<table style="width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin-bottom: 60px; font-size: 15px;">
<tbody>
<tr style="background: #30358C; color: white;"><th style="padding: 20px; text-align: left; font-weight: 600;">Parameter</th><th style="padding: 20px; text-align: left; font-weight: 600;">Wert</th></tr>
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px; font-size: 17px; font-weight: bold;">Stringwechselrichter Modell SUN-50K-G04</td>
</tr>
<!-- PV-Eingangsdaten -->
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px; font-size: 17px; font-weight: bold;">PV-Eingangsdaten</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. PV-Eingangsleistung</td>
<td style="padding: 14px 20px;">65 kW</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. PV-Eingangsspannung</td>
<td style="padding: 14px 20px;">1100 V</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Anlaufspannung</td>
<td style="padding: 14px 20px;">250 V</td>
</tr>
<tr>
<td style="padding: 14px 20px;">MPPT-Spannungsbereich</td>
<td style="padding: 14px 20px;">200&#8211;1000 V</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Nenn-PV-Eingangsspannung</td>
<td style="padding: 14px 20px;">600 V</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. Betriebsstrom PV-Eingang</td>
<td style="padding: 14px 20px;">40 + 40 + 40 + 40 A</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. Kurzschlussstrom</td>
<td style="padding: 14px 20px;">60 + 60 + 60 + 60 A</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Anzahl MPP-Tracker / Strings pro Tracker</td>
<td style="padding: 14px 20px;">4 / 3+3+3+3</td>
</tr>
<!-- AC-Ausgangsdaten -->
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px; font-size: 17px; font-weight: bold;">AC-Ausgangsdaten</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Nenn-AC-Ausgangsleistung</td>
<td style="padding: 14px 20px;">50 kW</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. AC-Scheinleistung</td>
<td style="padding: 14px 20px;">55 kVA</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Nenn-AC-Ausgangsstrom</td>
<td style="padding: 14px 20px;">75,8 A / 72,5 A (bei 220 V / 230 V)</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Max. AC-Ausgangsstrom</td>
<td style="padding: 14px 20px;">83,3 A / 79,7 A</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Nennspannung / Bereich</td>
<td style="padding: 14px 20px;">220/380 V, 230/400 V (0,85 Un &#8211; 1,1 Un)</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Netzanschluss</td>
<td style="padding: 14px 20px;">3L/N/PE</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Nennfrequenz / Bereich</td>
<td style="padding: 14px 20px;">50/60 Hz (45&#8211;55 Hz / 55&#8211;65 Hz)</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Leistungsfaktor-Bereich</td>
<td style="padding: 14px 20px;">0,8 vor- bis 0,8 nacheilend</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Klirrfaktor THDi</td>
<td style="padding: 14px 20px;">&lt; 3 %</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Gleichstrom-Einspeisung</td>
<td style="padding: 14px 20px;">&lt; 0,5 % In</td>
</tr>
<!-- Wirkungsgrad -->
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px; font-size: 17px; font-weight: bold;">Wirkungsgrad</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. Wirkungsgrad</td>
<td style="padding: 14px 20px;">98,7 %</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Europ. Wirkungsgrad</td>
<td style="padding: 14px 20px;">98,1 %</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">MPPT-Wirkungsgrad</td>
<td style="padding: 14px 20px;">&gt; 99 %</td>
</tr>
<!-- Schutzfunktionen -->
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px; font-size: 17px; font-weight: bold;">Schutzfunktionen</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">DC-Verpolungsschutz</td>
<td style="padding: 14px 20px;">Ja</td>
</tr>
<tr>
<td style="padding: 14px 20px;">AC-&#220;berstrom- / &#220;berspannungs- / Kurzschlussschutz</td>
<td style="padding: 14px 20px;">Ja</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Thermische Abschaltung</td>
<td style="padding: 14px 20px;">Ja</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Isolations&#252;berwachung / Fehlerstrom&#252;berwachung</td>
<td style="padding: 14px 20px;">Ja</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Inselnetzerkennung</td>
<td style="padding: 14px 20px;">Ja</td>
</tr>
<tr>
<td style="padding: 14px 20px;">&#220;berspannungsschutz</td>
<td style="padding: 14px 20px;">Typ II (DC), Typ II (AC)</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">DC-Schalter</td>
<td style="padding: 14px 20px;">Ja</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Lichtbogenschutz (AFCI)</td>
<td style="padding: 14px 20px;">Optional</td>
</tr>
<!-- Schnittstellen -->
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px; font-size: 17px; font-weight: bold;">Schnittstellen</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Kommunikation</td>
<td style="padding: 14px 20px;">RS485/RS232</td>
</tr>
<tr>
<td style="padding: 14px 20px;">&#220;berwachungsmodi</td>
<td style="padding: 14px 20px;">GPRS/WLAN/Bluetooth/4G/LAN (optional)</td>
</tr>
<!-- Allgemeine Daten -->
<tr style="background: #30358C; color: white;">
<td colspan="2" style="padding: 16px 20px; font-size: 17px; font-weight: bold;">Allgemeine Daten</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Betriebstemperatur</td>
<td style="padding: 14px 20px;">-25 &#176;C bis +60 &#176;C (&gt;45 &#176;C Derating)</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Zul&#228;ssige Luftfeuchtigkeit</td>
<td style="padding: 14px 20px;">0&#8211;100 %</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Max. H&#246;he</td>
<td style="padding: 14px 20px;">4000 m</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Ger&#228;uschentwicklung</td>
<td style="padding: 14px 20px;">&lt; 65 dB</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Schutzart</td>
<td style="padding: 14px 20px;">IP65</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Topologie</td>
<td style="padding: 14px 20px;">Nicht isoliert</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">&#220;berspannungskategorie</td>
<td style="padding: 14px 20px;">OVC II (DC), OVC III (AC)</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Abmessungen (B &#215; H &#215; T)</td>
<td style="padding: 14px 20px;">434 &#215; 570 &#215; 243 mm (ohne Stecker)</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Gewicht</td>
<td style="padding: 14px 20px;">39 kg</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Garantie</td>
<td style="padding: 14px 20px;">5 Jahre</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">K&#252;hlung</td>
<td style="padding: 14px 20px;">Intelligente Luftk&#252;hlung</td>
</tr>
<tr>
<td style="padding: 14px 20px;">Netzvorschriften</td>
<td style="padding: 14px 20px;">IEC 61727, IEC 62116, CEI 0-21, EN 50549, NRS 097, RD 140, UNE 217002, OVE-Richtlinie R25, G99, VDE-AR-N 4105</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 14px 20px;">Sicherheit / EMV</td>
<td style="padding: 14px 20px;">IEC/EN 61000-6-1/2/3/4, IEC/EN 62109-1, IEC/EN 62109-2</td>
</tr>
</tbody>
</table>