td>\r\n<td width=\"500\"><span>37</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max.Discharging Current(A)</span></td>\r\n<td width=\"500\"><span>37</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Charging Strategy for Li-ion Battery</span></td>\r\n<td width=\"800\"><span>Self-adaption to BMS</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Number of battery input</span></td>\r\n<td width=\"800\"><span>1</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>PV String Input Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<div><span>Max. PV Access Power (W)</span></div>\r\n</td>\r\n<td><span>20000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max. PV Input Power (W)</span></td>\r\n<td width=\"100\"><span>16000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max. PV Input Voltage (V)</span></td>\r\n<td width=\"800\"><span>1000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Start-up Voltage&#65288;V&#65289;</span></td>\r\n<td width=\"800\"><span>180</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>MPPT Voltage Range&#65288;V&#65289;</span></td>\r\n<td width=\"800\"><span>150-850</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Rated DC Input Voltage(V)</span></td>\r\n<td width=\"700\"><span>600</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max Input Short-Circuit Current&#65288;A&#65289;</span></td>\r\n<td width=\"400\"><span>30+30</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max Operating PV Input Current&#65288;A&#65289;</span></td>\r\n<td width=\"400\"><span>20+20</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>No.of MPP Trackers/No.of String Per MPP Tracker</span></td>\r\n<td width=\"400\"><span>2/1+1</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>AC Input/Output Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Rated AC Input/Output Active Power&#65288;W&#65289;</span></td>\r\n<td width=\"100\"><span>10000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max AC Input/Output Apparent Power &#65288;VA&#65289;</span></td>\r\n<td width=\"100\"><span>11000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Peak Power (off-grid)&#65288;W&#65289;</span></td>\r\n<td width=\"800\"><span>1.5 times of rated power,10s</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Rated AC Input/Output Current&#65288;A&#65289;</span></td>\r\n<td width=\"100\"><span>15.2/14.5</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max AC Input/Output Current&#65288;A&#65289;</span></td>\r\n<td width=\"100\"><span>16.7/16</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max Continuous AC Passthrough (grid to load)&#65288;A&#65289;</span></td>\r\n<td width=\"400\"><span>40</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Rated Input/Output Voltage/Range(V)</span></td>\r\n<td width=\"800\"><span>220/380V&#65292;230/400V 0.85Un-1.1Un</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Grid Connection Form</span></td>\r\n<td width=\"800\"><span>3L+N+PE</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Rated Input/Output Grid Frequency/Range</span></td>\r\n<td width=\"800\"><span>50Hz/45Hz-55Hz&#160; 60Hz/55Hz-65Hz</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Power Factor Adjustment Range</span></td>\r\n<td width=\"800\"><span>0.8 leading to 0.8 lagging</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Total Current Harmonic Distortion THDi</span></td>\r\n<td width=\"800\"><span>&lt;3% (of nominal power)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>DC Injection Current</span></td>\r\n<td width=\"800\"><span>&lt;0.5%ln</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Efficiency</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max Efficiency</span></td>\r\n<td width=\"800\"><span>97.6%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Euro Efficiency</span></td>\r\n<td width=\"800\"><span>97.0%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>MPPT Efficiency</span></td>\r\n<td width=\"800\"><span>&#65310;99%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Equipment Protection</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<div><span>Integrated</span></div>\r\n</td>\r\n<td width=\"800\">\r\n<div>\r\n<div><span>DC Reverse Polarity Protection, AC Output Overcurrent Protection, Thermal Protection, AC Output Overvoltage</span></div>\r\n<div><span>Protection,&#160;</span><span>AC Output Short Circuit Protection, DC Component Monitoring, Arc Fault Circuit Interrupter (optional),</span></div>\r\n<div><span>Anti-islanding Protection, DC Switch,&#160;</span><span>Insulation Impedance Detection, Residual Current Detection</span></div>\r\n</div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Surge Protection Level</span></td>\r\n<td width=\"800\"><span>TYPE II(DC),TYPE II(AC)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Interface</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<div>\r\n<div><span>Communication Interface</span></div>\r\n</div>\r\n</td>\r\n<td width=\"800\">\r\n<div><span>RS485/RS232/CAN</span></div>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<div><span>Monitor Mode</span></div>\r\n</td>\r\n<td>\r\n<div><span>GPRS/WIFI/Bluetooth/4G/LAN(optional)</span></div>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<div><span>LCD/LED Display</span></div>\r\n</td>\r\n<td>\r\n<div><span>LCD</span></div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>General Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Operating Temperature Range</span></td>\r\n<td width=\"800\">\r\n<div><span>-40 to +60&#8451;, &gt;45&#8451; Derating</span></div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Permissible Ambient Humidity</span></td>\r\n<td width=\"800\"><span>0-100%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Permissible Altitude</span></td>\r\n<td width=\"800\"><span>2000m</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Noise</span></td>\r\n<td width=\"800\"><span>&#8804; 55 dB(A)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Ingress Protection(IP) Rating</span></td>\r\n<td width=\"800\"><span>IP 65</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Inverter Topology</span></td>\r\n<td width=\"800\"><span>Non-Isolated</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Over Voltage Category</span></td>\r\n<td width=\"800\"><span>OVC II(DC),OVC III(AC)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Cabinet size&#65288;W*H*D&#65289;[mm]</span></td>\r\n<td width=\"800\"><span>408*638*237&#65288;Excluding connectors and brackets&#65289;</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Weight[kg]</span></td>\r\n<td width=\"800\"><span>30.5</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Warranty</span></td>\r\n<td width=\"800\">\r\n<div><span>5 Years/10 Years</span></div>\r\n<div><span>the Warranty Period Depends the Final Installation Site of Inverter, More Info Please Refer to Warranty Policy</span></div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Type Of Cooling</span></td>\r\n<td width=\"600\"><span>Intelligent air cooling</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Grid Regulation</span></td>\r\n<td width=\"800\">\r\n<p><span>IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</span></p>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Safety EMC/Standard</span></td>\r\n<td width=\"800\"><span>IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</span></td>\r\n</tr>\r\n</tbody>\r\n</table>', 2, 'SUN-10K-SG01HP3-EU | Three-Phase Hybrid Inverter | 2 MPPT | HV Battery Supported', '<p>The Deye SUN-10K-SG01HP3-EU is a powerful three-phase hybrid inverter designed for high-performance solar energy systems. Equipped with 2 MPPTs and high-voltage battery support, it ensures exceptional efficiency and flexibility. This inverter supports 100% unbalanced output, allowing each phase to independently deliver up to 50% of the rated power&#8212;ideal for uneven load distribution. Thanks to its AC coupling capability, it can seamlessly retrofit into existing PV systems, enhancing performance without requiring a full overhaul. It allows for parallel operation of up to 10 units in both on-grid and off-grid modes and supports multiple batteries in parallel, offering excellent scalability. With a maximum charging and discharging current of 37A, it maintains efficient and reliable energy flow. Additionally, users can configure six charging and discharging time periods, optimizing battery use based on energy demand and tariff rates. The inverter is also compatible with diesel generators, ensuring dependable backup power in areas with unstable grid supply.</p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-005.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\r\n<p></p>\r\n<h3>Key Features</h3>\r\n<ul>\r\n<li data-start=\"0\" data-end=\"152\">\r\n<p data-start=\"2\" data-end=\"152\"><strong data-start=\"2\" data-end=\"29\" data-is-only-node=\"\">100% Unbalanced Output:</strong>&#160;Each phase can operate independently with up to 50% of the rated power, ensuring flexibility for varied load conditions.</p>\r\n</li>\r\n<li data-start=\"153\" data-end=\"296\">\r\n<p data-start=\"155\" data-end=\"296\"><strong data-start=\"155\" data-end=\"184\" data-is-only-node=\"\">AC Coupling for Retrofit:</strong>&#160;Easily integrates into existing solar systems, enabling efficient performance upgrades without major changes.</p>\r\n</li>\r\n<li data-start=\"297\" data-end=\"468\">\r\n<p data-start=\"299\" data-end=\"468\"><strong data-start=\"299\" data-end=\"331\" data-is-only-node=\"\">Scalable Parallel Operation:</strong>&#160;Supports up to 10 units in parallel for both on-grid and off-grid modes, with compatibility for multiple parallel battery connections.</p>\r\n</li>\r\n<li data-start=\"469\" data-end=\"605\">\r\n<p data-start=\"471\" data-end=\"605\"><strong data-start=\"471\" data-end=\"516\" data-is-only-node=\"\">Max. Charging/Discharging Current of 37A:</strong>&#160;Ensures stable and efficient energy flow for both charging and discharging operations.</p>\r\n</li>\r\n<li data-start=\"606\" data-end=\"731\">\r\n<p data-start=\"608\" data-end=\"731\"><strong data-start=\"608\" data-end=\"641\" data-is-only-node=\"\">High Voltage Battery Support:</strong>&#160;Utilizes high-voltage batteries to increase system efficiency and reduce energy losses.</p>\r\n</li>\r\n<li data-start=\"732\" data-end=\"899\">\r\n<p data-start=\"734\" data-end=\"899\"><strong data-start=\"734\" data-end=\"768\" data-is-only-node=\"\">Time-based Battery Management:</strong>&#160;Allows for six configurable time periods for optimized battery charging and discharging based on energy consumption and tariffs.</p>\r\n</li>\r\n<li data-start=\"900\" data-end=\"1059\" data-is-last-node=\"\">\r\n<p data-start=\"902\" data-end=\"1059\" data-is-last-node=\"\"><strong data-start=\"902\" data-end=\"937\" data-is-only-node=\"\">Diesel Generator Compatibility:</strong>&#160;Capable of storing energy from diesel generators, offering reliable backup in areas with unstable or limited grid access.</p>\r\n</li>\r\n</ul>\r\n<p></p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\r\n<p></p>\r\n<h3>Technical Specifications</h3>\r\n<ul>\r\n<li><strong data-start=\"283\" data-end=\"305\">Battery Input Data<br /><br /></strong>\r\n<ul data-start=\"306\" data-end=\"596\">\r\n<li data-start=\"306\" data-end=\"384\"><strong data-start=\"308\" data-end=\"334\">Battery Compatibility:</strong>&#160;Lithium-ion batteries (lead-acid not supported)</li>\r\n<li data-start=\"385\" data-end=\"424\"><strong data-start=\"387\" data-end=\"413\">Battery Voltage Range:</strong>&#160;160&#8211;700V</li>\r\n<li data-start=\"425\" data-end=\"471\"><strong data-start=\"427\" data-end=\"465\">Max. Charging/Discharging Current:</strong>&#160;37A</li>\r\n<li data-start=\"472\" data-end=\"506\"><strong data-start=\"474\" data-end=\"492\">Battery Input:</strong>&#160;Single port</li>\r\n<li data-start=\"507\" data-end=\"596\"><strong data-start=\"509\" data-end=\"531\">BMS Communication:</strong>&#160;Self-adaptive, ensuring compatibility with various BMS protocols<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"608\" data-end=\"632\">PV String Input Data<br /><br /></strong>\r\n<ul data-start=\"633\" data-end=\"1003\">\r\n<li data-start=\"633\" data-end=\"670\"><strong data-start=\"635\" data-end=\"660\">Max. PV Access Power:</strong>&#160;20000W</li>\r\n<li data-start=\"671\" data-end=\"707\"><strong data-start=\"673\" data-end=\"697\">Max. PV Input Power:</strong>&#160;16000W</li>\r\n<li data-start=\"708\" data-end=\"744\"><strong data-start=\"710\" data-end=\"736\">Max. PV Input Voltage:</strong>&#160;1000V</li>\r\n<li data-start=\"745\" data-end=\"781\"><strong data-start=\"747\" data-end=\"770\">MPPT Voltage Range:</strong>&#160;150&#8211;850V</li>\r\n<li data-start=\"782\" data-end=\"812\"><strong data-start=\"784\" data-end=\"805\">Start-up Voltage:</strong>&#160;180V</li>\r\n<li data-start=\"813\" data-end=\"849\"><strong data-start=\"815\" data-end=\"842\">Rated DC Input Voltage:</strong>&#160;600V</li>\r\n<li data-start=\"850\" data-end=\"903\"><strong data-start=\"852\" data-end=\"891\">Number of MPPTs / Strings per MPPT:</strong>&#160;2 / (1+1)</li>\r\n<li data-start=\"904\" data-end=\"954\"><strong data-start=\"906\" data-end=\"942\">Max. Operating PV Input Current:</strong>&#160;20A + 20A</li>\r\n<li data-start=\"955\" data-end=\"1003\"><strong data-start=\"957\" data-end=\"991\">Max. PV Short-Circuit Current:</strong>&#160;30A + 30A<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1015\" data-end=\"1041\">AC Input / Output Data<br /><br /></strong>\r\n<ul data-start=\"1042\" data-end=\"1623\">\r\n<li data-start=\"1042\" data-end=\"1084\"><strong data-start=\"1044\" data-end=\"1076\">Rated AC Input/Output Power:</strong>&#160;10000W</li>\r\n<li data-start=\"1085\" data-end=\"1120\"><strong data-start=\"1087\" data-end=\"1111\">Max. Apparent Power:</strong>&#160;11000A</li>\r\n<li data-start=\"1121\" data-end=\"1185\"><strong data-start=\"1123\" data-end=\"1149\">Peak Power (Off-Grid):</strong>&#160;1.5&#215; rated power (for 10 seconds)</li>\r\n<li data-start=\"1186\" data-end=\"1238\"><strong data-start=\"1188\" data-end=\"1222\">Rated AC Input/Output Current:</strong>&#160;<span>15.2/14.5</span></li>\r\n<li data-start=\"1239\" data-end=\"1290\"><strong data-start=\"1241\" data-end=\"1274\">Max. AC Input/Output Current:</strong>&#160;<span>16.7/16</span></li>\r\n<li data-start=\"1291\" data-end=\"1349\"><strong data-start=\"1293\" data-end=\"1343\">Max. Continuous AC Passthrough (Grid to Load):</strong>&#160;40A</li>\r\n<li data-start=\"1350\" data-end=\"1401\"><strong data-start=\"1352\" data-end=\"1370\">Rated Voltage:</strong>&#160;220/380V, 230/400V (3L+N+PE)</li>\r\n<li data-start=\"1402\" data-end=\"1462\"><strong data-start=\"1404\" data-end=\"1429\">Grid Frequency Range:</strong>&#160;50Hz (45&#8211;55Hz), 60Hz (55&#8211;65Hz)</li>\r\n<li data-start=\"1463\" data-end=\"1522\"><strong data-start=\"1465\" data-end=\"1493\">Power Factor Adjustment:</strong>&#160;0.8 leading to 0.8 lagging</li>\r\n<li data-start=\"1523\" data-end=\"1568\"><strong data-start=\"1525\" data-end=\"1562\">Total Harmonic Distortion (THDi):</strong>&#160;&lt;3%</li>\r\n<li data-start=\"1569\" data-end=\"1623\"><strong data-start=\"1571\" data-end=\"1596\">DC Injection Current:</strong>&#160;&lt;0.5% of nominal current<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1635\" data-end=\"1649\">Efficiency<br /><br /></strong>\r\n<ul data-start=\"1650\" data-end=\"1745\">\r\n<li data-start=\"1650\" data-end=\"1680\"><strong data-start=\"1652\" data-end=\"1672\">Max. Efficiency:</strong>&#160;97.6%</li>\r\n<li data-start=\"1681\" data-end=\"1715\"><strong data-start=\"1683\" data-end=\"1707\">European Efficiency:</strong>&#160;97.0%</li>\r\n<li data-start=\"1716\" data-end=\"1745\"><strong data-start=\"1718\" data-end=\"1738\">MPPT Efficiency:</strong>&#160;&gt;99%<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"1783\" data-end=\"1810\">Integrated Protections:<br /><br /></strong><strong data-start=\"2073\" data-end=\"2094\"></strong></li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"2073\" data-end=\"2094\">Surge Protection:</strong>&#160;Type II (both DC &amp; AC sides)<br /><br />\r\n<ul data-start=\"1815\" data-end=\"2070\">\r\n<li data-start=\"1815\" data-end=\"1838\">DC reverse polarity</li>\r\n<li data-start=\"1841\" data-end=\"1866\">AC output overcurrent</li>\r\n<li data-start=\"1869\" data-end=\"1887\">AC overvoltage</li>\r\n<li data-start=\"1890\" data-end=\"1907\">Short circuit</li>\r\n<li data-start=\"1910\" data-end=\"1932\">Thermal protection</li>\r\n<li data-start=\"1935\" data-end=\"1965\">Residual current detection</li>\r\n<li data-start=\"1968\" data-end=\"2004\">Insulation resistance monitoring</li>\r\n<li data-start=\"2007\" data-end=\"2040\">Optional arc fault protection</li>\r\n<li data-start=\"2043\" data-end=\"2070\">DC component monitoring<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2128\" data-end=\"2142\">DC Switch:</strong>&#160;Included<br /><br /></li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2165\" data-end=\"2191\">Standards &amp; Compliance<br /><br /></strong>\r\n<ul data-start=\"2192\" data-end=\"2430\">\r\n<li data-start=\"2192\" data-end=\"2339\"><strong data-start=\"2194\" data-end=\"2214\">Grid Compliance:</strong><br data-start=\"2214\" data-end=\"2217\" />IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,<br data-start=\"2289\" data-end=\"2292\" />OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</li>\r\n<li data-start=\"2340\" data-end=\"2430\"><strong data-start=\"2342\" data-end=\"2369\">Safety &amp; EMC Standards:</strong><br data-start=\"2369\" data-end=\"2372\" />IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2442\" data-end=\"2486\">Environmental &amp; Physical Characteristics<br /><br /></strong>\r\n<ul data-start=\"2487\" data-end=\"2880\">\r\n<li data-start=\"2487\" data-end=\"2560\"><strong data-start=\"2489\" data-end=\"2521\">Operating Temperature Range:</strong>&#160;-40&#176;C to +60&#176;C (derating above 45&#176;C)</li>\r\n<li data-start=\"2561\" data-end=\"2585\"><strong data-start=\"2563\" data-end=\"2576\">Humidity:</strong>&#160;0&#8211;100%</li>\r\n<li data-start=\"2586\" data-end=\"2617\"><strong data-start=\"2588\" data-end=\"2609\">Maximum Altitude:</strong>&#160;2000m</li>\r\n<li data-start=\"2618\" data-end=\"2648\"><strong data-start=\"2620\" data-end=\"2636\">Noise Level:</strong>&#160;&#8804;55 dB(A)</li>\r\n<li data-start=\"2649\" data-end=\"2705\"><strong data-start=\"2651\" data-end=\"2670\">Cooling Method:</strong>&#160;<span>Intelligent Air Cooling</span></li>\r\n<li data-start=\"2706\" data-end=\"2773\"><strong data-start=\"2708\" data-end=\"2733\">IP Protection Rating:</strong>&#160;IP65 (dust-tight and water-resistant)</li>\r\n<li data-start=\"2774\" data-end=\"2856\"><strong data-start=\"2776\" data-end=\"2803\">Dimensions (W &#215; H &#215; D):</strong>&#160;408 &#215; 638 &#215; 237 mm (excluding connectors/brackets)</li>\r\n<li data-start=\"2857\" data-end=\"2880\"><strong data-start=\"2859\" data-end=\"2870\">Weight:</strong>&#160;30.5 kg<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2892\" data-end=\"2921\">Interface &amp; Communication<br /><br /></strong>\r\n<ul data-start=\"2922\" data-end=\"3039\">\r\n<li data-start=\"2922\" data-end=\"2992\"><strong data-start=\"2924\" data-end=\"2947\">Monitoring Options:</strong>&#160;GPRS, Wi-Fi, Bluetooth, 4G, LAN (optional)</li>\r\n<li data-start=\"2993\" data-end=\"3039\"><strong data-start=\"2995\" data-end=\"3019\">Communication Ports:</strong>&#160;RS485, RS232, CAN</li>\r\n</ul>\r\n</li>\r\n</ul>\r\n<strong>The Deye SUN-10K-SG01HP3-EU is a three-phase hybrid inverter designed for intelligent energy management. With dual MPPTs, high-voltage battery support, and robust protection features, it ensures efficient solar integration, seamless backup power, and long-term reliability for residential and small commercial applications.</strong>', 'The Deye SUN-10K-SG01HP3-EU-AM2 is a high-performance three-phase hybrid inverter tailored for residential and light commercial applications. Designed to seamlessly integrate solar energy, high-voltage lithium-ion battery storage, and grid power, this inverter enables smart and efficient energy management. With dual MPPTs, a wide PV voltage range of 150&#8211;850V, and support for up to 10000W of PV input, it maximizes solar harvest and system flexibility. Its advanced protection features, natural cooling system, and IP65-rated housing ensure reliable operation under various environmental conditions. Whether for new installations or retrofitting existing systems, the SUN-10K-SG01HP3-EU-AM2 offers a compact, robust, and future-ready energy solution.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\r\n\r\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\r\n\r\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\r\n\r\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\r\n\r\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\r\n\r\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\r\n\r\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(541, '<table selecttype=\"cells\">\r\n<tbody>\r\n<tr height=\"24\">\r\n<td width=\"273\"><strong>Battery Input Data</strong></td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Battery Type</td>\r\n<td width=\"800\">Lithium-ion</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Battery Voltage Range(V)</td>\r\n<td width=\"800\">160-700</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max.Charging Current(A)</td>\r\n<td width=\"500\">37</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max.Discharging Current(A)</td>\r\n<td width=\"500\">37</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Charging Strategy for Li-ion Battery</td>\r\n<td width=\"800\">Self-adaption to BMS</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Number of battery input</td>\r\n<td width=\"800\">1</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>PV String Input Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr>\r\n<td>Max. PV Access Power (W)</td>\r\n<td>20000</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max. PV Input Power (W)</td>\r\n<td width=\"100\">16000</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max. PV Input Voltage (V)</td>\r\n<td width=\"800\">1000</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Start-up Voltage&#65288;V&#65289;</td>\r\n<td width=\"800\">180</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">MPPT Voltage Range&#65288;V&#65289;</td>\r\n<td width=\"800\">150-850</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated DC Input Voltage(V)</td>\r\n<td width=\"700\">600</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max Input Short-Circuit Current&#65288;A&#65289;</td>\r\n<td width=\"400\">30+30</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max Operating PV Input Current&#65288;A&#65289;</td>\r\n<td width=\"400\">20+20</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">No.of MPP Trackers/No.of String Per MPP Tracker</td>\r\n<td width=\"400\">2/1+1</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>AC Input/Output Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated AC Input/Output Active Power&#65288;W&#65289;</td>\r\n<td width=\"100\">10000</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max AC Input/Output Apparent Power &#65288;VA&#65289;</td>\r\n<td width=\"100\">11000</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Peak Power (off-grid)&#65288;W&#65289;</td>\r\n<td width=\"800\">1.5 times of rated power,10s</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated AC Input/Output Current&#65288;A&#65289;</td>\r\n<td width=\"100\">15.2/14.5</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max AC Input/Output Current&#65288;A&#65289;</td>\r\n<td width=\"100\">16.7/16</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max Continuous AC Passthrough (grid to load)&#65288;A&#65289;</td>\r\n<td width=\"400\">40</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated Input/Output Voltage/Range(V)</td>\r\n<td width=\"800\">220/380V&#65292;230/400V 0.85Un-1.1Un</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Grid Connection Form</td>\r\n<td width=\"800\">3L+N+PE</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated Input/Output Grid Frequency/Range</td>\r\n<td width=\"800\">50Hz/45Hz-55Hz&#160; 60Hz/55Hz-65Hz</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Power Factor Adjustment Range</td>\r\n<td width=\"800\">0.8 leading to 0.8 lagging</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Total Current Harmonic Distortion THDi</td>\r\n<td width=\"800\">&lt;3% (of nominal power)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">DC Injection Current</td>\r\n<td width=\"800\">&lt;0.5%ln</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Efficiency</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max Efficiency</td>\r\n<td width=\"800\">97.6%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Euro Efficiency</td>\r\n<td width=\"800\">97.0%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">MPPT Efficiency</td>\r\n<td width=\"800\">&#65310;99%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Equipment Protection</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Integrated</td>\r\n<td width=\"800\">\r\n<div>DC Reverse Polarity Protection, AC Output Overcurrent Protection, Thermal Protection, AC Output Overvoltage</div>\r\n<div>Protection,&#160;AC Output Short Circuit Protection, DC Component Monitoring, Arc Fault Circuit Interrupter (optional),</div>\r\n<div>Anti-islanding Protection, DC Switch,&#160;Insulation Impedance Detection, Residual Current Detection</div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Surge Protection Level</td>\r\n<td width=\"800\">TYPE II(DC),TYPE II(AC)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Interface</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Communication Interface</td>\r\n<td width=\"800\">RS485/RS232/CAN</td>\r\n</tr>\r\n<tr>\r\n<td>Monitor Mode</td>\r\n<td>GPRS/WIFI/Bluetooth/4G/LAN(optional)</td>\r\n</tr>\r\n<tr>\r\n<td>LCD/LED Display</td>\r\n<td>LCD</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>General Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Operating Temperature Range</td>\r\n<td width=\"800\">-40 to +60&#8451;, &gt;45&#8451; Derating</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Permissible Ambient Humidity</td>\r\n<td width=\"800\">0-100%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Permissible Altitude</td>\r\n<td width=\"800\">2000m</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Noise</td>\r\n<td width=\"800\">&#8804; 55 dB(A)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Ingress Protection(IP) Rating</td>\r\n<td width=\"800\">IP 65</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Inverter Topology</td>\r\n<td width=\"800\">Non-Isolated</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Over Voltage Category</td>\r\n<td width=\"800\">OVC II(DC),OVC III(AC)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Cabinet size&#65288;W*H*D&#65289;[mm]</td>\r\n<td width=\"800\">408*638*237&#65288;Excluding connectors and brackets&#65289;</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Weight[kg]</td>\r\n<td width=\"800\">30.5</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Warranty</td>\r\n<td width=\"800\">\r\n<div>5 Years/10 Years</div>\r\n<div>the Warranty Period Depends the Final Installation Site of Inverter, More Info Please Refer to Warranty Policy</div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Type Of Cooling</td>\r\n<td width=\"600\">Intelligent air cooling</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Grid Regulation</td>\r\n<td width=\"800\">\r\n<p>IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</p>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Safety EMC/Standard</td>\r\n<td width=\"800\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</td>\r\n</tr>\r\n</tbody>\r\n</table>', 3, 'SUN-10K-SG01HP3-EU | Three-Phase Hybrid Inverter | 2 MPPT | HV Battery Supported', '<p>The Deye SUN-10K-SG01HP3-EU is a powerful three-phase hybrid inverter designed for high-performance solar energy systems. Equipped with 2 MPPTs and high-voltage battery support, it ensures exceptional efficiency and flexibility. This inverter supports 100% unbalanced output, allowing each phase to independently deliver up to 50% of the rated power&#8212;ideal for uneven load distribution. Thanks to its AC coupling capability, it can seamlessly retrofit into existing PV systems, enhancing performance without requiring a full overhaul. It allows for parallel operation of up to 10 units in both on-grid and off-grid modes and supports multiple batteries in parallel, offering excellent scalability. With a maximum charging and discharging current of 37A, it maintains efficient and reliable energy flow. Additionally, users can configure six charging and discharging time periods, optimizing battery use based on energy demand and tariff rates. The inverter is also compatible with diesel generators, ensuring dependable backup power in areas with unstable grid supply.</p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-005.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" /></p>\r\n<p></p>\r\n<h3>Key Features</h3>\r\n<ul>\r\n<li data-start=\"0\" data-end=\"152\">\r\n<p data-start=\"2\" data-end=\"152\"><strong data-start=\"2\" data-end=\"29\" data-is-only-node=\"\">100% Unbalanced Output:</strong>&#160;Each phase can operate independently with up to 50% of the rated power, ensuring flexibility for varied load conditions.</p>\r\n</li>\r\n<li data-start=\"153\" data-end=\"296\">\r\n<p data-start=\"155\" data-end=\"296\"><strong data-start=\"155\" data-end=\"184\" data-is-only-node=\"\">AC Coupling for Retrofit:</strong>&#160;Easily integrates into existing solar systems, enabling efficient performance upgrades without major changes.</p>\r\n</li>\r\n<li data-start=\"297\" data-end=\"468\">\r\n<p data-start=\"299\" data-end=\"468\"><strong data-start=\"299\" data-end=\"331\" data-is-only-node=\"\">Scalable Parallel Operation:</strong>&#160;Supports up to 10 units in parallel for both on-grid and off-grid modes, with compatibility for multiple parallel battery connections.</p>\r\n</li>\r\n<li data-start=\"469\" data-end=\"605\">\r\n<p data-start=\"471\" data-end=\"605\"><strong data-start=\"471\" data-end=\"516\" data-is-only-node=\"\">Max. Charging/Discharging Current of 37A:</strong>&#160;Ensures stable and efficient energy flow for both charging and discharging operations.</p>\r\n</li>\r\n<li data-start=\"606\" data-end=\"731\">\r\n<p data-start=\"608\" data-end=\"731\"><strong data-start=\"608\" data-end=\"641\" data-is-only-node=\"\">High Voltage Battery Support:</strong>&#160;Utilizes high-voltage batteries to increase system efficiency and reduce energy losses.</p>\r\n</li>\r\n<li data-start=\"732\" data-end=\"899\">\r\n<p data-start=\"734\" data-end=\"899\"><strong data-start=\"734\" data-end=\"768\" data-is-only-node=\"\">Time-based Battery Management:</strong>&#160;Allows for six configurable time periods for optimized battery charging and discharging based on energy consumption and tariffs.</p>\r\n</li>\r\n<li data-start=\"900\" data-end=\"1059\" data-is-last-node=\"\">\r\n<p data-start=\"902\" data-end=\"1059\" data-is-last-node=\"\"><strong data-start=\"902\" data-end=\"937\" data-is-only-node=\"\">Diesel Generator Compatibility:</strong>&#160;Capable of storing energy from diesel generators, offering reliable backup in areas with unstable or limited grid access.</p>\r\n</li>\r\n</ul>\r\n<p></p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" /></p>\r\n<p></p>\r\n<h3>Technical Specifications</h3>\r\n<ul>\r\n<li><strong data-start=\"283\" data-end=\"305\">Battery Input Data<br /><br /></strong>\r\n<ul data-start=\"306\" data-end=\"596\">\r\n<li data-start=\"306\" data-end=\"384\"><strong data-start=\"308\" data-end=\"334\">Battery Compatibility:</strong>&#160;Lithium-ion batteries (lead-acid not supported)</li>\r\n<li data-start=\"385\" data-end=\"424\"><strong data-start=\"387\" data-end=\"413\">Battery Voltage Range:</strong>&#160;160&#8211;700V</li>\r\n<li data-start=\"425\" data-end=\"471\"><strong data-start=\"427\" data-end=\"465\">Max. Charging/Discharging Current:</strong>&#160;37A</li>\r\n<li data-start=\"472\" data-end=\"506\"><strong data-start=\"474\" data-end=\"492\">Battery Input:</strong>&#160;Single port</li>\r\n<li data-start=\"507\" data-end=\"596\"><strong data-start=\"509\" data-end=\"531\">BMS Communication:</strong>&#160;Self-adaptive, ensuring compatibility with various BMS protocols<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"608\" data-end=\"632\">PV String Input Data<br /><br /></strong>\r\n<ul data-start=\"633\" data-end=\"1003\">\r\n<li data-start=\"633\" data-end=\"670\"><strong data-start=\"635\" data-end=\"660\">Max. PV Access Power:</strong>&#160;20000W</li>\r\n<li data-start=\"671\" data-end=\"707\"><strong data-start=\"673\" data-end=\"697\">Max. PV Input Power:</strong>&#160;16000W</li>\r\n<li data-start=\"708\" data-end=\"744\"><strong data-start=\"710\" data-end=\"736\">Max. PV Input Voltage:</strong>&#160;1000V</li>\r\n<li data-start=\"745\" data-end=\"781\"><strong data-start=\"747\" data-end=\"770\">MPPT Voltage Range:</strong>&#160;150&#8211;850V</li>\r\n<li data-start=\"782\" data-end=\"812\"><strong data-start=\"784\" data-end=\"805\">Start-up Voltage:</strong>&#160;180V</li>\r\n<li data-start=\"813\" data-end=\"849\"><strong data-start=\"815\" data-end=\"842\">Rated DC Input Voltage:</strong>&#160;600V</li>\r\n<li data-start=\"850\" data-end=\"903\"><strong data-start=\"852\" data-end=\"891\">Number of MPPTs / Strings per MPPT:</strong>&#160;2 / (1+1)</li>\r\n<li data-start=\"904\" data-end=\"954\"><strong data-start=\"906\" data-end=\"942\">Max. Operating PV Input Current:</strong>&#160;20A + 20A</li>\r\n<li data-start=\"955\" data-end=\"1003\"><strong data-start=\"957\" data-end=\"991\">Max. PV Short-Circuit Current:</strong>&#160;30A + 30A<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1015\" data-end=\"1041\">AC Input / Output Data<br /><br /></strong>\r\n<ul data-start=\"1042\" data-end=\"1623\">\r\n<li data-start=\"1042\" data-end=\"1084\"><strong data-start=\"1044\" data-end=\"1076\">Rated AC Input/Output Power:</strong>&#160;10000W</li>\r\n<li data-start=\"1085\" data-end=\"1120\"><strong data-start=\"1087\" data-end=\"1111\">Max. Apparent Power:</strong>&#160;11000A</li>\r\n<li data-start=\"1121\" data-end=\"1185\"><strong data-start=\"1123\" data-end=\"1149\">Peak Power (Off-Grid):</strong>&#160;1.5&#215; rated power (for 10 seconds)</li>\r\n<li data-start=\"1186\" data-end=\"1238\"><strong data-start=\"1188\" data-end=\"1222\">Rated AC Input/Output Current:</strong>&#160;15.2/14.5</li>\r\n<li data-start=\"1239\" data-end=\"1290\"><strong data-start=\"1241\" data-end=\"1274\">Max. AC Input/Output Current:</strong>&#160;<span>16.7/16</span></li>\r\n<li data-start=\"1291\" data-end=\"1349\"><strong data-start=\"1293\" data-end=\"1343\">Max. Continuous AC Passthrough (Grid to Load):</strong>&#160;40A</li>\r\n<li data-start=\"1350\" data-end=\"1401\"><strong data-start=\"1352\" data-end=\"1370\">Rated Voltage:</strong>&#160;220/380V, 230/400V (3L+N+PE)</li>\r\n<li data-start=\"1402\" data-end=\"1462\"><strong data-start=\"1404\" data-end=\"1429\">Grid Frequency Range:</strong>&#160;50Hz (45&#8211;55Hz), 60Hz (55&#8211;65Hz)</li>\r\n<li data-start=\"1463\" data-end=\"1522\"><strong data-start=\"1465\" data-end=\"1493\">Power Factor Adjustment:</strong>&#160;0.8 leading to 0.8 lagging</li>\r\n<li data-start=\"1523\" data-end=\"1568\"><strong data-start=\"1525\" data-end=\"1562\">Total Harmonic Distortion (THDi):</strong>&#160;&lt;3%</li>\r\n<li data-start=\"1569\" data-end=\"1623\"><strong data-start=\"1571\" data-end=\"1596\">DC Injection Current:</strong>&#160;&lt;0.5% of nominal current<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1635\" data-end=\"1649\">Efficiency<br /><br /></strong>\r\n<ul data-start=\"1650\" data-end=\"1745\">\r\n<li data-start=\"1650\" data-end=\"1680\"><strong data-start=\"1652\" data-end=\"1672\">Max. Efficiency:</strong>&#160;97.6%</li>\r\n<li data-start=\"1681\" data-end=\"1715\"><strong data-start=\"1683\" data-end=\"1707\">European Efficiency:</strong>&#160;97.0%</li>\r\n<li data-start=\"1716\" data-end=\"1745\"><strong data-start=\"1718\" data-end=\"1738\">MPPT Efficiency:</strong>&#160;&gt;99%<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"1783\" data-end=\"1810\">Integrated Protections:<br /><br /></strong><strong data-start=\"2073\" data-end=\"2094\"></strong></li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"2073\" data-end=\"2094\">Surge Protection:</strong>&#160;Type II (both DC &amp; AC sides)<br /><br />\r\n<ul data-start=\"1815\" data-end=\"2070\">\r\n<li data-start=\"1815\" data-end=\"1838\">DC reverse polarity</li>\r\n<li data-start=\"1841\" data-end=\"1866\">AC output overcurrent</li>\r\n<li data-start=\"1869\" data-end=\"1887\">AC overvoltage</li>\r\n<li data-start=\"1890\" data-end=\"1907\">Short circuit</li>\r\n<li data-start=\"1910\" data-end=\"1932\">Thermal protection</li>\r\n<li data-start=\"1935\" data-end=\"1965\">Residual current detection</li>\r\n<li data-start=\"1968\" data-end=\"2004\">Insulation resistance monitoring</li>\r\n<li data-start=\"2007\" data-end=\"2040\">Optional arc fault protection</li>\r\n<li data-start=\"2043\" data-end=\"2070\">DC component monitoring<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2128\" data-end=\"2142\">DC Switch:</strong>&#160;Included<br /><br /></li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2165\" data-end=\"2191\">Standards &amp; Compliance<br /><br /></strong>\r\n<ul data-start=\"2192\" data-end=\"2430\">\r\n<li data-start=\"2192\" data-end=\"2339\"><strong data-start=\"2194\" data-end=\"2214\">Grid Compliance:</strong><br data-start=\"2214\" data-end=\"2217\" />IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,<br data-start=\"2289\" data-end=\"2292\" />OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</li>\r\n<li data-start=\"2340\" data-end=\"2430\"><strong data-start=\"2342\" data-end=\"2369\">Safety &amp; EMC Standards:</strong><br data-start=\"2369\" data-end=\"2372\" />IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2442\" data-end=\"2486\">Environmental &amp; Physical Characteristics<br /><br /></strong>\r\n<ul data-start=\"2487\" data-end=\"2880\">\r\n<li data-start=\"2487\" data-end=\"2560\"><strong data-start=\"2489\" data-end=\"2521\">Operating Temperature Range:</strong>&#160;-40&#176;C to +60&#176;C (derating above 45&#176;C)</li>\r\n<li data-start=\"2561\" data-end=\"2585\"><strong data-start=\"2563\" data-end=\"2576\">Humidity:</strong>&#160;0&#8211;100%</li>\r\n<li data-start=\"2586\" data-end=\"2617\"><strong data-start=\"2588\" data-end=\"2609\">Maximum Altitude:</strong>&#160;2000m</li>\r\n<li data-start=\"2618\" data-end=\"2648\"><strong data-start=\"2620\" data-end=\"2636\">Noise Level:</strong>&#160;&#8804;55 dB(A)</li>\r\n<li data-start=\"2649\" data-end=\"2705\"><strong data-start=\"2651\" data-end=\"2670\">Cooling Method:</strong>&#160;Intelligent Air Cooling</li>\r\n<li data-start=\"2706\" data-end=\"2773\"><strong data-start=\"2708\" data-end=\"2733\">IP Protection Rating:</strong>&#160;IP65 (dust-tight and water-resistant)</li>\r\n<li data-start=\"2774\" data-end=\"2856\"><strong data-start=\"2776\" data-end=\"2803\">Dimensions (W &#215; H &#215; D):</strong>&#160;408 &#215; 638 &#215; 237 mm (excluding connectors/brackets)</li>\r\n<li data-start=\"2857\" data-end=\"2880\"><strong data-start=\"2859\" data-end=\"2870\">Weight:</strong>&#160;30.5 kg<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2892\" data-end=\"2921\">Interface &amp; Communication<br /><br /></strong>\r\n<ul data-start=\"2922\" data-end=\"3039\">\r\n<li data-start=\"2922\" data-end=\"2992\"><strong data-start=\"2924\" data-end=\"2947\">Monitoring Options:</strong>&#160;GPRS, Wi-Fi, Bluetooth, 4G, LAN (optional)</li>\r\n<li data-start=\"2993\" data-end=\"3039\"><strong data-start=\"2995\" data-end=\"3019\">Communication Ports:</strong>&#160;RS485, RS232, CAN</li>\r\n</ul>\r\n</li>\r\n</ul>\r\n<p><strong>The Deye SUN-10K-SG01HP3-EU is a three-phase hybrid inverter designed for intelligent energy management. With dual MPPTs, high-voltage battery support, and robust protection features, it ensures efficient solar integration, seamless backup power, and long-term reliability for residential and small commercial applications.</strong></p>', 'The Deye SUN-10K-SG01HP3-EU-AM2 is a high-performance three-phase hybrid inverter tailored for residential and light commercial applications. Designed to seamlessly integrate solar energy, high-voltage lithium-ion battery storage, and grid power, this inverter enables smart and efficient energy management. With dual MPPTs, a wide PV voltage range of 150&#8211;850V, and support for up to 10000W of PV input, it maximizes solar harvest and system flexibility. Its advanced protection features, natural cooling system, and IP65-rated housing ensure reliable operation under various environmental conditions. Whether for new installations or retrofitting existing systems, the SUN-10K-SG01HP3-EU-AM2 offers a compact, robust, and future-ready energy solution.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\r\n\r\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\r\n\r\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\r\n\r\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\r\n\r\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\r\n\r\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\r\n\r\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', '');
INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(542, '<table selecttype=\"cells\">\r\n<tbody>\r\n<tr height=\"24\">\r\n<td width=\"273\"><strong>Battery Input Data</strong></td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Battery Type</span></td>\r\n<td width=\"800\"><span>Lithium-ion</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Battery Voltage Range(V)</span></td>\r\n<td width=\"800\"><span>160-700</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max.Charging Current(A)</span></td>\r\n<td width=\"500\"><span>37</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max.Discharging Current(A)</span></td>\r\n<td width=\"500\"><span>37</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Charging Strategy for Li-ion Battery</span></td>\r\n<td width=\"800\"><span>Self-adaption to BMS</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Number of battery input</span></td>\r\n<td width=\"800\"><span>1</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>PV String Input Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<div><span>Max. PV Access Power (W)</span></div>\r\n</td>\r\n<td><span>24000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max. PV Input Power (W)</span></td>\r\n<td width=\"100\"><span>19200</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max. PV Input Voltage (V)</span></td>\r\n<td width=\"800\"><span>1000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Start-up Voltage&#65288;V&#65289;</span></td>\r\n<td width=\"800\"><span>180</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>MPPT Voltage Range&#65288;V&#65289;</span></td>\r\n<td width=\"800\"><span>150-850</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Rated DC Input Voltage(V)</span></td>\r\n<td width=\"700\"><span>600</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max Input Short-Circuit Current&#65288;A&#65289;</span></td>\r\n<td width=\"200\"><span>39+30</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max Operating PV Input Current&#65288;A&#65289;</span></td>\r\n<td width=\"200\"><span>26+20</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>No.of MPP Trackers/No.of String Per MPP Tracker</span></td>\r\n<td width=\"200\"><span>2/2+1</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>AC Input/Output Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Rated AC Input/Output Active Power&#65288;W&#65289;</span></td>\r\n<td width=\"100\"><span>12000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max AC Input/Output Apparent Power &#65288;VA&#65289;</span></td>\r\n<td width=\"100\"><span>13200</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Peak Power (off-grid)&#65288;W&#65289;</span></td>\r\n<td width=\"800\"><span>1.5 times of rated power,10s</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Rated AC Input/Output Current&#65288;A&#65289;</span></td>\r\n<td width=\"100\"><span>18.2/17.4</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max AC Input/Output Current&#65288;A&#65289;</span></td>\r\n<td width=\"100\"><span>20/19.2</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max Continuous AC Passthrough (grid to load)&#65288;A&#65289;</span></td>\r\n<td width=\"400\"><span>80</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Rated Input/Output Voltage/Range(V)</span></td>\r\n<td width=\"800\"><span>220/380V&#65292;230/400V 0.85Un-1.1Un</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Grid Connection Form</span></td>\r\n<td width=\"800\"><span>3L+N+PE</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Rated Input/Output Grid Frequency/Range</span></td>\r\n<td width=\"800\"><span>50Hz/45Hz-55Hz&#160; 60Hz/55Hz-65Hz</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Power Factor Adjustment Range</span></td>\r\n<td width=\"800\"><span>0.8 leading to 0.8 lagging</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Total Current Harmonic Distortion THDi</span></td>\r\n<td width=\"800\"><span>&lt;3% (of nominal power)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>DC Injection Current</span></td>\r\n<td width=\"800\"><span>&lt;0.5%ln</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Efficiency</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max Efficiency</span></td>\r\n<td width=\"800\"><span>97.6%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Euro Efficiency</span></td>\r\n<td width=\"800\"><span>97.0%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>MPPT Efficiency</span></td>\r\n<td width=\"800\"><span>&#65310;99%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Equipment Protection</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<div><span>Integrated</span></div>\r\n</td>\r\n<td width=\"800\">\r\n<div>\r\n<div><span>DC Reverse Polarity Protection, AC Output Overcurrent Protection, Thermal Protection, AC Output Overvoltage</span></div>\r\n<div><span>Protection,&#160;</span><span>AC Output Short Circuit Protection, DC Component Monitoring, Arc Fault Circuit Interrupter (optional),</span></div>\r\n<div><span>Anti-islanding Protection, DC Switch,&#160;</span><span>Insulation Impedance Detection, Residual Current Detection</span></div>\r\n</div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Surge Protection Level</span></td>\r\n<td width=\"800\"><span>TYPE II(DC),TYPE II(AC)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Interface</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<div>\r\n<div><span>Communication Interface</span></div>\r\n</div>\r\n</td>\r\n<td width=\"800\">\r\n<div><span>RS485/RS232/CAN</span></div>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<div><span>Monitor Mode</span></div>\r\n</td>\r\n<td>\r\n<div><span>GPRS/WIFI/Bluetooth/4G/LAN(optional)</span></div>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<div><span>LCD/LED Display</span></div>\r\n</td>\r\n<td>\r\n<div><span>LCD</span></div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>General Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Operating Temperature Range</span></td>\r\n<td width=\"800\">\r\n<div><span>-40 to +60&#8451;, &gt;45&#8451; Derating</span></div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Permissible Ambient Humidity</span></td>\r\n<td width=\"800\"><span>0-100%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Permissible Altitude</span></td>\r\n<td width=\"800\"><span>2000m</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Noise</span></td>\r\n<td width=\"800\"><span>&#8804; 55 dB(A)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Ingress Protection(IP) Rating</span></td>\r\n<td width=\"800\"><span>IP 65</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Inverter Topology</span></td>\r\n<td width=\"800\"><span>Non-Isolated</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Over Voltage Category</span></td>\r\n<td width=\"800\"><span>OVC II(DC),OVC III(AC)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Cabinet size&#65288;W*H*D&#65289;[mm]</span></td>\r\n<td width=\"800\"><span>408*638*237&#65288;Excluding connectors and brackets&#65289;</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Weight[kg]</span></td>\r\n<td width=\"800\"><span>30.5</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Warranty</span></td>\r\n<td width=\"800\">\r\n<div><span>5 Years/10 Years</span></div>\r\n<div><span>the Warranty Period Depends the Final Installation Site of Inverter, More Info Please Refer to Warranty Policy</span></div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Type Of Cooling</span></td>\r\n<td width=\"600\"><span>Intelligent air cooling</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Grid Regulation</span></td>\r\n<td width=\"800\">\r\n<p><span>IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</span></p>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Safety EMC/Standard</span></td>\r\n<td width=\"800\"><span>IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2<br /><br /></span></td>\r\n</tr>\r\n</tbody>\r\n</table>', 2, 'SUN-12K-SG01HP3-EU | Three-Phase Hybrid Inverter | 2 MPPT | HV Battery Supported', '<p>The Deye SUN-12K-SG01HP3-EU is a powerful three-phase hybrid inverter designed for high-performance solar energy systems. Equipped with 2 MPPTs and high-voltage battery support, it ensures exceptional efficiency and flexibility. This inverter supports 100% unbalanced output, allowing each phase to independently deliver up to 50% of the rated power&#8212;ideal for uneven load distribution. Thanks to its AC coupling capability, it can seamlessly retrofit into existing PV systems, enhancing performance without requiring a full overhaul. It allows for parallel operation of up to 10 units in both on-grid and off-grid modes and supports multiple batteries in parallel, offering excellent scalability. With a maximum charging and discharging current of 37A, it maintains efficient and reliable energy flow. Additionally, users can configure six charging and discharging time periods, optimizing battery use based on energy demand and tariff rates. The inverter is also compatible with diesel generators, ensuring dependable backup power in areas with unstable grid supply.</p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-005.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\r\n<p></p>\r\n<h3>Key Features</h3>\r\n<ul>\r\n<li data-start=\"0\" data-end=\"152\">\r\n<p data-start=\"2\" data-end=\"152\"><strong data-start=\"2\" data-end=\"29\" data-is-only-node=\"\">100% Unbalanced Output:</strong>&#160;Each phase can operate independently with up to 50% of the rated power, ensuring flexibility for varied load conditions.</p>\r\n</li>\r\n<li data-start=\"153\" data-end=\"296\">\r\n<p data-start=\"155\" data-end=\"296\"><strong data-start=\"155\" data-end=\"184\" data-is-only-node=\"\">AC Coupling for Retrofit:</strong>&#160;Easily integrates into existing solar systems, enabling efficient performance upgrades without major changes.</p>\r\n</li>\r\n<li data-start=\"297\" data-end=\"468\">\r\n<p data-start=\"299\" data-end=\"468\"><strong data-start=\"299\" data-end=\"331\" data-is-only-node=\"\">Scalable Parallel Operation:</strong>&#160;Supports up to 10 units in parallel for both on-grid and off-grid modes, with compatibility for multiple parallel battery connections.</p>\r\n</li>\r\n<li data-start=\"469\" data-end=\"605\">\r\n<p data-start=\"471\" data-end=\"605\"><strong data-start=\"471\" data-end=\"516\" data-is-only-node=\"\">Max. Charging/Discharging Current of 37A:</strong>&#160;Ensures stable and efficient energy flow for both charging and discharging operations.</p>\r\n</li>\r\n<li data-start=\"606\" data-end=\"731\">\r\n<p data-start=\"608\" data-end=\"731\"><strong data-start=\"608\" data-end=\"641\" data-is-only-node=\"\">High Voltage Battery Support:</strong>&#160;Utilizes high-voltage batteries to increase system efficiency and reduce energy losses.</p>\r\n</li>\r\n<li data-start=\"732\" data-end=\"899\">\r\n<p data-start=\"734\" data-end=\"899\"><strong data-start=\"734\" data-end=\"768\" data-is-only-node=\"\">Time-based Battery Management:</strong>&#160;Allows for six configurable time periods for optimized battery charging and discharging based on energy consumption and tariffs.</p>\r\n</li>\r\n<li data-start=\"900\" data-end=\"1059\" data-is-last-node=\"\">\r\n<p data-start=\"902\" data-end=\"1059\" data-is-last-node=\"\"><strong data-start=\"902\" data-end=\"937\" data-is-only-node=\"\">Diesel Generator Compatibility:</strong>&#160;Capable of storing energy from diesel generators, offering reliable backup in areas with unstable or limited grid access.</p>\r\n</li>\r\n</ul>\r\n<p></p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\r\n<p></p>\r\n<h3>Technical Specifications</h3>\r\n<ul>\r\n<li><strong data-start=\"283\" data-end=\"305\">Battery Input Data<br /><br /></strong>\r\n<ul data-start=\"306\" data-end=\"596\">\r\n<li data-start=\"306\" data-end=\"384\"><strong data-start=\"308\" data-end=\"334\">Battery Compatibility:</strong>&#160;Lithium-ion batteries (lead-acid not supported)</li>\r\n<li data-start=\"385\" data-end=\"424\"><strong data-start=\"387\" data-end=\"413\">Battery Voltage Range:</strong>&#160;160&#8211;700V</li>\r\n<li data-start=\"425\" data-end=\"471\"><strong data-start=\"427\" data-end=\"465\">Max. Charging/Discharging Current:</strong>&#160;37A</li>\r\n<li data-start=\"472\" data-end=\"506\"><strong data-start=\"474\" data-end=\"492\">Battery Input:</strong>&#160;Single port</li>\r\n<li data-start=\"507\" data-end=\"596\"><strong data-start=\"509\" data-end=\"531\">BMS Communication:</strong>&#160;Self-adaptive, ensuring compatibility with various BMS protocols<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"608\" data-end=\"632\">PV String Input Data<br /><br /></strong>\r\n<ul data-start=\"633\" data-end=\"1003\">\r\n<li data-start=\"633\" data-end=\"670\"><strong data-start=\"635\" data-end=\"660\">Max. PV Access Power:</strong>&#160;24000W</li>\r\n<li data-start=\"671\" data-end=\"707\"><strong data-start=\"673\" data-end=\"697\">Max. PV Input Power:</strong>&#160;<span>19200</span>W</li>\r\n<li data-start=\"708\" data-end=\"744\"><strong data-start=\"710\" data-end=\"736\">Max. PV Input Voltage:</strong>&#160;1000V</li>\r\n<li data-start=\"745\" data-end=\"781\"><strong data-start=\"747\" data-end=\"770\">MPPT Voltage Range:</strong>&#160;150&#8211;850V</li>\r\n<li data-start=\"782\" data-end=\"812\"><strong data-start=\"784\" data-end=\"805\">Start-up Voltage:</strong>&#160;180V</li>\r\n<li data-start=\"813\" data-end=\"849\"><strong data-start=\"815\" data-end=\"842\">Rated DC Input Voltage:</strong>&#160;600V</li>\r\n<li data-start=\"850\" data-end=\"903\"><strong data-start=\"852\" data-end=\"891\">Number of MPPTs / Strings per MPPT:</strong>&#160;2 / (1+1)</li>\r\n<li data-start=\"904\" data-end=\"954\"><strong data-start=\"906\" data-end=\"942\">Max. Operating PV Input Current:</strong>&#160;<span>26A + 20A</span></li>\r\n<li data-start=\"955\" data-end=\"1003\"><strong data-start=\"957\" data-end=\"991\">Max. PV Short-Circuit Current:</strong>&#160;39A + 30A<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1015\" data-end=\"1041\">AC Input / Output Data<br /><br /></strong>\r\n<ul data-start=\"1042\" data-end=\"1623\">\r\n<li data-start=\"1042\" data-end=\"1084\"><strong data-start=\"1044\" data-end=\"1076\">Rated AC Input/Output Power:</strong>&#160;12000W</li>\r\n<li data-start=\"1085\" data-end=\"1120\"><strong data-start=\"1087\" data-end=\"1111\">Max. Apparent Power:</strong>&#160;13200A</li>\r\n<li data-start=\"1121\" data-end=\"1185\"><strong data-start=\"1123\" data-end=\"1149\">Peak Power (Off-Grid):</strong>&#160;1.5&#215; rated power (for 10 seconds)</li>\r\n<li data-start=\"1186\" data-end=\"1238\"><strong data-start=\"1188\" data-end=\"1222\">Rated AC Input/Output Current:</strong>&#160;<span>18.2/17.4</span></li>\r\n<li data-start=\"1239\" data-end=\"1290\"><strong data-start=\"1241\" data-end=\"1274\">Max. AC Input/Output Current:</strong>&#160;<span>20/19.2</span></li>\r\n<li data-start=\"1291\" data-end=\"1349\"><strong data-start=\"1293\" data-end=\"1343\">Max. Continuous AC Passthrough (Grid to Load):</strong>&#160;80A</li>\r\n<li data-start=\"1350\" data-end=\"1401\"><strong data-start=\"1352\" data-end=\"1370\">Rated Voltage:</strong>&#160;220/380V, 230/400V (3L+N+PE)</li>\r\n<li data-start=\"1402\" data-end=\"1462\"><strong data-start=\"1404\" data-end=\"1429\">Grid Frequency Range:</strong>&#160;50Hz (45&#8211;55Hz), 60Hz (55&#8211;65Hz)</li>\r\n<li data-start=\"1463\" data-end=\"1522\"><strong data-start=\"1465\" data-end=\"1493\">Power Factor Adjustment:</strong>&#160;0.8 leading to 0.8 lagging</li>\r\n<li data-start=\"1523\" data-end=\"1568\"><strong data-start=\"1525\" data-end=\"1562\">Total Harmonic Distortion (THDi):</strong>&#160;&lt;3%</li>\r\n<li data-start=\"1569\" data-end=\"1623\"><strong data-start=\"1571\" data-end=\"1596\">DC Injection Current:</strong>&#160;&lt;0.5% of nominal current<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1635\" data-end=\"1649\">Efficiency<br /><br /></strong>\r\n<ul data-start=\"1650\" data-end=\"1745\">\r\n<li data-start=\"1650\" data-end=\"1680\"><strong data-start=\"1652\" data-end=\"1672\">Max. Efficiency:</strong>&#160;97.6%</li>\r\n<li data-start=\"1681\" data-end=\"1715\"><strong data-start=\"1683\" data-end=\"1707\">European Efficiency:</strong>&#160;97.0%</li>\r\n<li data-start=\"1716\" data-end=\"1745\"><strong data-start=\"1718\" data-end=\"1738\">MPPT Efficiency:</strong>&#160;&gt;99%<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"1783\" data-end=\"1810\">Integrated Protections:<br /><br /></strong><strong data-start=\"2073\" data-end=\"2094\"></strong></li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"2073\" data-end=\"2094\">Surge Protection:</strong>&#160;Type II (both DC &amp; AC sides)<br /><br />\r\n<ul data-start=\"1815\" data-end=\"2070\">\r\n<li data-start=\"1815\" data-end=\"1838\">DC reverse polarity</li>\r\n<li data-start=\"1841\" data-end=\"1866\">AC output overcurrent</li>\r\n<li data-start=\"1869\" data-end=\"1887\">AC overvoltage</li>\r\n<li data-start=\"1890\" data-end=\"1907\">Short circuit</li>\r\n<li data-start=\"1910\" data-end=\"1932\">Thermal protection</li>\r\n<li data-start=\"1935\" data-end=\"1965\">Residual current detection</li>\r\n<li data-start=\"1968\" data-end=\"2004\">Insulation resistance monitoring</li>\r\n<li data-start=\"2007\" data-end=\"2040\">Optional arc fault protection</li>\r\n<li data-start=\"2043\" data-end=\"2070\">DC component monitoring<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2128\" data-end=\"2142\">DC Switch:</strong>&#160;Included<br /><br /></li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2165\" data-end=\"2191\">Standards &amp; Compliance<br /><br /></strong>\r\n<ul data-start=\"2192\" data-end=\"2430\">\r\n<li data-start=\"2192\" data-end=\"2339\"><strong data-start=\"2194\" data-end=\"2214\">Grid Compliance:</strong><br data-start=\"2214\" data-end=\"2217\" />IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,<br data-start=\"2289\" data-end=\"2292\" />OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</li>\r\n<li data-start=\"2340\" data-end=\"2430\"><strong data-start=\"2342\" data-end=\"2369\">Safety &amp; EMC Standards:</strong><br data-start=\"2369\" data-end=\"2372\" />IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2442\" data-end=\"2486\">Environmental &amp; Physical Characteristics<br /><br /></strong>\r\n<ul data-start=\"2487\" data-end=\"2880\">\r\n<li data-start=\"2487\" data-end=\"2560\"><strong data-start=\"2489\" data-end=\"2521\">Operating Temperature Range:</strong>&#160;-40&#176;C to +60&#176;C (derating above 45&#176;C)</li>\r\n<li data-start=\"2561\" data-end=\"2585\"><strong data-start=\"2563\" data-end=\"2576\">Humidity:</strong>&#160;0&#8211;100%</li>\r\n<li data-start=\"2586\" data-end=\"2617\"><strong data-start=\"2588\" data-end=\"2609\">Maximum Altitude:</strong>&#160;2000m</li>\r\n<li data-start=\"2618\" data-end=\"2648\"><strong data-start=\"2620\" data-end=\"2636\">Noise Level:</strong>&#160;&#8804;55 dB(A)</li>\r\n<li data-start=\"2649\" data-end=\"2705\"><strong data-start=\"2651\" data-end=\"2670\">Cooling Method:</strong>&#160;<span>Intelligent Air Cooling</span></li>\r\n<li data-start=\"2706\" data-end=\"2773\"><strong data-start=\"2708\" data-end=\"2733\">IP Protection Rating:</strong>&#160;IP65 (dust-tight and water-resistant)</li>\r\n<li data-start=\"2774\" data-end=\"2856\"><strong data-start=\"2776\" data-end=\"2803\">Dimensions (W &#215; H &#215; D):</strong>&#160;408 &#215; 638 &#215; 237 mm (excluding connectors/brackets)</li>\r\n<li data-start=\"2857\" data-end=\"2880\"><strong data-start=\"2859\" data-end=\"2870\">Weight:</strong>&#160;30.5 kg<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2892\" data-end=\"2921\">Interface &amp; Communication<br /><br /></strong>\r\n<ul data-start=\"2922\" data-end=\"3039\">\r\n<li data-start=\"2922\" data-end=\"2992\"><strong data-start=\"2924\" data-end=\"2947\">Monitoring Options:</strong>&#160;GPRS, Wi-Fi, Bluetooth, 4G, LAN (optional)</li>\r\n<li data-start=\"2993\" data-end=\"3039\"><strong data-start=\"2995\" data-end=\"3019\">Communication Ports:</strong>&#160;RS485, RS232, CAN</li>\r\n</ul>\r\n</li>\r\n</ul>\r\n<p><strong>The Deye SUN-12K-SG01HP3-EU is a three-phase hybrid inverter designed for intelligent energy management. With dual MPPTs, high-voltage battery support, and robust protection features, it ensures efficient solar integration, seamless backup power, and long-term reliability for residential and small commercial applications.</strong></p>', 'The Deye SUN-12K-SG01HP3-EU-AM2 is a high-performance three-phase hybrid inverter tailored for residential and light commercial applications. Designed to seamlessly integrate solar energy, high-voltage lithium-ion battery storage, and grid power, this inverter enables smart and efficient energy management. With dual MPPTs, a wide PV voltage range of 150&#8211;850V, and support for up to 12000W of PV input, it maximizes solar harvest and system flexibility. Its advanced protection features, natural cooling system, and IP65-rated housing ensure reliable operation under various environmental conditions. Whether for new installations or retrofitting existing systems, the SUN-12K-SG01HP3-EU-AM2 offers a compact, robust, and future-ready energy solution.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\r\n\r\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\r\n\r\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\r\n\r\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\r\n\r\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\r\n\r\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\r\n\r\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(542, '<table selecttype=\"cells\">\r\n<tbody>\r\n<tr height=\"24\">\r\n<td width=\"273\"><strong>Battery Input Data</strong></td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Battery Type</td>\r\n<td width=\"800\">Lithium-ion</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Battery Voltage Range(V)</td>\r\n<td width=\"800\">160-700</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max.Charging Current(A)</td>\r\n<td width=\"500\">37</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max.Discharging Current(A)</td>\r\n<td width=\"500\">37</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Charging Strategy for Li-ion Battery</td>\r\n<td width=\"800\">Self-adaption to BMS</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Number of battery input</td>\r\n<td width=\"800\">1</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>PV String Input Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr>\r\n<td>Max. PV Access Power (W)</td>\r\n<td>24000</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max. PV Input Power (W)</td>\r\n<td width=\"100\">19200</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max. PV Input Voltage (V)</td>\r\n<td width=\"800\">1000</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Start-up Voltage&#65288;V&#65289;</td>\r\n<td width=\"800\">180</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">MPPT Voltage Range&#65288;V&#65289;</td>\r\n<td width=\"800\">150-850</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated DC Input Voltage(V)</td>\r\n<td width=\"700\">600</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max Input Short-Circuit Current&#65288;A&#65289;</td>\r\n<td width=\"200\">39+30</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max Operating PV Input Current&#65288;A&#65289;</td>\r\n<td width=\"200\">26+20</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">No.of MPP Trackers/No.of String Per MPP Tracker</td>\r\n<td width=\"200\">2/2+1</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>AC Input/Output Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated AC Input/Output Active Power&#65288;W&#65289;</td>\r\n<td width=\"100\">12000</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max AC Input/Output Apparent Power &#65288;VA&#65289;</td>\r\n<td width=\"100\">13200</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Peak Power (off-grid)&#65288;W&#65289;</td>\r\n<td width=\"800\">1.5 times of rated power,10s</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated AC Input/Output Current&#65288;A&#65289;</td>\r\n<td width=\"100\">18.2/17.4</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max AC Input/Output Current&#65288;A&#65289;</td>\r\n<td width=\"100\">20/19.2</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max Continuous AC Passthrough (grid to load)&#65288;A&#65289;</td>\r\n<td width=\"400\">80</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated Input/Output Voltage/Range(V)</td>\r\n<td width=\"800\">220/380V&#65292;230/400V 0.85Un-1.1Un</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Grid Connection Form</td>\r\n<td width=\"800\">3L+N+PE</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated Input/Output Grid Frequency/Range</td>\r\n<td width=\"800\">50Hz/45Hz-55Hz&#160; 60Hz/55Hz-65Hz</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Power Factor Adjustment Range</td>\r\n<td width=\"800\">0.8 leading to 0.8 lagging</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Total Current Harmonic Distortion THDi</td>\r\n<td width=\"800\">&lt;3% (of nominal power)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">DC Injection Current</td>\r\n<td width=\"800\">&lt;0.5%ln</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Efficiency</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max Efficiency</td>\r\n<td width=\"800\">97.6%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Euro Efficiency</td>\r\n<td width=\"800\">97.0%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">MPPT Efficiency</td>\r\n<td width=\"800\">&#65310;99%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Equipment Protection</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Integrated</td>\r\n<td width=\"800\">\r\n<div>DC Reverse Polarity Protection, AC Output Overcurrent Protection, Thermal Protection, AC Output Overvoltage</div>\r\n<div>Protection,&#160;AC Output Short Circuit Protection, DC Component Monitoring, Arc Fault Circuit Interrupter (optional),</div>\r\n<div>Anti-islanding Protection, DC Switch,&#160;Insulation Impedance Detection, Residual Current Detection</div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Surge Protection Level</td>\r\n<td width=\"800\">TYPE II(DC),TYPE II(AC)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Interface</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Communication Interface</td>\r\n<td width=\"800\">RS485/RS232/CAN</td>\r\n</tr>\r\n<tr>\r\n<td>Monitor Mode</td>\r\n<td>GPRS/WIFI/Bluetooth/4G/LAN(optional)</td>\r\n</tr>\r\n<tr>\r\n<td>LCD/LED Display</td>\r\n<td>LCD</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>General Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Operating Temperature Range</td>\r\n<td width=\"800\">-40 to +60&#8451;, &gt;45&#8451; Derating</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Permissible Ambient Humidity</td>\r\n<td width=\"800\">0-100%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Permissible Altitude</td>\r\n<td width=\"800\">2000m</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Noise</td>\r\n<td width=\"800\">&#8804; 55 dB(A)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Ingress Protection(IP) Rating</td>\r\n<td width=\"800\">IP 65</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Inverter Topology</td>\r\n<td width=\"800\">Non-Isolated</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Over Voltage Category</td>\r\n<td width=\"800\">OVC II(DC),OVC III(AC)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Cabinet size&#65288;W*H*D&#65289;[mm]</td>\r\n<td width=\"800\">408*638*237&#65288;Excluding connectors and brackets&#65289;</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Weight[kg]</td>\r\n<td width=\"800\">30.5</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Warranty</td>\r\n<td width=\"800\">\r\n<div>5 Years/10 Years</div>\r\n<div>the Warranty Period Depends the Final Installation Site of Inverter, More Info Please Refer to Warranty Policy</div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Type Of Cooling</td>\r\n<td width=\"600\">Intelligent air cooling</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Grid Regulation</td>\r\n<td width=\"800\">\r\n<p>IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</p>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Safety EMC/Standard</td>\r\n<td width=\"800\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2<br /><br /></td>\r\n</tr>\r\n</tbody>\r\n</table>', 3, 'SUN-12K-SG01HP3-EU | Three-Phase Hybrid Inverter | 2 MPPT | HV Battery Supported', '<p>The Deye SUN-12K-SG01HP3-EU is a powerful three-phase hybrid inverter designed for high-performance solar energy systems. Equipped with 2 MPPTs and high-voltage battery support, it ensures exceptional efficiency and flexibility. This inverter supports 100% unbalanced output, allowing each phase to independently deliver up to 50% of the rated power&#8212;ideal for uneven load distribution. Thanks to its AC coupling capability, it can seamlessly retrofit into existing PV systems, enhancing performance without requiring a full overhaul. It allows for parallel operation of up to 10 units in both on-grid and off-grid modes and supports multiple batteries in parallel, offering excellent scalability. With a maximum charging and discharging current of 37A, it maintains efficient and reliable energy flow. Additionally, users can configure six charging and discharging time periods, optimizing battery use based on energy demand and tariff rates. The inverter is also compatible with diesel generators, ensuring dependable backup power in areas with unstable grid supply.</p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-005.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" /></p>\r\n<p></p>\r\n<h3>Key Features</h3>\r\n<ul>\r\n<li data-start=\"0\" data-end=\"152\">\r\n<p data-start=\"2\" data-end=\"152\"><strong data-start=\"2\" data-end=\"29\" data-is-only-node=\"\">100% Unbalanced Output:</strong>&#160;Each phase can operate independently with up to 50% of the rated power, ensuring flexibility for varied load conditions.</p>\r\n</li>\r\n<li data-start=\"153\" data-end=\"296\">\r\n<p data-start=\"155\" data-end=\"296\"><strong data-start=\"155\" data-end=\"184\" data-is-only-node=\"\">AC Coupling for Retrofit:</strong>&#160;Easily integrates into existing solar systems, enabling efficient performance upgrades without major changes.</p>\r\n</li>\r\n<li data-start=\"297\" data-end=\"468\">\r\n<p data-start=\"299\" data-end=\"468\"><strong data-start=\"299\" data-end=\"331\" data-is-only-node=\"\">Scalable Parallel Operation:</strong>&#160;Supports up to 10 units in parallel for both on-grid and off-grid modes, with compatibility for multiple parallel battery connections.</p>\r\n</li>\r\n<li data-start=\"469\" data-end=\"605\">\r\n<p data-start=\"471\" data-end=\"605\"><strong data-start=\"471\" data-end=\"516\" data-is-only-node=\"\">Max. Charging/Discharging Current of 37A:</strong>&#160;Ensures stable and efficient energy flow for both charging and discharging operations.</p>\r\n</li>\r\n<li data-start=\"606\" data-end=\"731\">\r\n<p data-start=\"608\" data-end=\"731\"><strong data-start=\"608\" data-end=\"641\" data-is-only-node=\"\">High Voltage Battery Support:</strong>&#160;Utilizes high-voltage batteries to increase system efficiency and reduce energy losses.</p>\r\n</li>\r\n<li data-start=\"732\" data-end=\"899\">\r\n<p data-start=\"734\" data-end=\"899\"><strong data-start=\"734\" data-end=\"768\" data-is-only-node=\"\">Time-based Battery Management:</strong>&#160;Allows for six configurable time periods for optimized battery charging and discharging based on energy consumption and tariffs.</p>\r\n</li>\r\n<li data-start=\"900\" data-end=\"1059\" data-is-last-node=\"\">\r\n<p data-start=\"902\" data-end=\"1059\" data-is-last-node=\"\"><strong data-start=\"902\" data-end=\"937\" data-is-only-node=\"\">Diesel Generator Compatibility:</strong>&#160;Capable of storing energy from diesel generators, offering reliable backup in areas with unstable or limited grid access.</p>\r\n</li>\r\n</ul>\r\n<p></p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" /></p>\r\n<p></p>\r\n<h3>Technical Specifications</h3>\r\n<ul>\r\n<li><strong data-start=\"283\" data-end=\"305\">Battery Input Data<br /><br /></strong>\r\n<ul data-start=\"306\" data-end=\"596\">\r\n<li data-start=\"306\" data-end=\"384\"><strong data-start=\"308\" data-end=\"334\">Battery Compatibility:</strong>&#160;Lithium-ion batteries (lead-acid not supported)</li>\r\n<li data-start=\"385\" data-end=\"424\"><strong data-start=\"387\" data-end=\"413\">Battery Voltage Range:</strong>&#160;160&#8211;700V</li>\r\n<li data-start=\"425\" data-end=\"471\"><strong data-start=\"427\" data-end=\"465\">Max. Charging/Discharging Current:</strong>&#160;37A</li>\r\n<li data-start=\"472\" data-end=\"506\"><strong data-start=\"474\" data-end=\"492\">Battery Input:</strong>&#160;Single port</li>\r\n<li data-start=\"507\" data-end=\"596\"><strong data-start=\"509\" data-end=\"531\">BMS Communication:</strong>&#160;Self-adaptive, ensuring compatibility with various BMS protocols<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"608\" data-end=\"632\">PV String Input Data<br /><br /></strong>\r\n<ul data-start=\"633\" data-end=\"1003\">\r\n<li data-start=\"633\" data-end=\"670\"><strong data-start=\"635\" data-end=\"660\">Max. PV Access Power:</strong>&#160;24000W</li>\r\n<li data-start=\"671\" data-end=\"707\"><strong data-start=\"673\" data-end=\"697\">Max. PV Input Power:</strong>&#160;19200W</li>\r\n<li data-start=\"708\" data-end=\"744\"><strong data-start=\"710\" data-end=\"736\">Max. PV Input Voltage:</strong>&#160;1000V</li>\r\n<li data-start=\"745\" data-end=\"781\"><strong data-start=\"747\" data-end=\"770\">MPPT Voltage Range:</strong>&#160;150&#8211;850V</li>\r\n<li data-start=\"782\" data-end=\"812\"><strong data-start=\"784\" data-end=\"805\">Start-up Voltage:</strong>&#160;180V</li>\r\n<li data-start=\"813\" data-end=\"849\"><strong data-start=\"815\" data-end=\"842\">Rated DC Input Voltage:</strong>&#160;600V</li>\r\n<li data-start=\"850\" data-end=\"903\"><strong data-start=\"852\" data-end=\"891\">Number of MPPTs / Strings per MPPT:</strong>&#160;2 / (1+1)</li>\r\n<li data-start=\"904\" data-end=\"954\"><strong data-start=\"906\" data-end=\"942\">Max. Operating PV Input Current:</strong>&#160;26A + 20A</li>\r\n<li data-start=\"955\" data-end=\"1003\"><strong data-start=\"957\" data-end=\"991\">Max. PV Short-Circuit Current:</strong>&#160;39A + 30A<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1015\" data-end=\"1041\">AC Input / Output Data<br /><br /></strong>\r\n<ul data-start=\"1042\" data-end=\"1623\">\r\n<li data-start=\"1042\" data-end=\"1084\"><strong data-start=\"1044\" data-end=\"1076\">Rated AC Input/Output Power:</strong>&#160;12000W</li>\r\n<li data-start=\"1085\" data-end=\"1120\"><strong data-start=\"1087\" data-end=\"1111\">Max. Apparent Power:</strong>&#160;13200A</li>\r\n<li data-start=\"1121\" data-end=\"1185\"><strong data-start=\"1123\" data-end=\"1149\">Peak Power (Off-Grid):</strong>&#160;1.5&#215; rated power (for 10 seconds)</li>\r\n<li data-start=\"1186\" data-end=\"1238\"><strong data-start=\"1188\" data-end=\"1222\">Rated AC Input/Output Current:</strong>&#160;18.2/17.4</li>\r\n<li data-start=\"1239\" data-end=\"1290\"><strong data-start=\"1241\" data-end=\"1274\">Max. AC Input/Output Current:</strong>&#160;20/19.2</li>\r\n<li data-start=\"1291\" data-end=\"1349\"><strong data-start=\"1293\" data-end=\"1343\">Max. Continuous AC Passthrough (Grid to Load):</strong>&#160;80A</li>\r\n<li data-start=\"1350\" data-end=\"1401\"><strong data-start=\"1352\" data-end=\"1370\">Rated Voltage:</strong>&#160;220/380V, 230/400V (3L+N+PE)</li>\r\n<li data-start=\"1402\" data-end=\"1462\"><strong data-start=\"1404\" data-end=\"1429\">Grid Frequency Range:</strong>&#160;50Hz (45&#8211;55Hz), 60Hz (55&#8211;65Hz)</li>\r\n<li data-start=\"1463\" data-end=\"1522\"><strong data-start=\"1465\" data-end=\"1493\">Power Factor Adjustment:</strong>&#160;0.8 leading to 0.8 lagging</li>\r\n<li data-start=\"1523\" data-end=\"1568\"><strong data-start=\"1525\" data-end=\"1562\">Total Harmonic Distortion (THDi):</strong>&#160;&lt;3%</li>\r\n<li data-start=\"1569\" data-end=\"1623\"><strong data-start=\"1571\" data-end=\"1596\">DC Injection Current:</strong>&#160;&lt;0.5% of nominal current<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1635\" data-end=\"1649\">Efficiency<br /><br /></strong>\r\n<ul data-start=\"1650\" data-end=\"1745\">\r\n<li data-start=\"1650\" data-end=\"1680\"><strong data-start=\"1652\" data-end=\"1672\">Max. Efficiency:</strong>&#160;97.6%</li>\r\n<li data-start=\"1681\" data-end=\"1715\"><strong data-start=\"1683\" data-end=\"1707\">European Efficiency:</strong>&#160;97.0%</li>\r\n<li data-start=\"1716\" data-end=\"1745\"><strong data-start=\"1718\" data-end=\"1738\">MPPT Efficiency:</strong>&#160;&gt;99%<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"1783\" data-end=\"1810\">Integrated Protections:<br /><br /></strong><strong data-start=\"2073\" data-end=\"2094\"></strong></li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"2073\" data-end=\"2094\">Surge Protection:</strong>&#160;Type II (both DC &amp; AC sides)<br /><br />\r\n<ul data-start=\"1815\" data-end=\"2070\">\r\n<li data-start=\"1815\" data-end=\"1838\">DC reverse polarity</li>\r\n<li data-start=\"1841\" data-end=\"1866\">AC output overcurrent</li>\r\n<li data-start=\"1869\" data-end=\"1887\">AC overvoltage</li>\r\n<li data-start=\"1890\" data-end=\"1907\">Short circuit</li>\r\n<li data-start=\"1910\" data-end=\"1932\">Thermal protection</li>\r\n<li data-start=\"1935\" data-end=\"1965\">Residual current detection</li>\r\n<li data-start=\"1968\" data-end=\"2004\">Insulation resistance monitoring</li>\r\n<li data-start=\"2007\" data-end=\"2040\">Optional arc fault protection</li>\r\n<li data-start=\"2043\" data-end=\"2070\">DC component monitoring<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2128\" data-end=\"2142\">DC Switch:</strong>&#160;Included<br /><br /></li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2165\" data-end=\"2191\">Standards &amp; Compliance<br /><br /></strong>\r\n<ul data-start=\"2192\" data-end=\"2430\">\r\n<li data-start=\"2192\" data-end=\"2339\"><strong data-start=\"2194\" data-end=\"2214\">Grid Compliance:</strong><br data-start=\"2214\" data-end=\"2217\" />IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,<br data-start=\"2289\" data-end=\"2292\" />OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</li>\r\n<li data-start=\"2340\" data-end=\"2430\"><strong data-start=\"2342\" data-end=\"2369\">Safety &amp; EMC Standards:</strong><br data-start=\"2369\" data-end=\"2372\" />IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2442\" data-end=\"2486\">Environmental &amp; Physical Characteristics<br /><br /></strong>\r\n<ul data-start=\"2487\" data-end=\"2880\">\r\n<li data-start=\"2487\" data-end=\"2560\"><strong data-start=\"2489\" data-end=\"2521\">Operating Temperature Range:</strong>&#160;-40&#176;C to +60&#176;C (derating above 45&#176;C)</li>\r\n<li data-start=\"2561\" data-end=\"2585\"><strong data-start=\"2563\" data-end=\"2576\">Humidity:</strong>&#160;0&#8211;100%</li>\r\n<li data-start=\"2586\" data-end=\"2617\"><strong data-start=\"2588\" data-end=\"2609\">Maximum Altitude:</strong>&#160;2000m</li>\r\n<li data-start=\"2618\" data-end=\"2648\"><strong data-start=\"2620\" data-end=\"2636\">Noise Level:</strong>&#160;&#8804;55 dB(A)</li>\r\n<li data-start=\"2649\" data-end=\"2705\"><strong data-start=\"2651\" data-end=\"2670\">Cooling Method:</strong>&#160;Intelligent Air Cooling</li>\r\n<li data-start=\"2706\" data-end=\"2773\"><strong data-start=\"2708\" data-end=\"2733\">IP Protection Rating:</strong>&#160;IP65 (dust-tight and water-resistant)</li>\r\n<li data-start=\"2774\" data-end=\"2856\"><strong data-start=\"2776\" data-end=\"2803\">Dimensions (W &#215; H &#215; D):</strong>&#160;408 &#215; 638 &#215; 237 mm (excluding connectors/brackets)</li>\r\n<li data-start=\"2857\" data-end=\"2880\"><strong data-start=\"2859\" data-end=\"2870\">Weight:</strong>&#160;30.5 kg<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2892\" data-end=\"2921\">Interface &amp; Communication<br /><br /></strong>\r\n<ul data-start=\"2922\" data-end=\"3039\">\r\n<li data-start=\"2922\" data-end=\"2992\"><strong data-start=\"2924\" data-end=\"2947\">Monitoring Options:</strong>&#160;GPRS, Wi-Fi, Bluetooth, 4G, LAN (optional)</li>\r\n<li data-start=\"2993\" data-end=\"3039\"><strong data-start=\"2995\" data-end=\"3019\">Communication Ports:</strong>&#160;RS485, RS232, CAN</li>\r\n</ul>\r\n</li>\r\n</ul>\r\n<p><strong>The Deye SUN-12K-SG01HP3-EU is a three-phase hybrid inverter designed for intelligent energy management. With dual MPPTs, high-voltage battery support, and robust protection features, it ensures efficient solar integration, seamless backup power, and long-term reliability for residential and small commercial applications.</strong></p>', 'The Deye SUN-12K-SG01HP3-EU-AM2 is a high-performance three-phase hybrid inverter tailored for residential and light commercial applications. Designed to seamlessly integrate solar energy, high-voltage lithium-ion battery storage, and grid power, this inverter enables smart and efficient energy management. With dual MPPTs, a wide PV voltage range of 150&#8211;850V, and support for up to 12000W of PV input, it maximizes solar harvest and system flexibility. Its advanced protection features, natural cooling system, and IP65-rated housing ensure reliable operation under various environmental conditions. Whether for new installations or retrofitting existing systems, the SUN-12K-SG01HP3-EU-AM2 offers a compact, robust, and future-ready energy solution.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\r\n\r\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\r\n\r\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\r\n\r\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\r\n\r\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\r\n\r\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\r\n\r\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', '');
INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(543, '<table selecttype=\"cells\">\r\n<tbody>\r\n<tr height=\"24\">\r\n<td width=\"273\"><strong>Battery Input Data</strong></td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Battery Type</span></td>\r\n<td width=\"800\"><span>Lithium-ion</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Battery Voltage Range(V)</span></td>\r\n<td width=\"800\"><span>160-700</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max.Charging Current(A)</span></td>\r\n<td width=\"500\"><span>37</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max.Discharging Current(A)</span></td>\r\n<td width=\"500\"><span>37</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Charging Strategy for Li-ion Battery</span></td>\r\n<td width=\"800\"><span>Self-adaption to BMS</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Number of battery input</span></td>\r\n<td width=\"800\"><span>1</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>PV String Input Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<div><span>Max. PV Access Power (W)</span></div>\r\n</td>\r\n<td><span>30000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max. PV Input Power (W)</span></td>\r\n<td width=\"100\"><span>24000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max. PV Input Voltage (V)</span></td>\r\n<td width=\"800\"><span>1000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Start-up Voltage&#65288;V&#65289;</span></td>\r\n<td width=\"800\"><span>180</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>MPPT Voltage Range&#65288;V&#65289;</span></td>\r\n<td width=\"800\"><span>150-850</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Rated DC Input Voltage(V)</span></td>\r\n<td width=\"700\"><span>600</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max Input Short-Circuit Current&#65288;A&#65289;</span></td>\r\n<td width=\"200\"><span>39+30</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max Operating PV Input Current&#65288;A&#65289;</span></td>\r\n<td width=\"200\"><span>26+20</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>No.of MPP Trackers/No.of String Per MPP Tracker</span></td>\r\n<td width=\"200\"><span>2/2+1</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>AC Input/Output Data</span></td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Rated AC Input/Output Active Power&#65288;W&#65289;</span></td>\r\n<td width=\"100\"><span>15000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max AC Input/Output Apparent Power &#65288;VA&#65289;</span></td>\r\n<td width=\"100\"><span>16500</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Peak Power (off-grid)&#65288;W&#65289;</span></td>\r\n<td width=\"800\"><span>1.5 times of rated power,10s</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Rated AC Input/Output Current&#65288;A&#65289;</span></td>\r\n<td width=\"100\"><span>22.8/21.8</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max AC Input/Output Current&#65288;A&#65289;</span></td>\r\n<td width=\"100\"><span>25/24</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max Continuous AC Passthrough (grid to load)&#65288;A&#65289;</span></td>\r\n<td width=\"400\"><span>80</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Rated Input/Output Voltage/Range(V)</span></td>\r\n<td width=\"800\"><span>220/380V&#65292;230/400V 0.85Un-1.1Un</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Grid Connection Form</span></td>\r\n<td width=\"800\"><span>3L+N+PE</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Rated Input/Output Grid Frequency/Range</span></td>\r\n<td width=\"800\"><span>50Hz/45Hz-55Hz&#160; 60Hz/55Hz-65Hz</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Power Factor Adjustment Range</span></td>\r\n<td width=\"800\"><span>0.8 leading to 0.8 lagging</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Total Current Harmonic Distortion THDi</span></td>\r\n<td width=\"800\"><span>&lt;3% (of nominal power)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>DC Injection Current</span></td>\r\n<td width=\"800\"><span>&lt;0.5%ln</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Efficiency</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max Efficiency</span></td>\r\n<td width=\"800\"><span>97.6%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Euro Efficiency</span></td>\r\n<td width=\"800\"><span>97.0%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>MPPT Efficiency</span></td>\r\n<td width=\"800\"><span>&#65310;99%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Equipment Protection</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<div><span>Integrated</span></div>\r\n</td>\r\n<td width=\"800\">\r\n<div>\r\n<div><span>DC Reverse Polarity Protection, AC Output Overcurrent Protection, Thermal Protection, AC Output Overvoltage</span></div>\r\n<div><span>Protection,&#160;</span><span>AC Output Short Circuit Protection, DC Component Monitoring, Arc Fault Circuit Interrupter (optional),</span></div>\r\n<div><span>Anti-islanding Protection, DC Switch,&#160;</span><span>Insulation Impedance Detection, Residual Current Detection</span></div>\r\n</div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Surge Protection Level</span></td>\r\n<td width=\"800\"><span>TYPE II(DC),TYPE II(AC)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Interface</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<div>\r\n<div><span>Communication Interface</span></div>\r\n</div>\r\n</td>\r\n<td width=\"800\">\r\n<div><span>RS485/RS232/CAN</span></div>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<div><span>Monitor Mode</span></div>\r\n</td>\r\n<td>\r\n<div><span>GPRS/WIFI/Bluetooth/4G/LAN(optional)</span></div>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<div><span>LCD/LED Display</span></div>\r\n</td>\r\n<td>\r\n<div><span>LCD</span></div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>General Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Operating Temperature Range</span></td>\r\n<td width=\"800\">\r\n<div><span>-40 to +60&#8451;, &gt;45&#8451; Derating</span></div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Permissible Ambient Humidity</span></td>\r\n<td width=\"800\"><span>0-100%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Permissible Altitude</span></td>\r\n<td width=\"800\"><span>2000m</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Noise</span></td>\r\n<td width=\"800\"><span>&#8804; 55 dB(A)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Ingress Protection(IP) Rating</span></td>\r\n<td width=\"800\"><span>IP 65</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Inverter Topology</span></td>\r\n<td width=\"800\"><span>Non-Isolated</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Over Voltage Category</span></td>\r\n<td width=\"800\"><span>OVC II(DC),OVC III(AC)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Cabinet size&#65288;W*H*D&#65289;[mm]</span></td>\r\n<td width=\"800\"><span>408*638*237&#65288;Excluding connectors and brackets&#65289;</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Weight[kg]</span></td>\r\n<td width=\"800\"><span>30.5</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Warranty</span></td>\r\n<td width=\"800\">\r\n<div><span>5 Years/10 Years</span></div>\r\n<div><span>the Warranty Period Depends the Final Installation Site of Inverter, More Info Please Refer to Warranty Policy</span></div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Type Of Cooling</span></td>\r\n<td width=\"600\"><span>Intelligent air cooling</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Grid Regulation</span></td>\r\n<td width=\"800\">\r\n<p><span>IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</span></p>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Safety EMC/Standard</span></td>\r\n<td width=\"800\"><span>IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</span></td>\r\n</tr>\r\n</tbody>\r\n</table>', 2, 'SUN-15K-SG01HP3-EU | Three-Phase Hybrid Inverter | 2 MPPT | HV Battery Supported', '<p>The Deye SUN-15K-SG01HP3-EU is a powerful three-phase hybrid inverter designed for high-performance solar energy systems. Equipped with 2 MPPTs and high-voltage battery support, it ensures exceptional efficiency and flexibility. This inverter supports 100% unbalanced output, allowing each phase to independently deliver up to 50% of the rated power&#8212;ideal for uneven load distribution. Thanks to its AC coupling capability, it can seamlessly retrofit into existing PV systems, enhancing performance without requiring a full overhaul. It allows for parallel operation of up to 10 units in both on-grid and off-grid modes and supports multiple batteries in parallel, offering excellent scalability. With a maximum charging and discharging current of 37A, it maintains efficient and reliable energy flow. Additionally, users can configure six charging and discharging time periods, optimizing battery use based on energy demand and tariff rates. The inverter is also compatible with diesel generators, ensuring dependable backup power in areas with unstable grid supply.</p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-005.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\r\n<p></p>\r\n<h3>Key Features</h3>\r\n<ul>\r\n<li data-start=\"0\" data-end=\"152\">\r\n<p data-start=\"2\" data-end=\"152\"><strong data-start=\"2\" data-end=\"29\" data-is-only-node=\"\">100% Unbalanced Output:</strong>&#160;Each phase can operate independently with up to 50% of the rated power, ensuring flexibility for varied load conditions.</p>\r\n</li>\r\n<li data-start=\"153\" data-end=\"296\">\r\n<p data-start=\"155\" data-end=\"296\"><strong data-start=\"155\" data-end=\"184\" data-is-only-node=\"\">AC Coupling for Retrofit:</strong>&#160;Easily integrates into existing solar systems, enabling efficient performance upgrades without major changes.</p>\r\n</li>\r\n<li data-start=\"297\" data-end=\"468\">\r\n<p data-start=\"299\" data-end=\"468\"><strong data-start=\"299\" data-end=\"331\" data-is-only-node=\"\">Scalable Parallel Operation:</strong>&#160;Supports up to 10 units in parallel for both on-grid and off-grid modes, with compatibility for multiple parallel battery connections.</p>\r\n</li>\r\n<li data-start=\"469\" data-end=\"605\">\r\n<p data-start=\"471\" data-end=\"605\"><strong data-start=\"471\" data-end=\"516\" data-is-only-node=\"\">Max. Charging/Discharging Current of 37A:</strong>&#160;Ensures stable and efficient energy flow for both charging and discharging operations.</p>\r\n</li>\r\n<li data-start=\"606\" data-end=\"731\">\r\n<p data-start=\"608\" data-end=\"731\"><strong data-start=\"608\" data-end=\"641\" data-is-only-node=\"\">High Voltage Battery Support:</strong>&#160;Utilizes high-voltage batteries to increase system efficiency and reduce energy losses.</p>\r\n</li>\r\n<li data-start=\"732\" data-end=\"899\">\r\n<p data-start=\"734\" data-end=\"899\"><strong data-start=\"734\" data-end=\"768\" data-is-only-node=\"\">Time-based Battery Management:</strong>&#160;Allows for six configurable time periods for optimized battery charging and discharging based on energy consumption and tariffs.</p>\r\n</li>\r\n<li data-start=\"900\" data-end=\"1059\" data-is-last-node=\"\">\r\n<p data-start=\"902\" data-end=\"1059\" data-is-last-node=\"\"><strong data-start=\"902\" data-end=\"937\" data-is-only-node=\"\">Diesel Generator Compatibility:</strong>&#160;Capable of storing energy from diesel generators, offering reliable backup in areas with unstable or limited grid access.</p>\r\n</li>\r\n</ul>\r\n<p></p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\r\n<p></p>\r\n<h3>Technical Specifications</h3>\r\n<ul>\r\n<li><strong data-start=\"283\" data-end=\"305\">Battery Input Data<br /><br /></strong>\r\n<ul data-start=\"306\" data-end=\"596\">\r\n<li data-start=\"306\" data-end=\"384\"><strong data-start=\"308\" data-end=\"334\">Battery Compatibility:</strong>&#160;Lithium-ion batteries (lead-acid not supported)</li>\r\n<li data-start=\"385\" data-end=\"424\"><strong data-start=\"387\" data-end=\"413\">Battery Voltage Range:</strong>&#160;160&#8211;700V</li>\r\n<li data-start=\"425\" data-end=\"471\"><strong data-start=\"427\" data-end=\"465\">Max. Charging/Discharging Current:</strong>&#160;37A</li>\r\n<li data-start=\"472\" data-end=\"506\"><strong data-start=\"474\" data-end=\"492\">Battery Input:</strong>&#160;Single port</li>\r\n<li data-start=\"507\" data-end=\"596\"><strong data-start=\"509\" data-end=\"531\">BMS Communication:</strong>&#160;Self-adaptive, ensuring compatibility with various BMS protocols<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"608\" data-end=\"632\">PV String Input Data<br /><br /></strong>\r\n<ul data-start=\"633\" data-end=\"1003\">\r\n<li data-start=\"633\" data-end=\"670\"><strong data-start=\"635\" data-end=\"660\">Max. PV Access Power:</strong>&#160;<span>30000</span>W</li>\r\n<li data-start=\"671\" data-end=\"707\"><strong data-start=\"673\" data-end=\"697\">Max. PV Input Power:</strong>&#160;<span>24000</span>W</li>\r\n<li data-start=\"708\" data-end=\"744\"><strong data-start=\"710\" data-end=\"736\">Max. PV Input Voltage:</strong>&#160;1000V</li>\r\n<li data-start=\"745\" data-end=\"781\"><strong data-start=\"747\" data-end=\"770\">MPPT Voltage Range:</strong>&#160;150&#8211;850V</li>\r\n<li data-start=\"782\" data-end=\"812\"><strong data-start=\"784\" data-end=\"805\">Start-up Voltage:</strong>&#160;180V</li>\r\n<li data-start=\"813\" data-end=\"849\"><strong data-start=\"815\" data-end=\"842\">Rated DC Input Voltage:</strong>&#160;600V</li>\r\n<li data-start=\"850\" data-end=\"903\"><strong data-start=\"852\" data-end=\"891\">Number of MPPTs / Strings per MPPT:</strong>&#160;2 / (1+1)</li>\r\n<li data-start=\"904\" data-end=\"954\"><strong data-start=\"906\" data-end=\"942\">Max. Operating PV Input Current:</strong>&#160;<span>26A + 20A</span></li>\r\n<li data-start=\"955\" data-end=\"1003\"><strong data-start=\"957\" data-end=\"991\">Max. PV Short-Circuit Current:</strong>&#160;39A + 30A<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1015\" data-end=\"1041\">AC Input / Output Data<br /><br /></strong>\r\n<ul data-start=\"1042\" data-end=\"1623\">\r\n<li data-start=\"1042\" data-end=\"1084\"><strong data-start=\"1044\" data-end=\"1076\">Rated AC Input/Output Power:</strong>&#160;15000W</li>\r\n<li data-start=\"1085\" data-end=\"1120\"><strong data-start=\"1087\" data-end=\"1111\">Max. Apparent Power:</strong>&#160;<span>16500</span>A</li>\r\n<li data-start=\"1121\" data-end=\"1185\"><strong data-start=\"1123\" data-end=\"1149\">Peak Power (Off-Grid):</strong>&#160;1.5&#215; rated power (for 10 seconds)</li>\r\n<li data-start=\"1186\" data-end=\"1238\"><strong data-start=\"1188\" data-end=\"1222\">Rated AC Input/Output Current:</strong>&#160;<span>22.8/21.8</span></li>\r\n<li data-start=\"1239\" data-end=\"1290\"><strong data-start=\"1241\" data-end=\"1274\">Max. AC Input/Output Current:</strong>&#160;<span>25/24</span></li>\r\n<li data-start=\"1291\" data-end=\"1349\"><strong data-start=\"1293\" data-end=\"1343\">Max. Continuous AC Passthrough (Grid to Load):</strong>&#160;80A</li>\r\n<li data-start=\"1350\" data-end=\"1401\"><strong data-start=\"1352\" data-end=\"1370\">Rated Voltage:</strong>&#160;220/380V, 230/400V (3L+N+PE)</li>\r\n<li data-start=\"1402\" data-end=\"1462\"><strong data-start=\"1404\" data-end=\"1429\">Grid Frequency Range:</strong>&#160;50Hz (45&#8211;55Hz), 60Hz (55&#8211;65Hz)</li>\r\n<li data-start=\"1463\" data-end=\"1522\"><strong data-start=\"1465\" data-end=\"1493\">Power Factor Adjustment:</strong>&#160;0.8 leading to 0.8 lagging</li>\r\n<li data-start=\"1523\" data-end=\"1568\"><strong data-start=\"1525\" data-end=\"1562\">Total Harmonic Distortion (THDi):</strong>&#160;&lt;3%</li>\r\n<li data-start=\"1569\" data-end=\"1623\"><strong data-start=\"1571\" data-end=\"1596\">DC Injection Current:</strong>&#160;&lt;0.5% of nominal current<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1635\" data-end=\"1649\">Efficiency<br /><br /></strong>\r\n<ul data-start=\"1650\" data-end=\"1745\">\r\n<li data-start=\"1650\" data-end=\"1680\"><strong data-start=\"1652\" data-end=\"1672\">Max. Efficiency:</strong>&#160;97.6%</li>\r\n<li data-start=\"1681\" data-end=\"1715\"><strong data-start=\"1683\" data-end=\"1707\">European Efficiency:</strong>&#160;97.0%</li>\r\n<li data-start=\"1716\" data-end=\"1745\"><strong data-start=\"1718\" data-end=\"1738\">MPPT Efficiency:</strong>&#160;&gt;99%<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"1783\" data-end=\"1810\">Integrated Protections:<br /><br /></strong><strong data-start=\"2073\" data-end=\"2094\"></strong></li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"2073\" data-end=\"2094\">Surge Protection:</strong>&#160;Type II (both DC &amp; AC sides)<br /><br />\r\n<ul data-start=\"1815\" data-end=\"2070\">\r\n<li data-start=\"1815\" data-end=\"1838\">DC reverse polarity</li>\r\n<li data-start=\"1841\" data-end=\"1866\">AC output overcurrent</li>\r\n<li data-start=\"1869\" data-end=\"1887\">AC overvoltage</li>\r\n<li data-start=\"1890\" data-end=\"1907\">Short circuit</li>\r\n<li data-start=\"1910\" data-end=\"1932\">Thermal protection</li>\r\n<li data-start=\"1935\" data-end=\"1965\">Residual current detection</li>\r\n<li data-start=\"1968\" data-end=\"2004\">Insulation resistance monitoring</li>\r\n<li data-start=\"2007\" data-end=\"2040\">Optional arc fault protection</li>\r\n<li data-start=\"2043\" data-end=\"2070\">DC component monitoring<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2128\" data-end=\"2142\">DC Switch:</strong>&#160;Included<br /><br /></li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2165\" data-end=\"2191\">Standards &amp; Compliance<br /><br /></strong>\r\n<ul data-start=\"2192\" data-end=\"2430\">\r\n<li data-start=\"2192\" data-end=\"2339\"><strong data-start=\"2194\" data-end=\"2214\">Grid Compliance:</strong><br data-start=\"2214\" data-end=\"2217\" />IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,<br data-start=\"2289\" data-end=\"2292\" />OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</li>\r\n<li data-start=\"2340\" data-end=\"2430\"><strong data-start=\"2342\" data-end=\"2369\">Safety &amp; EMC Standards:</strong><br data-start=\"2369\" data-end=\"2372\" />IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2442\" data-end=\"2486\">Environmental &amp; Physical Characteristics<br /><br /></strong>\r\n<ul data-start=\"2487\" data-end=\"2880\">\r\n<li data-start=\"2487\" data-end=\"2560\"><strong data-start=\"2489\" data-end=\"2521\">Operating Temperature Range:</strong>&#160;-40&#176;C to +60&#176;C (derating above 45&#176;C)</li>\r\n<li data-start=\"2561\" data-end=\"2585\"><strong data-start=\"2563\" data-end=\"2576\">Humidity:</strong>&#160;0&#8211;100%</li>\r\n<li data-start=\"2586\" data-end=\"2617\"><strong data-start=\"2588\" data-end=\"2609\">Maximum Altitude:</strong>&#160;2000m</li>\r\n<li data-start=\"2618\" data-end=\"2648\"><strong data-start=\"2620\" data-end=\"2636\">Noise Level:</strong>&#160;&#8804;55 dB(A)</li>\r\n<li data-start=\"2649\" data-end=\"2705\"><strong data-start=\"2651\" data-end=\"2670\">Cooling Method:</strong>&#160;<span>Intelligent Air Cooling</span></li>\r\n<li data-start=\"2706\" data-end=\"2773\"><strong data-start=\"2708\" data-end=\"2733\">IP Protection Rating:</strong>&#160;IP65 (dust-tight and water-resistant)</li>\r\n<li data-start=\"2774\" data-end=\"2856\"><strong data-start=\"2776\" data-end=\"2803\">Dimensions (W &#215; H &#215; D):</strong>&#160;408 &#215; 638 &#215; 237 mm (excluding connectors/brackets)</li>\r\n<li data-start=\"2857\" data-end=\"2880\"><strong data-start=\"2859\" data-end=\"2870\">Weight:</strong>&#160;30.5 kg<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2892\" data-end=\"2921\">Interface &amp; Communication<br /><br /></strong>\r\n<ul data-start=\"2922\" data-end=\"3039\">\r\n<li data-start=\"2922\" data-end=\"2992\"><strong data-start=\"2924\" data-end=\"2947\">Monitoring Options:</strong>&#160;GPRS, Wi-Fi, Bluetooth, 4G, LAN (optional)</li>\r\n<li data-start=\"2993\" data-end=\"3039\"><strong data-start=\"2995\" data-end=\"3019\">Communication Ports:</strong>&#160;RS485, RS232, CAN</li>\r\n</ul>\r\n</li>\r\n</ul>\r\n<p><strong>The Deye SUN-15K-SG01HP3-EU is a three-phase hybrid inverter designed for intelligent energy management. With dual MPPTs, high-voltage battery support, and robust protection features, it ensures efficient solar integration, seamless backup power, and long-term reliability for residential and small commercial applications.</strong></p>', 'The Deye SUN-15K-SG01HP3-EU-AM2 is a high-performance three-phase hybrid inverter tailored for residential and light commercial applications. Designed to seamlessly integrate solar energy, high-voltage lithium-ion battery storage, and grid power, this inverter enables smart and efficient energy management. With dual MPPTs, a wide PV voltage range of 150&#8211;850V, and support for up to 15000W of PV input, it maximizes solar harvest and system flexibility. Its advanced protection features, natural cooling system, and IP65-rated housing ensure reliable operation under various environmental conditions. Whether for new installations or retrofitting existing systems, the SUN-15K-SG01HP3-EU-AM2 offers a compact, robust, and future-ready energy solution.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\r\n\r\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\r\n\r\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\r\n\r\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\r\n\r\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\r\n\r\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\r\n\r\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', '');
INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(545, '<table selecttype=\"cells\">\r\n<tbody>\r\n<tr height=\"24\">\r\n<td width=\"273\"><strong>Battery Input Data</strong></td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Battery Type</span></td>\r\n<td width=\"800\"><span>Lithium-ion</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Battery Voltage Range(V)</span></td>\r\n<td width=\"800\"><span>160-700</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max.Charging Current(A)</span></td>\r\n<td width=\"100\"><span>50</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max.Discharging Current(A)</span></td>\r\n<td width=\"100\"><span>50</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Charging Strategy for Li-ion Battery</span></td>\r\n<td width=\"800\"><span>Self-adaption to BMS</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Number of battery input</span></td>\r\n<td width=\"800\"><span>1</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>PV String Input Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<div><span>Max. PV Access Power (W)</span></div>\r\n</td>\r\n<td><span>50000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max. PV Input Power (W)</span></td>\r\n<td width=\"100\"><span>40000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max. PV Input Voltage (V)</span></td>\r\n<td width=\"800\"><span>1000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Start-up Voltage&#65288;V&#65289;</span></td>\r\n<td width=\"800\"><span>180</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>MPPT Voltage Range&#65288;V&#65289;</span></td>\r\n<td width=\"800\"><span>150-850</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Rated DC Input Voltage(V)</span></td>\r\n<td width=\"100\"><span>700</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max Input Short-Circuit Current&#65288;A&#65289;</span></td>\r\n<td width=\"200\"><span>39+39</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max Operating PV Input Current&#65288;A&#65289;</span></td>\r\n<td width=\"200\"><span>26+26</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>No.of MPP Trackers/No.of String Per MPP Tracker</span></td>\r\n<td width=\"200\"><span>2/2+2</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>AC Input/Output Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Rated AC Input/Output Active Power&#65288;W&#65289;</span></td>\r\n<td width=\"100\"><span>25000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max AC Input/Output Apparent Power &#65288;VA&#65289;</span></td>\r\n<td width=\"100\"><span>27500</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Peak Power (off-grid)&#65288;W&#65289;</span></td>\r\n<td width=\"800\"><span>1.5 times of rated power,10s</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Rated AC Input/Output Current&#65288;A&#65289;</span></td>\r\n<td width=\"100\"><span>37.9/36.3</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max AC Input/Output Current&#65288;A&#65289;</span></td>\r\n<td width=\"100\"><span>41.7/39.9</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max Continuous AC Passthrough (grid to load)&#65288;A&#65289;</span></td>\r\n<td width=\"400\"><span>80</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Rated Input/Output Voltage/Range(V)</span></td>\r\n<td width=\"800\"><span>220/380V&#65292;230/400V 0.85Un-1.1Un</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Grid Connection Form</span></td>\r\n<td width=\"800\"><span>3L+N+PE</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Rated Input/Output Grid Frequency/Range</span></td>\r\n<td width=\"800\"><span>50Hz/45Hz-55Hz&#160; 60Hz/55Hz-65Hz</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Power Factor Adjustment Range</span></td>\r\n<td width=\"800\"><span>0.8 leading to 0.8 lagging</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Total Current Harmonic Distortion THDi</span></td>\r\n<td width=\"800\"><span>&lt;3% (of nominal power)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>DC Injection Current</span></td>\r\n<td width=\"800\"><span>&lt;0.5%ln</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Efficiency</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max Efficiency</span></td>\r\n<td width=\"800\"><span>97.6%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Euro Efficiency</span></td>\r\n<td width=\"800\"><span>97.0%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>MPPT Efficiency</span></td>\r\n<td width=\"800\"><span>&#65310;99%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Equipment Protection</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<div><span>Integrated</span></div>\r\n</td>\r\n<td width=\"800\">\r\n<div>\r\n<div><span>DC Reverse Polarity Protection, AC Output Overcurrent Protection, Thermal Protection, AC Output Overvoltage</span></div>\r\n<div><span>Protection,&#160;</span><span>AC Output Short Circuit Protection, DC Component Monitoring, Arc Fault Circuit Interrupter (optional),</span></div>\r\n<div><span>Anti-islanding Protection, DC Switch,&#160;</span><span>Insulation Impedance Detection, Residual Current Detection</span></div>\r\n</div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Surge Protection Level</span></td>\r\n<td width=\"800\"><span>TYPE II(DC),TYPE II(AC)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Interface</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<div>\r\n<div><span>Communication Interface</span></div>\r\n</div>\r\n</td>\r\n<td width=\"800\">\r\n<div><span>RS485/RS232/CAN</span></div>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<div><span>Monitor Mode</span></div>\r\n</td>\r\n<td>\r\n<div><span>GPRS/WIFI/Bluetooth/4G/LAN(optional)</span></div>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<div><span>LCD/LED Display</span></div>\r\n</td>\r\n<td>\r\n<div><span>LCD</span></div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>General Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Operating Temperature Range</span></td>\r\n<td width=\"800\">\r\n<div><span>-40 to +60&#8451;, &gt;45&#8451; Derating</span></div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Permissible Ambient Humidity</span></td>\r\n<td width=\"800\"><span>0-100%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Permissible Altitude</span></td>\r\n<td width=\"800\"><span>2000m</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Noise</span></td>\r\n<td width=\"800\"><span>&#8804; 55 dB(A)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Ingress Protection(IP) Rating</span></td>\r\n<td width=\"800\"><span>IP 65</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Inverter Topology</span></td>\r\n<td width=\"800\"><span>Non-Isolated</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Over Voltage Category</span></td>\r\n<td width=\"800\"><span>OVC II(DC),OVC III(AC)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Cabinet size&#65288;W*H*D&#65289;[mm]</span></td>\r\n<td width=\"800\"><span>408*638*237&#65288;Excluding connectors and brackets&#65289;</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Weight[kg]</span></td>\r\n<td width=\"800\"><span>30.5</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Warranty</span></td>\r\n<td width=\"800\">\r\n<div><span>5 Years/10 Years</span></div>\r\n<div><span>the Warranty Period Depends the Final Installation Site of Inverter, More Info Please Refer to Warranty Policy</span></div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Type Of Cooling</span></td>\r\n<td width=\"600\"><span>Intelligent air cooling</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Grid Regulation</span></td>\r\n<td width=\"800\">\r\n<p><span>IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</span></p>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Safety EMC/Standard</span></td>\r\n<td width=\"800\"><span>IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</span></td>\r\n</tr>\r\n</tbody>\r\n</table>', 2, 'SUN-25K-SG01HP3-EU | Three-Phase Hybrid Inverter | 2 MPPT | HV Battery Supported', '<p>The Deye SUN-25K-SG01HP3-EU is a powerful three-phase hybrid inverter designed for high-performance solar energy systems. Equipped with 2 MPPTs and high-voltage battery support, it ensures exceptional efficiency and flexibility. This inverter supports 100% unbalanced output, allowing each phase to independently deliver up to 50% of the rated power&#8212;ideal for uneven load distribution. Thanks to its AC coupling capability, it can seamlessly retrofit into existing PV systems, enhancing performance without requiring a full overhaul. It allows for parallel operation of up to 10 units in both on-grid and off-grid modes and supports multiple batteries in parallel, offering excellent scalability. With a maximum charging and discharging current of 50A, it maintains efficient and reliable energy flow. Additionally, users can configure six charging and discharging time periods, optimizing battery use based on energy demand and tariff rates. The inverter is also compatible with diesel generators, ensuring dependable backup power in areas with unstable grid supply.</p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-005.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\r\n<p></p>\r\n<h3>Key Features</h3>\r\n<ul>\r\n<li data-start=\"0\" data-end=\"152\">\r\n<p data-start=\"2\" data-end=\"152\"><strong data-start=\"2\" data-end=\"29\" data-is-only-node=\"\">100% Unbalanced Output:</strong>&#160;Each phase can operate independently with up to 50% of the rated power, ensuring flexibility for varied load conditions.</p>\r\n</li>\r\n<li data-start=\"153\" data-end=\"296\">\r\n<p data-start=\"155\" data-end=\"296\"><strong data-start=\"155\" data-end=\"184\" data-is-only-node=\"\">AC Coupling for Retrofit:</strong>&#160;Easily integrates into existing solar systems, enabling efficient performance upgrades without major changes.</p>\r\n</li>\r\n<li data-start=\"297\" data-end=\"468\">\r\n<p data-start=\"299\" data-end=\"468\"><strong data-start=\"299\" data-end=\"331\" data-is-only-node=\"\">Scalable Parallel Operation:</strong>&#160;Supports up to 10 units in parallel for both on-grid and off-grid modes, with compatibility for multiple parallel battery connections.</p>\r\n</li>\r\n<li data-start=\"469\" data-end=\"605\">\r\n<p data-start=\"471\" data-end=\"605\"><strong data-start=\"471\" data-end=\"516\" data-is-only-node=\"\">Max. Charging/Discharging Current of 50A:</strong>&#160;Ensures stable and efficient energy flow for both charging and discharging operations.</p>\r\n</li>\r\n<li data-start=\"606\" data-end=\"731\">\r\n<p data-start=\"608\" data-end=\"731\"><strong data-start=\"608\" data-end=\"641\" data-is-only-node=\"\">High Voltage Battery Support:</strong>&#160;Utilizes high-voltage batteries to increase system efficiency and reduce energy losses.</p>\r\n</li>\r\n<li data-start=\"732\" data-end=\"899\">\r\n<p data-start=\"734\" data-end=\"899\"><strong data-start=\"734\" data-end=\"768\" data-is-only-node=\"\">Time-based Battery Management:</strong>&#160;Allows for six configurable time periods for optimized battery charging and discharging based on energy consumption and tariffs.</p>\r\n</li>\r\n<li data-start=\"900\" data-end=\"1059\" data-is-last-node=\"\">\r\n<p data-start=\"902\" data-end=\"1059\" data-is-last-node=\"\"><strong data-start=\"902\" data-end=\"937\" data-is-only-node=\"\">Diesel Generator Compatibility:</strong>&#160;Capable of storing energy from diesel generators, offering reliable backup in areas with unstable or limited grid access.</p>\r\n</li>\r\n</ul>\r\n<p></p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\r\n<p></p>\r\n<h3>Technical Specifications</h3>\r\n<ul>\r\n<li><strong data-start=\"283\" data-end=\"305\">Battery Input Data<br /><br /></strong>\r\n<ul data-start=\"306\" data-end=\"596\">\r\n<li data-start=\"306\" data-end=\"384\"><strong data-start=\"308\" data-end=\"334\">Battery Compatibility:</strong>&#160;Lithium-ion batteries (lead-acid not supported)</li>\r\n<li data-start=\"385\" data-end=\"424\"><strong data-start=\"387\" data-end=\"413\">Battery Voltage Range:</strong>&#160;160&#8211;700V</li>\r\n<li data-start=\"425\" data-end=\"471\"><strong data-start=\"427\" data-end=\"465\">Max. Charging/Discharging Current:</strong>&#160;37A</li>\r\n<li data-start=\"472\" data-end=\"506\"><strong data-start=\"474\" data-end=\"492\">Battery Input:</strong>&#160;Single port</li>\r\n<li data-start=\"507\" data-end=\"596\"><strong data-start=\"509\" data-end=\"531\">BMS Communication:</strong>&#160;Self-adaptive, ensuring compatibility with various BMS protocols<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"608\" data-end=\"632\">PV String Input Data<br /><br /></strong>\r\n<ul data-start=\"633\" data-end=\"1003\">\r\n<li data-start=\"633\" data-end=\"670\"><strong data-start=\"635\" data-end=\"660\">Max. PV Access Power:</strong>&#160;5<span>0000</span>W</li>\r\n<li data-start=\"671\" data-end=\"707\"><strong data-start=\"673\" data-end=\"697\">Max. PV Input Power:</strong>&#160;40<span>000</span>W</li>\r\n<li data-start=\"708\" data-end=\"744\"><strong data-start=\"710\" data-end=\"736\">Max. PV Input Voltage:</strong>&#160;1000V</li>\r\n<li data-start=\"745\" data-end=\"781\"><strong data-start=\"747\" data-end=\"770\">MPPT Voltage Range:</strong>&#160;150&#8211;850V</li>\r\n<li data-start=\"782\" data-end=\"812\"><strong data-start=\"784\" data-end=\"805\">Start-up Voltage:</strong>&#160;180V</li>\r\n<li data-start=\"813\" data-end=\"849\"><strong data-start=\"815\" data-end=\"842\">Rated DC Input Voltage:</strong>&#160;600V</li>\r\n<li data-start=\"850\" data-end=\"903\"><strong data-start=\"852\" data-end=\"891\">Number of MPPTs / Strings per MPPT:</strong>&#160;2 / (1+1)</li>\r\n<li data-start=\"904\" data-end=\"954\"><strong data-start=\"906\" data-end=\"942\">Max. Operating PV Input Current:</strong>&#160;<span>26A + 26A</span></li>\r\n<li data-start=\"955\" data-end=\"1003\"><strong data-start=\"957\" data-end=\"991\">Max. PV Short-Circuit Current:</strong>&#160;39A + 39A<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1015\" data-end=\"1041\">AC Input / Output Data<br /><br /></strong>\r\n<ul data-start=\"1042\" data-end=\"1623\">\r\n<li data-start=\"1042\" data-end=\"1084\"><strong data-start=\"1044\" data-end=\"1076\">Rated AC Input/Output Power:</strong>&#160;25000W</li>\r\n<li data-start=\"1085\" data-end=\"1120\"><strong data-start=\"1087\" data-end=\"1111\">Max. Apparent Power:</strong>&#160;<span>27500</span>A</li>\r\n<li data-start=\"1121\" data-end=\"1185\"><strong data-start=\"1123\" data-end=\"1149\">Peak Power (Off-Grid):</strong>&#160;1.5&#215; rated power (for 10 seconds)</li>\r\n<li data-start=\"1186\" data-end=\"1238\"><strong data-start=\"1188\" data-end=\"1222\">Rated AC Input/Output Current:</strong>&#160;<span>37.9/36.3</span></li>\r\n<li data-start=\"1239\" data-end=\"1290\"><strong data-start=\"1241\" data-end=\"1274\">Max. AC Input/Output Current:</strong>&#160;<span>41.7/39.9</span></li>\r\n<li data-start=\"1291\" data-end=\"1349\"><strong data-start=\"1293\" data-end=\"1343\">Max. Continuous AC Passthrough (Grid to Load):</strong>&#160;80A</li>\r\n<li data-start=\"1350\" data-end=\"1401\"><strong data-start=\"1352\" data-end=\"1370\">Rated Voltage:</strong>&#160;220/380V, 230/400V (3L+N+PE)</li>\r\n<li data-start=\"1402\" data-end=\"1462\"><strong data-start=\"1404\" data-end=\"1429\">Grid Frequency Range:</strong>&#160;50Hz (45&#8211;55Hz), 60Hz (55&#8211;65Hz)</li>\r\n<li data-start=\"1463\" data-end=\"1522\"><strong data-start=\"1465\" data-end=\"1493\">Power Factor Adjustment:</strong>&#160;0.8 leading to 0.8 lagging</li>\r\n<li data-start=\"1523\" data-end=\"1568\"><strong data-start=\"1525\" data-end=\"1562\">Total Harmonic Distortion (THDi):</strong>&#160;&lt;3%</li>\r\n<li data-start=\"1569\" data-end=\"1623\"><strong data-start=\"1571\" data-end=\"1596\">DC Injection Current:</strong>&#160;&lt;0.5% of nominal current<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1635\" data-end=\"1649\">Efficiency<br /><br /></strong>\r\n<ul data-start=\"1650\" data-end=\"1745\">\r\n<li data-start=\"1650\" data-end=\"1680\"><strong data-start=\"1652\" data-end=\"1672\">Max. Efficiency:</strong>&#160;97.6%</li>\r\n<li data-start=\"1681\" data-end=\"1715\"><strong data-start=\"1683\" data-end=\"1707\">European Efficiency:</strong>&#160;97.0%</li>\r\n<li data-start=\"1716\" data-end=\"1745\"><strong data-start=\"1718\" data-end=\"1738\">MPPT Efficiency:</strong>&#160;&gt;99%<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"1783\" data-end=\"1810\">Integrated Protections:<br /><br /></strong><strong data-start=\"2073\" data-end=\"2094\"></strong></li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"2073\" data-end=\"2094\">Surge Protection:</strong>&#160;Type II (both DC &amp; AC sides)<br /><br />\r\n<ul data-start=\"1815\" data-end=\"2070\">\r\n<li data-start=\"1815\" data-end=\"1838\">DC reverse polarity</li>\r\n<li data-start=\"1841\" data-end=\"1866\">AC output overcurrent</li>\r\n<li data-start=\"1869\" data-end=\"1887\">AC overvoltage</li>\r\n<li data-start=\"1890\" data-end=\"1907\">Short circuit</li>\r\n<li data-start=\"1910\" data-end=\"1932\">Thermal protection</li>\r\n<li data-start=\"1935\" data-end=\"1965\">Residual current detection</li>\r\n<li data-start=\"1968\" data-end=\"2004\">Insulation resistance monitoring</li>\r\n<li data-start=\"2007\" data-end=\"2040\">Optional arc fault protection</li>\r\n<li data-start=\"2043\" data-end=\"2070\">DC component monitoring<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2128\" data-end=\"2142\">DC Switch:</strong>&#160;Included<br /><br /></li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2165\" data-end=\"2191\">Standards &amp; Compliance<br /><br /></strong>\r\n<ul data-start=\"2192\" data-end=\"2430\">\r\n<li data-start=\"2192\" data-end=\"2339\"><strong data-start=\"2194\" data-end=\"2214\">Grid Compliance:</strong><br data-start=\"2214\" data-end=\"2217\" />IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,<br data-start=\"2289\" data-end=\"2292\" />OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</li>\r\n<li data-start=\"2340\" data-end=\"2430\"><strong data-start=\"2342\" data-end=\"2369\">Safety &amp; EMC Standards:</strong><br data-start=\"2369\" data-end=\"2372\" />IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2442\" data-end=\"2486\">Environmental &amp; Physical Characteristics<br /><br /></strong>\r\n<ul data-start=\"2487\" data-end=\"2880\">\r\n<li data-start=\"2487\" data-end=\"2560\"><strong data-start=\"2489\" data-end=\"2521\">Operating Temperature Range:</strong>&#160;-40&#176;C to +60&#176;C (derating above 45&#176;C)</li>\r\n<li data-start=\"2561\" data-end=\"2585\"><strong data-start=\"2563\" data-end=\"2576\">Humidity:</strong>&#160;0&#8211;100%</li>\r\n<li data-start=\"2586\" data-end=\"2617\"><strong data-start=\"2588\" data-end=\"2609\">Maximum Altitude:</strong>&#160;2000m</li>\r\n<li data-start=\"2618\" data-end=\"2648\"><strong data-start=\"2620\" data-end=\"2636\">Noise Level:</strong>&#160;&#8804;55 dB(A)</li>\r\n<li data-start=\"2649\" data-end=\"2705\"><strong data-start=\"2651\" data-end=\"2670\">Cooling Method:</strong>&#160;<span>Intelligent Air Cooling</span></li>\r\n<li data-start=\"2706\" data-end=\"2773\"><strong data-start=\"2708\" data-end=\"2733\">IP Protection Rating:</strong>&#160;IP65 (dust-tight and water-resistant)</li>\r\n<li data-start=\"2774\" data-end=\"2856\"><strong data-start=\"2776\" data-end=\"2803\">Dimensions (W &#215; H &#215; D):</strong>&#160;408 &#215; 638 &#215; 237 mm (excluding connectors/brackets)</li>\r\n<li data-start=\"2857\" data-end=\"2880\"><strong data-start=\"2859\" data-end=\"2870\">Weight:</strong>&#160;30.5 kg<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2892\" data-end=\"2921\">Interface &amp; Communication<br /><br /></strong>\r\n<ul data-start=\"2922\" data-end=\"3039\">\r\n<li data-start=\"2922\" data-end=\"2992\"><strong data-start=\"2924\" data-end=\"2947\">Monitoring Options:</strong>&#160;GPRS, Wi-Fi, Bluetooth, 4G, LAN (optional)</li>\r\n<li data-start=\"2993\" data-end=\"3039\"><strong data-start=\"2995\" data-end=\"3019\">Communication Ports:</strong>&#160;RS485, RS232, CAN</li>\r\n</ul>\r\n</li>\r\n</ul>\r\n<strong>The Deye SUN-25K-SG01HP3-EU is a three-phase hybrid inverter designed for intelligent energy management. With dual MPPTs, high-voltage battery support, and robust protection features, it ensures efficient solar integration, seamless backup power, and long-term reliability for residential and small commercial applications.<br /></strong>', 'The Deye SUN-25K-SG01HP3-EU-AM2 is a high-performance three-phase hybrid inverter tailored for residential and light commercial applications. Designed to seamlessly integrate solar energy, high-voltage lithium-ion battery storage, and grid power, this inverter enables smart and efficient energy management. With dual MPPTs, a wide PV voltage range of 150&#8211;850V, and support for up to 25000W of PV input, it maximizes solar harvest and system flexibility. Its advanced protection features, natural cooling system, and IP65-rated housing ensure reliable operation under various environmental conditions. Whether for new installations or retrofitting existing systems, the SUN-25K-SG01HP3-EU-AM2 offers a compact, robust, and future-ready energy solution.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\r\n\r\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\r\n\r\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\r\n\r\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\r\n\r\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\r\n\r\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\r\n\r\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(543, '<table selecttype=\"cells\">\r\n<tbody>\r\n<tr height=\"24\">\r\n<td width=\"273\"><strong>Battery Input Data</strong></td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Battery Type</td>\r\n<td width=\"800\">Lithium-ion</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Battery Voltage Range(V)</td>\r\n<td width=\"800\">160-700</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max.Charging Current(A)</td>\r\n<td width=\"500\">37</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max.Discharging Current(A)</td>\r\n<td width=\"500\">37</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Charging Strategy for Li-ion Battery</td>\r\n<td width=\"800\">Self-adaption to BMS</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Number of battery input</td>\r\n<td width=\"800\">1</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>PV String Input Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr>\r\n<td>Max. PV Access Power (W)</td>\r\n<td>30000</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max. PV Input Power (W)</td>\r\n<td width=\"100\">24000</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max. PV Input Voltage (V)</td>\r\n<td width=\"800\">1000</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Start-up Voltage&#65288;V&#65289;</td>\r\n<td width=\"800\">180</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">MPPT Voltage Range&#65288;V&#65289;</td>\r\n<td width=\"800\">150-850</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated DC Input Voltage(V)</td>\r\n<td width=\"700\">600</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max Input Short-Circuit Current&#65288;A&#65289;</td>\r\n<td width=\"200\">39+30</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max Operating PV Input Current&#65288;A&#65289;</td>\r\n<td width=\"200\">26+20</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">No.of MPP Trackers/No.of String Per MPP Tracker</td>\r\n<td width=\"200\">2/2+1</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">AC Input/Output Data</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated AC Input/Output Active Power&#65288;W&#65289;</td>\r\n<td width=\"100\">15000</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max AC Input/Output Apparent Power &#65288;VA&#65289;</td>\r\n<td width=\"100\">16500</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Peak Power (off-grid)&#65288;W&#65289;</td>\r\n<td width=\"800\">1.5 times of rated power,10s</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated AC Input/Output Current&#65288;A&#65289;</td>\r\n<td width=\"100\">22.8/21.8</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max AC Input/Output Current&#65288;A&#65289;</td>\r\n<td width=\"100\">25/24</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max Continuous AC Passthrough (grid to load)&#65288;A&#65289;</td>\r\n<td width=\"400\">80</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated Input/Output Voltage/Range(V)</td>\r\n<td width=\"800\">220/380V&#65292;230/400V 0.85Un-1.1Un</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Grid Connection Form</td>\r\n<td width=\"800\">3L+N+PE</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated Input/Output Grid Frequency/Range</td>\r\n<td width=\"800\">50Hz/45Hz-55Hz&#160; 60Hz/55Hz-65Hz</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Power Factor Adjustment Range</td>\r\n<td width=\"800\">0.8 leading to 0.8 lagging</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Total Current Harmonic Distortion THDi</td>\r\n<td width=\"800\">&lt;3% (of nominal power)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">DC Injection Current</td>\r\n<td width=\"800\">&lt;0.5%ln</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Efficiency</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max Efficiency</td>\r\n<td width=\"800\">97.6%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Euro Efficiency</td>\r\n<td width=\"800\">97.0%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">MPPT Efficiency</td>\r\n<td width=\"800\">&#65310;99%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Equipment Protection</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Integrated</td>\r\n<td width=\"800\">\r\n<div>DC Reverse Polarity Protection, AC Output Overcurrent Protection, Thermal Protection, AC Output Overvoltage</div>\r\n<div>Protection,&#160;AC Output Short Circuit Protection, DC Component Monitoring, Arc Fault Circuit Interrupter (optional),</div>\r\n<div>Anti-islanding Protection, DC Switch,&#160;Insulation Impedance Detection, Residual Current Detection</div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Surge Protection Level</td>\r\n<td width=\"800\">TYPE II(DC),TYPE II(AC)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Interface</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Communication Interface</td>\r\n<td width=\"800\">RS485/RS232/CAN</td>\r\n</tr>\r\n<tr>\r\n<td>Monitor Mode</td>\r\n<td>GPRS/WIFI/Bluetooth/4G/LAN(optional)</td>\r\n</tr>\r\n<tr>\r\n<td>LCD/LED Display</td>\r\n<td>LCD</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>General Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Operating Temperature Range</td>\r\n<td width=\"800\">-40 to +60&#8451;, &gt;45&#8451; Derating</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Permissible Ambient Humidity</td>\r\n<td width=\"800\">0-100%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Permissible Altitude</td>\r\n<td width=\"800\">2000m</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Noise</td>\r\n<td width=\"800\">&#8804; 55 dB(A)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Ingress Protection(IP) Rating</td>\r\n<td width=\"800\">IP 65</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Inverter Topology</td>\r\n<td width=\"800\">Non-Isolated</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Over Voltage Category</td>\r\n<td width=\"800\">OVC II(DC),OVC III(AC)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Cabinet size&#65288;W*H*D&#65289;[mm]</td>\r\n<td width=\"800\">408*638*237&#65288;Excluding connectors and brackets&#65289;</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Weight[kg]</td>\r\n<td width=\"800\">30.5</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Warranty</td>\r\n<td width=\"800\">\r\n<div>5 Years/10 Years</div>\r\n<div>the Warranty Period Depends the Final Installation Site of Inverter, More Info Please Refer to Warranty Policy</div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Type Of Cooling</td>\r\n<td width=\"600\">Intelligent air cooling</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Grid Regulation</td>\r\n<td width=\"800\">\r\n<p>IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</p>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Safety EMC/Standard</td>\r\n<td width=\"800\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2<br /><br /></td>\r\n</tr>\r\n</tbody>\r\n</table>', 3, 'SUN-15K-SG01HP3-EU | Three-Phase Hybrid Inverter | 2 MPPT | HV Battery Supported', '<p>The Deye SUN-15K-SG01HP3-EU is a powerful three-phase hybrid inverter designed for high-performance solar energy systems. Equipped with 2 MPPTs and high-voltage battery support, it ensures exceptional efficiency and flexibility. This inverter supports 100% unbalanced output, allowing each phase to independently deliver up to 50% of the rated power&#8212;ideal for uneven load distribution. Thanks to its AC coupling capability, it can seamlessly retrofit into existing PV systems, enhancing performance without requiring a full overhaul. It allows for parallel operation of up to 10 units in both on-grid and off-grid modes and supports multiple batteries in parallel, offering excellent scalability. With a maximum charging and discharging current of 37A, it maintains efficient and reliable energy flow. Additionally, users can configure six charging and discharging time periods, optimizing battery use based on energy demand and tariff rates. The inverter is also compatible with diesel generators, ensuring dependable backup power in areas with unstable grid supply.</p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-005.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" /></p>\r\n<p></p>\r\n<h3>Key Features</h3>\r\n<ul>\r\n<li data-start=\"0\" data-end=\"152\">\r\n<p data-start=\"2\" data-end=\"152\"><strong data-start=\"2\" data-end=\"29\" data-is-only-node=\"\">100% Unbalanced Output:</strong>&#160;Each phase can operate independently with up to 50% of the rated power, ensuring flexibility for varied load conditions.</p>\r\n</li>\r\n<li data-start=\"153\" data-end=\"296\">\r\n<p data-start=\"155\" data-end=\"296\"><strong data-start=\"155\" data-end=\"184\" data-is-only-node=\"\">AC Coupling for Retrofit:</strong>&#160;Easily integrates into existing solar systems, enabling efficient performance upgrades without major changes.</p>\r\n</li>\r\n<li data-start=\"297\" data-end=\"468\">\r\n<p data-start=\"299\" data-end=\"468\"><strong data-start=\"299\" data-end=\"331\" data-is-only-node=\"\">Scalable Parallel Operation:</strong>&#160;Supports up to 10 units in parallel for both on-grid and off-grid modes, with compatibility for multiple parallel battery connections.</p>\r\n</li>\r\n<li data-start=\"469\" data-end=\"605\">\r\n<p data-start=\"471\" data-end=\"605\"><strong data-start=\"471\" data-end=\"516\" data-is-only-node=\"\">Max. Charging/Discharging Current of 37A:</strong>&#160;Ensures stable and efficient energy flow for both charging and discharging operations.</p>\r\n</li>\r\n<li data-start=\"606\" data-end=\"731\">\r\n<p data-start=\"608\" data-end=\"731\"><strong data-start=\"608\" data-end=\"641\" data-is-only-node=\"\">High Voltage Battery Support:</strong>&#160;Utilizes high-voltage batteries to increase system efficiency and reduce energy losses.</p>\r\n</li>\r\n<li data-start=\"732\" data-end=\"899\">\r\n<p data-start=\"734\" data-end=\"899\"><strong data-start=\"734\" data-end=\"768\" data-is-only-node=\"\">Time-based Battery Management:</strong>&#160;Allows for six configurable time periods for optimized battery charging and discharging based on energy consumption and tariffs.</p>\r\n</li>\r\n<li data-start=\"900\" data-end=\"1059\" data-is-last-node=\"\">\r\n<p data-start=\"902\" data-end=\"1059\" data-is-last-node=\"\"><strong data-start=\"902\" data-end=\"937\" data-is-only-node=\"\">Diesel Generator Compatibility:</strong>&#160;Capable of storing energy from diesel generators, offering reliable backup in areas with unstable or limited grid access.</p>\r\n</li>\r\n</ul>\r\n<p></p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" /></p>\r\n<p></p>\r\n<h3>Technical Specifications</h3>\r\n<ul>\r\n<li><strong data-start=\"283\" data-end=\"305\">Battery Input Data<br /><br /></strong>\r\n<ul data-start=\"306\" data-end=\"596\">\r\n<li data-start=\"306\" data-end=\"384\"><strong data-start=\"308\" data-end=\"334\">Battery Compatibility:</strong>&#160;Lithium-ion batteries (lead-acid not supported)</li>\r\n<li data-start=\"385\" data-end=\"424\"><strong data-start=\"387\" data-end=\"413\">Battery Voltage Range:</strong>&#160;160&#8211;700V</li>\r\n<li data-start=\"425\" data-end=\"471\"><strong data-start=\"427\" data-end=\"465\">Max. Charging/Discharging Current:</strong>&#160;37A</li>\r\n<li data-start=\"472\" data-end=\"506\"><strong data-start=\"474\" data-end=\"492\">Battery Input:</strong>&#160;Single port</li>\r\n<li data-start=\"507\" data-end=\"596\"><strong data-start=\"509\" data-end=\"531\">BMS Communication:</strong>&#160;Self-adaptive, ensuring compatibility with various BMS protocols<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"608\" data-end=\"632\">PV String Input Data<br /><br /></strong>\r\n<ul data-start=\"633\" data-end=\"1003\">\r\n<li data-start=\"633\" data-end=\"670\"><strong data-start=\"635\" data-end=\"660\">Max. PV Access Power:</strong>&#160;30000W</li>\r\n<li data-start=\"671\" data-end=\"707\"><strong data-start=\"673\" data-end=\"697\">Max. PV Input Power:</strong>&#160;24000W</li>\r\n<li data-start=\"708\" data-end=\"744\"><strong data-start=\"710\" data-end=\"736\">Max. PV Input Voltage:</strong>&#160;1000V</li>\r\n<li data-start=\"745\" data-end=\"781\"><strong data-start=\"747\" data-end=\"770\">MPPT Voltage Range:</strong>&#160;150&#8211;850V</li>\r\n<li data-start=\"782\" data-end=\"812\"><strong data-start=\"784\" data-end=\"805\">Start-up Voltage:</strong>&#160;180V</li>\r\n<li data-start=\"813\" data-end=\"849\"><strong data-start=\"815\" data-end=\"842\">Rated DC Input Voltage:</strong>&#160;600V</li>\r\n<li data-start=\"850\" data-end=\"903\"><strong data-start=\"852\" data-end=\"891\">Number of MPPTs / Strings per MPPT:</strong>&#160;2 / (1+1)</li>\r\n<li data-start=\"904\" data-end=\"954\"><strong data-start=\"906\" data-end=\"942\">Max. Operating PV Input Current:</strong>&#160;26A + 20A</li>\r\n<li data-start=\"955\" data-end=\"1003\"><strong data-start=\"957\" data-end=\"991\">Max. PV Short-Circuit Current:</strong>&#160;39A + 30A<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1015\" data-end=\"1041\">AC Input / Output Data<br /><br /></strong>\r\n<ul data-start=\"1042\" data-end=\"1623\">\r\n<li data-start=\"1042\" data-end=\"1084\"><strong data-start=\"1044\" data-end=\"1076\">Rated AC Input/Output Power:</strong>&#160;15000W</li>\r\n<li data-start=\"1085\" data-end=\"1120\"><strong data-start=\"1087\" data-end=\"1111\">Max. Apparent Power:</strong>&#160;16500A</li>\r\n<li data-start=\"1121\" data-end=\"1185\"><strong data-start=\"1123\" data-end=\"1149\">Peak Power (Off-Grid):</strong>&#160;1.5&#215; rated power (for 10 seconds)</li>\r\n<li data-start=\"1186\" data-end=\"1238\"><strong data-start=\"1188\" data-end=\"1222\">Rated AC Input/Output Current:</strong>&#160;22.8/21.8</li>\r\n<li data-start=\"1239\" data-end=\"1290\"><strong data-start=\"1241\" data-end=\"1274\">Max. AC Input/Output Current:</strong>&#160;25/24</li>\r\n<li data-start=\"1291\" data-end=\"1349\"><strong data-start=\"1293\" data-end=\"1343\">Max. Continuous AC Passthrough (Grid to Load):</strong>&#160;80A</li>\r\n<li data-start=\"1350\" data-end=\"1401\"><strong data-start=\"1352\" data-end=\"1370\">Rated Voltage:</strong>&#160;220/380V, 230/400V (3L+N+PE)</li>\r\n<li data-start=\"1402\" data-end=\"1462\"><strong data-start=\"1404\" data-end=\"1429\">Grid Frequency Range:</strong>&#160;50Hz (45&#8211;55Hz), 60Hz (55&#8211;65Hz)</li>\r\n<li data-start=\"1463\" data-end=\"1522\"><strong data-start=\"1465\" data-end=\"1493\">Power Factor Adjustment:</strong>&#160;0.8 leading to 0.8 lagging</li>\r\n<li data-start=\"1523\" data-end=\"1568\"><strong data-start=\"1525\" data-end=\"1562\">Total Harmonic Distortion (THDi):</strong>&#160;&lt;3%</li>\r\n<li data-start=\"1569\" data-end=\"1623\"><strong data-start=\"1571\" data-end=\"1596\">DC Injection Current:</strong>&#160;&lt;0.5% of nominal current<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1635\" data-end=\"1649\">Efficiency<br /><br /></strong>\r\n<ul data-start=\"1650\" data-end=\"1745\">\r\n<li data-start=\"1650\" data-end=\"1680\"><strong data-start=\"1652\" data-end=\"1672\">Max. Efficiency:</strong>&#160;97.6%</li>\r\n<li data-start=\"1681\" data-end=\"1715\"><strong data-start=\"1683\" data-end=\"1707\">European Efficiency:</strong>&#160;97.0%</li>\r\n<li data-start=\"1716\" data-end=\"1745\"><strong data-start=\"1718\" data-end=\"1738\">MPPT Efficiency:</strong>&#160;&gt;99%<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"1783\" data-end=\"1810\">Integrated Protections:<br /><br /></strong><strong data-start=\"2073\" data-end=\"2094\"></strong></li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"2073\" data-end=\"2094\">Surge Protection:</strong>&#160;Type II (both DC &amp; AC sides)<br /><br />\r\n<ul data-start=\"1815\" data-end=\"2070\">\r\n<li data-start=\"1815\" data-end=\"1838\">DC reverse polarity</li>\r\n<li data-start=\"1841\" data-end=\"1866\">AC output overcurrent</li>\r\n<li data-start=\"1869\" data-end=\"1887\">AC overvoltage</li>\r\n<li data-start=\"1890\" data-end=\"1907\">Short circuit</li>\r\n<li data-start=\"1910\" data-end=\"1932\">Thermal protection</li>\r\n<li data-start=\"1935\" data-end=\"1965\">Residual current detection</li>\r\n<li data-start=\"1968\" data-end=\"2004\">Insulation resistance monitoring</li>\r\n<li data-start=\"2007\" data-end=\"2040\">Optional arc fault protection</li>\r\n<li data-start=\"2043\" data-end=\"2070\">DC component monitoring<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2128\" data-end=\"2142\">DC Switch:</strong>&#160;Included<br /><br /></li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2165\" data-end=\"2191\">Standards &amp; Compliance<br /><br /></strong>\r\n<ul data-start=\"2192\" data-end=\"2430\">\r\n<li data-start=\"2192\" data-end=\"2339\"><strong data-start=\"2194\" data-end=\"2214\">Grid Compliance:</strong><br data-start=\"2214\" data-end=\"2217\" />IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,<br data-start=\"2289\" data-end=\"2292\" />OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</li>\r\n<li data-start=\"2340\" data-end=\"2430\"><strong data-start=\"2342\" data-end=\"2369\">Safety &amp; EMC Standards:</strong><br data-start=\"2369\" data-end=\"2372\" />IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2442\" data-end=\"2486\">Environmental &amp; Physical Characteristics<br /><br /></strong>\r\n<ul data-start=\"2487\" data-end=\"2880\">\r\n<li data-start=\"2487\" data-end=\"2560\"><strong data-start=\"2489\" data-end=\"2521\">Operating Temperature Range:</strong>&#160;-40&#176;C to +60&#176;C (derating above 45&#176;C)</li>\r\n<li data-start=\"2561\" data-end=\"2585\"><strong data-start=\"2563\" data-end=\"2576\">Humidity:</strong>&#160;0&#8211;100%</li>\r\n<li data-start=\"2586\" data-end=\"2617\"><strong data-start=\"2588\" data-end=\"2609\">Maximum Altitude:</strong>&#160;2000m</li>\r\n<li data-start=\"2618\" data-end=\"2648\"><strong data-start=\"2620\" data-end=\"2636\">Noise Level:</strong>&#160;&#8804;55 dB(A)</li>\r\n<li data-start=\"2649\" data-end=\"2705\"><strong data-start=\"2651\" data-end=\"2670\">Cooling Method:</strong>&#160;Intelligent Air Cooling</li>\r\n<li data-start=\"2706\" data-end=\"2773\"><strong data-start=\"2708\" data-end=\"2733\">IP Protection Rating:</strong>&#160;IP65 (dust-tight and water-resistant)</li>\r\n<li data-start=\"2774\" data-end=\"2856\"><strong data-start=\"2776\" data-end=\"2803\">Dimensions (W &#215; H &#215; D):</strong>&#160;408 &#215; 638 &#215; 237 mm (excluding connectors/brackets)</li>\r\n<li data-start=\"2857\" data-end=\"2880\"><strong data-start=\"2859\" data-end=\"2870\">Weight:</strong>&#160;30.5 kg<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2892\" data-end=\"2921\">Interface &amp; Communication<br /><br /></strong>\r\n<ul data-start=\"2922\" data-end=\"3039\">\r\n<li data-start=\"2922\" data-end=\"2992\"><strong data-start=\"2924\" data-end=\"2947\">Monitoring Options:</strong>&#160;GPRS, Wi-Fi, Bluetooth, 4G, LAN (optional)</li>\r\n<li data-start=\"2993\" data-end=\"3039\"><strong data-start=\"2995\" data-end=\"3019\">Communication Ports:</strong>&#160;RS485, RS232, CAN</li>\r\n</ul>\r\n</li>\r\n</ul>\r\n<p><strong>The Deye SUN-15K-SG01HP3-EU is a three-phase hybrid inverter designed for intelligent energy management. With dual MPPTs, high-voltage battery support, and robust protection features, it ensures efficient solar integration, seamless backup power, and long-term reliability for residential and small commercial applications.</strong></p>', 'The Deye SUN-15K-SG01HP3-EU-AM2 is a high-performance three-phase hybrid inverter tailored for residential and light commercial applications. Designed to seamlessly integrate solar energy, high-voltage lithium-ion battery storage, and grid power, this inverter enables smart and efficient energy management. With dual MPPTs, a wide PV voltage range of 150&#8211;850V, and support for up to 15000W of PV input, it maximizes solar harvest and system flexibility. Its advanced protection features, natural cooling system, and IP65-rated housing ensure reliable operation under various environmental conditions. Whether for new installations or retrofitting existing systems, the SUN-15K-SG01HP3-EU-AM2 offers a compact, robust, and future-ready energy solution.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\r\n\r\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\r\n\r\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\r\n\r\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\r\n\r\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\r\n\r\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\r\n\r\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', '');
INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(544, '<table selecttype=\"cells\">\r\n<tbody>\r\n<tr height=\"24\">\r\n<td width=\"273\"><strong>Battery Input Data</strong></td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Battery Type</span></td>\r\n<td width=\"800\"><span>Lithium-ion</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Battery Voltage Range(V)</span></td>\r\n<td width=\"800\"><span>160-700</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max.Charging Current(A)</span></td>\r\n<td width=\"500\"><span>37</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max.Discharging Current(A)</span></td>\r\n<td width=\"500\"><span>37</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Charging Strategy for Li-ion Battery</span></td>\r\n<td width=\"800\"><span>Self-adaption to BMS</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Number of battery input</span></td>\r\n<td width=\"800\"><span>1</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>PV String Input Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<div><span>Max. PV Access Power (W)</span></div>\r\n</td>\r\n<td><span>40000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max. PV Input Power (W)</span></td>\r\n<td width=\"100\"><span>32000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max. PV Input Voltage (V)</span></td>\r\n<td width=\"800\"><span>1000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Start-up Voltage&#65288;V&#65289;</span></td>\r\n<td width=\"800\"><span>180</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>MPPT Voltage Range&#65288;V&#65289;</span></td>\r\n<td width=\"800\"><span>150-850</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Rated DC Input Voltage(V)</span></td>\r\n<td width=\"700\"><span>600</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max Input Short-Circuit Current&#65288;A&#65289;</span></td>\r\n<td width=\"200\"><span>39+39</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max Operating PV Input Current&#65288;A&#65289;</span></td>\r\n<td width=\"200\"><span>26+26</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>No.of MPP Trackers/No.of String Per MPP Tracker</span></td>\r\n<td width=\"200\"><span>2/2+2</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>AC Input/Output Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Rated AC Input/Output Active Power&#65288;W&#65289;</span></td>\r\n<td width=\"100\"><span>20000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max AC Input/Output Apparent Power &#65288;VA&#65289;</span></td>\r\n<td width=\"100\"><span>22000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Peak Power (off-grid)&#65288;W&#65289;</span></td>\r\n<td width=\"800\"><span>1.5 times of rated power,10s</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Rated AC Input/Output Current&#65288;A&#65289;</span></td>\r\n<td width=\"100\"><span>30.4/29</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max AC Input/Output Current&#65288;A&#65289;</span></td>\r\n<td width=\"100\"><span>33.4/31.9</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max Continuous AC Passthrough (grid to load)&#65288;A&#65289;</span></td>\r\n<td width=\"400\"><span>80</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Rated Input/Output Voltage/Range(V)</span></td>\r\n<td width=\"800\"><span>220/380V&#65292;230/400V 0.85Un-1.1Un</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Grid Connection Form</span></td>\r\n<td width=\"800\"><span>3L+N+PE</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Rated Input/Output Grid Frequency/Range</span></td>\r\n<td width=\"800\"><span>50Hz/45Hz-55Hz&#160; 60Hz/55Hz-65Hz</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Power Factor Adjustment Range</span></td>\r\n<td width=\"800\"><span>0.8 leading to 0.8 lagging</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Total Current Harmonic Distortion THDi</span></td>\r\n<td width=\"800\"><span>&lt;3% (of nominal power)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>DC Injection Current</span></td>\r\n<td width=\"800\"><span>&lt;0.5%ln</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Efficiency</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Max Efficiency</span></td>\r\n<td width=\"800\"><span>97.6%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Euro Efficiency</span></td>\r\n<td width=\"800\"><span>97.0%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>MPPT Efficiency</span></td>\r\n<td width=\"800\"><span>&#65310;99%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Equipment Protection</span></td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<div><span>Integrated</span></div>\r\n</td>\r\n<td width=\"800\">\r\n<div>\r\n<div><span>DC Reverse Polarity Protection, AC Output Overcurrent Protection, Thermal Protection, AC Output Overvoltage</span></div>\r\n<div><span>Protection,&#160;</span><span>AC Output Short Circuit Protection, DC Component Monitoring, Arc Fault Circuit Interrupter (optional),</span></div>\r\n<div><span>Anti-islanding Protection, DC Switch,&#160;</span><span>Insulation Impedance Detection, Residual Current Detection</span></div>\r\n</div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Surge Protection Level</span></td>\r\n<td width=\"800\"><span>TYPE II(DC),TYPE II(AC)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Interface</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<div>\r\n<div><span>Communication Interface</span></div>\r\n</div>\r\n</td>\r\n<td width=\"800\">\r\n<div><span>RS485/RS232/CAN</span></div>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<div><span>Monitor Mode</span></div>\r\n</td>\r\n<td>\r\n<div><span>GPRS/WIFI/Bluetooth/4G/LAN(optional)</span></div>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<div><span>LCD/LED Display</span></div>\r\n</td>\r\n<td>\r\n<div><span>LCD</span></div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>General Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Operating Temperature Range</span></td>\r\n<td width=\"800\">\r\n<div><span>-40 to +60&#8451;, &gt;45&#8451; Derating</span></div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Permissible Ambient Humidity</span></td>\r\n<td width=\"800\"><span>0-100%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Permissible Altitude</span></td>\r\n<td width=\"800\"><span>2000m</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Noise</span></td>\r\n<td width=\"800\"><span>&#8804; 55 dB(A)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Ingress Protection(IP) Rating</span></td>\r\n<td width=\"800\"><span>IP 65</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Inverter Topology</span></td>\r\n<td width=\"800\"><span>Non-Isolated</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Over Voltage Category</span></td>\r\n<td width=\"800\"><span>OVC II(DC),OVC III(AC)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Cabinet size&#65288;W*H*D&#65289;[mm]</span></td>\r\n<td width=\"800\"><span>408*638*237&#65288;Excluding connectors and brackets&#65289;</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Weight[kg]</span></td>\r\n<td width=\"800\"><span>30.5</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Warranty</span></td>\r\n<td width=\"800\">\r\n<div><span>5 Years/10 Years</span></div>\r\n<div><span>the Warranty Period Depends the Final Installation Site of Inverter, More Info Please Refer to Warranty Policy</span></div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Type Of Cooling</span></td>\r\n<td width=\"600\"><span>Intelligent air cooling</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Grid Regulation</span></td>\r\n<td width=\"800\">\r\n<p><span>IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</span></p>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\"><span>Safety EMC/Standard</span></td>\r\n<td width=\"800\"><span>IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</span></td>\r\n</tr>\r\n</tbody>\r\n</table>', 2, 'SUN-20K-SG01HP3-EU | Three-Phase Hybrid Inverter | 2 MPPT | HV Battery Supported', '<p>The Deye SUN-20K-SG01HP3-EU is a powerful three-phase hybrid inverter designed for high-performance solar energy systems. Equipped with 2 MPPTs and high-voltage battery support, it ensures exceptional efficiency and flexibility. This inverter supports 100% unbalanced output, allowing each phase to independently deliver up to 50% of the rated power&#8212;ideal for uneven load distribution. Thanks to its AC coupling capability, it can seamlessly retrofit into existing PV systems, enhancing performance without requiring a full overhaul. It allows for parallel operation of up to 10 units in both on-grid and off-grid modes and supports multiple batteries in parallel, offering excellent scalability. With a maximum charging and discharging current of 37A, it maintains efficient and reliable energy flow. Additionally, users can configure six charging and discharging time periods, optimizing battery use based on energy demand and tariff rates. The inverter is also compatible with diesel generators, ensuring dependable backup power in areas with unstable grid supply.</p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-005.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\r\n<p></p>\r\n<h3>Key Features</h3>\r\n<ul>\r\n<li data-start=\"0\" data-end=\"152\">\r\n<p data-start=\"2\" data-end=\"152\"><strong data-start=\"2\" data-end=\"29\" data-is-only-node=\"\">100% Unbalanced Output:</strong>&#160;Each phase can operate independently with up to 50% of the rated power, ensuring flexibility for varied load conditions.</p>\r\n</li>\r\n<li data-start=\"153\" data-end=\"296\">\r\n<p data-start=\"155\" data-end=\"296\"><strong data-start=\"155\" data-end=\"184\" data-is-only-node=\"\">AC Coupling for Retrofit:</strong>&#160;Easily integrates into existing solar systems, enabling efficient performance upgrades without major changes.</p>\r\n</li>\r\n<li data-start=\"297\" data-end=\"468\">\r\n<p data-start=\"299\" data-end=\"468\"><strong data-start=\"299\" data-end=\"331\" data-is-only-node=\"\">Scalable Parallel Operation:</strong>&#160;Supports up to 10 units in parallel for both on-grid and off-grid modes, with compatibility for multiple parallel battery connections.</p>\r\n</li>\r\n<li data-start=\"469\" data-end=\"605\">\r\n<p data-start=\"471\" data-end=\"605\"><strong data-start=\"471\" data-end=\"516\" data-is-only-node=\"\">Max. Charging/Discharging Current of 37A:</strong>&#160;Ensures stable and efficient energy flow for both charging and discharging operations.</p>\r\n</li>\r\n<li data-start=\"606\" data-end=\"731\">\r\n<p data-start=\"608\" data-end=\"731\"><strong data-start=\"608\" data-end=\"641\" data-is-only-node=\"\">High Voltage Battery Support:</strong>&#160;Utilizes high-voltage batteries to increase system efficiency and reduce energy losses.</p>\r\n</li>\r\n<li data-start=\"732\" data-end=\"899\">\r\n<p data-start=\"734\" data-end=\"899\"><strong data-start=\"734\" data-end=\"768\" data-is-only-node=\"\">Time-based Battery Management:</strong>&#160;Allows for six configurable time periods for optimized battery charging and discharging based on energy consumption and tariffs.</p>\r\n</li>\r\n<li data-start=\"900\" data-end=\"1059\" data-is-last-node=\"\">\r\n<p data-start=\"902\" data-end=\"1059\" data-is-last-node=\"\"><strong data-start=\"902\" data-end=\"937\" data-is-only-node=\"\">Diesel Generator Compatibility:</strong>&#160;Capable of storing energy from diesel generators, offering reliable backup in areas with unstable or limited grid access.</p>\r\n</li>\r\n</ul>\r\n<p></p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\r\n<p></p>\r\n<h3>Technical Specifications</h3>\r\n<ul>\r\n<li><strong data-start=\"283\" data-end=\"305\">Battery Input Data<br /><br /></strong>\r\n<ul data-start=\"306\" data-end=\"596\">\r\n<li data-start=\"306\" data-end=\"384\"><strong data-start=\"308\" data-end=\"334\">Battery Compatibility:</strong>&#160;Lithium-ion batteries (lead-acid not supported)</li>\r\n<li data-start=\"385\" data-end=\"424\"><strong data-start=\"387\" data-end=\"413\">Battery Voltage Range:</strong>&#160;160&#8211;700V</li>\r\n<li data-start=\"425\" data-end=\"471\"><strong data-start=\"427\" data-end=\"465\">Max. Charging/Discharging Current:</strong>&#160;37A</li>\r\n<li data-start=\"472\" data-end=\"506\"><strong data-start=\"474\" data-end=\"492\">Battery Input:</strong>&#160;Single port</li>\r\n<li data-start=\"507\" data-end=\"596\"><strong data-start=\"509\" data-end=\"531\">BMS Communication:</strong>&#160;Self-adaptive, ensuring compatibility with various BMS protocols<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"608\" data-end=\"632\">PV String Input Data<br /><br /></strong>\r\n<ul data-start=\"633\" data-end=\"1003\">\r\n<li data-start=\"633\" data-end=\"670\"><strong data-start=\"635\" data-end=\"660\">Max. PV Access Power:</strong>&#160;4<span>0000</span>W</li>\r\n<li data-start=\"671\" data-end=\"707\"><strong data-start=\"673\" data-end=\"697\">Max. PV Input Power:</strong>&#160;<span>32000</span>W</li>\r\n<li data-start=\"708\" data-end=\"744\"><strong data-start=\"710\" data-end=\"736\">Max. PV Input Voltage:</strong>&#160;1000V</li>\r\n<li data-start=\"745\" data-end=\"781\"><strong data-start=\"747\" data-end=\"770\">MPPT Voltage Range:</strong>&#160;150&#8211;850V</li>\r\n<li data-start=\"782\" data-end=\"812\"><strong data-start=\"784\" data-end=\"805\">Start-up Voltage:</strong>&#160;180V</li>\r\n<li data-start=\"813\" data-end=\"849\"><strong data-start=\"815\" data-end=\"842\">Rated DC Input Voltage:</strong>&#160;600V</li>\r\n<li data-start=\"850\" data-end=\"903\"><strong data-start=\"852\" data-end=\"891\">Number of MPPTs / Strings per MPPT:</strong>&#160;2 / (1+1)</li>\r\n<li data-start=\"904\" data-end=\"954\"><strong data-start=\"906\" data-end=\"942\">Max. Operating PV Input Current:</strong>&#160;<span>26A + 26A</span></li>\r\n<li data-start=\"955\" data-end=\"1003\"><strong data-start=\"957\" data-end=\"991\">Max. PV Short-Circuit Current:</strong>&#160;39A + 39A<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1015\" data-end=\"1041\">AC Input / Output Data<br /><br /></strong>\r\n<ul data-start=\"1042\" data-end=\"1623\">\r\n<li data-start=\"1042\" data-end=\"1084\"><strong data-start=\"1044\" data-end=\"1076\">Rated AC Input/Output Power:</strong>&#160;20000W</li>\r\n<li data-start=\"1085\" data-end=\"1120\"><strong data-start=\"1087\" data-end=\"1111\">Max. Apparent Power:</strong>&#160;<span>22000</span>A</li>\r\n<li data-start=\"1121\" data-end=\"1185\"><strong data-start=\"1123\" data-end=\"1149\">Peak Power (Off-Grid):</strong>&#160;1.5&#215; rated power (for 10 seconds)</li>\r\n<li data-start=\"1186\" data-end=\"1238\"><strong data-start=\"1188\" data-end=\"1222\">Rated AC Input/Output Current:</strong>&#160;<span>30.4/29</span></li>\r\n<li data-start=\"1239\" data-end=\"1290\"><strong data-start=\"1241\" data-end=\"1274\">Max. AC Input/Output Current:</strong>&#160;<span>33.4/31.9</span></li>\r\n<li data-start=\"1291\" data-end=\"1349\"><strong data-start=\"1293\" data-end=\"1343\">Max. Continuous AC Passthrough (Grid to Load):</strong>&#160;80A</li>\r\n<li data-start=\"1350\" data-end=\"1401\"><strong data-start=\"1352\" data-end=\"1370\">Rated Voltage:</strong>&#160;220/380V, 230/400V (3L+N+PE)</li>\r\n<li data-start=\"1402\" data-end=\"1462\"><strong data-start=\"1404\" data-end=\"1429\">Grid Frequency Range:</strong>&#160;50Hz (45&#8211;55Hz), 60Hz (55&#8211;65Hz)</li>\r\n<li data-start=\"1463\" data-end=\"1522\"><strong data-start=\"1465\" data-end=\"1493\">Power Factor Adjustment:</strong>&#160;0.8 leading to 0.8 lagging</li>\r\n<li data-start=\"1523\" data-end=\"1568\"><strong data-start=\"1525\" data-end=\"1562\">Total Harmonic Distortion (THDi):</strong>&#160;&lt;3%</li>\r\n<li data-start=\"1569\" data-end=\"1623\"><strong data-start=\"1571\" data-end=\"1596\">DC Injection Current:</strong>&#160;&lt;0.5% of nominal current<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1635\" data-end=\"1649\">Efficiency<br /><br /></strong>\r\n<ul data-start=\"1650\" data-end=\"1745\">\r\n<li data-start=\"1650\" data-end=\"1680\"><strong data-start=\"1652\" data-end=\"1672\">Max. Efficiency:</strong>&#160;97.6%</li>\r\n<li data-start=\"1681\" data-end=\"1715\"><strong data-start=\"1683\" data-end=\"1707\">European Efficiency:</strong>&#160;97.0%</li>\r\n<li data-start=\"1716\" data-end=\"1745\"><strong data-start=\"1718\" data-end=\"1738\">MPPT Efficiency:</strong>&#160;&gt;99%<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"1783\" data-end=\"1810\">Integrated Protections:<br /><br /></strong><strong data-start=\"2073\" data-end=\"2094\"></strong></li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"2073\" data-end=\"2094\">Surge Protection:</strong>&#160;Type II (both DC &amp; AC sides)<br /><br />\r\n<ul data-start=\"1815\" data-end=\"2070\">\r\n<li data-start=\"1815\" data-end=\"1838\">DC reverse polarity</li>\r\n<li data-start=\"1841\" data-end=\"1866\">AC output overcurrent</li>\r\n<li data-start=\"1869\" data-end=\"1887\">AC overvoltage</li>\r\n<li data-start=\"1890\" data-end=\"1907\">Short circuit</li>\r\n<li data-start=\"1910\" data-end=\"1932\">Thermal protection</li>\r\n<li data-start=\"1935\" data-end=\"1965\">Residual current detection</li>\r\n<li data-start=\"1968\" data-end=\"2004\">Insulation resistance monitoring</li>\r\n<li data-start=\"2007\" data-end=\"2040\">Optional arc fault protection</li>\r\n<li data-start=\"2043\" data-end=\"2070\">DC component monitoring<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2128\" data-end=\"2142\">DC Switch:</strong>&#160;Included<br /><br /></li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2165\" data-end=\"2191\">Standards &amp; Compliance<br /><br /></strong>\r\n<ul data-start=\"2192\" data-end=\"2430\">\r\n<li data-start=\"2192\" data-end=\"2339\"><strong data-start=\"2194\" data-end=\"2214\">Grid Compliance:</strong><br data-start=\"2214\" data-end=\"2217\" />IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,<br data-start=\"2289\" data-end=\"2292\" />OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</li>\r\n<li data-start=\"2340\" data-end=\"2430\"><strong data-start=\"2342\" data-end=\"2369\">Safety &amp; EMC Standards:</strong><br data-start=\"2369\" data-end=\"2372\" />IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2442\" data-end=\"2486\">Environmental &amp; Physical Characteristics<br /><br /></strong>\r\n<ul data-start=\"2487\" data-end=\"2880\">\r\n<li data-start=\"2487\" data-end=\"2560\"><strong data-start=\"2489\" data-end=\"2521\">Operating Temperature Range:</strong>&#160;-40&#176;C to +60&#176;C (derating above 45&#176;C)</li>\r\n<li data-start=\"2561\" data-end=\"2585\"><strong data-start=\"2563\" data-end=\"2576\">Humidity:</strong>&#160;0&#8211;100%</li>\r\n<li data-start=\"2586\" data-end=\"2617\"><strong data-start=\"2588\" data-end=\"2609\">Maximum Altitude:</strong>&#160;2000m</li>\r\n<li data-start=\"2618\" data-end=\"2648\"><strong data-start=\"2620\" data-end=\"2636\">Noise Level:</strong>&#160;&#8804;55 dB(A)</li>\r\n<li data-start=\"2649\" data-end=\"2705\"><strong data-start=\"2651\" data-end=\"2670\">Cooling Method:</strong>&#160;<span>Intelligent Air Cooling</span></li>\r\n<li data-start=\"2706\" data-end=\"2773\"><strong data-start=\"2708\" data-end=\"2733\">IP Protection Rating:</strong>&#160;IP65 (dust-tight and water-resistant)</li>\r\n<li data-start=\"2774\" data-end=\"2856\"><strong data-start=\"2776\" data-end=\"2803\">Dimensions (W &#215; H &#215; D):</strong>&#160;408 &#215; 638 &#215; 237 mm (excluding connectors/brackets)</li>\r\n<li data-start=\"2857\" data-end=\"2880\"><strong data-start=\"2859\" data-end=\"2870\">Weight:</strong>&#160;30.5 kg<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2892\" data-end=\"2921\">Interface &amp; Communication<br /><br /></strong>\r\n<ul data-start=\"2922\" data-end=\"3039\">\r\n<li data-start=\"2922\" data-end=\"2992\"><strong data-start=\"2924\" data-end=\"2947\">Monitoring Options:</strong>&#160;GPRS, Wi-Fi, Bluetooth, 4G, LAN (optional)</li>\r\n<li data-start=\"2993\" data-end=\"3039\"><strong data-start=\"2995\" data-end=\"3019\">Communication Ports:</strong>&#160;RS485, RS232, CAN</li>\r\n</ul>\r\n</li>\r\n</ul>\r\n<strong>The Deye SUN-20K-SG01HP3-EU is a three-phase hybrid inverter designed for intelligent energy management. With dual MPPTs, high-voltage battery support, and robust protection features, it ensures efficient solar integration, seamless backup power, and long-term reliability for residential and small commercial applications.<br /></strong>', 'The Deye SUN-20K-SG01HP3-EU-AM2 is a high-performance three-phase hybrid inverter tailored for residential and light commercial applications. Designed to seamlessly integrate solar energy, high-voltage lithium-ion battery storage, and grid power, this inverter enables smart and efficient energy management. With dual MPPTs, a wide PV voltage range of 150&#8211;850V, and support for up to 20000W of PV input, it maximizes solar harvest and system flexibility. Its advanced protection features, natural cooling system, and IP65-rated housing ensure reliable operation under various environmental conditions. Whether for new installations or retrofitting existing systems, the SUN-20K-SG01HP3-EU-AM2 offers a compact, robust, and future-ready energy solution.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\r\n\r\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\r\n\r\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\r\n\r\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\r\n\r\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\r\n\r\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\r\n\r\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(544, '<table selecttype=\"cells\">\r\n<tbody>\r\n<tr height=\"24\">\r\n<td width=\"273\"><strong>Battery Input Data</strong></td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Battery Type</td>\r\n<td width=\"800\">Lithium-ion</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Battery Voltage Range(V)</td>\r\n<td width=\"800\">160-700</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max.Charging Current(A)</td>\r\n<td width=\"500\">37</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max.Discharging Current(A)</td>\r\n<td width=\"500\">37</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Charging Strategy for Li-ion Battery</td>\r\n<td width=\"800\">Self-adaption to BMS</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Number of battery input</td>\r\n<td width=\"800\">1</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>PV String Input Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr>\r\n<td>Max. PV Access Power (W)</td>\r\n<td>40000</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max. PV Input Power (W)</td>\r\n<td width=\"100\">32000</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max. PV Input Voltage (V)</td>\r\n<td width=\"800\">1000</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Start-up Voltage&#65288;V&#65289;</td>\r\n<td width=\"800\">180</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">MPPT Voltage Range&#65288;V&#65289;</td>\r\n<td width=\"800\">150-850</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated DC Input Voltage(V)</td>\r\n<td width=\"700\">600</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max Input Short-Circuit Current&#65288;A&#65289;</td>\r\n<td width=\"200\">39+39</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max Operating PV Input Current&#65288;A&#65289;</td>\r\n<td width=\"200\">26+26</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">No.of MPP Trackers/No.of String Per MPP Tracker</td>\r\n<td width=\"200\">2/2+2</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>AC Input/Output Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated AC Input/Output Active Power&#65288;W&#65289;</td>\r\n<td width=\"100\">20000</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max AC Input/Output Apparent Power &#65288;VA&#65289;</td>\r\n<td width=\"100\">22000</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Peak Power (off-grid)&#65288;W&#65289;</td>\r\n<td width=\"800\">1.5 times of rated power,10s</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated AC Input/Output Current&#65288;A&#65289;</td>\r\n<td width=\"100\">30.4/29</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max AC Input/Output Current&#65288;A&#65289;</td>\r\n<td width=\"100\">33.4/31.9</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max Continuous AC Passthrough (grid to load)&#65288;A&#65289;</td>\r\n<td width=\"400\">80</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated Input/Output Voltage/Range(V)</td>\r\n<td width=\"800\">220/380V&#65292;230/400V 0.85Un-1.1Un</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Grid Connection Form</td>\r\n<td width=\"800\">3L+N+PE</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated Input/Output Grid Frequency/Range</td>\r\n<td width=\"800\">50Hz/45Hz-55Hz&#160; 60Hz/55Hz-65Hz</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Power Factor Adjustment Range</td>\r\n<td width=\"800\">0.8 leading to 0.8 lagging</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Total Current Harmonic Distortion THDi</td>\r\n<td width=\"800\">&lt;3% (of nominal power)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">DC Injection Current</td>\r\n<td width=\"800\">&lt;0.5%ln</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Efficiency</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max Efficiency</td>\r\n<td width=\"800\">97.6%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Euro Efficiency</td>\r\n<td width=\"800\">97.0%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">MPPT Efficiency</td>\r\n<td width=\"800\">&#65310;99%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Equipment Protection</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Integrated</td>\r\n<td width=\"800\">\r\n<div>DC Reverse Polarity Protection, AC Output Overcurrent Protection, Thermal Protection, AC Output Overvoltage</div>\r\n<div>Protection,&#160;AC Output Short Circuit Protection, DC Component Monitoring, Arc Fault Circuit Interrupter (optional),</div>\r\n<div>Anti-islanding Protection, DC Switch,&#160;Insulation Impedance Detection, Residual Current Detection</div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Surge Protection Level</td>\r\n<td width=\"800\">TYPE II(DC),TYPE II(AC)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Interface</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Communication Interface</td>\r\n<td width=\"800\">RS485/RS232/CAN</td>\r\n</tr>\r\n<tr>\r\n<td>Monitor Mode</td>\r\n<td>GPRS/WIFI/Bluetooth/4G/LAN(optional)</td>\r\n</tr>\r\n<tr>\r\n<td>LCD/LED Display</td>\r\n<td>LCD</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>General Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Operating Temperature Range</td>\r\n<td width=\"800\">-40 to +60&#8451;, &gt;45&#8451; Derating</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Permissible Ambient Humidity</td>\r\n<td width=\"800\">0-100%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Permissible Altitude</td>\r\n<td width=\"800\">2000m</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Noise</td>\r\n<td width=\"800\">&#8804; 55 dB(A)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Ingress Protection(IP) Rating</td>\r\n<td width=\"800\">IP 65</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Inverter Topology</td>\r\n<td width=\"800\">Non-Isolated</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Over Voltage Category</td>\r\n<td width=\"800\">OVC II(DC),OVC III(AC)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Cabinet size&#65288;W*H*D&#65289;[mm]</td>\r\n<td width=\"800\">408*638*237&#65288;Excluding connectors and brackets&#65289;</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Weight[kg]</td>\r\n<td width=\"800\">30.5</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Warranty</td>\r\n<td width=\"800\">\r\n<div>5 Years/10 Years</div>\r\n<div>the Warranty Period Depends the Final Installation Site of Inverter, More Info Please Refer to Warranty Policy</div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Type Of Cooling</td>\r\n<td width=\"600\">Intelligent air cooling</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Grid Regulation</td>\r\n<td width=\"800\">\r\n<p>IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</p>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Safety EMC/Standard</td>\r\n<td width=\"800\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</td>\r\n</tr>\r\n</tbody>\r\n</table>', 3, 'SUN-20K-SG01HP3-EU | Three-Phase Hybrid Inverter | 2 MPPT | HV Battery Supported', '<p>The Deye SUN-20K-SG01HP3-EU is a powerful three-phase hybrid inverter designed for high-performance solar energy systems. Equipped with 2 MPPTs and high-voltage battery support, it ensures exceptional efficiency and flexibility. This inverter supports 100% unbalanced output, allowing each phase to independently deliver up to 50% of the rated power&#8212;ideal for uneven load distribution. Thanks to its AC coupling capability, it can seamlessly retrofit into existing PV systems, enhancing performance without requiring a full overhaul. It allows for parallel operation of up to 10 units in both on-grid and off-grid modes and supports multiple batteries in parallel, offering excellent scalability. With a maximum charging and discharging current of 37A, it maintains efficient and reliable energy flow. Additionally, users can configure six charging and discharging time periods, optimizing battery use based on energy demand and tariff rates. The inverter is also compatible with diesel generators, ensuring dependable backup power in areas with unstable grid supply.</p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-005.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" /></p>\r\n<p></p>\r\n<h3>Key Features</h3>\r\n<ul>\r\n<li data-start=\"0\" data-end=\"152\">\r\n<p data-start=\"2\" data-end=\"152\"><strong data-start=\"2\" data-end=\"29\" data-is-only-node=\"\">100% Unbalanced Output:</strong>&#160;Each phase can operate independently with up to 50% of the rated power, ensuring flexibility for varied load conditions.</p>\r\n</li>\r\n<li data-start=\"153\" data-end=\"296\">\r\n<p data-start=\"155\" data-end=\"296\"><strong data-start=\"155\" data-end=\"184\" data-is-only-node=\"\">AC Coupling for Retrofit:</strong>&#160;Easily integrates into existing solar systems, enabling efficient performance upgrades without major changes.</p>\r\n</li>\r\n<li data-start=\"297\" data-end=\"468\">\r\n<p data-start=\"299\" data-end=\"468\"><strong data-start=\"299\" data-end=\"331\" data-is-only-node=\"\">Scalable Parallel Operation:</strong>&#160;Supports up to 10 units in parallel for both on-grid and off-grid modes, with compatibility for multiple parallel battery connections.</p>\r\n</li>\r\n<li data-start=\"469\" data-end=\"605\">\r\n<p data-start=\"471\" data-end=\"605\"><strong data-start=\"471\" data-end=\"516\" data-is-only-node=\"\">Max. Charging/Discharging Current of 37A:</strong>&#160;Ensures stable and efficient energy flow for both charging and discharging operations.</p>\r\n</li>\r\n<li data-start=\"606\" data-end=\"731\">\r\n<p data-start=\"608\" data-end=\"731\"><strong data-start=\"608\" data-end=\"641\" data-is-only-node=\"\">High Voltage Battery Support:</strong>&#160;Utilizes high-voltage batteries to increase system efficiency and reduce energy losses.</p>\r\n</li>\r\n<li data-start=\"732\" data-end=\"899\">\r\n<p data-start=\"734\" data-end=\"899\"><strong data-start=\"734\" data-end=\"768\" data-is-only-node=\"\">Time-based Battery Management:</strong>&#160;Allows for six configurable time periods for optimized battery charging and discharging based on energy consumption and tariffs.</p>\r\n</li>\r\n<li data-start=\"900\" data-end=\"1059\" data-is-last-node=\"\">\r\n<p data-start=\"902\" data-end=\"1059\" data-is-last-node=\"\"><strong data-start=\"902\" data-end=\"937\" data-is-only-node=\"\">Diesel Generator Compatibility:</strong>&#160;Capable of storing energy from diesel generators, offering reliable backup in areas with unstable or limited grid access.</p>\r\n</li>\r\n</ul>\r\n<p></p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" /></p>\r\n<p></p>\r\n<h3>Technical Specifications</h3>\r\n<ul>\r\n<li><strong data-start=\"283\" data-end=\"305\">Battery Input Data<br /><br /></strong>\r\n<ul data-start=\"306\" data-end=\"596\">\r\n<li data-start=\"306\" data-end=\"384\"><strong data-start=\"308\" data-end=\"334\">Battery Compatibility:</strong>&#160;Lithium-ion batteries (lead-acid not supported)</li>\r\n<li data-start=\"385\" data-end=\"424\"><strong data-start=\"387\" data-end=\"413\">Battery Voltage Range:</strong>&#160;160&#8211;700V</li>\r\n<li data-start=\"425\" data-end=\"471\"><strong data-start=\"427\" data-end=\"465\">Max. Charging/Discharging Current:</strong>&#160;37A</li>\r\n<li data-start=\"472\" data-end=\"506\"><strong data-start=\"474\" data-end=\"492\">Battery Input:</strong>&#160;Single port</li>\r\n<li data-start=\"507\" data-end=\"596\"><strong data-start=\"509\" data-end=\"531\">BMS Communication:</strong>&#160;Self-adaptive, ensuring compatibility with various BMS protocols<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"608\" data-end=\"632\">PV String Input Data<br /><br /></strong>\r\n<ul data-start=\"633\" data-end=\"1003\">\r\n<li data-start=\"633\" data-end=\"670\"><strong data-start=\"635\" data-end=\"660\">Max. PV Access Power:</strong>&#160;40000W</li>\r\n<li data-start=\"671\" data-end=\"707\"><strong data-start=\"673\" data-end=\"697\">Max. PV Input Power:</strong>&#160;32000W</li>\r\n<li data-start=\"708\" data-end=\"744\"><strong data-start=\"710\" data-end=\"736\">Max. PV Input Voltage:</strong>&#160;1000V</li>\r\n<li data-start=\"745\" data-end=\"781\"><strong data-start=\"747\" data-end=\"770\">MPPT Voltage Range:</strong>&#160;150&#8211;850V</li>\r\n<li data-start=\"782\" data-end=\"812\"><strong data-start=\"784\" data-end=\"805\">Start-up Voltage:</strong>&#160;180V</li>\r\n<li data-start=\"813\" data-end=\"849\"><strong data-start=\"815\" data-end=\"842\">Rated DC Input Voltage:</strong>&#160;600V</li>\r\n<li data-start=\"850\" data-end=\"903\"><strong data-start=\"852\" data-end=\"891\">Number of MPPTs / Strings per MPPT:</strong>&#160;2 / (1+1)</li>\r\n<li data-start=\"904\" data-end=\"954\"><strong data-start=\"906\" data-end=\"942\">Max. Operating PV Input Current:</strong>&#160;26A + 26A</li>\r\n<li data-start=\"955\" data-end=\"1003\"><strong data-start=\"957\" data-end=\"991\">Max. PV Short-Circuit Current:</strong>&#160;39A + 39A<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1015\" data-end=\"1041\">AC Input / Output Data<br /><br /></strong>\r\n<ul data-start=\"1042\" data-end=\"1623\">\r\n<li data-start=\"1042\" data-end=\"1084\"><strong data-start=\"1044\" data-end=\"1076\">Rated AC Input/Output Power:</strong>&#160;20000W</li>\r\n<li data-start=\"1085\" data-end=\"1120\"><strong data-start=\"1087\" data-end=\"1111\">Max. Apparent Power:</strong>&#160;22000A</li>\r\n<li data-start=\"1121\" data-end=\"1185\"><strong data-start=\"1123\" data-end=\"1149\">Peak Power (Off-Grid):</strong>&#160;1.5&#215; rated power (for 10 seconds)</li>\r\n<li data-start=\"1186\" data-end=\"1238\"><strong data-start=\"1188\" data-end=\"1222\">Rated AC Input/Output Current:</strong>&#160;30.4/29</li>\r\n<li data-start=\"1239\" data-end=\"1290\"><strong data-start=\"1241\" data-end=\"1274\">Max. AC Input/Output Current:</strong>&#160;33.4/31.9</li>\r\n<li data-start=\"1291\" data-end=\"1349\"><strong data-start=\"1293\" data-end=\"1343\">Max. Continuous AC Passthrough (Grid to Load):</strong>&#160;80A</li>\r\n<li data-start=\"1350\" data-end=\"1401\"><strong data-start=\"1352\" data-end=\"1370\">Rated Voltage:</strong>&#160;220/380V, 230/400V (3L+N+PE)</li>\r\n<li data-start=\"1402\" data-end=\"1462\"><strong data-start=\"1404\" data-end=\"1429\">Grid Frequency Range:</strong>&#160;50Hz (45&#8211;55Hz), 60Hz (55&#8211;65Hz)</li>\r\n<li data-start=\"1463\" data-end=\"1522\"><strong data-start=\"1465\" data-end=\"1493\">Power Factor Adjustment:</strong>&#160;0.8 leading to 0.8 lagging</li>\r\n<li data-start=\"1523\" data-end=\"1568\"><strong data-start=\"1525\" data-end=\"1562\">Total Harmonic Distortion (THDi):</strong>&#160;&lt;3%</li>\r\n<li data-start=\"1569\" data-end=\"1623\"><strong data-start=\"1571\" data-end=\"1596\">DC Injection Current:</strong>&#160;&lt;0.5% of nominal current<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1635\" data-end=\"1649\">Efficiency<br /><br /></strong>\r\n<ul data-start=\"1650\" data-end=\"1745\">\r\n<li data-start=\"1650\" data-end=\"1680\"><strong data-start=\"1652\" data-end=\"1672\">Max. Efficiency:</strong>&#160;97.6%</li>\r\n<li data-start=\"1681\" data-end=\"1715\"><strong data-start=\"1683\" data-end=\"1707\">European Efficiency:</strong>&#160;97.0%</li>\r\n<li data-start=\"1716\" data-end=\"1745\"><strong data-start=\"1718\" data-end=\"1738\">MPPT Efficiency:</strong>&#160;&gt;99%<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"1783\" data-end=\"1810\">Integrated Protections:<br /><br /></strong><strong data-start=\"2073\" data-end=\"2094\"></strong></li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"2073\" data-end=\"2094\">Surge Protection:</strong>&#160;Type II (both DC &amp; AC sides)<br /><br />\r\n<ul data-start=\"1815\" data-end=\"2070\">\r\n<li data-start=\"1815\" data-end=\"1838\">DC reverse polarity</li>\r\n<li data-start=\"1841\" data-end=\"1866\">AC output overcurrent</li>\r\n<li data-start=\"1869\" data-end=\"1887\">AC overvoltage</li>\r\n<li data-start=\"1890\" data-end=\"1907\">Short circuit</li>\r\n<li data-start=\"1910\" data-end=\"1932\">Thermal protection</li>\r\n<li data-start=\"1935\" data-end=\"1965\">Residual current detection</li>\r\n<li data-start=\"1968\" data-end=\"2004\">Insulation resistance monitoring</li>\r\n<li data-start=\"2007\" data-end=\"2040\">Optional arc fault protection</li>\r\n<li data-start=\"2043\" data-end=\"2070\">DC component monitoring<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2128\" data-end=\"2142\">DC Switch:</strong>&#160;Included<br /><br /></li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2165\" data-end=\"2191\">Standards &amp; Compliance<br /><br /></strong>\r\n<ul data-start=\"2192\" data-end=\"2430\">\r\n<li data-start=\"2192\" data-end=\"2339\"><strong data-start=\"2194\" data-end=\"2214\">Grid Compliance:</strong><br data-start=\"2214\" data-end=\"2217\" />IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,<br data-start=\"2289\" data-end=\"2292\" />OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</li>\r\n<li data-start=\"2340\" data-end=\"2430\"><strong data-start=\"2342\" data-end=\"2369\">Safety &amp; EMC Standards:</strong><br data-start=\"2369\" data-end=\"2372\" />IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2442\" data-end=\"2486\">Environmental &amp; Physical Characteristics<br /><br /></strong>\r\n<ul data-start=\"2487\" data-end=\"2880\">\r\n<li data-start=\"2487\" data-end=\"2560\"><strong data-start=\"2489\" data-end=\"2521\">Operating Temperature Range:</strong>&#160;-40&#176;C to +60&#176;C (derating above 45&#176;C)</li>\r\n<li data-start=\"2561\" data-end=\"2585\"><strong data-start=\"2563\" data-end=\"2576\">Humidity:</strong>&#160;0&#8211;100%</li>\r\n<li data-start=\"2586\" data-end=\"2617\"><strong data-start=\"2588\" data-end=\"2609\">Maximum Altitude:</strong>&#160;2000m</li>\r\n<li data-start=\"2618\" data-end=\"2648\"><strong data-start=\"2620\" data-end=\"2636\">Noise Level:</strong>&#160;&#8804;55 dB(A)</li>\r\n<li data-start=\"2649\" data-end=\"2705\"><strong data-start=\"2651\" data-end=\"2670\">Cooling Method:</strong>&#160;Intelligent Air Cooling</li>\r\n<li data-start=\"2706\" data-end=\"2773\"><strong data-start=\"2708\" data-end=\"2733\">IP Protection Rating:</strong>&#160;IP65 (dust-tight and water-resistant)</li>\r\n<li data-start=\"2774\" data-end=\"2856\"><strong data-start=\"2776\" data-end=\"2803\">Dimensions (W &#215; H &#215; D):</strong>&#160;408 &#215; 638 &#215; 237 mm (excluding connectors/brackets)</li>\r\n<li data-start=\"2857\" data-end=\"2880\"><strong data-start=\"2859\" data-end=\"2870\">Weight:</strong>&#160;30.5 kg<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2892\" data-end=\"2921\">Interface &amp; Communication<br /><br /></strong>\r\n<ul data-start=\"2922\" data-end=\"3039\">\r\n<li data-start=\"2922\" data-end=\"2992\"><strong data-start=\"2924\" data-end=\"2947\">Monitoring Options:</strong>&#160;GPRS, Wi-Fi, Bluetooth, 4G, LAN (optional)</li>\r\n<li data-start=\"2993\" data-end=\"3039\"><strong data-start=\"2995\" data-end=\"3019\">Communication Ports:</strong>&#160;RS485, RS232, CAN</li>\r\n</ul>\r\n</li>\r\n</ul>\r\n<p><strong>The Deye SUN-20K-SG01HP3-EU is a three-phase hybrid inverter designed for intelligent energy management. With dual MPPTs, high-voltage battery support, and robust protection features, it ensures efficient solar integration, seamless backup power, and long-term reliability for residential and small commercial applications.</strong></p>', 'The Deye SUN-20K-SG01HP3-EU-AM2 is a high-performance three-phase hybrid inverter tailored for residential and light commercial applications. Designed to seamlessly integrate solar energy, high-voltage lithium-ion battery storage, and grid power, this inverter enables smart and efficient energy management. With dual MPPTs, a wide PV voltage range of 150&#8211;850V, and support for up to 20000W of PV input, it maximizes solar harvest and system flexibility. Its advanced protection features, natural cooling system, and IP65-rated housing ensure reliable operation under various environmental conditions. Whether for new installations or retrofitting existing systems, the SUN-20K-SG01HP3-EU-AM2 offers a compact, robust, and future-ready energy solution.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\r\n\r\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\r\n\r\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\r\n\r\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\r\n\r\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\r\n\r\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\r\n\r\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', '');
INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(545, '<table selecttype=\"cells\">\r\n<tbody>\r\n<tr height=\"24\">\r\n<td width=\"273\"><strong>Battery Input Data</strong></td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Battery Type</td>\r\n<td width=\"800\">Lithium-ion</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Battery Voltage Range(V)</td>\r\n<td width=\"800\">160-700</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max.Charging Current(A)</td>\r\n<td width=\"100\">50</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max.Discharging Current(A)</td>\r\n<td width=\"100\">50</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Charging Strategy for Li-ion Battery</td>\r\n<td width=\"800\">Self-adaption to BMS</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Number of battery input</td>\r\n<td width=\"800\">1</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>PV String Input Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr>\r\n<td>Max. PV Access Power (W)</td>\r\n<td>50000</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max. PV Input Power (W)</td>\r\n<td width=\"100\">40000</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max. PV Input Voltage (V)</td>\r\n<td width=\"800\">1000</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Start-up Voltage&#65288;V&#65289;</td>\r\n<td width=\"800\">180</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">MPPT Voltage Range&#65288;V&#65289;</td>\r\n<td width=\"800\">150-850</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated DC Input Voltage(V)</td>\r\n<td width=\"100\">700</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max Input Short-Circuit Current&#65288;A&#65289;</td>\r\n<td width=\"200\">39+39</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max Operating PV Input Current&#65288;A&#65289;</td>\r\n<td width=\"200\">26+26</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">No.of MPP Trackers/No.of String Per MPP Tracker</td>\r\n<td width=\"200\">2/2+2</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>AC Input/Output Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated AC Input/Output Active Power&#65288;W&#65289;</td>\r\n<td width=\"100\">25000</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max AC Input/Output Apparent Power &#65288;VA&#65289;</td>\r\n<td width=\"100\">27500</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Peak Power (off-grid)&#65288;W&#65289;</td>\r\n<td width=\"800\">1.5 times of rated power,10s</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated AC Input/Output Current&#65288;A&#65289;</td>\r\n<td width=\"100\">37.9/36.3</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max AC Input/Output Current&#65288;A&#65289;</td>\r\n<td width=\"100\">41.7/39.9</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max Continuous AC Passthrough (grid to load)&#65288;A&#65289;</td>\r\n<td width=\"400\">80</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated Input/Output Voltage/Range(V)</td>\r\n<td width=\"800\">220/380V&#65292;230/400V 0.85Un-1.1Un</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Grid Connection Form</td>\r\n<td width=\"800\">3L+N+PE</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Rated Input/Output Grid Frequency/Range</td>\r\n<td width=\"800\">50Hz/45Hz-55Hz&#160; 60Hz/55Hz-65Hz</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Power Factor Adjustment Range</td>\r\n<td width=\"800\">0.8 leading to 0.8 lagging</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Total Current Harmonic Distortion THDi</td>\r\n<td width=\"800\">&lt;3% (of nominal power)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">DC Injection Current</td>\r\n<td width=\"800\">&lt;0.5%ln</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Efficiency</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Max Efficiency</td>\r\n<td width=\"800\">97.6%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Euro Efficiency</td>\r\n<td width=\"800\">97.0%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">MPPT Efficiency</td>\r\n<td width=\"800\">&#65310;99%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Equipment Protection</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Integrated</td>\r\n<td width=\"800\">\r\n<div>DC Reverse Polarity Protection, AC Output Overcurrent Protection, Thermal Protection, AC Output Overvoltage</div>\r\n<div>Protection,&#160;AC Output Short Circuit Protection, DC Component Monitoring, Arc Fault Circuit Interrupter (optional),</div>\r\n<div>Anti-islanding Protection, DC Switch,&#160;Insulation Impedance Detection, Residual Current Detection</div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Surge Protection Level</td>\r\n<td width=\"800\">TYPE II(DC),TYPE II(AC)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>Interface</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Communication Interface</td>\r\n<td width=\"800\">RS485/RS232/CAN</td>\r\n</tr>\r\n<tr>\r\n<td>Monitor Mode</td>\r\n<td>GPRS/WIFI/Bluetooth/4G/LAN(optional)</td>\r\n</tr>\r\n<tr>\r\n<td>LCD/LED Display</td>\r\n<td>LCD</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">\r\n<p></p>\r\n<p><strong>General Data</strong></p>\r\n</td>\r\n<td width=\"800\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Operating Temperature Range</td>\r\n<td width=\"800\">-40 to +60&#8451;, &gt;45&#8451; Derating</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Permissible Ambient Humidity</td>\r\n<td width=\"800\">0-100%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Permissible Altitude</td>\r\n<td width=\"800\">2000m</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Noise</td>\r\n<td width=\"800\">&#8804; 55 dB(A)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Ingress Protection(IP) Rating</td>\r\n<td width=\"800\">IP 65</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Inverter Topology</td>\r\n<td width=\"800\">Non-Isolated</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Over Voltage Category</td>\r\n<td width=\"800\">OVC II(DC),OVC III(AC)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Cabinet size&#65288;W*H*D&#65289;[mm]</td>\r\n<td width=\"800\">408*638*237&#65288;Excluding connectors and brackets&#65289;</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Weight[kg]</td>\r\n<td width=\"800\">30.5</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Warranty</td>\r\n<td width=\"800\">\r\n<div>5 Years/10 Years</div>\r\n<div>the Warranty Period Depends the Final Installation Site of Inverter, More Info Please Refer to Warranty Policy</div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Type Of Cooling</td>\r\n<td width=\"600\">Intelligent air cooling</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Grid Regulation</td>\r\n<td width=\"800\">\r\n<p>IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</p>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"273\">Safety EMC/Standard</td>\r\n<td width=\"800\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</td>\r\n</tr>\r\n</tbody>\r\n</table>', 3, 'SUN-25K-SG01HP3-EU | Three-Phase Hybrid Inverter | 2 MPPT | HV Battery Supported', '<p>The Deye SUN-25K-SG01HP3-EU is a powerful three-phase hybrid inverter designed for high-performance solar energy systems. Equipped with 2 MPPTs and high-voltage battery support, it ensures exceptional efficiency and flexibility. This inverter supports 100% unbalanced output, allowing each phase to independently deliver up to 50% of the rated power&#8212;ideal for uneven load distribution. Thanks to its AC coupling capability, it can seamlessly retrofit into existing PV systems, enhancing performance without requiring a full overhaul. It allows for parallel operation of up to 10 units in both on-grid and off-grid modes and supports multiple batteries in parallel, offering excellent scalability. With a maximum charging and discharging current of 50A, it maintains efficient and reliable energy flow. Additionally, users can configure six charging and discharging time periods, optimizing battery use based on energy demand and tariff rates. The inverter is also compatible with diesel generators, ensuring dependable backup power in areas with unstable grid supply.</p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-005.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" /></p>\r\n<p></p>\r\n<h3>Key Features</h3>\r\n<ul>\r\n<li data-start=\"0\" data-end=\"152\">\r\n<p data-start=\"2\" data-end=\"152\"><strong data-start=\"2\" data-end=\"29\" data-is-only-node=\"\">100% Unbalanced Output:</strong>&#160;Each phase can operate independently with up to 50% of the rated power, ensuring flexibility for varied load conditions.</p>\r\n</li>\r\n<li data-start=\"153\" data-end=\"296\">\r\n<p data-start=\"155\" data-end=\"296\"><strong data-start=\"155\" data-end=\"184\" data-is-only-node=\"\">AC Coupling for Retrofit:</strong>&#160;Easily integrates into existing solar systems, enabling efficient performance upgrades without major changes.</p>\r\n</li>\r\n<li data-start=\"297\" data-end=\"468\">\r\n<p data-start=\"299\" data-end=\"468\"><strong data-start=\"299\" data-end=\"331\" data-is-only-node=\"\">Scalable Parallel Operation:</strong>&#160;Supports up to 10 units in parallel for both on-grid and off-grid modes, with compatibility for multiple parallel battery connections.</p>\r\n</li>\r\n<li data-start=\"469\" data-end=\"605\">\r\n<p data-start=\"471\" data-end=\"605\"><strong data-start=\"471\" data-end=\"516\" data-is-only-node=\"\">Max. Charging/Discharging Current of 50A:</strong>&#160;Ensures stable and efficient energy flow for both charging and discharging operations.</p>\r\n</li>\r\n<li data-start=\"606\" data-end=\"731\">\r\n<p data-start=\"608\" data-end=\"731\"><strong data-start=\"608\" data-end=\"641\" data-is-only-node=\"\">High Voltage Battery Support:</strong>&#160;Utilizes high-voltage batteries to increase system efficiency and reduce energy losses.</p>\r\n</li>\r\n<li data-start=\"732\" data-end=\"899\">\r\n<p data-start=\"734\" data-end=\"899\"><strong data-start=\"734\" data-end=\"768\" data-is-only-node=\"\">Time-based Battery Management:</strong>&#160;Allows for six configurable time periods for optimized battery charging and discharging based on energy consumption and tariffs.</p>\r\n</li>\r\n<li data-start=\"900\" data-end=\"1059\" data-is-last-node=\"\">\r\n<p data-start=\"902\" data-end=\"1059\" data-is-last-node=\"\"><strong data-start=\"902\" data-end=\"937\" data-is-only-node=\"\">Diesel Generator Compatibility:</strong>&#160;Capable of storing energy from diesel generators, offering reliable backup in areas with unstable or limited grid access.</p>\r\n</li>\r\n</ul>\r\n<p></p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" /></p>\r\n<p></p>\r\n<h3>Technical Specifications</h3>\r\n<ul>\r\n<li><strong data-start=\"283\" data-end=\"305\">Battery Input Data<br /><br /></strong>\r\n<ul data-start=\"306\" data-end=\"596\">\r\n<li data-start=\"306\" data-end=\"384\"><strong data-start=\"308\" data-end=\"334\">Battery Compatibility:</strong>&#160;Lithium-ion batteries (lead-acid not supported)</li>\r\n<li data-start=\"385\" data-end=\"424\"><strong data-start=\"387\" data-end=\"413\">Battery Voltage Range:</strong>&#160;160&#8211;700V</li>\r\n<li data-start=\"425\" data-end=\"471\"><strong data-start=\"427\" data-end=\"465\">Max. Charging/Discharging Current:</strong>&#160;37A</li>\r\n<li data-start=\"472\" data-end=\"506\"><strong data-start=\"474\" data-end=\"492\">Battery Input:</strong>&#160;Single port</li>\r\n<li data-start=\"507\" data-end=\"596\"><strong data-start=\"509\" data-end=\"531\">BMS Communication:</strong>&#160;Self-adaptive, ensuring compatibility with various BMS protocols<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"608\" data-end=\"632\">PV String Input Data<br /><br /></strong>\r\n<ul data-start=\"633\" data-end=\"1003\">\r\n<li data-start=\"633\" data-end=\"670\"><strong data-start=\"635\" data-end=\"660\">Max. PV Access Power:</strong>&#160;50000W</li>\r\n<li data-start=\"671\" data-end=\"707\"><strong data-start=\"673\" data-end=\"697\">Max. PV Input Power:</strong>&#160;40000W</li>\r\n<li data-start=\"708\" data-end=\"744\"><strong data-start=\"710\" data-end=\"736\">Max. PV Input Voltage:</strong>&#160;1000V</li>\r\n<li data-start=\"745\" data-end=\"781\"><strong data-start=\"747\" data-end=\"770\">MPPT Voltage Range:</strong>&#160;150&#8211;850V</li>\r\n<li data-start=\"782\" data-end=\"812\"><strong data-start=\"784\" data-end=\"805\">Start-up Voltage:</strong>&#160;180V</li>\r\n<li data-start=\"813\" data-end=\"849\"><strong data-start=\"815\" data-end=\"842\">Rated DC Input Voltage:</strong>&#160;600V</li>\r\n<li data-start=\"850\" data-end=\"903\"><strong data-start=\"852\" data-end=\"891\">Number of MPPTs / Strings per MPPT:</strong>&#160;2 / (1+1)</li>\r\n<li data-start=\"904\" data-end=\"954\"><strong data-start=\"906\" data-end=\"942\">Max. Operating PV Input Current:</strong>&#160;26A + 26A</li>\r\n<li data-start=\"955\" data-end=\"1003\"><strong data-start=\"957\" data-end=\"991\">Max. PV Short-Circuit Current:</strong>&#160;39A + 39A<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1015\" data-end=\"1041\">AC Input / Output Data<br /><br /></strong>\r\n<ul data-start=\"1042\" data-end=\"1623\">\r\n<li data-start=\"1042\" data-end=\"1084\"><strong data-start=\"1044\" data-end=\"1076\">Rated AC Input/Output Power:</strong>&#160;25000W</li>\r\n<li data-start=\"1085\" data-end=\"1120\"><strong data-start=\"1087\" data-end=\"1111\">Max. Apparent Power:</strong>&#160;27500A</li>\r\n<li data-start=\"1121\" data-end=\"1185\"><strong data-start=\"1123\" data-end=\"1149\">Peak Power (Off-Grid):</strong>&#160;1.5&#215; rated power (for 10 seconds)</li>\r\n<li data-start=\"1186\" data-end=\"1238\"><strong data-start=\"1188\" data-end=\"1222\">Rated AC Input/Output Current:</strong>&#160;37.9/36.3</li>\r\n<li data-start=\"1239\" data-end=\"1290\"><strong data-start=\"1241\" data-end=\"1274\">Max. AC Input/Output Current:</strong>&#160;41.7/39.9</li>\r\n<li data-start=\"1291\" data-end=\"1349\"><strong data-start=\"1293\" data-end=\"1343\">Max. Continuous AC Passthrough (Grid to Load):</strong>&#160;80A</li>\r\n<li data-start=\"1350\" data-end=\"1401\"><strong data-start=\"1352\" data-end=\"1370\">Rated Voltage:</strong>&#160;220/380V, 230/400V (3L+N+PE)</li>\r\n<li data-start=\"1402\" data-end=\"1462\"><strong data-start=\"1404\" data-end=\"1429\">Grid Frequency Range:</strong>&#160;50Hz (45&#8211;55Hz), 60Hz (55&#8211;65Hz)</li>\r\n<li data-start=\"1463\" data-end=\"1522\"><strong data-start=\"1465\" data-end=\"1493\">Power Factor Adjustment:</strong>&#160;0.8 leading to 0.8 lagging</li>\r\n<li data-start=\"1523\" data-end=\"1568\"><strong data-start=\"1525\" data-end=\"1562\">Total Harmonic Distortion (THDi):</strong>&#160;&lt;3%</li>\r\n<li data-start=\"1569\" data-end=\"1623\"><strong data-start=\"1571\" data-end=\"1596\">DC Injection Current:</strong>&#160;&lt;0.5% of nominal current<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1635\" data-end=\"1649\">Efficiency<br /><br /></strong>\r\n<ul data-start=\"1650\" data-end=\"1745\">\r\n<li data-start=\"1650\" data-end=\"1680\"><strong data-start=\"1652\" data-end=\"1672\">Max. Efficiency:</strong>&#160;97.6%</li>\r\n<li data-start=\"1681\" data-end=\"1715\"><strong data-start=\"1683\" data-end=\"1707\">European Efficiency:</strong>&#160;97.0%</li>\r\n<li data-start=\"1716\" data-end=\"1745\"><strong data-start=\"1718\" data-end=\"1738\">MPPT Efficiency:</strong>&#160;&gt;99%<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"1783\" data-end=\"1810\">Integrated Protections:<br /><br /></strong><strong data-start=\"2073\" data-end=\"2094\"></strong></li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"2073\" data-end=\"2094\">Surge Protection:</strong>&#160;Type II (both DC &amp; AC sides)<br /><br />\r\n<ul data-start=\"1815\" data-end=\"2070\">\r\n<li data-start=\"1815\" data-end=\"1838\">DC reverse polarity</li>\r\n<li data-start=\"1841\" data-end=\"1866\">AC output overcurrent</li>\r\n<li data-start=\"1869\" data-end=\"1887\">AC overvoltage</li>\r\n<li data-start=\"1890\" data-end=\"1907\">Short circuit</li>\r\n<li data-start=\"1910\" data-end=\"1932\">Thermal protection</li>\r\n<li data-start=\"1935\" data-end=\"1965\">Residual current detection</li>\r\n<li data-start=\"1968\" data-end=\"2004\">Insulation resistance monitoring</li>\r\n<li data-start=\"2007\" data-end=\"2040\">Optional arc fault protection</li>\r\n<li data-start=\"2043\" data-end=\"2070\">DC component monitoring<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2128\" data-end=\"2142\">DC Switch:</strong>&#160;Included<br /><br /></li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2165\" data-end=\"2191\">Standards &amp; Compliance<br /><br /></strong>\r\n<ul data-start=\"2192\" data-end=\"2430\">\r\n<li data-start=\"2192\" data-end=\"2339\"><strong data-start=\"2194\" data-end=\"2214\">Grid Compliance:</strong><br data-start=\"2214\" data-end=\"2217\" />IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,<br data-start=\"2289\" data-end=\"2292\" />OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</li>\r\n<li data-start=\"2340\" data-end=\"2430\"><strong data-start=\"2342\" data-end=\"2369\">Safety &amp; EMC Standards:</strong><br data-start=\"2369\" data-end=\"2372\" />IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2442\" data-end=\"2486\">Environmental &amp; Physical Characteristics<br /><br /></strong>\r\n<ul data-start=\"2487\" data-end=\"2880\">\r\n<li data-start=\"2487\" data-end=\"2560\"><strong data-start=\"2489\" data-end=\"2521\">Operating Temperature Range:</strong>&#160;-40&#176;C to +60&#176;C (derating above 45&#176;C)</li>\r\n<li data-start=\"2561\" data-end=\"2585\"><strong data-start=\"2563\" data-end=\"2576\">Humidity:</strong>&#160;0&#8211;100%</li>\r\n<li data-start=\"2586\" data-end=\"2617\"><strong data-start=\"2588\" data-end=\"2609\">Maximum Altitude:</strong>&#160;2000m</li>\r\n<li data-start=\"2618\" data-end=\"2648\"><strong data-start=\"2620\" data-end=\"2636\">Noise Level:</strong>&#160;&#8804;55 dB(A)</li>\r\n<li data-start=\"2649\" data-end=\"2705\"><strong data-start=\"2651\" data-end=\"2670\">Cooling Method:</strong>&#160;Intelligent Air Cooling</li>\r\n<li data-start=\"2706\" data-end=\"2773\"><strong data-start=\"2708\" data-end=\"2733\">IP Protection Rating:</strong>&#160;IP65 (dust-tight and water-resistant)</li>\r\n<li data-start=\"2774\" data-end=\"2856\"><strong data-start=\"2776\" data-end=\"2803\">Dimensions (W &#215; H &#215; D):</strong>&#160;408 &#215; 638 &#215; 237 mm (excluding connectors/brackets)</li>\r\n<li data-start=\"2857\" data-end=\"2880\"><strong data-start=\"2859\" data-end=\"2870\">Weight:</strong>&#160;30.5 kg<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2892\" data-end=\"2921\">Interface &amp; Communication<br /><br /></strong>\r\n<ul data-start=\"2922\" data-end=\"3039\">\r\n<li data-start=\"2922\" data-end=\"2992\"><strong data-start=\"2924\" data-end=\"2947\">Monitoring Options:</strong>&#160;GPRS, Wi-Fi, Bluetooth, 4G, LAN (optional)</li>\r\n<li data-start=\"2993\" data-end=\"3039\"><strong data-start=\"2995\" data-end=\"3019\">Communication Ports:</strong>&#160;RS485, RS232, CAN</li>\r\n</ul>\r\n</li>\r\n</ul>\r\n<p><strong>The Deye SUN-25K-SG01HP3-EU is a three-phase hybrid inverter designed for intelligent energy management. With dual MPPTs, high-voltage battery support, and robust protection features, it ensures efficient solar integration, seamless backup power, and long-term reliability for residential and small commercial applications.</strong></p>', 'The Deye SUN-20K-SG01HP3-EU-AM2 is a high-performance three-phase hybrid inverter tailored for residential and light commercial applications. Designed to seamlessly integrate solar energy, high-voltage lithium-ion battery storage, and grid power, this inverter enables smart and efficient energy management. With dual MPPTs, a wide PV voltage range of 150&#8211;850V, and support for up to 20000W of PV input, it maximizes solar harvest and system flexibility. Its advanced protection features, natural cooling system, and IP65-rated housing ensure reliable operation under various environmental conditions. Whether for new installations or retrofitting existing systems, the SUN-20K-SG01HP3-EU-AM2 offers a compact, robust, and future-ready energy solution.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\r\n\r\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\r\n\r\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\r\n\r\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\r\n\r\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\r\n\r\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\r\n\r\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(546, '<table selecttype=\"cells\">\r\n<tbody>\r\n<tr height=\"24\">\r\n<td width=\"250\"><strong>Battery Input Data</strong></td>\r\n<td width=\"750\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Battery Type</span></td>\r\n<td width=\"750\"><span>Lithium-ion</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Battery Voltage Range(V)</span></td>\r\n<td width=\"750\"><span>160-800</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Max.Charging Current(A)</span></td>\r\n<td width=\"750\"><span>50+50</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Max.Discharging Current(A)</span></td>\r\n<td width=\"750\"><span>50+50</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Charging Strategy for Li-ion Battery</span></td>\r\n<td width=\"750\"><span>Self-adaption to BMS</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Number of battery input</span></td>\r\n<td width=\"750\"><span>2</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">\r\n<p></p>\r\n<p><strong>PV String Input Data</strong></p>\r\n</td>\r\n<td width=\"750\"></td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<div><span>Max. PV Access Power (W)</span></div>\r\n</td>\r\n<td><span>59800</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Max DC Input Power&#65288;W&#65289;</span></td>\r\n<td width=\"150\"><span>47840</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Max DC Input Voltage&#65288;V&#65289;</span></td>\r\n<td width=\"750\"><span>1000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Start-up Voltage&#65288;V&#65289;</span></td>\r\n<td width=\"750\"><span>180</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>MPPT Voltage Range&#65288;V&#65289;</span></td>\r\n<td width=\"750\"><span>150-850</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Rated DC Input Voltage(V)</span></td>\r\n<td width=\"750\"><span>600</span></td>\r\n</tr>\r\n<tr height=\"32\">\r\n<td width=\"250\"><span>Max Input Short-Circuit Current&#65288;A&#65289;</span></td>\r\n<td width=\"450\"><span>55+55+55</span></td>\r\n</tr>\r\n<tr height=\"40\">\r\n<td width=\"250\"><span>Max Operating PV Input Current&#65288;A&#65289;</span></td>\r\n<td width=\"450\"><span>36+36+36</span></td>\r\n</tr>\r\n<tr height=\"40\">\r\n<td width=\"250\"><span>No.of MPP Trackers/No.of String Per MPP Tracker</span></td>\r\n<td width=\"450\"><span>3/2+2+2</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">\r\n<p></p>\r\n<p><strong>AC Input/Output Data</strong></p>\r\n</td>\r\n<td width=\"750\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Rated AC Input/Output Active Power&#65288;W&#65289;</span></td>\r\n<td width=\"150\"><span>29900</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Max AC Input/Output Apparent Power &#65288;VA&#65289;</span></td>\r\n<td width=\"150\"><span>29900</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Peak Power (off-grid)&#65288;W&#65289;</span></td>\r\n<td width=\"750\"><span>1.5 times of rated power,10s</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Rated AC Input/Output Current&#65288;A&#65289;</span></td>\r\n<td width=\"150\"><span>45.4/43.4</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Max AC Input/Output Current&#65288;A&#65289;</span></td>\r\n<td width=\"150\"><span>45.4/43.4</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Max Continuous AC Passthrough (grid to load)&#65288;A&#65289;</span></td>\r\n<td width=\"750\"><span>200</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Rated Input/Output Voltage/Range(V)</span></td>\r\n<td width=\"750\"><span>220/380V&#65292;230/400V 0.85Un-1.1Un</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Grid Connection Form</span></td>\r\n<td width=\"750\"><span>3L+N+PE</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Rated Input/Output Grid Frequency/Range</span></td>\r\n<td width=\"750\"><span>50/45-55, 60/55-65</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Power Factor Adjustment Range</span></td>\r\n<td width=\"750\"><span>0.8 leading-0.8 lagging</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Total Current Harmonic Distortion THDi</span></td>\r\n<td width=\"750\"><span>&lt;3% (of nominal power)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">DC Injection Current</td>\r\n<td width=\"750\"><span>&lt;0.5%ln</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">\r\n<p></p>\r\n<p><strong>Efficiency</strong></p>\r\n</td>\r\n<td width=\"750\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Max Efficiency</span></td>\r\n<td width=\"750\"><span>97.60%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Euro Efficiency</span></td>\r\n<td width=\"750\"><span>97.0%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>MPPT Efficiency</span></td>\r\n<td width=\"750\"><span>&#65310;99%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">\r\n<p></p>\r\n<p><strong>Equipment Protection</strong></p>\r\n</td>\r\n<td width=\"750\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">\r\n<div><span>Integrated</span></div>\r\n</td>\r\n<td width=\"750\">\r\n<div>\r\n<div><span>DC Reverse Polarity Protection, AC Output Overcurrent Protection, Thermal Protection, AC Output Overvoltage</span></div>\r\n<div><span>Protection,&#160;</span><span>AC Output Short Circuit Protection, DC Component Monitoring, Arc Fault Circuit</span></div>\r\n<div><span>Interrupter (optional), Anti-islanding Protection,&#160;</span><span>DC Switch, Insulation Impedance Detection,</span></div>\r\n<div><span>Residual Current Detection</span></div>\r\n</div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Surge Protection Level</span></td>\r\n<td width=\"750\"><span>TYPE II(DC), TYPE II(AC)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">\r\n<p></p>\r\n<p><strong>Interface</strong></p>\r\n</td>\r\n<td width=\"750\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Communication Interface</span></td>\r\n<td width=\"750\">RS485/RS232/CAN</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<div><span>Monitor Mode</span></div>\r\n</td>\r\n<td>\r\n<div><span>GPRS/WIFI/Bluetooth/4G/LAN(optional)</span></div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">\r\n<p></p>\r\n<p><strong>General Data</strong></p>\r\n</td>\r\n<td width=\"750\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Operating Temperature Range</span></td>\r\n<td width=\"750\"><span>-40&#8451;+60&#8451;,&#65310;45&#8451; Derating</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Permissible Ambient Humidity</span></td>\r\n<td width=\"750\"><span>0-100%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Permissible Altitude</span></td>\r\n<td width=\"750\"><span>2000m</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Noise</span></td>\r\n<td width=\"750\"><span>&#8804; 65 dB(A)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Ingress Protection(IP) Rating</span></td>\r\n<td width=\"750\"><span>IP 65</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Inverter Topology</span></td>\r\n<td width=\"750\"><span>Non-Isolated</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Over Voltage Category</span></td>\r\n<td width=\"750\"><span>OVC II(DC),OVC III(AC)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Cabinet size&#65288;W*H*D&#65289;[mm]</span></td>\r\n<td width=\"750\"><span>527*894*294&#65288;Excluding connectors and brackets&#65289;</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Weight[kg]</span></td>\r\n<td width=\"750\"><span>80</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Warranty</span></td>\r\n<td width=\"750\"><span>5 Years/10 Years</span><br /><span>the Warranty Period Depends the Final Installation Site of Inverter, More Info Please Refer to Warranty Policy</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Type Of Cooling</span></td>\r\n<td width=\"750\"><span>Intelligent air cooling</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Grid Regulation</span></td>\r\n<td width=\"750\"><span>IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,</span><br /><span>OVE-Richtlinie R25, G99, VDE-AR-N 4105</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Safety EMC/Standard</span></td>\r\n<td width=\"750\"><span>IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</span></td>\r\n</tr>\r\n</tbody>\r\n</table>', 2, 'SUN-29.9K-SG01HP3-EU-BM3 | Three-Phase Hybrid Inverter | 3 MPPT | HV Battery Supported', '<p>The Deye SUN-29.9K-SG01HP3-EU-BM3 is a powerful three-phase hybrid inverter designed for high-performance solar energy systems. Equipped with 3 MPPTs and high-voltage battery support, it ensures exceptional efficiency and flexibility. This inverter supports 100% unbalanced output, allowing each phase to independently deliver up to 50% of the rated power&#8212;ideal for uneven load distribution. Thanks to its AC coupling capability, it can seamlessly retrofit into existing PV systems, enhancing performance without requiring a full overhaul. It allows for parallel operation of up to 10 units in both on-grid and off-grid modes and supports multiple batteries in parallel, offering excellent scalability. With a maximum charging and discharging current of 50A + 50A, it maintains efficient and reliable energy flow. Additionally, users can configure six charging and discharging time periods, optimizing battery use based on energy demand and tariff rates. The inverter is also compatible with diesel generators, ensuring dependable backup power in areas with unstable grid supply.</p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-006.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\r\n<p></p>\r\n<h3>Key Features</h3>\r\n<ul>\r\n<li data-start=\"0\" data-end=\"152\">\r\n<p data-start=\"2\" data-end=\"152\"><strong data-start=\"2\" data-end=\"29\" data-is-only-node=\"\">100% Unbalanced Output:</strong>&#160;Each phase can operate independently with up to 50% of the rated power, ensuring flexibility for varied load conditions.</p>\r\n</li>\r\n<li data-start=\"153\" data-end=\"296\">\r\n<p data-start=\"155\" data-end=\"296\"><strong data-start=\"155\" data-end=\"184\" data-is-only-node=\"\">AC Coupling for Retrofit:</strong>&#160;Easily integrates into existing solar systems, enabling efficient performance upgrades without major changes.</p>\r\n</li>\r\n<li data-start=\"297\" data-end=\"468\">\r\n<p data-start=\"299\" data-end=\"468\"><strong data-start=\"299\" data-end=\"331\" data-is-only-node=\"\">Scalable Parallel Operation:</strong>&#160;Supports up to 10 units in parallel for both on-grid and off-grid modes, with compatibility for multiple parallel battery connections.</p>\r\n</li>\r\n<li data-start=\"469\" data-end=\"605\">\r\n<p data-start=\"471\" data-end=\"605\"><strong data-start=\"471\" data-end=\"516\" data-is-only-node=\"\">Max. Charging/Discharging Current of 50A + 50A:</strong>&#160;Ensures stable and efficient energy flow for both charging and discharging operations.</p>\r\n</li>\r\n<li data-start=\"606\" data-end=\"731\">\r\n<p data-start=\"608\" data-end=\"731\"><strong data-start=\"608\" data-end=\"641\" data-is-only-node=\"\">High Voltage Battery Support:</strong>&#160;Utilizes high-voltage batteries to increase system efficiency and reduce energy losses.</p>\r\n</li>\r\n<li data-start=\"732\" data-end=\"899\">\r\n<p data-start=\"734\" data-end=\"899\"><strong data-start=\"734\" data-end=\"768\" data-is-only-node=\"\">Time-based Battery Management:</strong>&#160;Allows for six configurable time periods for optimized battery charging and discharging based on energy consumption and tariffs.</p>\r\n</li>\r\n<li data-start=\"900\" data-end=\"1059\" data-is-last-node=\"\">\r\n<p data-start=\"902\" data-end=\"1059\" data-is-last-node=\"\"><strong data-start=\"902\" data-end=\"937\" data-is-only-node=\"\">Diesel Generator Compatibility:</strong>&#160;Capable of storing energy from diesel generators, offering reliable backup in areas with unstable or limited grid access.</p>\r\n</li>\r\n</ul>\r\n<p></p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\r\n<p></p>\r\n<h3>Technical Specifications</h3>\r\n<ul>\r\n<li><strong data-start=\"283\" data-end=\"305\">Battery Input Data<br /><br /></strong>\r\n<ul data-start=\"306\" data-end=\"596\">\r\n<li data-start=\"306\" data-end=\"384\"><strong data-start=\"308\" data-end=\"334\">Battery Compatibility:</strong>&#160;Lithium-ion batteries (lead-acid not supported)</li>\r\n<li data-start=\"385\" data-end=\"424\"><strong data-start=\"387\" data-end=\"413\">Battery Voltage Range:</strong>&#160;160&#8211;800V</li>\r\n<li data-start=\"425\" data-end=\"471\"><strong data-start=\"427\" data-end=\"465\">Max. Charging/Discharging Current:</strong>&#160;50A + 50A</li>\r\n<li data-start=\"472\" data-end=\"506\"><strong data-start=\"474\" data-end=\"492\">Battery Input:</strong>&#160;Single port</li>\r\n<li data-start=\"507\" data-end=\"596\"><strong data-start=\"509\" data-end=\"531\">BMS Communication:</strong>&#160;Self-adaptive, ensuring compatibility with various BMS protocols<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"608\" data-end=\"632\">PV String Input Data<br /><br /></strong>\r\n<ul data-start=\"633\" data-end=\"1003\">\r\n<li data-start=\"633\" data-end=\"670\"><strong data-start=\"635\" data-end=\"660\">Max. PV Access Power:</strong>&#160;<span>59800</span>W</li>\r\n<li data-start=\"671\" data-end=\"707\"><strong data-start=\"673\" data-end=\"697\">Max. PV Input Power:</strong>&#160;<span>47840</span>W</li>\r\n<li data-start=\"708\" data-end=\"744\"><strong data-start=\"710\" data-end=\"736\">Max. PV Input Voltage:</strong>&#160;1000V</li>\r\n<li data-start=\"745\" data-end=\"781\"><strong data-start=\"747\" data-end=\"770\">MPPT Voltage Range:</strong>&#160;150&#8211;850V</li>\r\n<li data-start=\"782\" data-end=\"812\"><strong data-start=\"784\" data-end=\"805\">Start-up Voltage:</strong>&#160;180V</li>\r\n<li data-start=\"813\" data-end=\"849\"><strong data-start=\"815\" data-end=\"842\">Rated DC Input Voltage:</strong>&#160;600V</li>\r\n<li data-start=\"850\" data-end=\"903\"><strong data-start=\"852\" data-end=\"891\">Number of MPPTs / Strings per MPPT:</strong>&#160;<span>3 / 2+2+2</span></li>\r\n<li data-start=\"904\" data-end=\"954\"><strong data-start=\"906\" data-end=\"942\">Max. Operating PV Input Current:</strong>&#160;<span>55A + 55A + 55A</span></li>\r\n<li data-start=\"955\" data-end=\"1003\"><strong data-start=\"957\" data-end=\"991\">Max. PV Short-Circuit Current:</strong>&#160;<span>36A + 36A + 36A</span><br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1015\" data-end=\"1041\">AC Input / Output Data<br /><br /></strong>\r\n<ul data-start=\"1042\" data-end=\"1623\">\r\n<li data-start=\"1042\" data-end=\"1084\"><strong data-start=\"1044\" data-end=\"1076\">Rated AC Input/Output Power:</strong>&#160;<span>29900</span>W</li>\r\n<li data-start=\"1085\" data-end=\"1120\"><strong data-start=\"1087\" data-end=\"1111\">Max. Apparent Power:</strong>&#160;<span>29900</span>A</li>\r\n<li data-start=\"1121\" data-end=\"1185\"><strong data-start=\"1123\" data-end=\"1149\">Peak Power (Off-Grid):</strong>&#160;1.5&#215; rated power (for 10 seconds)</li>\r\n<li data-start=\"1186\" data-end=\"1238\"><strong data-start=\"1188\" data-end=\"1222\">Rated AC Input/Output Current:</strong>&#160;<span>45.4/43.4</span></li>\r\n<li data-start=\"1239\" data-end=\"1290\"><strong data-start=\"1241\" data-end=\"1274\">Max. AC Input/Output Current:</strong>&#160;<span>45.4/43.4</span></li>\r\n<li data-start=\"1291\" data-end=\"1349\"><strong data-start=\"1293\" data-end=\"1343\">Max. Continuous AC Passthrough (Grid to Load):</strong>&#160;<span>200</span>A</li>\r\n<li data-start=\"1350\" data-end=\"1401\"><strong data-start=\"1352\" data-end=\"1370\">Rated Voltage:</strong>&#160;220/380V, 230/400V (3L+N+PE)</li>\r\n<li data-start=\"1402\" data-end=\"1462\"><strong data-start=\"1404\" data-end=\"1429\">Grid Frequency Range:</strong>&#160;50Hz (45&#8211;55Hz), 60Hz (55&#8211;65Hz)</li>\r\n<li data-start=\"1463\" data-end=\"1522\"><strong data-start=\"1465\" data-end=\"1493\">Power Factor Adjustment:</strong>&#160;0.8 leading to 0.8 lagging</li>\r\n<li data-start=\"1523\" data-end=\"1568\"><strong data-start=\"1525\" data-end=\"1562\">Total Harmonic Distortion (THDi):</strong>&#160;&lt;3%</li>\r\n<li data-start=\"1569\" data-end=\"1623\"><strong data-start=\"1571\" data-end=\"1596\">DC Injection Current:</strong>&#160;&lt;0.5% of nominal current<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1635\" data-end=\"1649\">Efficiency<br /><br /></strong>\r\n<ul data-start=\"1650\" data-end=\"1745\">\r\n<li data-start=\"1650\" data-end=\"1680\"><strong data-start=\"1652\" data-end=\"1672\">Max. Efficiency:</strong>&#160;97.6%</li>\r\n<li data-start=\"1681\" data-end=\"1715\"><strong data-start=\"1683\" data-end=\"1707\">European Efficiency:</strong>&#160;97.0%</li>\r\n<li data-start=\"1716\" data-end=\"1745\"><strong data-start=\"1718\" data-end=\"1738\">MPPT Efficiency:</strong>&#160;&gt;99%<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"1783\" data-end=\"1810\">Integrated Protections:<br /><br /></strong><strong data-start=\"2073\" data-end=\"2094\"></strong></li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"2073\" data-end=\"2094\">Surge Protection:</strong>&#160;Type II (both DC &amp; AC sides)<br /><br />\r\n<ul data-start=\"1815\" data-end=\"2070\">\r\n<li data-start=\"1815\" data-end=\"1838\">DC reverse polarity</li>\r\n<li data-start=\"1841\" data-end=\"1866\">AC output overcurrent</li>\r\n<li data-start=\"1869\" data-end=\"1887\">AC overvoltage</li>\r\n<li data-start=\"1890\" data-end=\"1907\">Short circuit</li>\r\n<li data-start=\"1910\" data-end=\"1932\">Thermal protection</li>\r\n<li data-start=\"1935\" data-end=\"1965\">Residual current detection</li>\r\n<li data-start=\"1968\" data-end=\"2004\">Insulation resistance monitoring</li>\r\n<li data-start=\"2007\" data-end=\"2040\">Optional arc fault protection</li>\r\n<li data-start=\"2043\" data-end=\"2070\">DC component monitoring<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2128\" data-end=\"2142\">DC Switch:</strong>&#160;Included<br /><br /></li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2165\" data-end=\"2191\">Standards &amp; Compliance<br /><br /></strong>\r\n<ul data-start=\"2192\" data-end=\"2430\">\r\n<li data-start=\"2192\" data-end=\"2339\"><strong data-start=\"2194\" data-end=\"2214\">Grid Compliance:</strong><br data-start=\"2214\" data-end=\"2217\" />IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,<br data-start=\"2289\" data-end=\"2292\" />OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</li>\r\n<li data-start=\"2340\" data-end=\"2430\"><strong data-start=\"2342\" data-end=\"2369\">Safety &amp; EMC Standards:</strong><br data-start=\"2369\" data-end=\"2372\" />IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2442\" data-end=\"2486\">Environmental &amp; Physical Characteristics<br /><br /></strong>\r\n<ul data-start=\"2487\" data-end=\"2880\">\r\n<li data-start=\"2487\" data-end=\"2560\"><strong data-start=\"2489\" data-end=\"2521\">Operating Temperature Range:</strong>&#160;-40&#176;C to +60&#176;C (derating above 45&#176;C)</li>\r\n<li data-start=\"2561\" data-end=\"2585\"><strong data-start=\"2563\" data-end=\"2576\">Humidity:</strong>&#160;0&#8211;100%</li>\r\n<li data-start=\"2586\" data-end=\"2617\"><strong data-start=\"2588\" data-end=\"2609\">Maximum Altitude:</strong>&#160;2000m</li>\r\n<li data-start=\"2618\" data-end=\"2648\"><strong data-start=\"2620\" data-end=\"2636\">Noise Level:</strong>&#160;&#8804;65 dB(A)</li>\r\n<li data-start=\"2649\" data-end=\"2705\"><strong data-start=\"2651\" data-end=\"2670\">Cooling Method:</strong>&#160;<span>Intelligent Air Cooling</span></li>\r\n<li data-start=\"2706\" data-end=\"2773\"><strong data-start=\"2708\" data-end=\"2733\">IP Protection Rating:</strong>&#160;IP65 (dust-tight and water-resistant)</li>\r\n<li data-start=\"2774\" data-end=\"2856\"><strong data-start=\"2776\" data-end=\"2803\">Dimensions (W &#215; H &#215; D):</strong>&#160;<span>527 x 894 x 294</span> mm (excluding connectors/brackets)</li>\r\n<li data-start=\"2857\" data-end=\"2880\"><strong data-start=\"2859\" data-end=\"2870\">Weight:</strong>&#160;80 kg<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2892\" data-end=\"2921\">Interface &amp; Communication<br /><br /></strong>\r\n<ul data-start=\"2922\" data-end=\"3039\">\r\n<li data-start=\"2922\" data-end=\"2992\"><strong data-start=\"2924\" data-end=\"2947\">Monitoring Options:</strong>&#160;GPRS, Wi-Fi, Bluetooth, 4G, LAN (optional)</li>\r\n<li data-start=\"2993\" data-end=\"3039\"><strong data-start=\"2995\" data-end=\"3019\">Communication Ports:</strong>&#160;RS485, RS232, CAN</li>\r\n</ul>\r\n</li>\r\n</ul>\r\n<strong>The Deye SUN-29.9K-SG01HP3-EU-BM3 is a three-phase hybrid inverter designed for intelligent energy management. With triple MPPTs, high-voltage battery support, and robust protection features, it ensures efficient solar integration, seamless backup power, and long-term reliability for residential and small commercial applications.<br /></strong>', 'The Deye SUN-29.9K-SG01HP3-EU-BM3 is a high-performance three-phase hybrid inverter tailored for residential and light commercial applications. Designed to seamlessly integrate solar energy, high-voltage lithium-ion battery storage, and grid power, this inverter enables smart and efficient energy management. With dual MPPTs, a wide PV voltage range of 150&#8211;850V, and support for up to <span>29900</span>W of PV input, it maximizes solar harvest and system flexibility. Its advanced protection features, natural cooling system, and IP65-rated housing ensure reliable operation under various environmental conditions. Whether for new installations or retrofitting existing systems, the SUN-29.9K-SG01HP3-EU-BM3 offers a compact, robust, and future-ready energy solution.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\r\n\r\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\r\n\r\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\r\n\r\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\r\n\r\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\r\n\r\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\r\n\r\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', '');
INSERT INTO `products_description` (`products_id`, `products_extra_text`, `language_id`, `products_name`, `products_description`, `products_short_description`, `products_meta_title`, `products_meta_description`, `products_meta_keywords`, `products_url`, `products_viewed`, `ebay_title`, `slave_title`, `products_condition`, `amazon_generic_keywords1`, `amazon_generic_keywords2`, `amazon_generic_keywords3`, `amazon_generic_keywords4`, `amazon_generic_keywords5`, `amazon_flatfile`, `amazon_browse_node_id`, `products_description_amazon`, `amazon_title`) VALUES
(546, '<table selecttype=\"cells\">\r\n<tbody>\r\n<tr height=\"24\">\r\n<td width=\"250\"><strong>Battery Input Data</strong></td>\r\n<td width=\"750\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Battery Type</td>\r\n<td width=\"750\">Lithium-ion</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Battery Voltage Range(V)</td>\r\n<td width=\"750\">160-800</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Max.Charging Current(A)</td>\r\n<td width=\"750\">50+50</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Max.Discharging Current(A)</td>\r\n<td width=\"750\">50+50</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Charging Strategy for Li-ion Battery</td>\r\n<td width=\"750\">Self-adaption to BMS</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Number of battery input</td>\r\n<td width=\"750\">2</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">\r\n<p></p>\r\n<p><strong>PV String Input Data</strong></p>\r\n</td>\r\n<td width=\"750\"></td>\r\n</tr>\r\n<tr>\r\n<td>Max. PV Access Power (W)</td>\r\n<td>59800</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Max DC Input Power&#65288;W&#65289;</td>\r\n<td width=\"150\">47840</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Max DC Input Voltage&#65288;V&#65289;</td>\r\n<td width=\"750\">1000</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Start-up Voltage&#65288;V&#65289;</td>\r\n<td width=\"750\">180</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">MPPT Voltage Range&#65288;V&#65289;</td>\r\n<td width=\"750\">150-850</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Rated DC Input Voltage(V)</td>\r\n<td width=\"750\">600</td>\r\n</tr>\r\n<tr height=\"32\">\r\n<td width=\"250\">Max Input Short-Circuit Current&#65288;A&#65289;</td>\r\n<td width=\"450\">55+55+55</td>\r\n</tr>\r\n<tr height=\"40\">\r\n<td width=\"250\">Max Operating PV Input Current&#65288;A&#65289;</td>\r\n<td width=\"450\">36+36+36</td>\r\n</tr>\r\n<tr height=\"40\">\r\n<td width=\"250\">No.of MPP Trackers/No.of String Per MPP Tracker</td>\r\n<td width=\"450\">3/2+2+2</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">\r\n<p></p>\r\n<p><strong>AC Input/Output Data</strong></p>\r\n</td>\r\n<td width=\"750\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Rated AC Input/Output Active Power&#65288;W&#65289;</td>\r\n<td width=\"150\">29900</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Max AC Input/Output Apparent Power &#65288;VA&#65289;</td>\r\n<td width=\"150\">29900</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Peak Power (off-grid)&#65288;W&#65289;</td>\r\n<td width=\"750\">1.5 times of rated power,10s</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Rated AC Input/Output Current&#65288;A&#65289;</td>\r\n<td width=\"150\">45.4/43.4</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Max AC Input/Output Current&#65288;A&#65289;</td>\r\n<td width=\"150\">45.4/43.4</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Max Continuous AC Passthrough (grid to load)&#65288;A&#65289;</td>\r\n<td width=\"750\">200</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Rated Input/Output Voltage/Range(V)</td>\r\n<td width=\"750\">220/380V&#65292;230/400V 0.85Un-1.1Un</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Grid Connection Form</td>\r\n<td width=\"750\">3L+N+PE</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Rated Input/Output Grid Frequency/Range</td>\r\n<td width=\"750\">50/45-55, 60/55-65</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Power Factor Adjustment Range</td>\r\n<td width=\"750\">0.8 leading-0.8 lagging</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Total Current Harmonic Distortion THDi</td>\r\n<td width=\"750\">&lt;3% (of nominal power)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">DC Injection Current</td>\r\n<td width=\"750\">&lt;0.5%ln</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">\r\n<p></p>\r\n<p><strong>Efficiency</strong></p>\r\n</td>\r\n<td width=\"750\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Max Efficiency</td>\r\n<td width=\"750\">97.60%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Euro Efficiency</td>\r\n<td width=\"750\">97.0%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">MPPT Efficiency</td>\r\n<td width=\"750\">&#65310;99%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">\r\n<p></p>\r\n<p><strong>Equipment Protection</strong></p>\r\n</td>\r\n<td width=\"750\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Integrated</td>\r\n<td width=\"750\">\r\n<div>DC Reverse Polarity Protection, AC Output Overcurrent Protection, Thermal Protection, AC Output Overvoltage</div>\r\n<div>Protection,&#160;AC Output Short Circuit Protection, DC Component Monitoring, Arc Fault Circuit</div>\r\n<div>Interrupter (optional), Anti-islanding Protection,&#160;DC Switch, Insulation Impedance Detection,</div>\r\n<div>Residual Current Detection</div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Surge Protection Level</td>\r\n<td width=\"750\">TYPE II(DC), TYPE II(AC)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">\r\n<p></p>\r\n<p><strong>Interface</strong></p>\r\n</td>\r\n<td width=\"750\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Communication Interface</td>\r\n<td width=\"750\">RS485/RS232/CAN</td>\r\n</tr>\r\n<tr>\r\n<td>Monitor Mode</td>\r\n<td>GPRS/WIFI/Bluetooth/4G/LAN(optional)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">\r\n<p></p>\r\n<p><strong>General Data</strong></p>\r\n</td>\r\n<td width=\"750\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Operating Temperature Range</td>\r\n<td width=\"750\">-40&#8451;+60&#8451;,&#65310;45&#8451; Derating</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Permissible Ambient Humidity</td>\r\n<td width=\"750\">0-100%</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Permissible Altitude</td>\r\n<td width=\"750\">2000m</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Noise</td>\r\n<td width=\"750\">&#8804; 65 dB(A)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Ingress Protection(IP) Rating</td>\r\n<td width=\"750\">IP 65</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Inverter Topology</td>\r\n<td width=\"750\">Non-Isolated</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Over Voltage Category</td>\r\n<td width=\"750\">OVC II(DC),OVC III(AC)</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Cabinet size&#65288;W*H*D&#65289;[mm]</td>\r\n<td width=\"750\">527*894*294&#65288;Excluding connectors and brackets&#65289;</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Weight[kg]</td>\r\n<td width=\"750\">80</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Warranty</td>\r\n<td width=\"750\">5 Years/10 Years<br />the Warranty Period Depends the Final Installation Site of Inverter, More Info Please Refer to Warranty Policy</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Type Of Cooling</td>\r\n<td width=\"750\">Intelligent air cooling</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Grid Regulation</td>\r\n<td width=\"750\">IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,<br />OVE-Richtlinie R25, G99, VDE-AR-N 4105</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">Safety EMC/Standard</td>\r\n<td width=\"750\">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2<br /><br /></td>\r\n</tr>\r\n</tbody>\r\n</table>', 3, 'SUN-29.9K-SG01HP3-EU-BM3 | Three-Phase Hybrid Inverter | 3 MPPT | HV Battery Supported', '<p>The Deye SUN-29.9K-SG01HP3-EU-BM3 is a powerful three-phase hybrid inverter designed for high-performance solar energy systems. Equipped with 3 MPPTs and high-voltage battery support, it ensures exceptional efficiency and flexibility. This inverter supports 100% unbalanced output, allowing each phase to independently deliver up to 50% of the rated power&#8212;ideal for uneven load distribution. Thanks to its AC coupling capability, it can seamlessly retrofit into existing PV systems, enhancing performance without requiring a full overhaul. It allows for parallel operation of up to 10 units in both on-grid and off-grid modes and supports multiple batteries in parallel, offering excellent scalability. With a maximum charging and discharging current of 50A + 50A, it maintains efficient and reliable energy flow. Additionally, users can configure six charging and discharging time periods, optimizing battery use based on energy demand and tariff rates. The inverter is also compatible with diesel generators, ensuring dependable backup power in areas with unstable grid supply.</p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-006.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" /></p>\r\n<p></p>\r\n<h3>Key Features</h3>\r\n<ul>\r\n<li data-start=\"0\" data-end=\"152\">\r\n<p data-start=\"2\" data-end=\"152\"><strong data-start=\"2\" data-end=\"29\" data-is-only-node=\"\">100% Unbalanced Output:</strong>&#160;Each phase can operate independently with up to 50% of the rated power, ensuring flexibility for varied load conditions.</p>\r\n</li>\r\n<li data-start=\"153\" data-end=\"296\">\r\n<p data-start=\"155\" data-end=\"296\"><strong data-start=\"155\" data-end=\"184\" data-is-only-node=\"\">AC Coupling for Retrofit:</strong>&#160;Easily integrates into existing solar systems, enabling efficient performance upgrades without major changes.</p>\r\n</li>\r\n<li data-start=\"297\" data-end=\"468\">\r\n<p data-start=\"299\" data-end=\"468\"><strong data-start=\"299\" data-end=\"331\" data-is-only-node=\"\">Scalable Parallel Operation:</strong>&#160;Supports up to 10 units in parallel for both on-grid and off-grid modes, with compatibility for multiple parallel battery connections.</p>\r\n</li>\r\n<li data-start=\"469\" data-end=\"605\">\r\n<p data-start=\"471\" data-end=\"605\"><strong data-start=\"471\" data-end=\"516\" data-is-only-node=\"\">Max. Charging/Discharging Current of 50A + 50A:</strong>&#160;Ensures stable and efficient energy flow for both charging and discharging operations.</p>\r\n</li>\r\n<li data-start=\"606\" data-end=\"731\">\r\n<p data-start=\"608\" data-end=\"731\"><strong data-start=\"608\" data-end=\"641\" data-is-only-node=\"\">High Voltage Battery Support:</strong>&#160;Utilizes high-voltage batteries to increase system efficiency and reduce energy losses.</p>\r\n</li>\r\n<li data-start=\"732\" data-end=\"899\">\r\n<p data-start=\"734\" data-end=\"899\"><strong data-start=\"734\" data-end=\"768\" data-is-only-node=\"\">Time-based Battery Management:</strong>&#160;Allows for six configurable time periods for optimized battery charging and discharging based on energy consumption and tariffs.</p>\r\n</li>\r\n<li data-start=\"900\" data-end=\"1059\" data-is-last-node=\"\">\r\n<p data-start=\"902\" data-end=\"1059\" data-is-last-node=\"\"><strong data-start=\"902\" data-end=\"937\" data-is-only-node=\"\">Diesel Generator Compatibility:</strong>&#160;Capable of storing energy from diesel generators, offering reliable backup in areas with unstable or limited grid access.</p>\r\n</li>\r\n</ul>\r\n<p></p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" /></p>\r\n<p></p>\r\n<h3>Technical Specifications</h3>\r\n<ul>\r\n<li><strong data-start=\"283\" data-end=\"305\">Battery Input Data<br /><br /></strong>\r\n<ul data-start=\"306\" data-end=\"596\">\r\n<li data-start=\"306\" data-end=\"384\"><strong data-start=\"308\" data-end=\"334\">Battery Compatibility:</strong>&#160;Lithium-ion batteries (lead-acid not supported)</li>\r\n<li data-start=\"385\" data-end=\"424\"><strong data-start=\"387\" data-end=\"413\">Battery Voltage Range:</strong>&#160;160&#8211;800V</li>\r\n<li data-start=\"425\" data-end=\"471\"><strong data-start=\"427\" data-end=\"465\">Max. Charging/Discharging Current:</strong>&#160;50A + 50A</li>\r\n<li data-start=\"472\" data-end=\"506\"><strong data-start=\"474\" data-end=\"492\">Battery Input:</strong>&#160;Single port</li>\r\n<li data-start=\"507\" data-end=\"596\"><strong data-start=\"509\" data-end=\"531\">BMS Communication:</strong>&#160;Self-adaptive, ensuring compatibility with various BMS protocols<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"608\" data-end=\"632\">PV String Input Data<br /><br /></strong>\r\n<ul data-start=\"633\" data-end=\"1003\">\r\n<li data-start=\"633\" data-end=\"670\"><strong data-start=\"635\" data-end=\"660\">Max. PV Access Power:</strong>&#160;59800W</li>\r\n<li data-start=\"671\" data-end=\"707\"><strong data-start=\"673\" data-end=\"697\">Max. PV Input Power:</strong>&#160;47840W</li>\r\n<li data-start=\"708\" data-end=\"744\"><strong data-start=\"710\" data-end=\"736\">Max. PV Input Voltage:</strong>&#160;1000V</li>\r\n<li data-start=\"745\" data-end=\"781\"><strong data-start=\"747\" data-end=\"770\">MPPT Voltage Range:</strong>&#160;150&#8211;850V</li>\r\n<li data-start=\"782\" data-end=\"812\"><strong data-start=\"784\" data-end=\"805\">Start-up Voltage:</strong>&#160;180V</li>\r\n<li data-start=\"813\" data-end=\"849\"><strong data-start=\"815\" data-end=\"842\">Rated DC Input Voltage:</strong>&#160;600V</li>\r\n<li data-start=\"850\" data-end=\"903\"><strong data-start=\"852\" data-end=\"891\">Number of MPPTs / Strings per MPPT:</strong>&#160;3 / 2+2+2</li>\r\n<li data-start=\"904\" data-end=\"954\"><strong data-start=\"906\" data-end=\"942\">Max. Operating PV Input Current:</strong>&#160;55A + 55A + 55A</li>\r\n<li data-start=\"955\" data-end=\"1003\"><strong data-start=\"957\" data-end=\"991\">Max. PV Short-Circuit Current:</strong>&#160;36A + 36A + 36A<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1015\" data-end=\"1041\">AC Input / Output Data<br /><br /></strong>\r\n<ul data-start=\"1042\" data-end=\"1623\">\r\n<li data-start=\"1042\" data-end=\"1084\"><strong data-start=\"1044\" data-end=\"1076\">Rated AC Input/Output Power:</strong>&#160;29900W</li>\r\n<li data-start=\"1085\" data-end=\"1120\"><strong data-start=\"1087\" data-end=\"1111\">Max. Apparent Power:</strong>&#160;29900A</li>\r\n<li data-start=\"1121\" data-end=\"1185\"><strong data-start=\"1123\" data-end=\"1149\">Peak Power (Off-Grid):</strong>&#160;1.5&#215; rated power (for 10 seconds)</li>\r\n<li data-start=\"1186\" data-end=\"1238\"><strong data-start=\"1188\" data-end=\"1222\">Rated AC Input/Output Current:</strong>&#160;45.4/43.4</li>\r\n<li data-start=\"1239\" data-end=\"1290\"><strong data-start=\"1241\" data-end=\"1274\">Max. AC Input/Output Current:</strong>&#160;45.4/43.4</li>\r\n<li data-start=\"1291\" data-end=\"1349\"><strong data-start=\"1293\" data-end=\"1343\">Max. Continuous AC Passthrough (Grid to Load):</strong>&#160;200A</li>\r\n<li data-start=\"1350\" data-end=\"1401\"><strong data-start=\"1352\" data-end=\"1370\">Rated Voltage:</strong>&#160;220/380V, 230/400V (3L+N+PE)</li>\r\n<li data-start=\"1402\" data-end=\"1462\"><strong data-start=\"1404\" data-end=\"1429\">Grid Frequency Range:</strong>&#160;50Hz (45&#8211;55Hz), 60Hz (55&#8211;65Hz)</li>\r\n<li data-start=\"1463\" data-end=\"1522\"><strong data-start=\"1465\" data-end=\"1493\">Power Factor Adjustment:</strong>&#160;0.8 leading to 0.8 lagging</li>\r\n<li data-start=\"1523\" data-end=\"1568\"><strong data-start=\"1525\" data-end=\"1562\">Total Harmonic Distortion (THDi):</strong>&#160;&lt;3%</li>\r\n<li data-start=\"1569\" data-end=\"1623\"><strong data-start=\"1571\" data-end=\"1596\">DC Injection Current:</strong>&#160;&lt;0.5% of nominal current<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1635\" data-end=\"1649\">Efficiency<br /><br /></strong>\r\n<ul data-start=\"1650\" data-end=\"1745\">\r\n<li data-start=\"1650\" data-end=\"1680\"><strong data-start=\"1652\" data-end=\"1672\">Max. Efficiency:</strong>&#160;97.6%</li>\r\n<li data-start=\"1681\" data-end=\"1715\"><strong data-start=\"1683\" data-end=\"1707\">European Efficiency:</strong>&#160;97.0%</li>\r\n<li data-start=\"1716\" data-end=\"1745\"><strong data-start=\"1718\" data-end=\"1738\">MPPT Efficiency:</strong>&#160;&gt;99%<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"1783\" data-end=\"1810\">Integrated Protections:<br /><br /></strong><strong data-start=\"2073\" data-end=\"2094\"></strong></li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"2073\" data-end=\"2094\">Surge Protection:</strong>&#160;Type II (both DC &amp; AC sides)<br /><br />\r\n<ul data-start=\"1815\" data-end=\"2070\">\r\n<li data-start=\"1815\" data-end=\"1838\">DC reverse polarity</li>\r\n<li data-start=\"1841\" data-end=\"1866\">AC output overcurrent</li>\r\n<li data-start=\"1869\" data-end=\"1887\">AC overvoltage</li>\r\n<li data-start=\"1890\" data-end=\"1907\">Short circuit</li>\r\n<li data-start=\"1910\" data-end=\"1932\">Thermal protection</li>\r\n<li data-start=\"1935\" data-end=\"1965\">Residual current detection</li>\r\n<li data-start=\"1968\" data-end=\"2004\">Insulation resistance monitoring</li>\r\n<li data-start=\"2007\" data-end=\"2040\">Optional arc fault protection</li>\r\n<li data-start=\"2043\" data-end=\"2070\">DC component monitoring<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2128\" data-end=\"2142\">DC Switch:</strong>&#160;Included<br /><br /></li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2165\" data-end=\"2191\">Standards &amp; Compliance<br /><br /></strong>\r\n<ul data-start=\"2192\" data-end=\"2430\">\r\n<li data-start=\"2192\" data-end=\"2339\"><strong data-start=\"2194\" data-end=\"2214\">Grid Compliance:</strong><br data-start=\"2214\" data-end=\"2217\" />IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,<br data-start=\"2289\" data-end=\"2292\" />OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</li>\r\n<li data-start=\"2340\" data-end=\"2430\"><strong data-start=\"2342\" data-end=\"2369\">Safety &amp; EMC Standards:</strong><br data-start=\"2369\" data-end=\"2372\" />IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2442\" data-end=\"2486\">Environmental &amp; Physical Characteristics<br /><br /></strong>\r\n<ul data-start=\"2487\" data-end=\"2880\">\r\n<li data-start=\"2487\" data-end=\"2560\"><strong data-start=\"2489\" data-end=\"2521\">Operating Temperature Range:</strong>&#160;-40&#176;C to +60&#176;C (derating above 45&#176;C)</li>\r\n<li data-start=\"2561\" data-end=\"2585\"><strong data-start=\"2563\" data-end=\"2576\">Humidity:</strong>&#160;0&#8211;100%</li>\r\n<li data-start=\"2586\" data-end=\"2617\"><strong data-start=\"2588\" data-end=\"2609\">Maximum Altitude:</strong>&#160;2000m</li>\r\n<li data-start=\"2618\" data-end=\"2648\"><strong data-start=\"2620\" data-end=\"2636\">Noise Level:</strong>&#160;&#8804;65 dB(A)</li>\r\n<li data-start=\"2649\" data-end=\"2705\"><strong data-start=\"2651\" data-end=\"2670\">Cooling Method:</strong>&#160;Intelligent Air Cooling</li>\r\n<li data-start=\"2706\" data-end=\"2773\"><strong data-start=\"2708\" data-end=\"2733\">IP Protection Rating:</strong>&#160;IP65 (dust-tight and water-resistant)</li>\r\n<li data-start=\"2774\" data-end=\"2856\"><strong data-start=\"2776\" data-end=\"2803\">Dimensions (W &#215; H &#215; D):</strong>&#160;527 x 894 x 294&#160;mm (excluding connectors/brackets)</li>\r\n<li data-start=\"2857\" data-end=\"2880\"><strong data-start=\"2859\" data-end=\"2870\">Weight:</strong>&#160;80 kg<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2892\" data-end=\"2921\">Interface &amp; Communication<br /><br /></strong>\r\n<ul data-start=\"2922\" data-end=\"3039\">\r\n<li data-start=\"2922\" data-end=\"2992\"><strong data-start=\"2924\" data-end=\"2947\">Monitoring Options:</strong>&#160;GPRS, Wi-Fi, Bluetooth, 4G, LAN (optional)</li>\r\n<li data-start=\"2993\" data-end=\"3039\"><strong data-start=\"2995\" data-end=\"3019\">Communication Ports:</strong>&#160;RS485, RS232, CAN</li>\r\n</ul>\r\n</li>\r\n</ul>\r\n<p><strong>The Deye SUN-29.9K-SG01HP3-EU-BM3 is a three-phase hybrid inverter designed for intelligent energy management. With triple MPPTs, high-voltage battery support, and robust protection features, it ensures efficient solar integration, seamless backup power, and long-term reliability for residential and small commercial applications.</strong></p>', 'The Deye SUN-29.9K-SG01HP3-EU-BM3 is a high-performance three-phase hybrid inverter tailored for residential and light commercial applications. Designed to seamlessly integrate solar energy, high-voltage lithium-ion battery storage, and grid power, this inverter enables smart and efficient energy management. With dual MPPTs, a wide PV voltage range of 150&#8211;850V, and support for up to&#160;29900W of PV input, it maximizes solar harvest and system flexibility. Its advanced protection features, natural cooling system, and IP65-rated housing ensure reliable operation under various environmental conditions. Whether for new installations or retrofitting existing systems, the SUN-29.9K-SG01HP3-EU-BM3 offers a compact, robust, and future-ready energy solution.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\r\n\r\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\r\n\r\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\r\n\r\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\r\n\r\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\r\n\r\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\r\n\r\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', ''),
(547, '<table selecttype=\"cells\">\r\n<tbody>\r\n<tr height=\"24\">\r\n<td width=\"250\"><strong>Battery Input Data</strong></td>\r\n<td width=\"750\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Battery Type</span></td>\r\n<td width=\"750\"><span>Lithium-ion</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Battery Voltage Range(V)</span></td>\r\n<td width=\"750\"><span>160-800</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Max.Charging Current(A)</span></td>\r\n<td width=\"750\"><span>50+50</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Max.Discharging Current(A)</span></td>\r\n<td width=\"750\"><span>50+50</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Charging Strategy for Li-ion Battery</span></td>\r\n<td width=\"750\"><span>Self-adaption to BMS</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Number of battery input</span></td>\r\n<td width=\"750\"><span>2</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">\r\n<p></p>\r\n<p><strong>PV String Input Data</strong></p>\r\n</td>\r\n<td width=\"750\"></td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<div><span>Max. PV Access Power (W)</span></div>\r\n</td>\r\n<td><span>60000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Max DC Input Power&#65288;W&#65289;</span></td>\r\n<td width=\"150\"><span>48000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Max DC Input Voltage&#65288;V&#65289;</span></td>\r\n<td width=\"750\"><span>1000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Start-up Voltage&#65288;V&#65289;</span></td>\r\n<td width=\"750\"><span>180</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>MPPT Voltage Range&#65288;V&#65289;</span></td>\r\n<td width=\"750\"><span>150-850</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Rated DC Input Voltage(V)</span></td>\r\n<td width=\"750\"><span>600</span></td>\r\n</tr>\r\n<tr height=\"32\">\r\n<td width=\"250\"><span>Max Input Short-Circuit Current&#65288;A&#65289;</span></td>\r\n<td width=\"450\"><span>55+55+55</span></td>\r\n</tr>\r\n<tr height=\"40\">\r\n<td width=\"250\"><span>Max Operating PV Input Current&#65288;A&#65289;</span></td>\r\n<td width=\"450\"><span>36+36+36</span></td>\r\n</tr>\r\n<tr height=\"40\">\r\n<td width=\"250\"><span>No.of MPP Trackers/No.of String Per MPP Tracker</span></td>\r\n<td width=\"450\"><span>3/2+2+2</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">\r\n<p></p>\r\n<p><strong>AC Input/Output Data</strong></p>\r\n</td>\r\n<td width=\"750\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Rated AC Input/Output Active Power&#65288;W&#65289;</span></td>\r\n<td width=\"150\"><span>30000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Max AC Input/Output Apparent Power &#65288;VA&#65289;</span></td>\r\n<td width=\"150\"><span>33000</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Peak Power (off-grid)&#65288;W&#65289;</span></td>\r\n<td width=\"750\"><span>1.5 times of rated power,10s</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Rated AC Input/Output Current&#65288;A&#65289;</span></td>\r\n<td width=\"150\"><span>45.5/43.5</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Max AC Input/Output Current&#65288;A&#65289;</span></td>\r\n<td width=\"150\"><span>50/47.9</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Max Continuous AC Passthrough (grid to load)&#65288;A&#65289;</span></td>\r\n<td width=\"750\"><span>200</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Rated Input/Output Voltage/Range(V)</span></td>\r\n<td width=\"750\"><span>220/380V&#65292;230/400V 0.85Un-1.1Un</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Grid Connection Form</span></td>\r\n<td width=\"750\"><span>3L+N+PE</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Rated Input/Output Grid Frequency/Range</span></td>\r\n<td width=\"750\"><span>50/45-55, 60/55-65</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Power Factor Adjustment Range</span></td>\r\n<td width=\"750\"><span>0.8 leading-0.8 lagging</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Total Current Harmonic Distortion THDi</span></td>\r\n<td width=\"750\"><span>&lt;3% (of nominal power)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">DC Injection Current</td>\r\n<td width=\"750\"><span>&lt;0.5%ln</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">\r\n<p></p>\r\n<p><strong>Efficiency</strong></p>\r\n</td>\r\n<td width=\"750\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Max Efficiency</span></td>\r\n<td width=\"750\"><span>97.60%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Euro Efficiency</span></td>\r\n<td width=\"750\"><span>97.0%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>MPPT Efficiency</span></td>\r\n<td width=\"750\"><span>&#65310;99%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">\r\n<p></p>\r\n<p><strong>Equipment Protection</strong></p>\r\n</td>\r\n<td width=\"750\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">\r\n<div><span>Integrated</span></div>\r\n</td>\r\n<td width=\"750\">\r\n<div>\r\n<div><span>DC Reverse Polarity Protection, AC Output Overcurrent Protection, Thermal Protection, AC Output Overvoltage</span></div>\r\n<div><span>Protection,&#160;</span><span>AC Output Short Circuit Protection, DC Component Monitoring, Arc Fault Circuit</span></div>\r\n<div><span>Interrupter (optional), Anti-islanding Protection,&#160;</span><span>DC Switch, Insulation Impedance Detection,</span></div>\r\n<div><span>Residual Current Detection</span></div>\r\n</div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Surge Protection Level</span></td>\r\n<td width=\"750\"><span>TYPE II(DC), TYPE II(AC)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">\r\n<p></p>\r\n<p><strong>Interface</strong></p>\r\n</td>\r\n<td width=\"750\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Communication Interface</span></td>\r\n<td width=\"750\">RS485/RS232/CAN</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<div><span>Monitor Mode</span></div>\r\n</td>\r\n<td>\r\n<div><span>GPRS/WIFI/Bluetooth/4G/LAN(optional)</span></div>\r\n</td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\">\r\n<p></p>\r\n<p><strong>General Data</strong></p>\r\n</td>\r\n<td width=\"750\"></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Operating Temperature Range</span></td>\r\n<td width=\"750\"><span>-40&#8451;+60&#8451;,&#65310;45&#8451; Derating</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Permissible Ambient Humidity</span></td>\r\n<td width=\"750\"><span>0-100%</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Permissible Altitude</span></td>\r\n<td width=\"750\"><span>2000m</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Noise</span></td>\r\n<td width=\"750\"><span>&#8804; 65 dB(A)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Ingress Protection(IP) Rating</span></td>\r\n<td width=\"750\"><span>IP 65</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Inverter Topology</span></td>\r\n<td width=\"750\"><span>Non-Isolated</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Over Voltage Category</span></td>\r\n<td width=\"750\"><span>OVC II(DC),OVC III(AC)</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Cabinet size&#65288;W*H*D&#65289;[mm]</span></td>\r\n<td width=\"750\"><span>527*894*294&#65288;Excluding connectors and brackets&#65289;</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Weight[kg]</span></td>\r\n<td width=\"750\"><span>80</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Warranty</span></td>\r\n<td width=\"750\"><span>5 Years/10 Years</span><br /><span>the Warranty Period Depends the Final Installation Site of Inverter, More Info Please Refer to Warranty Policy</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Type Of Cooling</span></td>\r\n<td width=\"750\"><span>Intelligent air cooling</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Grid Regulation</span></td>\r\n<td width=\"750\"><span>IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,</span><br /><span>OVE-Richtlinie R25, G99, VDE-AR-N 4105</span></td>\r\n</tr>\r\n<tr height=\"24\">\r\n<td width=\"250\"><span>Safety EMC/Standard</span></td>\r\n<td width=\"750\"><span>IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</span></td>\r\n</tr>\r\n</tbody>\r\n</table>', 2, 'SUN-30K-SG02HP3-EU-AM3 | Three-Phase Hybrid Inverter | 3 MPPT | HV Battery Supported', '<p>The Deye SUN-30K-SG01HP3-EU-BM3 is a powerful three-phase hybrid inverter designed for high-performance solar energy systems. Equipped with 3 MPPTs and high-voltage battery support, it ensures exceptional efficiency and flexibility. This inverter supports 100% unbalanced output, allowing each phase to independently deliver up to 50% of the rated power&#8212;ideal for uneven load distribution. Thanks to its AC coupling capability, it can seamlessly retrofit into existing PV systems, enhancing performance without requiring a full overhaul. It allows for parallel operation of up to 10 units in both on-grid and off-grid modes and supports multiple batteries in parallel, offering excellent scalability. With a maximum charging and discharging current of 50A + 50A, it maintains efficient and reliable energy flow. Additionally, users can configure six charging and discharging time periods, optimizing battery use based on energy demand and tariff rates. The inverter is also compatible with diesel generators, ensuring dependable backup power in areas with unstable grid supply.</p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-006.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\r\n<p></p>\r\n<h3>Key Features</h3>\r\n<ul>\r\n<li data-start=\"0\" data-end=\"152\">\r\n<p data-start=\"2\" data-end=\"152\"><strong data-start=\"2\" data-end=\"29\" data-is-only-node=\"\">100% Unbalanced Output:</strong>&#160;Each phase can operate independently with up to 50% of the rated power, ensuring flexibility for varied load conditions.</p>\r\n</li>\r\n<li data-start=\"153\" data-end=\"296\">\r\n<p data-start=\"155\" data-end=\"296\"><strong data-start=\"155\" data-end=\"184\" data-is-only-node=\"\">AC Coupling for Retrofit:</strong>&#160;Easily integrates into existing solar systems, enabling efficient performance upgrades without major changes.</p>\r\n</li>\r\n<li data-start=\"297\" data-end=\"468\">\r\n<p data-start=\"299\" data-end=\"468\"><strong data-start=\"299\" data-end=\"331\" data-is-only-node=\"\">Scalable Parallel Operation:</strong>&#160;Supports up to 10 units in parallel for both on-grid and off-grid modes, with compatibility for multiple parallel battery connections.</p>\r\n</li>\r\n<li data-start=\"469\" data-end=\"605\">\r\n<p data-start=\"471\" data-end=\"605\"><strong data-start=\"471\" data-end=\"516\" data-is-only-node=\"\">Max. Charging/Discharging Current of 50A + 50A:</strong>&#160;Ensures stable and efficient energy flow for both charging and discharging operations.</p>\r\n</li>\r\n<li data-start=\"606\" data-end=\"731\">\r\n<p data-start=\"608\" data-end=\"731\"><strong data-start=\"608\" data-end=\"641\" data-is-only-node=\"\">High Voltage Battery Support:</strong>&#160;Utilizes high-voltage batteries to increase system efficiency and reduce energy losses.</p>\r\n</li>\r\n<li data-start=\"732\" data-end=\"899\">\r\n<p data-start=\"734\" data-end=\"899\"><strong data-start=\"734\" data-end=\"768\" data-is-only-node=\"\">Time-based Battery Management:</strong>&#160;Allows for six configurable time periods for optimized battery charging and discharging based on energy consumption and tariffs.</p>\r\n</li>\r\n<li data-start=\"900\" data-end=\"1059\" data-is-last-node=\"\">\r\n<p data-start=\"902\" data-end=\"1059\" data-is-last-node=\"\"><strong data-start=\"902\" data-end=\"937\" data-is-only-node=\"\">Diesel Generator Compatibility:</strong>&#160;Capable of storing energy from diesel generators, offering reliable backup in areas with unstable or limited grid access.</p>\r\n</li>\r\n</ul>\r\n<p></p>\r\n<p></p>\r\n<p><img src=\"https://syd-green-energy.com/files/images/syd-solar-mood-002.jpg\" alt=\"SYD Green Energy - Solar systems and accessories from the experts\" style=\"width: 100%;\" /></p>\r\n<p></p>\r\n<h3>Technical Specifications</h3>\r\n<ul>\r\n<li><strong data-start=\"283\" data-end=\"305\">Battery Input Data<br /><br /></strong>\r\n<ul data-start=\"306\" data-end=\"596\">\r\n<li data-start=\"306\" data-end=\"384\"><strong data-start=\"308\" data-end=\"334\">Battery Compatibility:</strong>&#160;Lithium-ion batteries (lead-acid not supported)</li>\r\n<li data-start=\"385\" data-end=\"424\"><strong data-start=\"387\" data-end=\"413\">Battery Voltage Range:</strong>&#160;160&#8211;800V</li>\r\n<li data-start=\"425\" data-end=\"471\"><strong data-start=\"427\" data-end=\"465\">Max. Charging/Discharging Current:</strong>&#160;50A + 50A</li>\r\n<li data-start=\"472\" data-end=\"506\"><strong data-start=\"474\" data-end=\"492\">Battery Input:</strong>&#160;Single port</li>\r\n<li data-start=\"507\" data-end=\"596\"><strong data-start=\"509\" data-end=\"531\">BMS Communication:</strong>&#160;Self-adaptive, ensuring compatibility with various BMS protocols<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"608\" data-end=\"632\">PV String Input Data<br /><br /></strong>\r\n<ul data-start=\"633\" data-end=\"1003\">\r\n<li data-start=\"633\" data-end=\"670\"><strong data-start=\"635\" data-end=\"660\">Max. PV Access Power:</strong>&#160;<span>60000</span>W</li>\r\n<li data-start=\"671\" data-end=\"707\"><strong data-start=\"673\" data-end=\"697\">Max. PV Input Power:</strong>&#160;<span>48000</span>W</li>\r\n<li data-start=\"708\" data-end=\"744\"><strong data-start=\"710\" data-end=\"736\">Max. PV Input Voltage:</strong>&#160;1000V</li>\r\n<li data-start=\"745\" data-end=\"781\"><strong data-start=\"747\" data-end=\"770\">MPPT Voltage Range:</strong>&#160;150&#8211;850V</li>\r\n<li data-start=\"782\" data-end=\"812\"><strong data-start=\"784\" data-end=\"805\">Start-up Voltage:</strong>&#160;180V</li>\r\n<li data-start=\"813\" data-end=\"849\"><strong data-start=\"815\" data-end=\"842\">Rated DC Input Voltage:</strong>&#160;600V</li>\r\n<li data-start=\"850\" data-end=\"903\"><strong data-start=\"852\" data-end=\"891\">Number of MPPTs / Strings per MPPT:</strong>&#160;<span>3 / 2+2+2</span></li>\r\n<li data-start=\"904\" data-end=\"954\"><strong data-start=\"906\" data-end=\"942\">Max. Operating PV Input Current:</strong>&#160;<span>55A + 55A + 55A</span></li>\r\n<li data-start=\"955\" data-end=\"1003\"><strong data-start=\"957\" data-end=\"991\">Max. PV Short-Circuit Current:</strong>&#160;<span>36A + 36A + 36A</span><br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1015\" data-end=\"1041\">AC Input / Output Data<br /><br /></strong>\r\n<ul data-start=\"1042\" data-end=\"1623\">\r\n<li data-start=\"1042\" data-end=\"1084\"><strong data-start=\"1044\" data-end=\"1076\">Rated AC Input/Output Power:</strong>&#160;<span>30000</span>W</li>\r\n<li data-start=\"1085\" data-end=\"1120\"><strong data-start=\"1087\" data-end=\"1111\">Max. Apparent Power:</strong>&#160;3300<span>0</span>A</li>\r\n<li data-start=\"1121\" data-end=\"1185\"><strong data-start=\"1123\" data-end=\"1149\">Peak Power (Off-Grid):</strong>&#160;1.5&#215; rated power (for 10 seconds)</li>\r\n<li data-start=\"1186\" data-end=\"1238\"><strong data-start=\"1188\" data-end=\"1222\">Rated AC Input/Output Current:</strong>&#160;<span>45.5/43.5</span></li>\r\n<li data-start=\"1239\" data-end=\"1290\"><strong data-start=\"1241\" data-end=\"1274\">Max. AC Input/Output Current:</strong>&#160;<span>50/47.9</span></li>\r\n<li data-start=\"1291\" data-end=\"1349\"><strong data-start=\"1293\" data-end=\"1343\">Max. Continuous AC Passthrough (Grid to Load):</strong>&#160;<span>200</span>A</li>\r\n<li data-start=\"1350\" data-end=\"1401\"><strong data-start=\"1352\" data-end=\"1370\">Rated Voltage:</strong>&#160;220/380V, 230/400V (3L+N+PE)</li>\r\n<li data-start=\"1402\" data-end=\"1462\"><strong data-start=\"1404\" data-end=\"1429\">Grid Frequency Range:</strong>&#160;50Hz (45&#8211;55Hz), 60Hz (55&#8211;65Hz)</li>\r\n<li data-start=\"1463\" data-end=\"1522\"><strong data-start=\"1465\" data-end=\"1493\">Power Factor Adjustment:</strong>&#160;0.8 leading to 0.8 lagging</li>\r\n<li data-start=\"1523\" data-end=\"1568\"><strong data-start=\"1525\" data-end=\"1562\">Total Harmonic Distortion (THDi):</strong>&#160;&lt;3%</li>\r\n<li data-start=\"1569\" data-end=\"1623\"><strong data-start=\"1571\" data-end=\"1596\">DC Injection Current:</strong>&#160;&lt;0.5% of nominal current<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"1635\" data-end=\"1649\">Efficiency<br /><br /></strong>\r\n<ul data-start=\"1650\" data-end=\"1745\">\r\n<li data-start=\"1650\" data-end=\"1680\"><strong data-start=\"1652\" data-end=\"1672\">Max. Efficiency:</strong>&#160;97.6%</li>\r\n<li data-start=\"1681\" data-end=\"1715\"><strong data-start=\"1683\" data-end=\"1707\">European Efficiency:</strong>&#160;97.0%</li>\r\n<li data-start=\"1716\" data-end=\"1745\"><strong data-start=\"1718\" data-end=\"1738\">MPPT Efficiency:</strong>&#160;&gt;99%<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"1783\" data-end=\"1810\">Integrated Protections:<br /><br /></strong><strong data-start=\"2073\" data-end=\"2094\"></strong></li>\r\n<li data-start=\"1781\" data-end=\"2070\"><strong data-start=\"2073\" data-end=\"2094\">Surge Protection:</strong>&#160;Type II (both DC &amp; AC sides)<br /><br />\r\n<ul data-start=\"1815\" data-end=\"2070\">\r\n<li data-start=\"1815\" data-end=\"1838\">DC reverse polarity</li>\r\n<li data-start=\"1841\" data-end=\"1866\">AC output overcurrent</li>\r\n<li data-start=\"1869\" data-end=\"1887\">AC overvoltage</li>\r\n<li data-start=\"1890\" data-end=\"1907\">Short circuit</li>\r\n<li data-start=\"1910\" data-end=\"1932\">Thermal protection</li>\r\n<li data-start=\"1935\" data-end=\"1965\">Residual current detection</li>\r\n<li data-start=\"1968\" data-end=\"2004\">Insulation resistance monitoring</li>\r\n<li data-start=\"2007\" data-end=\"2040\">Optional arc fault protection</li>\r\n<li data-start=\"2043\" data-end=\"2070\">DC component monitoring<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2128\" data-end=\"2142\">DC Switch:</strong>&#160;Included<br /><br /></li>\r\n<li data-start=\"2126\" data-end=\"2153\"><strong data-start=\"2165\" data-end=\"2191\">Standards &amp; Compliance<br /><br /></strong>\r\n<ul data-start=\"2192\" data-end=\"2430\">\r\n<li data-start=\"2192\" data-end=\"2339\"><strong data-start=\"2194\" data-end=\"2214\">Grid Compliance:</strong><br data-start=\"2214\" data-end=\"2217\" />IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002,<br data-start=\"2289\" data-end=\"2292\" />OVE-Richtlinie R25, G98, G99, VDE-AR-N 4105</li>\r\n<li data-start=\"2340\" data-end=\"2430\"><strong data-start=\"2342\" data-end=\"2369\">Safety &amp; EMC Standards:</strong><br data-start=\"2369\" data-end=\"2372\" />IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2442\" data-end=\"2486\">Environmental &amp; Physical Characteristics<br /><br /></strong>\r\n<ul data-start=\"2487\" data-end=\"2880\">\r\n<li data-start=\"2487\" data-end=\"2560\"><strong data-start=\"2489\" data-end=\"2521\">Operating Temperature Range:</strong>&#160;-40&#176;C to +60&#176;C (derating above 45&#176;C)</li>\r\n<li data-start=\"2561\" data-end=\"2585\"><strong data-start=\"2563\" data-end=\"2576\">Humidity:</strong>&#160;0&#8211;100%</li>\r\n<li data-start=\"2586\" data-end=\"2617\"><strong data-start=\"2588\" data-end=\"2609\">Maximum Altitude:</strong>&#160;2000m</li>\r\n<li data-start=\"2618\" data-end=\"2648\"><strong data-start=\"2620\" data-end=\"2636\">Noise Level:</strong>&#160;&#8804;65 dB(A)</li>\r\n<li data-start=\"2649\" data-end=\"2705\"><strong data-start=\"2651\" data-end=\"2670\">Cooling Method:</strong>&#160;<span>Intelligent Air Cooling</span></li>\r\n<li data-start=\"2706\" data-end=\"2773\"><strong data-start=\"2708\" data-end=\"2733\">IP Protection Rating:</strong>&#160;IP65 (dust-tight and water-resistant)</li>\r\n<li data-start=\"2774\" data-end=\"2856\"><strong data-start=\"2776\" data-end=\"2803\">Dimensions (W &#215; H &#215; D):</strong>&#160;<span>527 x 894 x 294</span> mm (excluding connectors/brackets)</li>\r\n<li data-start=\"2857\" data-end=\"2880\"><strong data-start=\"2859\" data-end=\"2870\">Weight:</strong>&#160;80 kg<br /><br /></li>\r\n</ul>\r\n</li>\r\n<li><strong data-start=\"2892\" data-end=\"2921\">Interface &amp; Communication<br /><br /></strong>\r\n<ul data-start=\"2922\" data-end=\"3039\">\r\n<li data-start=\"2922\" data-end=\"2992\"><strong data-start=\"2924\" data-end=\"2947\">Monitoring Options:</strong>&#160;GPRS, Wi-Fi, Bluetooth, 4G, LAN (optional)</li>\r\n<li data-start=\"2993\" data-end=\"3039\"><strong data-start=\"2995\" data-end=\"3019\">Communication Ports:</strong>&#160;RS485, RS232, CAN</li>\r\n</ul>\r\n</li>\r\n</ul>\r\n<strong>The Deye SUN-30K-SG01HP3-EU is a three-phase hybrid inverter designed for intelligent energy management. With triple MPPTs, high-voltage battery support, and robust protection features, it ensures efficient solar integration, seamless backup power, and long-term reliability for residential and small commercial applications.<br /></strong>', 'The Deye SUN-30K-SG01HP3-EU-BM3 is a high-performance three-phase hybrid inverter tailored for residential and light commercial applications. Designed to seamlessly integrate solar energy, high-voltage lithium-ion battery storage, and grid power, this inverter enables smart and efficient energy management. With dual MPPTs, a wide PV voltage range of 150&#8211;850V, and support for up to <span>30000</span>W of PV input, it maximizes solar harvest and system flexibility. Its advanced protection features, natural cooling system, and IP65-rated housing ensure reliable operation under various environmental conditions. Whether for new installations or retrofitting existing systems, the SUN-30K-SG01HP3-EU-BM3 offers a compact, robust, and future-ready energy solution.', 'Deye SUN-3.6K-SG05LP1-EU | Single Phase Hybrid Inverter | 2 MPPT | LV Battery Supported', 'High Charging/Discharging Capabilities: The Deye SUN-3.6K-SG05LP1-EU inverters support a maximum charging/discharging current of 90A. This high capacity ensures efficient energy storage and discharge, enhancing overall energy utilization.\r\n\r\nDiesel Generator Compatibility: These inverters can store energy from diesel generators, offering an added layer of power reliability and ensuring that backup power sources are effectively utilized.\r\n\r\nParallel Operation: One of the standout features of this series is its ability to support up to 16 units in parallel for both on-grid and off-grid configurations. This parallel capability provides significant scalability, accommodating increasing energy demands without compromising performance.\r\n\r\nBattery Versatility: The inverters are compatible with both lead-acid and lithium-ion batteries. Additionally, multiple batteries can be connected in parallel to extend energy storage capacity, catering to various storage needs.\r\n\r\nRetrofit Capabilities: The ability to AC couple with existing solar systems makes these inverters ideal for retrofitting, allowing users to upgrade their energy systems without a complete overhaul.\r\n\r\nUser-friendly Interface: A colorful touch LCD screen provides an intuitive interface for monitoring and control, ensuring that users can easily access and manage system information.\r\n\r\nDurable Design: Built to last, these inverters boast an IP65 protection rating, which guards against dust and water ingress, making them suitable for installation in various environmental conditions.', 'Deye, SUN-3.6K-SG05LP1-EU, Single Phase Hybrid Inverter, 2 MPPT, LV Battery Supported', '', 0, '', '', '', '', '', '', '', '', '', '', '', '');
