<div style="font-family: 'Segoe UI',Arial,sans-serif; max-width: 1000px; margin: 0 auto; line-height: 1.6; color: #333;">
<p style="font-size: 19px; font-weight: 300; color: #222; margin-bottom: 40px;">The MS-LC430-2H2 Series is a fully integrated commercial &amp; industrial energy solution that combines photovoltaic input, liquid-cooled 430 kWh LiFePO&#8324; storage and up to 420 kW ultra-fast DC charging in one extremely compact and scalable system. Featuring intelligent cloud-based EMS, 5-level safety concept (aerosol + active water fire suppression), highest energy density and full EU certification, it is the perfect turnkey solution for charging hubs, industrial plants, peak-shaving and virtual power plants.</p>
<div style="margin: 50px 0;"><img src="https://syd-green-energy.com/files/images/syd-solar-mood-027.jpg" alt="MS-LC430-2H2 Series &#8211; Integrated PV + BESS + DC Fast Charging" style="width: 100%; border-radius: 14px; box-shadow: 0 12px 35px rgba(0,0,0,.15);" /></div>
<h3 style="color: #30358c; font-size: 30px; font-weight: bold; margin: 60px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;">Key Features</h3>
<div style="display: grid; grid-template-columns: repeat(auto-fit,minmax(380px,1fr)); gap: 24px; margin-bottom: 60px;">
<div style="background: #f8f9fc; padding: 24px; border-radius: 14px; border-left: 6px solid #30358C; box-shadow: 0 8px 25px rgba(48,53,140,.1);"><strong style="color: #30358c; font-size: 18px;">All-in-One Integration</strong> PV + 430 kWh liquid-cooled storage + 420 kW DC fast charging on minimal footprint</div>
<div style="background: #f8f9fc; padding: 24px; border-radius: 14px; border-left: 6px solid #30358C; box-shadow: 0 8px 25px rgba(48,53,140,.1);"><strong style="color: #30358c; font-size: 18px;">420 kW Ultra-Fast Charging</strong> 8 &#215; 250 A branches, dual 180 kW CCS2 guns</div>
<div style="background: #f8f9fc; padding: 24px; border-radius: 14px; border-left: 6px solid #30358C; box-shadow: 0 8px 25px rgba(48,53,140,.1);"><strong style="color: #30358c; font-size: 18px;">Intelligent Cloud EMS</strong> 24/7 monitoring, revenue stacking, VPP-ready, demand response</div>
<div style="background: #f8f9fc; padding: 24px; border-radius: 14px; border-left: 6px solid #30358C; box-shadow: 0 8px 25px rgba(48,53,140,.1);"><strong style="color: #30358c; font-size: 18px;">5-Level Safety</strong> Liquid cooling + aerosol + water fire suppression + explosion-proof design</div>
<div style="background: #f8f9fc; padding: 24px; border-radius: 14px; border-left: 6px solid #30358C; box-shadow: 0 8px 25px rgba(48,53,140,.1);"><strong style="color: #30358c; font-size: 18px;">Maximum Scalability</strong> Up to 10 cabinets in parallel, 2&#8211;8 h configurations, PV-DC coupling possible</div>
</div>
<h3 style="color: #30358c; font-size: 30px; font-weight: bold; margin: 60px 0 40px; text-transform: uppercase; letter-spacing: 1.5px;">Technical Specifications</h3>
<table style="width: 100%; border-collapse: collapse; background: #fff; border-radius: 14px; overflow: hidden; box-shadow: 0 10px 35px rgba(0,0,0,.12); margin-bottom: 60px;">
<tbody>
<tr style="background: #30358C; color: white;"><th style="padding: 20px; text-align: left; font-size: 18px;">Category</th><th style="padding: 20px; text-align: left; font-size: 18px;">Details</th></tr>
<tr style="background: #f8f9fc;">
<td style="padding: 20px; font-weight: 600; width: 35%; vertical-align: top;">MS-LC430-2H2 (AC BESS)</td>
<td style="padding: 20px;">
<ul style="margin: 0; padding-left: 20px;">
<li>Battery: LiFePO&#8324;, 430.08 kWh, 768 V</li>
<li>Rated Power: 200 kW (max. 220 kW)</li>
<li>Cooling: Liquid cooling</li>
<li>Fire Suppression: Aerosol + Water</li>
<li>Protection: IP54, &#8805;C4 anticorrosion</li>
<li>Dimensions: 2000 &#215; 1300 &#215; 2480 mm</li>
</ul>
</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 20px; font-weight: 600; width: 35%; vertical-align: top;">MS-DC420-2 Charging Cabinet</td>
<td style="padding: 20px;">
<ul style="margin: 0; padding-left: 20px;">
<li>Max. Charging Power: 420 kW simultaneous</li>
<li>Outputs: 8 &#215; 250 A, 50&#8211;1000 Vdc</li>
<li>Efficiency: &#8805;97.5 %</li>
</ul>
</td>
</tr>
<tr style="background: #f8f9fc;">
<td style="padding: 20px; font-weight: 600; width: 35%; vertical-align: top;">MS-MPPT400-2 PV Cabinet</td>
<td style="padding: 20px;">
<ul style="margin: 0; padding-left: 20px;">
<li>Max. PV Input: 400 kW</li>
<li>16 MPPTs (2 &#215; 8), efficiency &gt;99.9 %</li>
<li>STS switching: &#8804;15 ms</li>
</ul>
</td>
</tr>
</tbody>
</table>
<div style="background: #30358C; color: white; padding: 40px; border-radius: 14px; text-align: center; font-size: 21px; font-weight: 600; box-shadow: 0 12px 30px rgba(48,53,140,.4);">The MS-LC430-2H2 Series &#8211; Your turnkey, future-proof solution for profitable commercial energy management with PV, storage and ultra-fast EV charging.</div>
</div>