<table style="width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin: 60px 0; font-size: 15px;">
<tbody>
<tr style="background: #30358C; color: white;"><th style="padding: 20px; text-align: left; font-weight: 600;">Parameter</th><th style="padding: 20px; text-align: left; font-weight: 600;">Wert</th></tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px; font-size: 17px; font-weight: bold;">Dreiphasiger Hybrid-Wechselrichter SUN-20K-SG05LP3-EU-SM2</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px;">Batterie-Eingangsdaten</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Batterietyp</td>
<td style="padding: 14px 20px;">Blei- oder Lithium-Ionen (40&#8211;60 V)</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. Lade-/Entladestrom</td>
<td style="padding: 14px 20px;">350 A</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Anzahl Batterie-Eing&#228;nge</td>
<td style="padding: 14px 20px;">1</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Ladestrategie</td>
<td style="padding: 14px 20px;">Selbstadaptiv an BMS</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px;">PV-String-Eingangsdaten</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. PV-Zugangsleistung</td>
<td style="padding: 14px 20px;">40 kW</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. DC-Eingangsleistung</td>
<td style="padding: 14px 20px;">32 kW</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. PV-Eingangsspannung</td>
<td style="padding: 14px 20px;">800 V</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Anlaufspannung</td>
<td style="padding: 14px 20px;">160 V</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">MPPT-Spannungsbereich</td>
<td style="padding: 14px 20px;">160&#8211;650 V</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Nenn-DC-Eingangsspannung</td>
<td style="padding: 14px 20px;">550 V</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Anzahl MPPT / Strings pro MPPT</td>
<td style="padding: 14px 20px;">2 / 2+2</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. Betriebsstrom PV</td>
<td style="padding: 14px 20px;">36 A + 36 A</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. Kurzschlussstrom PV</td>
<td style="padding: 14px 20px;">54 A + 54 A</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px;">AC-Ausgangsdaten (Netzbetrieb)</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Nenn-Ausgangsleistung</td>
<td style="padding: 14px 20px;">20 kW</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. Scheinleistung</td>
<td style="padding: 14px 20px;">22 kVA</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Nenn-AC-Strom (400 V / 380 V)</td>
<td style="padding: 14px 20px;">29 A / 30,4 A</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. AC-Strom</td>
<td style="padding: 14px 20px;">31,9 A / 33,4 A</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Spitzenleistung (Inselbetrieb)</td>
<td style="padding: 14px 20px;">2 &#215; Nennleistung, 10 s</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. Dauer-AC-Durchgang</td>
<td style="padding: 14px 20px;">70 A</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Nenn-Netzspannung</td>
<td style="padding: 14px 20px;">220/380 V, 230/400 V (3L+N+PE)</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px;">Wirkungsgrad</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. Wirkungsgrad</td>
<td style="padding: 14px 20px;">97,6 %</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Europ&#228;ischer Wirkungsgrad</td>
<td style="padding: 14px 20px;">97,0 %</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">MPPT-Wirkungsgrad</td>
<td style="padding: 14px 20px;">&gt; 99 %</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px;">Schutz &amp; Funktionen</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">100 % unsymmetrische Last</td>
<td style="padding: 14px 20px;">Ja (jede Phase bis 50 %)</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Parallelbetrieb</td>
<td style="padding: 14px 20px;">Bis 10 Ger&#228;te (Netz- &amp; Inselbetrieb)</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Dieselgenerator-Kompatibilit&#228;t</td>
<td style="padding: 14px 20px;">Ja</td>
</tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px;">Allgemeine Daten</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Abmessungen (B &#215; H &#215; T)</td>
<td style="padding: 14px 20px;">456 &#215; 750 &#215; 268,5 mm</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Gewicht</td>
<td style="padding: 14px 20px;">51,9 kg</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">K&#252;hlung</td>
<td style="padding: 14px 20px;">Intelligente Luftk&#252;hlung</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Ger&#228;uschpegel</td>
<td style="padding: 14px 20px;">&#8804; 60 dB</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Schutzart</td>
<td style="padding: 14px 20px;">IP65</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Garantie</td>
<td style="padding: 14px 20px;">5 Jahre (verl&#228;ngerbar auf 10 Jahre)</td>
</tr>
</tbody>
</table>